Nominal pipe size - wikipedia Nominal pipe size This article is about the U.S. standard for pipe sizes, abbreviated NPS. For the U.S. standard for the straight thread form on pipe ( also abbreviated NPS ), see National Pipe Thread. Nominal Pipe Size ( NPS ) is a North American set of standard sizes for pipes used for high or low pressures and temperatures. `` Nominal '' refers to pipe in non-specific terms and identifies the diameter of the hole with a non-dimensional number ( for example -- 2 - inch nominal steel pipe '' consists of many varieties of steel pipe with the only criterion being a 2.375 - inch ( 60.3 mm ) outside diameter ). Specific pipe is identified by pipe diameter and another non-dimensional number for wall thickness referred to as the Schedule ( Sched. or Sch., for example -- `` 2 - inch diameter pipe, Schedule 40 '' ). NPS is often incorrectly called National Pipe Size, due to confusion with the American standard for pipe threads, `` national pipe straight '', which also abbreviates as `` NPS ''. The European and international designation equivalent to NPS is DN ( diamètre nominal / nominal diameter / Durchmesser nach Norm ), in which sizes are measured in millimetres, see ISO 6708. The term NB ( nominal bore ) is also frequently used interchangeably with NPS. In March 1927 the American Standards Association authorized a committee to standardize the dimensions of wrought steel and wrought iron pipe and tubing. At that time only a small selection of wall thicknesses were in use : standard weight ( STD ), extra-strong ( XS ), and double extra-strong ( XXS ), based on the iron pipe size ( IPS ) system of the day. However these three sizes did not fit all applications. Also, in 1939, it was hoped that the designations of STD, XS, and XXS would be phased out by schedule numbers, however those original terms are still in common use today ( although sometimes referred to as standard, extra-heavy ( XH ), and double extra-heavy ( XXH ), respectively ). Since the original schedules were created, there have been many revisions and additions to the tables of pipe sizes based on industry use and on standards from API, ASTM, and others. Stainless steel pipes, which were coming into more common use in the mid 20th century, permitted the use of thinner pipe walls with much less risk of failure due to corrosion. By 1949 thinner schedules 5S and 10S, which were based on the pressure requirements modified to the nearest BWG number, had been created, and other `` S '' sizes followed later. Due to their thin walls, the smaller `` S '' sizes can not be threaded together according to ASME code, but must be fusion welded. Contents 1 Application 2 Blockage or ball test 3 NPS tables for selected sizes 3.1 NPS 1⁄8 to NPS 31⁄2 3.2 NPS 4 to NPS 9 3.3 NPS 10 to NPS 24 3.4 NPS 26 to NPS 36 3.5 Additional sizes ( NPS ) 4 International usage 5 See also 6 Notes 7 References 8 External links Application Based on the NPS and schedule of a pipe, the pipe outside diameter ( OD ) and wall thickness can be obtained from reference tables such as those below, which are based on ASME standards B36. 