Keep the technical equipment outside. Only cosiness stays inside.

The new Daikin Altherma Monobloc All-in-one solution for residential heating Our promise... ... is to ensure that customers can depend on Daikin for the ultimate in comfort, so that they are free to focus on their own working and home lives.

We promise to dedicate ourselves to technological excellence, a design focus and the highest quality standards so that our customers can trust and rely on the comfort we deliver. Our promise to the planet is absolute. Our products are at the forefront of low energy-usage and we will innovate to further reduce the environmental impact of our heating solutions. From residential to collective heating solutions, from renovation to new build, we commit ourselves to answer all our customers' needs. Our heat pump DNA combined with our in-house combustion developments positions Daikin as a leader, for now and the decades to come.

## Contents

| Introduction	                             |   2 |
|-----------------------------|-----|
| Daikin Altherma             |     |
| low temperature monobloc    |   4 |
| E(B/D)LQ-CV3                |   6 |
| E(B/D)LQ011-016CV3/CW1      |   7 |
| E(B/D)LQ011-016C3V3/C3W1    |   8 |
| Options                     |   9 |
| Thermal stores and tanks    |  10 |
| EKHWP-B/EKHWP-PB            |  12 |
| EKHWS(U)-D                  |  13 |
| Always in control           |  14 |
| Daikin Online Controller    |  14 |
| EKRUCBL                     |  15 |
| EKRTR1/EKRTWA               |     15	 |
| Supporting tools            |  18 |
| Heating Solutions Navigator |  19 |
| Stand By Me                 |     19	 |

## Daikin Altherma Low Temperature Monobloc

The reversible air-to-water heat pump monobloc system is the ideal system for users that have limited installation space inside. Delivering cutting-edge performance within the market's most compact monobloc outdoor unit, Daikin Altherma low temperature monobloc offers heating and cooling, with an optional connection to provide domestic hot water 

## High Performance A Simple Solution

›
› Improved seasonal efficiency ErP label up to A++
›
› High capacity at low ambient temperatures
The monobloc system combines all the features of heating and cooling (with optional domestic hot water) into one unit 

›
› Quiet and space-saving design that's easy to 
commission and install 
›
› Connection to new stainless steel DHW tank 
(EKHWS(U)-D) with improved energy efficiency label B 
 
›
› All hydraulic components are combined into one 
outdoor unit 

## Easy Installation

›
› Reliable operation is guaranteed, even with outdoor 
temperatures as low as -25°C 
›
› Sealed refrigerant means there is no need for 
refrigerant handling or F-gas qualifications 
›
› Combine with an  
  thermal store to 
provide thermal support
›
› Key hydraulic parts reduce the risk of installation 
errors and need for external parts such as expansion vessel, pump or isolation valves 
›
› Combine with a stainless steel tank for domestic hot 
water
›
› Fewer components lower the installation time and 
help maximise profits on the job 
 

## Year-Round Reliability

›
› Delivers higher heating capacity at low ambient 
temperatures 
›
› Flow temperatures up to 55°C, perfect for new build  
applications using UFH 
›
› Reliable operation is guaranteed, even with outdoor 
temperatures as low as -25°C 
›
› Equipped with optional backup heater 
 

## Easy Connection

›
› The LAN adapter allows to control the unit via the 
heating app

## The 5-7 Kw Range Of Daikin Altherma Monobloc

›
› Back-up heater less models
›
› Separate indoor wiring centre (control box)
›
› Separate back-up heater kit

## The 11-16 Kw Range Of Daikin Altherma Monobloc

›
› Smaller casing
›
› Back-up heater less models and models with 3V 
integrated back-up heater for maximum installation flexibility
›
› 1 ph and 3 ph models
›
› Reversible and heating only models
›
› LAN Adapter connection
›
› A++ heating energy label (from G to A++)

