Sump pump - wikipedia Sump pump This article needs additional citations for verification. Please help improve this article by adding citations to reliable sources. Unsourced material may be challenged and removed. ( April 2017 ) A small submersible AC sump pump with a garden hose connector A sump pump is a pump used to remove water that has accumulated in a water - collecting sump basin, commonly found in the basements of homes. The water may enter via the perimeter drains of a basement waterproofing system, funneling into the basin or because of rain or natural ground water, if the basement is below the water table level. Sump pumps are used where basement flooding happens regularly and to solve dampness where the water table is above the foundation of a home. Sump pumps send water away from a house to any place where it is no longer problematic, such as a municipal storm drain or a dry well. Pumps may discharge to the sanitary sewer in older installations. Once considered acceptable, this practice may now violate the plumbing code or municipal bylaws, because it can overwhelm the municipal sewage treatment system. Municipalities urge homeowners to disconnect and reroute sump pump discharge away from sanitary sewers. Fines may be imposed for noncompliance. Many homeowners have inherited their sump pump configurations and do not realize that the pump discharges into the sewer. Usually hardwired into a home 's electrical system, sump pumps may have a battery backup. The home 's pressurized water supply powers some pumps, eliminating the need for electricity at the expense of using potable water, potentially making them more expensive to operate than electrical pumps and creating an additional water disposal problem. Since a sump basin may overflow if not constantly pumped, a backup system is important for cases when the main power is out for prolonged periods of time, as during a severe storm. There are generally two types of sump pumps -- pedestal and submersible. In the case of the pedestal pump, the motor is mounted above the sump -- where it is more easily serviced, but is also more conspicuous. The pump impeller is driven by a long, vertical extension shaft and the impeller is in a scroll housing in the base of the pump. The submersible pump, on the other hand, is entirely mounted inside the sump, and is specially sealed to prevent electrical short circuits. There is debate about which variety of sump pump is better. Pedestal sump pumps usually last longer ( 25 to 30 years ) if they are installed properly and kept free of debris. They are less expensive and easier to remove. Submersible pumps will only last 5 to 15 years. They are more expensive to purchase but can take up debris without clogging. Sump pump systems are also utilized in industrial and commercial applications to control water table - related problems in surface soil. An artesian aquifer or periodic high water table situation can cause the ground to become unstable due to water saturation. As long as the pump functions, the surface soil will remain stable. These sumps are typically ten feet in depth or more ; lined with corrugated metal pipe that contains perforations or drain holes throughout. They may include electronic control systems with visual and audible alarms and are usually covered to prevent debris and animals from falling in. Contents 1 Components 2 Pump selection 3 Backup components 4 Maintenance 5 Footnotes 6 Resources Components Modern sump pump components in the United States are standardized. They consist of : A plastic, metal, or concrete container forming a sump basin, approximately 2 feet ( 0.6 m ) across and 2 to 3 feet ( 0.6 to 1 m ) deep, 15 to 25 U.S. gallons ( 60 to 100 litre ) capacity ; A sump pump, either 1 / 3 or 1 / 2 horsepower ( 200 or 400 W ), either battery or mains powered ( or both ). Pump selection Selection of a sump pump may consider : Automatic vs. manual operation -- pump may be controlled automatically by a level switch. Power -- Sump pump motive power will vary from 1 / 4 horsepower to multiple horsepower. Head pressure -- The hydraulic head pressure of a sump pump describes the maximum height that the pump will move water. For instance, a sump pump with a 15 feet ( 4.6 m ) maximum head ( also called a shutoff head ) will raise water up 15 feet ( 4.6 m ) before it completely loses flow... Power cord length -- Running a more powerful electrical motor a long distance from the main service panel will require heavier gauge wiring to assure sufficient voltage at the motor for proper pump performance. Phase and voltage -- Sump pumps powered from the AC mains are available with single - phase or three - phase induction motors, rated for 110 -- 120, 220 -- 240, or 460 volts. Three - phase power is typically not available in residential locations. Water level sensing switch type -- Pressure switches are fully enclosed, usually inside the pump body, making them immune to obstructions or floating debris in the sump basin. Float switches, particularly the types attached to the end of a short length of flexible electrical cable, can get tangled or obstructed, especially if the pump is prone to movement in the basin due to torque effects when starting and stopping. Pressure switches are typically factory set and not adjustable, while float switches can be adjusted in place to set the high and low water levels in the sump basin. There is a solid state switch utilizing field - effect technology, which will turn on and off the pump through use of an internal switch and a piggyback plug. Backup system and alarm for critical applications. Backup components A secondary, typically battery - powered sump pump can operate if the first pump fails. A battery - powered secondary pump requires the following components in parallel with the above others : A battery - driven 12 volt sump pump with its own water - level sensor, piping, and check valve ( the pipes usually join after the check valves to prevent reverse flow through the primary when the secondary unit is pumping ) ; It must be a marine deep cycle battery, or special long - life standby battery. Standard automobile batteries are not suitable for this application. Auto batteries are designed to deliver a high current for a short period. Sump pumps need a smaller current for a long time. A trickle - charge battery charger. It may alternately have a specialized controller to manage, monitor and test that the battery