10M and B36. 19M. For example, NPS 14 Sch 40 has an OD of 14 inches ( 360 mm ) and a wall thickness of 0.437 inches ( 11.1 mm ). However the NPS and OD values are not always equal, which can create confusion. For NPS 1⁄8 to 12, the NPS and OD values are different. For example, the OD of an NPS 12 pipe is actually 12.75 inches ( 324 mm ). To find the actual OD for each NPS value, refer to the tables below. ( Note that for tubing, the size indicates actual dimensions, not nominal. ) For NPS 14 and up, the NPS and OD values are equal. In other words, an NPS 14 pipe is actually 14 inches ( 360 mm ) OD. The reason for the discrepancy for NPS 1⁄8 to 12 inches is that these NPS values were originally set to give the same inside diameter ( ID ) based on wall thicknesses standard at the time. However, as the set of available wall thicknesses evolved, the ID changed and NPS became only indirectly related to ID and OD. For a given NPS, the OD stays fixed and the wall thickness increases with schedule. For a given schedule, the OD increases with NPS while the wall thickness stays constant or increases. Using equations and rules in ASME B31. 3 Process Piping, it can be shown that pressure rating decreases with increasing NPS and constant schedule. Some specifications use pipe schedules called standard wall ( STD ), extra strong ( XS ), and double extra strong ( XXS ), although these actually belong to an older system called iron pipe size ( IPS ). The IPS number is the same as the NPS number. STD is identical to SCH 40S, and 40S is identical to 40 for NPS 1 / 8 to NPS 10, inclusive. XS is identical to SCH 80S, and 80S is identical to 80 for NPS 1 / 8 to NPS 8, inclusive. XXS wall is thicker than schedule 160 from NPS 1 / 8 in to NPS 6 in inclusive, and schedule 160 is thicker than XXS wall for NPS 8 in and larger. Blockage or ball test When a pipe is welded or bent the most common method to inspect blockages, misalignment, ovality, and weld bead dimensional conformity is to pass a round ball through the pipe coil or circuit. If the inner pipe dimension is to be measured then the weld bead should be subtracted, if welding is applicable. Typically, the clearance tolerance for the ball must not exceed 1 millimetre ( 0.039 in ). Allowable ovality of any pipe is measured on the inside dimension of the pipe, normally 5 % to 10 % ovality can be accepted. If no other test is conducted to verify ovality, or blockages, this test must be seen as a standard requirement. A flow test can not be used in lieu of a blockage or ball test. See pipe dimensional table, Specification ASME B36. 