## Daikin Altherma Low Temperature Monobloc

Reversible air to water monobloc system, ideal when indoor space is limited

›
› Compact reversible monobloc for space heating & cooling with 
optional domestic hot water
›
› Compact heating only monobloc for space heating with optional 
domestic hot water
›
› Fuss-free installation : only water connections required
›
› Reliable operation even when -25°C outside thanks to frost 
protection features such as free hanging coil
›
› COP up to 5

| General                   | ηs (Seasonal space                |
|---------------------------|-----------------------------------|
| heating efficiency)       |                                   |
| %                         | 125                               |
| Single Unit               | EBLQ/EDLQ                         |
| Space heating             |                                   |
|                           |                                   |
| Average                   |                                   |
| climate                   |                                   |
| water outlet              |                                   |
| 55°C                      |                                   |
| SCOP                      | 3.20                              |
| Seasonal space heating    |                                   |
| eff. class                |                                   |
| A++                       |                                   |
| General                   | ηs (Seasonal space                |
| heating efficiency)       |                                   |
| %                         | 172                               |
| climate                   |                                   |
| water outlet              |                                   |
| 35°C                      |                                   |
| SCOP                      | 4.39                              |
| Seasonal space heating    |                                   |
| eff. class                |                                   |
| A++                       |                                   |
| Heating capacity          | Nom.                              |
| Cooling capacity          | Nom.                              |
| Power input               | Cooling                           |
| Heating                   | Nom.                              |
| COP                       | 5.00(1) / 3.58(2)                 |
| EER                       | 4.07(1) / 2.07(2)                 |
| Dimensions                | Unit                              |
| Weight                    | Unit                              |
| Operation range           | Heating                           |
| Cooling                   | Ambient                           |
| Water side Min.~Max.      | °C                                |
| Domestic                  |                                   |
| hot water                 |                                   |
| Ambient                   | Min.~Max.                         |
| Water side Min.~Max.      | °C                                |
| Refrigerant               | Type                              |
| GWP                       | 2,088                             |
| Charge                    | kg                                |
| Charge                    | TCO2Eq                            |
| Control                   | Expansion valve (electronic type) |
| Sound power level Heating | Nom.                              |
| Cooling                   | Nom.                              |
| Sound pressure            |                                   |
| level                     |                                   |
| Heating                   | Nom.                              |
| Cooling                   | Nom.                              |
| Wiring centre             | EKCB07CV3                         |
| Casing                    | Colour                            |
| Material                  | Precoated sheet metal             |
| Dimensions                | Unit                              |
| Weight                    | Unit                              |
| Back-up heater kit        | EKMBUHC3V3                        |
| Casing                    | Colour                            |
| Material                  | Precoated sheet metal             |
| Dimensions                | Unit                              |
| Weight                    | Unit                              |

(1) Cooling Ta 35°C - LWE 18°C (DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 35°C (DT = 5°C) (2) Cooling Ta 35°C - LWE 7°C ( DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 45°C ( DT = 5°C )  

## Daikin Altherma Low Temperature Monobloc Without Back-Up Heater

Reversible air to water monobloc system, ideal when indoor space is limited

›
› Monobloc all-in-one concept including hydraulic parts
›
› Separate indoor wiring center (control box)
›
› LAN Adapter connection
›
› Possible to combine with domestic hot water
›
› Energy efficient heating only system based on air-to-water heat 
pump technology
›
› A++ heating energy label (from G to A++)

Average climate water outlet 
Single Unit
EBLQ/EDLQ
011CV3
014CV3
016CV3
011CW1
014CW1
016CW1
Space heating 
General
ŋs (Seasonal space heating efficiency)
120
123
119
120
123
119
SCOP
3.09
3.16
3.06
3.09
3.16
3.06
55°C
Seasonal space heating eff. class
A+
Average climate water outlet 
General
ŋs (Seasonal space heating efficiency)
156
153
149
156
153
149
SCOP
3.98
3.90
3.80
3.98
3.90
3.80
35°C
Seasonal space heating eff. class
A++
A+
A++
A+
Heating capacity
Nom.
kW
11.2 (1) / 11.0 (2)
14.5 (1) / 13.6 (2)
16.0 (1) / 15.2 (2)
11.2 (1) / 11.0 (2)
14.5 (1) / 13.6 (2)
16.0 (1) / 15.2 (2)
Cooling capacity 
(only applicable to EBLQ)
Nom.
kW
12.4 (1) / 11.6 (2)
12.8 (1) / 12.6 (2)
13.9 (1) / 13.6 (2)
12.4 (1) / 11.6 (2)
12.8 (1) / 12.6 (2)
13.9 (1) / 13.6 (2)
Power input
Cooling
Nom.
kW
3.18 (1) / 5.09 (2)
3.16 (1) / 5.14 (2)
3.56 (1) / 5.96 (2)
3.18 (1) / 5.09 (2)
3.16 (1) / 5.14 (2)
3.56 (1) / 5.96 (2)
Heating
Nom.
kW
2.43 (1) / 3.10 (2)
3.37 (1) / 4.10 (2)
3.76 (1) / 4.66 (2)
2.43 (1) / 3.10 (2)
3.37 (1) / 4.10 (2)
3.76 (1) / 4.66 (2)
COP
4.61 (1) / 3.55 (2)
4.30 (1) / 3.32 (2)
4.26 (1) / 3.26 (2)
4.61 (1) / 3.55 (2)
4.30 (1) / 3.32 (2)
4.26 (1) / 3.26 (2)
EER (only applicable to EBLQ)
3.90 (1) / 2.28 (2)
4.05 (1) / 2.45 (2)
3.90 (1) / 2.28 (2) 3.90 (1) / 2.28 (2)
4.05 (1) / 2.45 (2)
3.90 (1) / 2.28 (2)
SEER (only applicable to EBLQ)
3.85
3.89
3.90
3.85
3.89
3.90
Dimensions
Unit
HeightxWidthxDepth
mm
1,348x1,160x380
Weight
Unit
kg
151
154
Operation range (3) Heating
Ambient
Min.~Max.
°CWB
-25~35
Water side Min.~Max.
°C
25~55
Operation range (3) 
 
