| 8.                                                                              | Noise & Vibration                                |
|---------------------------------------------------------------------------------|--------------------------------------------------|
|                                                                                 |                                                  |
| 1                                                                               |                                                  |
| 8.1                                                                             | Introduction                                     |
|                                                                                 |                                                  |
| 1                                                                               |                                                  |
| 8.2                                                                             | Legislation, Planning Policy and Guidance        |
|                                                                                 |                                                  |
| 1                                                                               |                                                  |
| 8.3                                                                             | Assessment Methodology and Significance Criteria |
|                                                                                 |                                                  |
| 12                                                                              |                                                  |
| 8.4                                                                             | Baseline Conditions                              |
|                                                                                 |                                                  |
| 34                                                                              |                                                  |
| 8.5                                                                             | Development Design and Impact Avoidance          |
|                                                                                 |                                                  |
| 46                                                                              |                                                  |
| 8.6                                                                             | Likely Impacts and Effects                       |
|                                                                                 |                                                  |
| 48                                                                              |                                                  |
| 8.7                                                                             | Mitigation and Enhancement Measures              |
|                                                                                 |                                                  |
| 60                                                                              |                                                  |
| 8.8                                                                             | Limitation or Difficulties                       |
|                                                                                 |                                                  |
| 66                                                                              |                                                  |
| 8.9                                                                             | Summary of Likely Significant Residual Effects   |
|                                                                                 |                                                  |
| 67                                                                              |                                                  |
| 8.10                                                                            | References                                       |
|                                                                                 |                                                  |
| 71                                                                              |                                                  |
| Tables                                                                          |                                                  |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 1: Summary of relevant NPS advice regarding Noise and Vibration                 | 4                                                |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 2: Planning Practice Guidance                                                   | 8                                                |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 3: Consultation summary table                                                   | 12                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 4: Summary of key changes to chapter since publication of the PEI Report        | 18                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 5: Monitoring locations                                                         | 20                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 6: Measurement equipment                                                        | 21                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 7: Daily overview of meteorological conditions                                  | 22                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 8: Construction Noise SOAEL and LOAEL for residential receptors                 | 24                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 9: Construction Noise magnitude of impact criteria for residential receptors    | 25                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 10: Traffic noise criteria                                                      | 26                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 11: Construction vibration threshold at residential dwellings                   | 26                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 12: Transient vibration guide values for cosmetic damage                        | 28                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 13: Magnitude of impact                                                         |                                                  |
| -                                                                               |                                                  |
| construction vibration building damage                                          | 29                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 14: Magnitude of impact for industrial noise including building services        | 31                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 15: Sensitivity/value of receptors                                              | 31                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 16: Classification of effects                                                   | 32                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 17: Baseline Sound Levels at ML1                                                |                                                  |
| -                                                                               |                                                  |
| 4 North Street, Sturton                                                         |                                                  |
| -                                                                               |                                                  |
| le                                                                              |                                                  |
| -                                                                               |                                                  |
| Steeple                                                                         | 34                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 18: Baseline Sound Levels at ML2                                                |                                                  |
| -                                                                               |                                                  |
| Crossing Keepers Cottage, West Burton                                           | 35                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 19: Baseline Sound Levels at ML3                                                |                                                  |
| -                                                                               |                                                  |
| Mill House Farm, West Burton                                                    | 37                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 20: Baseline Sound Levels at ML4                                                |                                                  |
| -                                                                               |                                                  |
| Manor Cottage, Bole                                                             | 38                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 21: Baseline Sound Levels at ML5                                                |                                                  |
| -                                                                               |                                                  |
| 194 Lea Road, Gainsborough                                                      | 39                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 22: Baseline Sound Levels at ML6                                                |                                                  |
| -                                                                               |                                                  |
| Green Lane, Lea                                                                 | 40                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 23: Baseline Sound Levels at ML7                                                |                                                  |
| -                                                                               |                                                  |
| Knaith Hall, Knaith                                                             | 41                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 24: Representative background sound levels                                      | 45                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 25: Construction noise predictions for the Proposed Development at nearby NSR   |                                                  |
| during daytime                                                                  | 50                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 26: Predicted effect on NSR resulting from construction of the Proposed         |                                                  |
| Development during daytime                                                      | 52                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 27: Scenario 1                                                                  |                                                  |
| -                                                                               |                                                  |
| 2029 Baseline and Committed Development traffic flows                           | 53                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 28: Scenario 2                                                                  |                                                  |
| -                                                                               |                                                  |
| 2029 Baseline, Committed Development and construction traffic                   |                                                  |
| flows                                                                           | 54                                               |
| Table 8                                                                         |                                                  |
| -                                                                               |                                                  |
| 29: Changes in BNL as a result of the Proposed Development construction traffic |                                                  |
| 55                                                                              |                                                  |
Table 8-30: Predicted worst-case operational *specific sound levels* LAeq,T - Proposed 
Power Plant Site without mitigation
58
Table 8-31: BS 4142 worst-case daytime excess of *rating level* over background sound 
level, without mitigation
58
Table 8-32: BS 4142 worst-case night-time excess of *rating level* over background sound 
level, without mitigation
59
Table 8-33: Maximum attenuation (dB) required to achieve daytime operational LOAEL 
criteria
62
Table 8-34: Maximum attenuation (dB) required to achieve night-time operational LOAEL 
criteria
62
Table 8-35: Practical sound power reductions for worst-case source components provided 
by a manufactures
63
Table 8-36: Predicted operational *specific sound levels* LAeq,T - Proposed Power Plant Site 
with mitigation
63
Table 8-37: BS 4142 daytime excess of *rating level* over *background sound level*, with 
mitigation
64
Table 8-38: BS 4142 night-time excess of *rating level* over *background sound level*, with 
mitigation
65
Table 8-39: Likely significant residual effects summary table
68

