TIA / EIA - 568 - wikipedia TIA / EIA - 568 ANSI / TIA - 568 is a set of telecommunications standards from the Telecommunications Industry Association ( TIA ). The standards address commercial building cabling for telecommunications products and services. As of 2017, the standard is at revision D, replacing the 2009 revision C, 2001 revision B, the 1995 revision A, and the initial issue of 1991, which are now obsolete. Perhaps the best known features of ANSI / TIA - 568 are the pin / pair assignments for eight - conductor 100 - ohm balanced twisted pair cabling. These assignments are named T568A and T568B. An IEC standard ISO / IEC 11801 provides similar standards for network cables. Contents 1 History 2 Goals 3 Cable categories 4 Structured cable system topologies 5 T568A and T568B termination 5.1 Wiring 5.2 Use for T1 connectivity 5.3 Backward compatibility 5.4 Theory 6 Standards 7 See also 8 References 9 Sources 10 External links History ANSI / TIA - 568 was developed through the efforts of more than 60 contributing organizations including manufacturers, end - users, and consultants. Work on the standard began with the EIA, to define standards for telecommunications cabling systems. EIA agreed to develop a set of standards, and formed the TR - 42 committee, with nine subcommittees to perform the work. The work continues to be maintained by TR - 42 within the TIA, EIA is not longer in existence and hence EIA has been removed from the name. The first revision of the standard, TIA / EIA - 568 - A. 1 - 1991 was released in 1991. The standard was updated to revision B in 1995. The demands placed upon commercial wiring systems increased dramatically over this period due to the adoption of personal computers and data communication networks and advances in those technologies. The development of high - performance twisted pair cabling and the popularization of fiber optic cables also drove significant change in the standards. These changes were first released in a revision C in 2009 which has subsequently been replaced by the D series. Goals ANSI / TIA - 568 defines structured cabling system standards for commercial buildings, and between buildings in campus environments. The bulk of the standards define cabling types, distances, connectors, cable system architectures, cable termination standards and performance characteristics, cable installation requirements and methods of testing installed cable. The main standard, ANSI / TIA - 568.0 - D defines general requirements, while ANSI / TIA - 568 - C. 2 focuses on components of balanced twisted - pair cable systems. ANSI / TIA - 568.3 - D addresses components of fiber optic cable systems, and ANSI / TIA - 568 - C. 4, addressed coaxial cabling components. The intent of these standards is to provide recommended practices for the design and installation of cabling systems that will support a wide variety of existing and future services. Developers hope the standards will provide a lifespan for commercial cabling systems in excess of ten years. This effort has been largely successful, as evidenced by the definition of category 5 cabling in 1991, a cabling standard that ( mostly ) satisfied cabling requirements for 1000BASE - T, released in 1999. Thus, the standardization process can reasonably be said to have provided at least a nine - year lifespan for premises cabling, and arguably a longer one. All these documents accompany related standards that define commercial pathways and spaces ( TIA - 569 - C - 1, February 2013 ), residential cabling ( ANSI / TIA - 570 - C, August 2012 ), administration standards ( ANSI / TIA - 606 - B, June 2012 ), grounding and bonding ( TIA - 607 - B - 2, August 2013 ), and outside plant cabling ( TIA - 758 - B, April 2012 ). Cable categories The standard defines categories of unshielded twisted pair cable systems, with different levels of performance in signal bandwidth, insertion loss, and cross-talk. Generally increasing category numbers correspond with a cable system suitable for higher rates of data transmission. Category 3 cable was suitable for telephone circuits and data rates up to 16 million bits per second. Category 5 cable, with more restrictions on attenuation and cross talk, has a bandwidth of 100 MHz. The 1995 edition of the standard defined categories 3, 4, and 5. Categories 1 and 2 were excluded from the standard since these categories were only used for voice circuits, not for data. The current revision includes Category 5e ( 100 MHz ), 6 ( 250 MHz ), 6A ( 500 MHz ) and 8 ( 2,000 MHz ). Structured cable system topologies ANSI / TIA - 568 - D defines a hierarchical cable system architecture, in which a main cross-connect ( MCC ) is connected via a star topology across backbone cabling