(only applicable to EBLQ)
Cooling
Ambient
Min.~Max.
°CDB
10~46
Water side Min.~Max.
°C
5~22
Operation range (3) Domestic 
hot water
Ambient
Min.~Max.
°CDB
-25~35
Water side Min.~Max.
°C
25~80
Refrigerant
Type
R-410A
GWP
2087.5
Charge
kg
3.40
Charge
TCO2Eq
7.10
Control
Expansion valve (electronic type)
Sound power level Heating
Nom.
dBA
64
66
64
66
Cooling
Nom.
dBA
64
66
69
64
66
69
Sound pressure level
Heating
Nom.
dBA
51
52
51
52
Cooling
Nom.
dBA
50
52
54
50
52
54
Wiring centre
EKCB07CV3
EK2CB07CV3
Casing
Colour
White
Material
Precoated sheet metal
Dimensions
Unit
HeightxWidthxDepth
mm
360x340x97.0
Weight
Unit
kg
4.00
Back-up heater kit
EKMBUHC3V3
EKMBUHC9W1
Casing
Colour
White
Material
Precoated sheet metal
Dimensions
Unit
HeightxWidthxDepth
mm
560x250x210
Weight
Unit
kg
11.0
13.0

(1) Condition 1: cooling Ta 35°C - LWE 18°C (DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 35°C (DT = 5°C) | (2)Condition 2: cooling Ta 35°C - LWE 7°C ( DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 45°C ( DT = 5°C ) | (3) Including back-up heater and/or booster heater, see details in databook. 

## Daikin Altherma Low Temperature Monobloc With Integrated Back-Up Heater

Reversible air to water monobloc system, ideal when indoor space is limited

›
› Monobloc all-in-one concept including hydraulic parts
›
› Separate indoor wiring center (control box)
›
› LAN Adapter connection
›
› Possible to combine with domestic hot water
›
› Energy efficient heating only system based on air-to-water heat 
pump technology
›
› A++ heating energy label (from G to A++)