## 8. Noise & Vibration 8.1 Introduction

 
This chapter of the Environmental Statement (ES) addresses the potential effects
8.1.1
of the construction, operation (including maintenance) and decommissioning of the proposed WBC gas fired generating station on the site of the West Burton Power Station (the Proposed Development) on noise and vibration receptors. The assessment considers:
·
the present-day and future baseline conditions during construction and at 
opening; 
·
the effects of construction of the Proposed Development on Noise Sensitive Receptors (NSR) during the site clearance and construction works and predicted changes in road traffic noise levels on the local road network; 
·
the effects of noise and vibration resulting from operation of the Proposed Development; and
·
the potential effects of the eventual decommissioning of the Proposed Development.
 
The cumulative effects of noise associated with the Proposed Development and
8.1.2
other committed developments in the vicinity are described in **Chapter 16**:
Cumulative and Combined Effects.
 
This chapter is supported by **Figure 8.1** (ES Volume III).
8.1.3
8.2
Legislation, Planning Policy and Guidance

## Legislative Background Environmental Protection Act 1990

 
The Environmental Protection Act 1990 (EPA) Part 3 (Ref 8-1) prescribes that
8.2.1
noise (and vibration) emitted from premises (including land) can be prejudicial to health and amount to a nuisance as a statutory nuisance.
 
Local Authorities are required to investigate any public complaints of noise and if
8.2.2
they are satisfied that a statutory nuisance exists, or is likely to occur or recur, they may serve a noise abatement notice.  A notice is served on the person responsible for the nuisance.  It requires either the abatement of the nuisance or works to abate the nuisance to be carried out, or it prohibits or restricts the activity. Contravention of a notice without reasonable excuse is an offence.  Right of appeal to the Magistrates Court exists within 21 days of the service of a noise abatement notice.
 
In determining if a noise complaint amounts to a statutory nuisance, the Local
8.2.3
Authority can take account of various guidance documents and existing case law; no statutory noise limits exist.  Demonstrating the use of 'Best Practicable Means' (BPM) to minimise noise levels is an accepted defence against a noise abatement
notice.

