## Part 6Ide Elevation Part Fir5T Floor Plan Part Rear Elevation Part Ground Floor Plan

ROOF CONSTRUCTION OVER UTILITY: Construct new roof with 125 x 50mm s.w. rotters at 450mm ctrs, set in hangers off 150 x 50mm pole plate bolted to existing wall at 600mm centres with MIO bolts and spicy cut to ditto wallplate at base, bedded in mortar and strapped down. Existing stone cversail to be safe guarded during works - see separate adjacent sketch. 

ROOF COVERING: Carefully strip off all Hardrow and ortificial files/slates from roof and corf away - replace with noturol welsh blue/grey slates, twice nailed each course on 38 x 25miTt s.w. tanalised battens at required gouge with 3.5mm diam, 50mm aluminium shank nails on Oaltex Roofshield breathable 

## Prev10Li6 Door Current Replacement Door

'underfed' (t50mm lops) on new rafters - fix 450mm wide dpc into gutter, set over tilt fiilet. Supply GROUND FLOOR CONSTRUCTION: Reclaimed stone flags bedded 125mm limecrete floor slob mix l:|:!. NHL5.0 IO-20mm a fix at! eaves and verge slates and bed as required in |:5 lime based mortar (NHL3.5). All lead work to diom. 'Optiroc' lime expanded cloy aggregate (LECA) and well graded sharp concreting sand on permeable geotextile be closely inspected and replaced as necessary using a minimum of code 4 lead to aprons, code 3 to matting on 100mm LECA {10-20mm diam.) on further layer of permeable geotextile matting. 

soakers and code 5 to valleys - oil treated with one coot of patination oil within 24 hours of fixing. All rainwater end associated fascia boards, etc. to be removed, eaves stone work made good and new cast iron GROUND FLOOR CEILING: The new sloping ceilings is to be 12.7mm foil-backed plaster board 8i skim (taped joints) 
rainwater goods fixed - with 
1 10mm half round gutters on rise and fall brackets end 63mm diam. down pipes with 90mm Celotex between new rafters with 50mm lold to underside, between 50 x 50mFn cross battens at 450mm fixed to walls with bobbins and pins. Joints to be sealed with linseed oil putty and oil goods decorated centres to take plosterboard - ensure 25mm gap to underside of roofing membrone. Note: Existing ceiling plasterboard. 

thereafter. All verges and ridges to be repointed - ridges to be retained and re-used and new ridges to be blue cloy ridges. 

EXTRACT FAN: Utility room to be fitted with extract fan capable of 30 litres/sec. extraction operated intermittently vie a fused switch. Kitchen to hove fan capable of extracting 60 litres/sec. or extractor hood capable of 30 
UTILITY ROOF: Replace corrugated sheeting with natural slates as above and fix continuous eaves and litres/sec. operated infermitfently via a fused spur switch. Rooms containing fans to hove 10mm gap under internal abutment vents for cross flow ventilation. Verges to roof fo overhang wall 50mm to avoid water ingress as doors to allow replacement of air. 

per good building practice. 

FRONT DOOR: Retrospective approval required for door replaced previously without consent - see above photos. 

CHIMNEY STACKS: Existing chimney, stocks to be carefully inspected and any necessary remedial works are to be as - to to as ho and 

## General Notes:

1. All work lo. comply with the Building Regulations 2000 and subsequent amendments. 
2. All materials supplied and Fitted in accordance with relevant British Standards, 
Codes of Practice, Agrement Certificates and Manufacturer's Instructions. 
3. Plumbing Works to comply with BS 5572 - 40mm diameter waste to sinks and 32mm 
to lavatory basins end if combined wastes to be 50mm diam. - all with 75mm deepseal 
traps. Connect oil wastes to existing gully as required on site. 

## Bed. •

4. All Electrical Work to comply with the requirements of fhe Electricity Board 8s those of the 17th Edition of the lEE Regulations - 85.7671:2008. All electrical, telephone, tv and other sockets to be a min. of 450mm above floor level with all switches at a max, of 1200mm above floor level - all certified to 85.7671:2008. 

5. All New Water installations to comply with the Bylaws of the Local Water Authority. 

All hot and cold feeds to be in copper with lead free soldered joints with isolation valve: 
to QH new fittings. Insulate and clip all pipework as per Good Practice Guide 302. All ho water taps are to be installed on the left of all sanitary ware/sinks, etc. 

6.This property is a dwelling house with Spread of Flame to oil surfoces Class I. 

7. New leodwork to be carried out in Code 4 milled lead unless otherwise specified and to IDA recommendations and it should be treated with one coat of pafination oil ofter fixing. 

8. All new structural timber is to be CI6 Grade 8i pressure treated with an approved preservative against Fungal 8i Insect attack. 

9. Existing Drains to be exposed 8i alt new works carried out to the drawings 8i to Building Inspector's approval in Hepworth's supersleve vitrified clay pipework or equol approved, as required. 

10. All new windows to be glazed as stated Histogloss, Slinilite or equal tOmm double glazed units bedded in modified putty or single glazed in accordance with manufacturers recommendations as stated elsewhere. 

1 1. Provide lime based render to base of walls where former skirtings and make good wall finishes elsewhere in Utility. 

12. Re-roofing works to be undertake in February and IVIarch to ovoid distruption to any bat i.e. during hibernation period, 

## Roof Plan A5 Proposed 00 Rics

noke khere is addikionai space under window cili ko skeepen roop pikch prom 20 ko 22.3 
degrees ko allow por greaka^ gap bekween new 

## The Mark Of Property Professionalism Worldwide

skrucKre and exisking oversail Do not scale from drawing - use written dimensions only 
-any discrepancies should be reported to the author. This drawing Is copyrigl-it and should not be reproduced with­
out written consent of REM ASSOCIATES, 

                                                                                              - 
                                                                                               •Ol im A 
                                                                                                                   A TCODD 
                                                                                                                         dn 

## Rlm Associates - •

Job oversail ko remain visible in Ukiliky Room GREEN FARM. KING STERNDALE. 

CLIENT, Mr. B. a Mrs. J. CLARBOUR. 

DRAWING 
PROPOSED DETAILS OF FARM HOUSE