Average climate water outlet 
Single Unit
EBLQ/EDLQ
011C3V3
014C3V3
016C3V3
011C3W1
014C3W1
016C3W1
Space heating 
General
ŋs (Seasonal space heating efficiency)
120
123
119
120
123
119
SCOP
3.09
3.16
3.06
3.09
3.16
3.06
55°C
Seasonal space heating eff. class
A+
Average climate water outlet 
General
ŋs (Seasonal space heating efficiency)
156
153
149
156
153
149
SCOP
3.98
3.90
3.80
3.98
3.90
3.80
35°C
Seasonal space heating eff. class
A++
A+
A++
A+
Heating capacity
Nom.
kW
11.2 (1) / 11.0 (2)
14.5 (1) / 13.6 (2)
16.0 (1) / 15.2 (2)
11.2 (1) / 11.0 (2)
14.5 (1) / 13.6 (2)
16.0 (1) / 15.2 (2)
Cooling capacity
(only applicable to EBLQ)
Nom.
kW
12.4 (1) / 11.6 (2)
12.8 (1) / 12.6 (2)
13.9 (1) / 13.6 (2)
12.4 (1) / 11.6 (2)
12.8 (1) / 12.6 (2)
13.9 (1) / 13.6 (2)
Power input
Cooling
Nom.
kW
3.18 (1) / 5.09 (2)
3.16 (1) / 5.14 (2)
3.56 (1) / 5.96 (2)
3.18 (1) / 5.09 (2)
3.16 (1) / 5.14 (2)
3.56 (1) / 5.96 (2)
Heating
Nom.
kW
2.43 (1) / 3.10 (2)
3.37 (1) / 4.10 (2)
3.76 (1) / 4.66 (2)
2.43 (1) / 3.10 (2)
3.37 (1) / 4.10 (2)
3.76 (1) / 4.66 (2)
COP
4.61 (1) / 3.55 (2)
4.30 (1) / 3.32 (2)
4.26 (1) / 3.26 (2)
4.61 (1) / 3.55 (2)
4.30 (1) / 3.32 (2)
4.26 (1) / 3.26 (2)
EER (only applicable to EBLQ)
3.90 (1) / 2.28 (2)
4.05 (1) / 2.45 (2)
3.90 (1) / 2.28 (2) 3.90 (1) / 2.28 (2)
4.05 (1) / 2.45 (2)
3.90 (1) / 2.28 (2)
SEER (only applicable to EBLQ)
3.85
3.89
3.90
3.85
3.89
3.90
Dimensions
Unit
HeightxWidthxDepth
mm
1,348x1,160x380
Weight
Unit
kg
157
160
Operation range (3) Heating
Ambient
Min.~Max.
°CWB
-25~35
Water side Min.~Max.
°C
25~55
Operation range (3)
(only applicable to EBLQ)
Cooling
Ambient
Min.~Max.
°CDB
10~46
Water side Min.~Max.
°C
5~22
Operation range (3) Domestic 
hot water
Ambient
Min.~Max.
°CDB
-25~35
Water side Min.~Max.
°C
25~80
Refrigerant
Type
R-410A
GWP
2087.5
Charge
kg
3.40
Charge
TCO2Eq
7.10
Control
Expansion valve (electronic type)
Sound power level Heating
Nom.
dBA
64
66
64
66
Cooling
Nom.
dBA
64
66
69
64
66
69
Sound pressure level
Heating
Nom.
dBA
51
52
51
52
Cooling
Nom.
dBA
50
52
54
50
52
54
Wiring centre
EKCB07C3V3
EK2CB07C3V3
Casing
Colour
White
Material
Precoated sheet metal
Dimensions
Unit
HeightxWidthxDepth
mm
360x340x97.0
Weight
Unit
kg
4.00
| Type                                   | Material name   |
|----------------------------------------|-----------------|
| LAN adapter                            | BRP069A62       |
| -                                      | -               |
| LAN adapter + PV solar connection      | BRP069A61       |
| -                                      | -               |
| Remote user interface (DE, FR, NL, IT) | EKRUCBL1        |
| -                                      | -               |
| Remote user interface (EN, ES, EL, PT) | EKRUCBL3        |
| -                                      | -               |
| Remote user interface (EN, SV, NO, FI) | EKRUCBL2        |
| -                                      | -               |
| Remote user interface (EN, TR, PL, RO) | EKRUCBL4        |
| -                                      | -               |
| Controls                               |                 |
| Remote user interface (DE, CS, SL, SK) | EKRUCBL5        |
| -                                      | -               |
| Remote user interface (EN, HR, HU, BG) | EKRUCBL6        |
| -                                      | -               |
| Remote user interface (EN, DE, RU, DA) | EKRUCBL7        |
| -                                      | -               |
| Simplified user interface              | EKRUCBSB        |
| -                                      |                 |
| Room thermostat (wired)                | EKRTWA          |
| -                                      | -               |
| Room thermostat (wireless)             | EKRTR1          |
| -                                      | -               |
| Adapter                                | Digital I/O PCB |
| -                                      |                 |
| Back-up heater monobloc                | EKMBUHC3V3/C9W1 |
| -                                      | -               |
| Back-up heater                         |                 |
| Bottom plate heater                    | EKBPHTH16A      |
| -                                      |                 |
| Drain                                  | Drain kit       |
| -                                      |                 |
| Remote sensor for OU                   | EKRSCA1         |
| -                                      | -               |
| Sensor                                 | External sensor |
| -                                      | -               |
| Remote sensor for IU                   | KRCS01-1        |
| -                                      | -               |
| Control box                            | EKCB07CAV3      |
| -                                      | -               |
| Wiring centre                          |                 |
| Option box                             | EK2CB07CAV3     |
| -                                      | -               |
| By pass                                | Valve kit       |
| -                                      | -               |
| Bizone                                 | Bizone kit      |
| -                                      | -               |
| Others                                 | Cable           |
| -                                      |                 |
Daikin Altherma LT monobloc
Illustration
5-7 kW
11-16 kW 
BUH-less
11-16 kW 
with 3V 
BUH

## Thermal Stores And Tanks Hot Water Heating Installation Options

294L

## Why Choose A Thermal Store Or Domestic Hot Water Tank

Whether you only need hot water or you want to combine your hot water with solar systems, we offer you the best solutions to the highest levels of comfort, energy efficiency and reliability. 