10M or B36. 19M for pipe dimensions per schedule. Stainless steel pipe is most often available in standard weight sizes ( noted by the S designation ; for example, NPS Sch 10S ). However stainless steel pipe can also be available in other schedules. Both polyvinyl chloride pipe ( PVC ) and chlorinated polyvinyl chloride pipe ( CPVC ) are made in NPS sizes. NPS tables for selected sizes NPS 1⁄8 to NPS 31⁄2 Note that DN does not exactly correspond to a size in millimeters, because ISO 6708 defines it as being a dimensionless specification only indirectly related to a diameter. The ISO 6708 sizes provide a metric name for existing inch sizes, resulting in a 1 : 1 correlation between NPS and DN sizes. ISO 6708 does not include values for `` DN 6 '' or `` DN 8 '', however ASME B36. 10M list the `` DN 6 '' and `` DN 8 ''. NPS DN ( dimensionless ) OD ( in ( mm ) ) Wall thickness ( in ( mm ) ) SCH 5s SCH 10s / 20 SCH 30 SCH 40s / 40 / STD SCH 80s / 80 / XS SCH 120 SCH 160 XXS 1⁄8 0.405 ( 10.29 ) 0.035 ( 0.889 ) 0.049 ( 1.245 ) 0.057 ( 1.448 ) 0.068 ( 1.727 ) 0.095 ( 2.413 ) -- -- -- 1⁄4 6 0.540 ( 13.72 ) 0.049 ( 1.245 ) 0.065 ( 1.651 ) 0.073 ( 1.854 ) 0.088 ( 2.235 ) 0.119 ( 3.023 ) -- -- -- 3⁄8 10 0.675 ( 17.15 ) 0.049 ( 1.245 ) 0.065 ( 1.651 ) 0.073 ( 1.854 ) 0.091 ( 2.311 ) 0.126 ( 3.200 ) -- -- 1⁄2 15 0.840 ( 21.34 ) 0.065 ( 1.651 ) 0.083 ( 2.108 ) 0.095 ( 2.413 ) 0.109 ( 2.769 ) 0.147 ( 3.734 ) -- 0.188 ( 4.775 ) 0.294 ( 7.468 ) 3⁄4 20 1.050 ( 26.67 ) 0.065 ( 1.651 ) 0.083 ( 2.108 ) 0.095 ( 2.413 ) 0.113 ( 2.870 ) 0.154 ( 3.912 ) -- 0.219 ( 5.563 ) 0.308 ( 7.823 ) 25 1.315 ( 33.40 ) 0.065 ( 1.651 ) 0.109 ( 2.769 ) 0.114 ( 2.896 ) 0.133 ( 3.378 ) 0.179 ( 4.547 ) -- 0.250 ( 6.350 ) 0.358 ( 9.093 ) 11⁄4 32 1.660 ( 42.16 ) 0.065 ( 1.651 ) 0.109 ( 2.769 ) 0.117 ( 2.972 ) 0.140 ( 3.556 ) 0.191 ( 4.851 ) -- 0.250 ( 6.350 ) 0.382 ( 9.703 ) 11⁄2 40 1.900 ( 48.26 ) 0.065 ( 1.651 ) 0.109 ( 2.769 ) 0.125 ( 3.175 ) 0.145 ( 3.683 ) 0.200 ( 5.080 ) -- 0.281 ( 7.137 ) 0.400 ( 10.160 ) 50 2.375 ( 60.33 ) 0.065 ( 1.651 ) 0.109 ( 2.769 ) 0.125 ( 3.175 ) 0.154 ( 3.912 ) 0.218 ( 5.537 ) 0.250 ( 6.350 ) 0.344 ( 8.738 ) 0.436 ( 11.074 ) 21⁄2 65 2.875 ( 73.03 ) 0.083 ( 2.108 ) 0.120 ( 3.048 ) 0.188 ( 4.775 ) 0.203 ( 5.156 ) 0.276 ( 7.010 ) 0.300 ( 7.620 ) 0.375 ( 9.525 ) 0.552 ( 14.021 ) 80 3.500 ( 88.90 ) 0.083 ( 2.108 ) 0.120 ( 3.048 ) 0.188 ( 4.775 ) 0.216 ( 5.486 ) 0.300 ( 7.620 ) 0.350 ( 8.890 ) 0.438 ( 11.125 ) 0.600 ( 15.240 ) 31⁄2 90 4.000 ( 101.60 ) 0.083 ( 2.108 ) 0.120 ( 3.048 ) 0.188 ( 4.775 ) 0.226 ( 5.740 ) 0.318 ( 8.077 ) -- -- 0.636 ( 16.154 ) Tolerance : The tolerance on pipe OD is + 1 / 64 (. 0156 ) inch ( 0.40 mm ), - 1 / 32 (. 