is holding a charge. Alternative sump pump systems can be driven by municipal water pressure. Water - powered sump pumps are similar to backup - battery - driven systems with a separate pump, float and check valves. During installation, the float is mounted in the sump pit above the normal high water mark. Under normal conditions, your main electric powered sump pump will handle all the pumping duties. When water rises higher than normal for any reason, the backup float in the sump is lifted and activates the backup sump pump. As municipal water rushes through the ejector, it creates a powerful suction force which causes the PVC pipe to act like a giant soda straw, drawing water up from the sump and ejecting it outdoors. There are no impellers, turbines, motors, or mechanical parts to wear out. There are no batteries, wires, or chargers to monitor, tend to, or replace. One can also use an ejector pump that uses an ordinary garden hose to supply high - pressure water and another garden hose to carry the water away. Although such ejector pumps waste water and are relatively inefficient, they have the advantage of having no moving parts and offer the utmost in reliability. If the backup sump system is rarely used, a component failure may not be noticed, and the system may fail when needed. Some battery control units test the system periodically and alert on failed electrical components. A simple, battery - powered water alarm can be hung a short distance below the top of the sump to sound an alarm should the water level rise too high. Maintenance Illustration of a typical pedestal - type sump pump. Sump basins and sump pumps must be maintained. Typical recommendations suggest examining equipment every year. Pumps running frequently due to higher water table, water drainage, or weather conditions should be examined more frequently. Sump pumps, being mechanical devices, will fail eventually, which could lead to a flooded basement and costly repairs. Redundancy in the system ( multiple / secondary pumps ) can help to avoid problems when maintenance and repairs are needed on the primary system. When examining a sump pump and cleaning it, dirt, gravel, sand, and other debris should be removed to increase efficiency and extend the life of the pump. These obstructions can also decrease the pump 's ability to drain the sump, and can allow the sump to overflow. The check valve can also jam from the debris. Examine the discharge line opening, when applicable, to ensure there are no obstructions in the line. Even a partially obstructed discharge line can force a sump pump to work harder and increase its chance of overheating and failure. Float switches are used to automatically turn the sump pump on when water rises to a preset level. Float switches must be clear of any obstructions within the sump. A float guard can be used to prevent the float switch from accidentally resting on the pump housing, and remaining on. As mechanical float switches can wear out, they should be periodically tested by actuating them manually to assure that they continue to move freely and that the switch contacts are opening and closing properly. If left in standing water, pedestal pumps should be manually run from time to time, even if the water in the sump is n't high enough to trip the float switch. This is because these pumps are incapable of removing all the water in a sump and the lower bearing or bushing for the pump impeller shaft tends to remain submerged, making it prone to corrosion and eventually freezing the drive shaft in the bearing. In the alternative, a pedestal pump that is expected to remain idle for an extended time should be removed from the sump and stored out of water, or the sump should be mopped out to bring the level of the remaining water well below the lower shaft bearing. Footnotes Jump up ^ `` Pedestal Sump Pumps ''. Retrieved January 14, 2014. Jump up ^ `` Sump Pumps : The Differences Between Common Pump Models ''. Basement Health Pros. Retrieved January 14, 2014. Jump up ^ `` Basepump Water - Powered Backup Sump Pump ''. Alpha Plumbing. Retrieved 27 September 2016. Jump up ^ `` Sump Pumps ''. Basement-repair.com. Retrieved 2013 - 09 - 17. Jump up ^ Author unknown ( Date unknown ). Basement Troubleshooting Guide : Failing Sump Pumps. Resources Ann Cameron Siegal, `` The Sump Pump 's Fault, or Yours ? '', Washington Post, August 9, 2008 `` Sump Pump Helps Keep Water Out '', North Dakota State University Extension Service, June 14, 2005 Thomas Scherer, `` Sump Pump Questions '', North Dakota State University Extension Service `` Sizing Up a Sump Pump '' ( pdf ), University of Illinois Extension John Newton & Co. `` Sump Pumps - Your Questions Answered '' Sewerage Types Combined sewer Decentralized wastewater system Drain - waste - vent system Effluent sewer Force main Gravity sewer Outfall Sanitary sewer Simplified sewerage Storm drain Vacuum sewer Construction materials Asbestos cement pipe Brickwork Cast iron pipe Concrete pipe Culvert Interceptor ditch Plastic pipe Reinforced concrete Steel pipe Vitrified clay pipe Related equipment Chopper pumps Combined sewer overflow Grease trap Grinder pump Manhole Lift station Sewage pumping Sewer dosing unit Sewer gas destructor lamp Stormwater detention vault Submersible pump Sump pump Trap Problems Biogenic sulfide corrosion Blocked Sewer First flush Infiltration / Inflow Sanitary sewer overflow Sewer fly Sewer gas Sewer rat Liquids transported Blackwater ( waste ) Greywater Industrial wastewater Sewage Stormwater Wastewater Retrieved from `` https://en.wikipedia.org/w/index.php?title=Sump_pump&oldid=818484601 '' Categories : Home appliances Plumbing Pumps Stormwater management Hidden categories : Articles needing additional references from April 2017 All articles needing additional references Talk Contents About Wikipedia Add links This page was last edited on 3 January 2018, at 21 : 03. Text is available under the Creative Commons Attribution - ShareAlike License ; additional terms may apply. By using this site, you agree to the Terms of Use and Privacy Policy. Wikipedia ® is a registered trademark of the Wikimedia Foundation, Inc., a non-profit organization. About Wikipedia

Question: where does the water in my sump pump come from
Answer: via the perimeter drains of a basement waterproofing system, funneling into the basin or because of rain or natural ground water, if the basement is below the water table level