## Comfort Efficiency

›
› High-quality insulation keeps heat loss to a minimum
›
› Efficient temperature heating: from 10°C to 50°C in 
only 60 minutes 
›
› Available in 150, 180, 200, 250 and 300 litres in  
stainless steel EKHWS(U)-D 
  
›
› Available as an integrated solution or separate tank

## Reliability

›
› At necessary intervals, the unit can heat up water up 
to 60°C to prevent the risk of bacteria growth

## Efficiency Thermal Store: Additional Hot Water Comfort

›
› Fit for the future: maximise renewable energy sources
Combine your monobloc with a thermal store to achieve the ultimate comfort at home. 

›
› Intelligent Heat Storage Management: ensures 
continuous heating during defrost mode, and uses stored heat for space heating
›
› Fresh water principle: receive domestic hot 
water on demand while eliminating the risk of contamination and sedimentation
›
› High-quality insulation keeps heat loss to a minimum 
 
 
Reliability  
›
› Optimal domestic hot water performance: the 
low temperature evolution enables high tapping 
performance
›
› Fit for the future: possibility to integrate with 
renewable solar energy and other heat sources, e.g. fireplace
›
› Maintenance-free tank: no corrosion, anode, scale or 
lime deposits, and no water loss through the safety valve 
›
› Lightweight and robust build of the unit combined 
with the cascade principle offers flexible installation options
 

## Pressureless (Drain-Back) Solar System

›
› The solar collectors are only filled with water when 
sufficient heating is provided by the sun 
›
› The pumps in the control and pump unit switch on 
briefly and fill the collectors with storage tank water  
›
› After filling, water circulation is maintained by the 
remaining pump 

## Thermal Store Plastic Domestic Hot Water Tank With Solar Support

›
› Tank designed for connection with pressurised thermal solar 
system
›
› Tank designed for connection with drainback thermal solar 
system
›
› Available in 300 and 500 liters
›
› Large hot water storage tank to provide domestic hot water at 
any time
›
› Heat loss is reduced to a minimum thanks to the high quality 
insulation
›
› Space heating support possible (500l tank only)