to intermediate cross-connects ( ICC ) and horizontal cross-connects ( HCC ). Telecommunications design traditions utilized a similar topology. Many people refer to cross-connects by their telecommunications names : `` distribution frames '' ( with the various hierarchies called MDFs, IDFs and wiring closets ). Backbone cabling is also used to interconnect entrance facilities ( such as telco demarcation points ) to the main cross-connect. Maximum allowable backbone fibre distances vary between 300m and 3000m, depending upon the cable type and use. Horizontal cross-connects provide a point for the consolidation of all horizontal cabling, which extends in a star topology to individual work areas such as cubicles and offices. Under TIA / EIA - 568 - B, maximum allowable horizontal cable distance is 90m of installed cabling, whether fibre or twisted - pair, with 100m of maximum total length including patch cords. No patch cord should be longer than 5m. Optional consolidation points are allowable in horizontal cables, often appropriate for open - plan office layouts where consolidation points or media converters may connect cables to several desks or via partitions. At the work area, equipment is connected by patch cords to horizontal cabling terminated at jackpoints. TIA / EIA - 568 also defines characteristics and cabling requirements for entrance facilities, equipment rooms and telecommunications rooms. T568A and T568B termination Perhaps the widest known and most discussed feature of ANSI / TIA - 568 is the definition of the pin - to - pair assignments, or pinout, between the pins in a connector ( a plug or a socket ) and the wires in a cable. The standard specifies how to connect eight - conductor 100 - ohm balanced twisted - pair cabling, such as Category 3 and Category 6 unshielded twisted - pair ( UTP ), to 8P8C eight - pin modular connectors ( often incorrectly called RJ45 connectors ). The standard defines two alternative pinouts : T568A and T568B. The pinout definitions occupy merely 1 of the standard 's 468 pages. Much attention is paid to them because cables do not function if the pinouts at their two ends are n't correctly matched. ANSI / TIA - 568 recommends the T568A pinout for horizontal cables. This pinout 's advantage is that it is compatible with the 1 - pair and 2 - pair Universal Service Order Codes ( USOC ) pinouts. The U.S. Government requires it in federal contracts. The standard also allows the T568B pinout, as an alternative `` if necessary to accommodate certain 8 - pin cabling systems ''. This pinout matches the older AT&T 258A ( Systimax ) pinout. In the 1990s, when the original TIA / EIA - 568 was published, 258A had the most widely installed UTP cabling infrastructure. Many organizations still use T568B out of inertia. The colors of the wire pairs in the cable, in order, are : blue ( for pair 1 ), orange, green, and brown ( for pair 4 ). Each pair consists of one conductor of solid color and a second conductor which is white with a stripe of the other color. The difference between the two pinouts is that the orange and green wire pairs are exchanged. Wiring See modular connector for numbering of the pins. Pin T568A pair T568B pair 10BASE - T 100BASE - TX 1000BASE - T signal ID Wire T568A color T568B color Pins on plug face ( socket is reversed ) 1 3 2 TX+ DA+ tip white / green stripe white / orange stripe 2 3 2 TX − DA − ring green solid orange solid 3 2 3 RX+ DB+ tip white / orange stripe white / green stripe 4 1 1 -- DC+ ring blue solid blue solid 5 1 1 -- DC − tip white / blue stripe white / blue stripe 6 2 3 RX − DB − ring orange solid green solid 7 4 4 -- DD+ tip white / brown stripe white / brown stripe 8 4 4 -- DD − ring brown solid brown solid Note that the only difference between T568A and T568B is that pairs 2 and 3 ( orange and green ) are swapped. Both configurations wire the pins `` straight through '', i.e., pins 1 through 8 on one end are connected to pins 1 through 8 on the other end. Also, the same sets of pins connect to the opposite ends that are paired in both configurations : pins 1 and 2 form a pair, as do 3 and 6, 4 and 5, and 7 and 8. One can use cables wired according to either configuration in the same installation without significant problem. The primary thing one has to be careful of, is not to accidentally wire the ends of the same cable according to different configurations ( unless one intends to create an ethernet crossover cable ) or, worse, swapping two lines from different pairs. This creates crosstalk, which is normally rectified by correctly twisting a pair together. These problems will be most apparent in the more stringent specifications such as Category 6. Use for T1 connectivity In Digital Signal 1 ( T1 ) service, the pairs 1 and 3 ( T568A ) are used, and the USOC - 8 jack is wired as per spec RJ - 48 C. The Telco termination jack is often wired to spec RJ - 48 X, which provides for a Transmit - to - Receive loopback when the plug is withdrawn. Vendor cables are often wired with tip and ring reversed -- i.e. pins 1 and 2 reversed, or pins 4 and 5 reversed. This has no effect on the signal quality of the T1 signal, which is fully differential, and uses the Alternate Mark Inversion ( AMI ) signaling scheme. Backward compatibility Because pair 1 connects to the center pins ( 4 and 5 ) of the 8P8C connector in both T568A and T568B, both standards are compatible with the first line of RJ11, RJ14, RJ25, and RJ61 connectors that all have the first pair in the center pins of these connectors. If the second line of an RJ14, RJ25 or RJ61 plug is used, it connects to pair 2 ( orange / white ) of jacks wired to T568A but to pair 3 ( green / white ) in jacks wired to T568B. This makes T568B potentially confusing in telephone applications. Because of different pin pairings, the RJ25 and RJ61 plugs can not pick up lines 3 or 4 from either T568A or T568B without splitting pairs. This would most likely result in unacceptable levels of hum, crosstalk and noise. Theory The original idea in wiring modular connectors, as seen in the registered jacks, was that the first pair would go in the center positions, the next pair on the next outermost ones, and so on. Also, signal shielding would be optimized by alternating the `` live '' and `` earthy '' pins of each pair. The terminations diverge slightly from this concept because on the 8 position connector, the resulting pinout would separate the outermost pair too far to meet the electrical echo requirements of high - speed LAN protocols. Standards ANSI / TIA - 568.0 - D, Generic Telecommunications Cabling for Customer Premises, Ed. D, 09 - 2015 ANSI / TIA - 568.1 - D, Commercial Building Telecommunications Cabling Standard, Ed. D, 09 - 2015 ANSI / TIA - 568 - C. 2, Balanced Twisted - Pair Telecommunication Cabling and Components Standard, Ed. C, Err. 04 - 2014 ANSI / TIA - 568.3 - D, Optical Fiber Cabling And Components Standard, Ed. D, 10 - 2016 ANSI / TIA - 568 - C. 4, Broadband Coaxial Cabling and Components Standard, Ed. C, 07 - 2011 See also Copper cable certification References Jump up ^ Andrew Oliviero, Bill Woodward `` Cabling : The Complete Guide to Copper and Fiber - Optic Networking '', John Wiley & Sons, 2009 ISBN 0470550058 page 68 Jump up ^ `` Standards and Technology Annual Report '' ( PDF ). TIA. Retrieved 2014 - 04 - 14. Jump up ^ `` TR - 42 - Telecommunications Cabling Systems ''. TIA. Retrieved 2014 - 04 - 14. Jump up ^ `` TIA - 568 Set : Commercial Building Telecommunications Cabling Standards Set ''. Jump up ^ `` TIA Publishes New Cabling Standards Designed to Improve Efficiency for Designers, Installers and End Users ''. TIA. 2009 - 03 - 12. Archived from the original on 2011 - 08 - 17. Jump up ^ William Stallings Knowing UTP wiring basics can boost local net performance, Network World 9 July 1996, page 29 Jump up ^ Charles E. Spurgeon, Ethernet : The Definitive Guide, ( O'Reilly Media, Inc., 2000 ) ISBN 1565926609 page 212 Jump up ^ `` Connector Pin Assignments ''. Cisco. Retrieved 2014 - 04 - 14. Jump up ^ `` RJ45 Pinout ''. Jump up ^ `` LAN Wiring & Pinouts ''. Sources `` National Communications System Federal Telecommunications Recommendation 1090 - 1997 ''. Retrieved 2014 - 04 - 14. External links Wikimedia Commons has media related to Computer network. CAT 5 / 5e / 6 / 6A / 6A / 7 Cable - RJ - 45 Connector, ProAV.de `` UTP Cable Termination Standards 568A Vs 568B '' ( 2006 ) Unshielded and shielded twisted pair cabling standards Categories Cat 1 Cat 2 Cat 3 Cat 4 Cat 5 / 5e Cat 6 / 6a Cat 7 / 7a Cat 8 / 8.1 / 8.2 See also TIA / EIA - 568 Ethernet over twisted pair Modular connector Twisted pair Retrieved from `` https://en.wikipedia.org/w/index.php?title=TIA/EIA-568&oldid=802350082 '' Categories : Ethernet Telecommunications standards Signal cables Networking standards EIA standards Talk Article Talk More Contents About Wikipedia Català Čeština Deutsch Eesti Español 한국어 עברית 日本 語 Polski Português Română Русский Svenska Türkçe Українська 中文 Edit links This page was last edited on 25 September 2017, at 16 : 28. Text is available under the Creative Commons Attribution - ShareAlike License ; additional terms may apply. By using this site, you agree to the Terms of Use and Privacy Policy. Wikipedia ® is a registered trademark of the Wikimedia Foundation, Inc., a non-profit organization. About Wikipedia

Question: what types of organizations were involved in developing the tia/eia-568-b standard
Answer: manufacturers