PUHZ-HW140VHA2(-BS)/YHA2(-BS)
Ecodan Monobloc Standalone Air Source Heat Pumps Heating Our range of Ecodan monobloc standalone air source heat pumps includes 5, 8.5, 11.2 and 14kW sizes.  Now with the ability to cascade up to six units of the same output, Ecodan monobloc systems offer a capacity range from 5 through to 84kW.  
Designed to suit a wide number of applications, these models offer a viable solution for the varying requirements that domestic and small commercial applications demand.

## Key Features

Self-contained unit, only requiring water and electric connections 

Designed 
to meet the 
demands of 
today's heating
needs

No need for gas supply, flues or ventilation
Low maintenance and quiet operation
Operates with outside temperatures as low as -25ºC
Optimised low ambient defrost control and operation
Hybrid function, for use with conventional boilers
Energy monitoring as standard

## Puhz-Hw140Vha2(-Bs)/Yha2(-Bs) Ecodan Monobloc Standalone Air Source Heat Pumps Heating

*1 Combination with EHPT20X-MHCW Cylinder
*2 Under normal heating conditions at outdoor temp: -3°CDB / -4°CWB, outlet water temp 35°C, inlet water temp 30°C.

*3 Under normal heating conditions at outdoor temp: 7°CDB / 6°CWB, outlet water temp 35°C, inlet water temp 30°C as tested to BS EN14511.

*4 Sound power level tested to BS EN12102.

*5 Grille.    *6 Flow Temperature Controller (FTC) for standalone systems PAC-IF062B-E Dimensions WxDxH (mm) - 520x150x450    *7 MCB Sizes BS EN60898-2 & BS EN60947-2.

ɳs is the seasonal space heating energy efficiency (SSHEE)      ɳwh is the water heating energy efficiency

## Dimensions

Telephone: 01707 282880
email: heating@meuk.mee.com web: les.mitsubishielectric.co.uk UNITED KINGDOM Mitsubishi Electric Europe Living Environment Systems Division Travellers Lane, Hatfield, Hertfordshire, AL10 8XB, England   General Enquiries Telephone: 01707 282880   Fax: 01707 278881
IRELAND Mitsubishi Electric Europe Westgate Business Park, Ballymount, Dublin 24, Ireland Telephone: Dublin (01) 419 8800   Fax: Dublin (01) 419 8890   International code: (003531)
Country of origin: United Kingdom - Japan - Thailand - Malaysia.  ©Mitsubishi Electric Europe 2018. Mitsubishi and Mitsubishi Electric are trademarks of Mitsubishi Electric Europe B.V. The company reserves the right to make any variation in technical specification to the equipment described, or to withdraw or replace products without prior notification or public announcement.  Mitsubishi Electric is constantly developing and improving its products. All descriptions, illustrations, drawings and specifications in this publication present only general particulars and shall not form part of any contract. All goods are supplied subject to the Company's General Conditions of Sale, a copy of which is available on request.

Third-party product and brand names may be trademarks or registered trademarks of their respective owners.

Note: The fuse rating is for guidance only. Please refer to the relevant databook for detailed specification. It is the responsibility of a qualified electrician/electrical engineer to select the correct cable size and fuse rating based on current regulation and site specific conditions. Mitsubishi Electric's air conditioning equipment and heat pump systems contain a fluorinated greenhouse gas, R410A (GWP:2088), R32 (GWP:675), R407C (GWP:1774) or R134a (GWP:1430). *These GWP
values are based on Regulation (EU) No 517/2014 from IPCC 4th edition. In case of Regulation (EU) No.626/2011 from IPCC 3rd edition, these are as follows. R410A (GWP:1975), R32 (GWP: 550), R407C (GWP:1650) or R134a (GWP:1300).