| Accessory                 | EKHWP                          | 300B                                          | 500B   | 300PB   | 500PB   |
|---------------------------|--------------------------------|-----------------------------------------------|--------|---------|---------|
| Casing                    | Colour                         | Traffic white (RAL9016) / Dark grey (RAL7011) |        |         |         |
| Material                  | Impact resistant polypropylene |                                               |        |         |         |
| Dimensions                | Unit                           | Width                                         | mm     | 595     | 790     |
| Depth                     | mm                             | 615                                           | 790    | 615     | 790     |
| Height                    | mm                             | 1,650                                         | 1,660  | 1,650   | 1,660   |
| Weight                    | Unit                           | Empty                                         | kg     | 58      | 82      |
| Tank                      |                                |                                               |        |         |         |
|                           |                                |                                               |        |         |         |
| Water volume              | l                              | 294                                           | 477    | 294     | 477     |
| Material                  | Polypropylen                   |                                               |        |         |         |
| Maximum water temperature | °C                             | 85                                            |        |         |         |
| Insulation Heat loss      |                                |                                               |        |         |         |
| kWh/24h                   | 1.5                            | 1.7                                           | 1.5    | 1.7     |         |
| Energy efficiency class   | B                              |                                               |        |         |         |
| Standing heat loss        | W                              | 64                                            | 72     | 64      | 72      |
| Storage volume            | l                              | 294                                           | 477    | 294     | 477     |
| Heat exchanger            | Domestic                       |                                               |        |         |         |
| hot water                 |                                |                                               |        |         |         |
| Quantity                  | 1                              |                                               |        |         |         |
| Tube material             | Stainless steel (DIN 1.4404)   |                                               |        |         |         |
| Face area                 | m²                             | 5.600                                         | 5.800  | 5.600   | 5.900   |
| Internal coil volume      | l                              | 27.1                                          | 28.1   | 27.1    | 28.1    |
| Operating pressure        | bar                            | 6                                             |        |         |         |
| Average specifc thermal   |                                |                                               |        |         |         |
| output                    |                                |                                               |        |         |         |
| W/K                       | 2,790                          | 2,825                                         | 2,790  | 2,825   |         |
| Charging                  | Quantity                       | 1                                             |        |         |         |
| Tube material             | Stainless steel (DIN 1.4404)   |                                               |        |         |         |
| Face area                 | m²                             | 3                                             | 4      | 3       | 4       |
| Internal coil volume      | l                              | 13                                            | 18     | 13      | 18      |
| Operating pressure        | bar                            | 3                                             |        |         |         |
| Average specifc thermal   |                                |                                               |        |         |         |
| output                    |                                |                                               |        |         |         |
| W/K                       | 1,300                          | 1,800                                         | 1,300  | 1,800   |         |
| Pressurised               |                                |                                               |        |         |         |
| solar                     |                                |                                               |        |         |         |
| Average specifc thermal   |                                |                                               |        |         |         |
| output                    |                                |                                               |        |         |         |
| W/K                       |                                |                                               |        |         |         |
| -                         |                                |                                               |        |         |         |
| 390.00                    | 840.00                         |                                               |        |         |         |
| Auxiliary                 |                                |                                               |        |         |         |
| solar                     |                                |                                               |        |         |         |
| heating                   |                                |                                               |        |         |         |
| Tube material             | -                              | Stainless steel                               |        |         |         |
| (DIN 1.4404)              |                                |                                               |        |         |         |
| -                         | Stainless steel                |                                               |        |         |         |
| (DIN 1.4404)              |                                |                                               |        |         |         |
| Face area                 | m²                             | -                                             | 1      | -       | 1       |
| Internal coil volume      | l                              | -                                             | 4      | -       | 4       |
| Operating pressure        | bar                            | -                                             | 3      | -       | 3       |
| Average specifc thermal   |                                |                                               |        |         |         |
| output                    |                                |                                               |        |         |         |
| W/K                       | -                              | 280                                           | -      | 280     |         |

## Domestic Hot Water Tank Stainless Steel Domestic Hot Water Tank

›
› Available in 150, 180, 200, 250 and 300l
›
› Energy efficiency class B
›
› Low standing losses (1,08 - 1,63 kWh/24h)
›
› Pre plumbed model (SU) for UK

| Accessory                 | EKHWS(U)                                     | 150D3V3       | 180D3V3   | 200D3V3   | 250D3V3   | 300D3V3   |
|---------------------------|----------------------------------------------|---------------|-----------|-----------|-----------|-----------|
| Casing                    | Colour                                       | Neutral white |           |           |           |           |
| Material                  | Epoxy coated steel / Epoxy-coated mild steel |               |           |           |           |           |
| Dimensions                | Unit                                         | Height        | Tank      | mm        | 1,000     | 1,164     |
| Weight                    | Unit                                         | Empty         | kg        | 45        | 50        | 53        |
| Tank                      |                                              |               |           |           |           |           |
|                           |                                              |               |           |           |           |           |
| Water volume              | l                                            | 145           | 174       | 192       | 242       | 292       |
| Material                  | Stainless steel (EN 1.4521)                  |               |           |           |           |           |
| Maximum water temperature | °C                                           | 75            |           |           |           |           |
| Insulation Heat loss      |                                              |               |           |           |           |           |
| kWh/24h                   | 1.1                                          | 1.2           | 1.3       | 1.4       | 1.6       |           |
| Energy efficiency class   | B                                            |               |           |           |           |           |
| Standing heat loss        | W                                            | 45            | 50        | 55        | 60        | 68        |
| Storage volume            | l                                            | 145           | 174       | 192       | 242       | 292       |
| Heat exchanger            | Domestic                                     |               |           |           |           |           |
| hot water                 |                                              |               |           |           |           |           |
| Quantity                  | 1                                            |               |           |           |           |           |
| Tube material             | Stainless steel (EN 1.4521)                  |               |           |           |           |           |
| Face area                 | m²                                           | 1.050         | 1.400     | 1.800     |           |           |
| Internal coil volume      | l                                            | 4.9           | 6.5       | 8.2       |           |           |
| Operating pressure        | bar                                          | 10            |           |           |           |           |
| Booster heater            | Capacity                                     | kW            | 3         |           |           |           |
| Power supply              | Phase/Frequency/Voltage                      | Hz/V          | 1~/50/230 |           |           |           |