0312 ) inch ( 0.79 mm ). As per ASME B36. 10M - 2015 Pipe wall thickness are rounded to nearest 0.01 mm ( 0.00039 in ), while converting Wall Thickness from inch to mm. NPS 4 to NPS 9 NPS DN OD ( in ( mm ) ) Wall thickness ( in ( mm ) ) SCH 5 SCH 10s / 10 SCH 20 SCH 30 SCH 40s / 40 / STD SCH 60 SCH 80s / 80 / XS SCH 100 SCH 120 SCH 140 SCH 160 XXS 100 4.500 ( 114.30 ) 0.083 ( 2.108 ) 0.120 ( 3.048 ) -- 0.188 ( 4.775 ) 0.237 ( 6.020 ) -- 0.337 ( 8.560 ) -- 0.437 ( 11.100 ) -- 0.531 ( 13.487 ) 0.674 ( 17.120 ) 41⁄2 115 5.000 ( 127.00 ) -- -- -- -- 0.247 ( 6.274 ) -- 0.355 ( 9.017 ) -- -- -- -- 0.710 ( 18.034 ) 5 125 5.563 ( 141.30 ) 0.109 ( 2.769 ) 0.134 ( 3.404 ) -- -- 0.258 ( 6.553 ) -- 0.375 ( 9.525 ) -- 0.500 ( 12.700 ) -- 0.625 ( 15.875 ) 0.750 ( 19.050 ) 6 150 6.625 ( 168.28 ) 0.109 ( 2.769 ) 0.134 ( 3.404 ) -- -- 0.280 ( 7.112 ) -- 0.432 ( 10.973 ) -- 0.562 ( 14.275 ) -- 0.719 ( 18.263 ) 0.864 ( 21.946 ) 7 -- 7.625 ( 193.68 ) -- -- -- -- 0.301 ( 7.645 ) -- 0.500 ( 12.700 ) -- -- -- -- 0.875 ( 22.225 ) 8 200 8.625 ( 219.08 ) 0.109 ( 2.769 ) 0.148 ( 3.759 ) 0.250 ( 6.350 ) 0.277 ( 7.036 ) 0.322 ( 8.179 ) 0.406 ( 10.312 ) 0.500 ( 12.700 ) 0.593 ( 15.062 ) 0.719 ( 18.263 ) 0.812 ( 20.625 ) 0.906 ( 23.012 ) 0.875 ( 22.225 ) 9 -- 9.625 ( 244.48 ) -- -- -- -- 0.342 ( 8.687 ) -- 0.500 ( 12.700 ) -- -- -- -- -- NPS 10 to NPS 24 NPS DN OD ( in ( mm ) ) Wall thickness ( in ( mm ) ) SCH 5s SCH 5 SCH 10s SCH 10 SCH 20 SCH 30 SCH STD / 40S 10 250 10.75 ( 273.05 ) 0.134 ( 3.404 ) 0.134 ( 3.404 ) 0.165 ( 4.191 ) 0.165 ( 4.191 ) 0.250 ( 6.350 ) 0.307 ( 7.798 ) 0.365 ( 9.271 ) 12 300 12.75 ( 323.85 ) 0.156 ( 3.962 ) 0.156 ( 3.962 ) 0.180 ( 4.572 ) 0.180 ( 4.572 ) 0.250 ( 6.350 ) 0.330 ( 8.382 ) 0.375 ( 9.525 ) 14 350 14.00 ( 355.60 ) 0.156 ( 3.962 ) 0.156 ( 3.962 ) 0.188 ( 4.775 ) 0.250 ( 6.350 ) 0.312 ( 7.925 ) 0.375 ( 9.525 ) 0.375 ( 9.525 ) 16 400 16.00 ( 406.40 ) 0.165 ( 4.191 ) 0.165 ( 4.191 ) 0.188 ( 4.775 ) 0.250 ( 6.350 ) 0.312 ( 7.925 ) 0.375 ( 9.525 ) 0.375 ( 9.525 ) 18 450 18.00 ( 457.20 ) 0.165 ( 4.191 ) 0.165 ( 4.191 ) 0.188 ( 4.775 ) 0.250 ( 6.350 ) 0.312 ( 7.925 ) 0.437 ( 11.100 ) 0.375 ( 9.525 ) 20 500 20.00 ( 508.00 ) 0.188 ( 4.775 ) 0.188 ( 4.775 ) 0.218 ( 5.537 ) 0.250 ( 6.350 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 0.375 ( 9.525 ) 22 550 22.00 ( 558.80 ) 0.188 ( 4.775 ) 0.188 ( 4.775 ) 0.218 ( 5.537 ) 0.250 ( 6.350 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 0.375 ( 9.525 ) 24 600 24.00 ( 609.60 ) 0.218 ( 5.537 ) 0.218 ( 5.537 ) 0.250 ( 6.350 ) 0.250 ( 6.350 ) 0.375 ( 9.525 ) 0.562 ( 14.275 ) 0.375 ( 9.525 ) NPS DN Wall thickness ( in ( mm ) ) SCH 40 SCH 60 SCH 80s / XS SCH 80 SCH 100 SCH 120 SCH 140 SCH 160 10 250 0.365 ( 9.271 ) 0.500 ( 12.700 ) 0.500 ( 12.700 ) 0.594 ( 15.088 ) 0.718 ( 18.237 ) 0.843 ( 21.412 ) 1.000 ( 