## Always In Control Daikin Online Controller

The Daikin Online Controller application can control and monitor the status of your heating system and allows you to: 

## Monitor

›
› The status of your heating system
›
› Your energy consumption graphs

## Schedule

›
› Schedule the set temperature and operation 
mode 
with up to **6 actions per day for 7 days** 
›
› Enable **holiday mode** 
›
› View in intuitive mode

## Control **

›
› The **operation mode** and set temperature 
›
› Remotely control your system and domestic 
hot water 
*Control via the app
›
› Room thermostat control for space heating and domestic 
hot water
›
› Leaving water temperature control for domestic hot water
›
› External control for domestic hot water
Daikin Online Heating Control The Daikin Online Control Heating app is a multifaceted programme that allows customers to control and monitor the status of their heating system. 

## Main Features

›
› Equipped with GDPR (data protection) 
›
› Remote firmware update of LAN Adapter 
›
› Control over multiple unit locations

## Ekrucbl* Control

›
› Manage space heating, cooling, domestic hot water 
and among others, booster mode  
General features Several languages possible depending on the model, including: English, German, Dutch, Spanish, Italian, French, Greek, Russian, etc.  

›
› User-friendly remote control with contemporary 
design
›
› Easy to use with direct accessibility to all main 
functions 

## Comfort

›
› An additional user interface can include a room 
thermostat in the space to be heated 
›
› Easy commissioning: intuitive interface for 
advanced menu settings 
* only in combination with EKRTETS

## Ekrtr1/Ekrtwa General Features

›
› Set the temperature of the room based on 
measurements from the built-in or external sensor
Control The LCD screen of the room thermostat presents the necessary information regarding the setting of the Daikin Altherma system.

›
› Off function (with integrated frost-protection 
function)
›
› Holiday function mode
›
› Comfort and reduced function modes
›
› Time (day and month)
›
› Programmable weekly timer with 2 user defined and 
5 preset programmes, with up to 12 actions per day
Comfort An external sensor (EKRTETS) can be placed between the underfloor heating and the floor, as an alternative to the wireless room thermostat. 

 

›
› Keylock function
›
› Set limits: the installer can change the upper and 
lower limits
›
› Floor temperature protection

## Wired Remote Control For Heating

Indoor unit
EKRUCBL/EKRUCBS
1
2
3
4
5
6
7
EKRUCBS
Control systems 
Class of temperature control
VI
Contribution to seasonal space heating efficiency
%
4.0

## Ekrtwa/Ekrtr Wired Remote Control For Heating

|                                        |                                      | EKRTR              | EKRTWA   |
|----------------------------------------|--------------------------------------|--------------------|----------|
| Dimensions                             | Unit                                 | Height/Width/Depth | mm       |
| -/-/-                                  | 87/125/34                            |                    |          |
| Thermostat                             | Height/Width/Depth                   | mm                 |          |
| 87/125/34                              | -/-/-                                |                    |          |
| Receiver                               | Height/Width/Depth                   | mm                 |          |
| 170/50/28                              | -/-/-                                |                    |          |
| Weight                                 | Unit                                 | g                  |          |
| -                                      | 215                                  |                    |          |
| Thermostat                             | g                                    |                    |          |
| 210                                    | -                                    |                    |          |
| Receiver                               | g                                    |                    |          |
| 125                                    | -                                    |                    |          |
| Ambient                                |                                      |                    |          |
| temperature                            |                                      |                    |          |
| Storage                                | Min./Max.                            | °C                 |          |
| -20/60                                 |                                      |                    |          |
| Operation                              | Min./Max.                            | °C                 |          |
| 0/50                                   |                                      |                    |          |
| Temperature                            |                                      |                    |          |
| setting range                          |                                      |                    |          |
| Heating                                | Min./Max.                            | °C                 |          |
| 4/37                                   |                                      |                    |          |
| Cooling                                | Min./Max.                            | °C                 |          |
| 4/37                                   |                                      |                    |          |
| Clock                                  |                                      |                    |          |
| Yes                                    |                                      |                    |          |
| Regulation function                    |                                      |                    |          |
| Proportional band                      |                                      |                    |          |
| Power supply                           | Voltage                              | V                  |          |
| -                                      | Battery powered 3* AA-LR6 (alkaline) |                    |          |
| Thermostat                             | Voltage                              | V                  |          |
| Battery powered 3x AA-LRG (alkaline)   | -                                    |                    |          |
| Receiver                               | Voltage                              | V                  |          |
| 230                                    | -                                    |                    |          |
| Frequency                              | Hz                                   |                    |          |
| 50                                     | -                                    |                    |          |
| Phase                                  |                                      |                    |          |
| 1~                                     | -                                    |                    |          |
| Connection                             | Type                                 |                    |          |
| -                                      | Wired                                |                    |          |
| Thermostat                             |                                      |                    |          |
| Wireless                               | -                                    |                    |          |
| Receiver                               |                                      |                    |          |
| Wired                                  | -                                    |                    |          |
| Maximum distance                       |                                      |                    |          |
| to receiver                            |                                      |                    |          |
| Indoor                                 | m                                    |                    |          |
| approx. 30m                            | -                                    |                    |          |
| Outdoor                                | m                                    |                    |          |
| approx. 100m                           | -                                    |                    |          |
| Control systems                        |                                      |                    |          |
|                                        |                                      |                    |          |
| Class of temperature control           |                                      |                    |          |
| IV                                     |                                      |                    |          |
| Contribution to seasonal space heating |                                      |                    |          |
| efficiency                             |                                      |                    |          |
| %                                      |                                      |                    |          |
| 2.0                                    |                                      |                    |          |
EKRUCBL
EKRTWA
EKRTR

## Supporting Tools Heating Solutions Navigator

HSN provides the best fit solution for your customers home:

›
› User-friendly interface showcases the wide array of Daikin Heating Solutions available
›
› Estimation of the required heat load from a simple intuitive approach to a deeper detailed room-by-room calculation
›
› Country specific elements are taken into account
›
› Create custom made piping & wiring diagrams
›
› Link to flue gas selection tool for gas based solutions
›
› Set the configuration of your installation
›
› Overview of all the options specifically for your installation
›
› Quick link to the installation specific literature
›
› Compare economic and ecological benefit of the Daikin solution against a conventional heating installation.
›
› Storage of all your leads on you Stand By Me account
›
› Easy conversion from lead to installation to invite your end user for extra after-sales services
Want to know more about our Heating Solutions Navigator?

›
› Have a look at our video on https://www.youtube.com/watch?v=RomRf4W6Ci8!

## Stand By Me, My Climate Of Security

With your customer's new Daikin installation and Stand By Me service programme, you can rest assured they are benefiting from the best comfort, energy efficiency, usability and service available on the market. 

After-sales services
service partners
Stand By Me offers after-sales services such as warranty extensions and maintenance contracts: 

	 warranty extension on parts and/or 
labour 

Daikin service partners are automatically 
linked with their customer after registration 
on www.standbyme.daikin.eu.  
A notification is sent when a customer 
purchases a maintenance contract. 
 
Your customer is guaranteed: 

	 starts on commissioning date
	 quick and reliable service complete installation logbook 
including registration documents, maintenance deadlines, repair reports etc.
›
› For more details about the Stand By Me services in your country, contact your local Daikin office.

## Business Portal E-Care App All-In-One App For The Dealer

›
› Learn more about Daikin's units on our extranet 
portal: **my.daikin.eu** 
›
› Register your installation on Stand By Me via 
simple **QR code** scanning
›
› Receive information in a matter of seconds using 
our powerful search tool 
›
› Quick configuration of your heat pump in only 
7 steps
›
› Customise search options to only see 
information that is relevant for you
›
› Diagnosis of malfunction by QR code scanning and 
error code input
›
› Accessible via a mobile device or computer 
The key account portal is the perfect solution for large accounts: 

	 keep track of all your installations 
	 project management remote metering (UK only) 

## New

Daikin Europe N.V.  Naamloze Vennootschap Zandvoordestraat 300 · 8400 Oostende · Belgium · www.daikin.eu · BE 0412 120 336 · RPR Oostende (Responsible Editor)
The present publication is drawn up by way of information only and does not constitute an offer binding upon Daikin Europe N.V. Daikin Europe N.V. has compiled the content of this publication to the best of its knowledge. No express or implied warranty is given for the completeness, accuracy, reliability or fitness for particular purpose of its content and the products and services presented therein. Specifications are subject to change without prior notice. Daikin Europe N.V. explicitly rejects any liability for any direct or indirect damage, in the broadest sense, arising from or related to the use and/or interpretation of this publication. All content is copyrighted by Daikin Europe N.V. Printed on non-chlorinated paper.