25.400 ) 1.125 ( 28.575 ) 12 300 0.406 ( 10.312 ) 0.562 ( 14.275 ) 0.500 ( 12.700 ) 0.687 ( 17.450 ) 0.843 ( 21.412 ) 1.000 ( 25.400 ) 1.125 ( 28.575 ) 1.312 ( 33.325 ) 14 350 0.437 ( 11.100 ) 0.593 ( 15.062 ) 0.500 ( 12.700 ) 0.750 ( 19.050 ) 0.937 ( 23.800 ) 1.093 ( 27.762 ) 1.250 ( 31.750 ) 1.406 ( 35.712 ) 16 400 0.500 ( 12.700 ) 0.656 ( 16.662 ) 0.5 ( 12.700 ) 0.843 ( 21.412 ) 1.031 ( 26.187 ) 1.218 ( 30.937 ) 1.437 ( 36.500 ) 1.594 ( 40.488 ) 18 450 0.562 ( 14.275 ) 0.750 ( 19.050 ) 0.500 ( 12.700 ) 0.937 ( 23.800 ) 1.156 ( 29.362 ) 1.375 ( 34.925 ) 1.562 ( 39.675 ) 1.781 ( 45.237 ) 20 500 0.593 ( 15.062 ) 0.812 ( 20.625 ) 0.500 ( 12.700 ) 1.031 ( 26.187 ) 1.280 ( 32.512 ) 1.500 ( 38.100 ) 1.750 ( 44.450 ) 1.968 ( 49.987 ) 22 550 -- 0.875 ( 22.225 ) 0.500 ( 12.700 ) 1.125 ( 28.575 ) 1.375 ( 34.925 ) 1.625 ( 41.275 ) 1.875 ( 47.625 ) 2.125 ( 53.975 ) 24 600 0.687 ( 17.450 ) 0.968 ( 24.587 ) 0.500 ( 12.700 ) 1.218 ( 30.937 ) 1.531 ( 38.887 ) 1.812 ( 46.025 ) 2.062 ( 52.375 ) 2.343 ( 59.512 ) NPS 26 to NPS 36 NPS DN OD ( in ( mm ) ) Wall thickness ( in ( mm ) ) SCH 5s SCH 10s SCH 10 SCH 20 SCH 30 SCH 40s / STD SCH 40 26 650 26.000 ( 660.400 ) -- -- 0.312 ( 7.925 ) 0.500 ( 12.700 ) -- 0.375 ( 9.525 ) -- 28 700 28.000 ( 711.200 ) -- ? 0.312 ( 7.925 ) 0.500 ( 12.700 ) 0.625 ( 15.875 ) 0.375 ( 9.525 ) -- 30 750 30.000 ( 762.000 ) 0.250 ( 6.350 ) 0.312 ( 7.925 ) 0.312 ( 7.925 ) 0.500 ( 12.700 ) 0.625 ( 15.875 ) 0.375 ( 9.525 ) -- 32 800 32.000 ( 812.800 ) -- -- 0.312 ( 7.925 ) 0.500 ( 12.700 ) 0.625 ( 15.875 ) 0.375 ( 9.525 ) 0.688 ( 17.475 ) 34 850 34.000 ( 863.600 ) -- -- 0.312 ( 7.925 ) 0.500 ( 12.700 ) 0.625 ( 15.875 ) 0.375 ( 9.525 ) 0.688 ( 17.475 ) 36 900 36.000 ( 914.400 ) -- -- 0.312 ( 7.925 ) 0.500 ( 12.700 ) -- 0.375 ( 9.525 ) -- Additional sizes ( NPS ) NPS DN OD ( in ( mm ) ) Wall thickness ( in ( mm ) ) STD. WT. SCH. XS SCH. XXS 40 1000 40.000 ( 1,016.000 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 42 1050 42.000 ( 1,066.800 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 44 1100 44.000 ( 1,117.600 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 46 1150 46.000 ( 1,168.400 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 48 1200 48.000 ( 1,219.200 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 52 1300 52.000 ( 1,320.800 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 56 1400 56.000 ( 1,422.400 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 60 1500 60.000 ( 1,524.000 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 64 1600 64.000 ( 1,625.600 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 68 1700 68.000 ( 1,727.200 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 72 1800 72.000 ( 1,828.800 ) 0.375 ( 9.525 ) 0.500 ( 12.700 ) 1.000 ( 25.400 ) 76 1900 76.000 ( 1,930.400 ) 80 2000 80.000 ( 2,032.000 ) 88 2200 88.000 ( 2,235.200 ) 92 2300 92.000 ( 2,336.800 ) International usage The term, nominal bore, is used in Australia and New Zealand with millimeter measurements. Hence, 50NB indicates a nominal bore of 50 mm ( 2.0 in ). See also British standard pipe thread sizes Copper tubing sizes Pipe thread sizes National pipe thread sizes Pipe ( fluid conveyance ) Pipe sizes Standard dimension ratio Notes Jump up ^ This is contrary to the Piping Handbook, which says that the schedule number can be converted to pressure by dividing the schedule by 1000 and multiplying by the allowable stress of the material. References Jump up ^ ASME B36. 10 2004, p. 1. ^ Jump up to : NPS - `` Nominal Pipe Size '' and DN - `` Diamètre Nominal '', EngineeringToolbox.com Jump up ^ ASME B36. 10 2004, p. iv. Jump up ^ ASME B36. 19 2004, p. iv. Jump up ^ `` Pipe Schedule Chart ''. HYSP Steel Pipe. Jump up ^ Nayyar 2000. ^ Jump up to : Table of Pipe Schedules from EngineersEdge.com. Jump up ^ `` A Complete Guide to Pipe Sizes and Pipe Schedule -- Free Pocket Chart ''. HardHat Engineer. Retrieved 2017 - 11 - 07. Jump up ^ A999 2014. `` ASTM A999 / A999M - 14 Standard Specification for General Requirements for Alloy and Stainless Steel Pipe ''. ASTM International. 2014. doi : 10.1520 / A0999_A0999M. Missing or empty url = ( help ) ; access - date = requires url = ( help ) Nayyar, Mohinder L. ( 2000 ). `` A1 ''. In Nayyar, Mohinder L. Piping Handbook ( 7th ed. ). New York : McGraw - Hill. ISBN 0 - 07 - 047106 - 1. B36. 10M Welded and Seamless Wrought Steel Pipe. The American Society of Mechanical Engineers. 2015. ISBN 9780791870273. Retrieved 2015 - 10 - 02. B36. 19M Stainless Steel Pipe. The American Society of Mechanical Engineers. 2004. ISBN 0791829170. Retrieved 2015 - 10 - 02. External links Notes on Pipe -- PVC Pipe weights and max PSI Quick calculator to determine standard pipe dimensions For Carbon Steel and Stainless Steel pipes as per ANSI. Nominal Pipe Size NPS, Nominal Bore NB, Outside Diameter OD Retrieved from `` https://en.wikipedia.org/w/index.php?title=Nominal_Pipe_Size&oldid=841291423 '' Categories : Piping Mechanical standards Hidden categories : Pages using web citations with no URL Pages using citations with accessdate and no URL Talk Contents About Wikipedia Deutsch Español Italiano Português Русский Українська Tiếng Việt Edit links This page was last edited on 14 May 2018, at 23 : 51. Text is available under the Creative Commons Attribution - ShareAlike License ; additional terms may apply. By using this site, you agree to the Terms of Use and Privacy Policy. Wikipedia ® is a registered trademark of the Wikimedia Foundation, Inc., a non-profit organization. About Wikipedia

Question: what is the meaning of schedule in pipes
Answer: wall thickness