## Control Of Pollution Act 1974

 
Sections 60 and 61 of the Control of Pollution Act 1974 (CoPA) (Ref 8-2) provide
8.2.4
the main legislation regarding demolition and construction site noise and vibration. If noise complaints are received, a Section 60 notice may be issued by the local planning authority with instructions to cease work until specific conditions to
reduce noise have been adopted.
 
Section 61 of the CoPA provides a means for applying for prior consent to carry
8.2.5
out noise generating activities during construction. Once prior consent has been agreed under Section 61, a Section 60 notice cannot be served provided the agreed conditions are maintained on-site.
 
CoPA requires that BPM (as defined in Section 72 of CoPA) be adopted for
8.2.6
construction noise on any given site. CoPA makes reference to British Standard (BS) 5228 as BPM.

## Environmental Permitting Regulations 2016

 
The Environmental Permitting (England and Wales Regulations) 2016 (Ref 8-3)
8.2.7
require the application of Best Available Techniques (BAT) to activities performed within installations regulated under an Environmental Permit in order to manage the impact of these operations on the surrounding environment. The Environmental Permit applies only to the operational and decommissioning periods; not to the construction period.
 
In terms of noise specifically, the selection of BAT will have to be considered and
8.2.8
balanced with releases to different environmental media (air, land and water) and to give due consideration to issues such as usage of energy and raw materials. Noise, therefore, cannot be considered in isolation from other impacts on the environment.
 
The definition of pollution includes "emissions which may be harmful to human
8.2.9
health or the quality of the environment, cause offence to human senses or impair
or interfere with amenities and other legitimate uses of the environment" (clause
2). BAT is therefore likely to be similar, in practice, to the requirements of the statutory nuisance legislation which requires the use of BPM to prevent or minimise noise nuisance.  In the case of noise, "offence of any human senses" may be judged by the likelihood of complaints. However, the lack of complaint should not necessarily imply the absence of a noise problem. In some cases, it may be possible, and desirable, to reduce noise emissions still further at reasonable costs and this may therefore represent BAT for the control of noise
emissions from an installation. Consequently, the aim of BAT should be to ensure that there is no reasonable cause for annoyance to persons beyond the installation boundary.

 Guidance regarding Environmental Permitting and noise is available in the
8.2.10
Environment Agency's Integrated Pollution Prevention and Control (IPPC) H3 document 'Horizontal Guidance for Noise Part 2 - Noise assessment and Control' (Ref 8-4).  However, 'Horizontal Guidance for Noise Part 1 - Regulation and Permitting' (Ref 8-5), which provided guidance relating to noise limits from industrial installations in terms of absolute rating levels and rating levels relative to background noise levels (as defined in BS 4142:1997 (now superseded)) was
withdrawn in February 2016.  Therefore industry wide noise limits no longer apply.
Planning Policy Context National Planning Policy National Policy Statements for Energy

 Section 5.11 of the Overarching National Policy Statement (NPS) for Energy (EN-
8.2.11
1) (Ref 8-6) refers to the Government's policy on noise within the Noise Policy Statement for England (NPSE) (discussed further below) and sets out requirements for noise and vibration assessment for Nationally Significant Infrastructure Projects (NSIP) such as the Proposed Development.
 With regards to decision making, NPS EN-1 states:
8.2.12
"The project should demonstrate good design through selection of the quietest cost-effective plant available; containment of noise within buildings wherever possible; optimisation of plant layout to minimise noise emissions; and, where possible, the use of landscaping, bunds or noise barriers to reduce noise transmission." (paragraph 5.11.8).

Section 8.5 describes the impact avoidance measures identified relevant to the
8.2.13
Proposed Development.

 The NPS for Fossil Fuel Electricity Generating Infrastructure (EN-2) (Ref 8-7) sets
8.2.14
out policy specific to fossil fuel power stations.  In paragraph 2.7.1, specific sources of noise are identified. Those that are relevant to the Proposed Development include "the gas and steam turbines that operate continuously during
normal operation".  It then reiterates the point made in NPS EN-1, stating that:
"The primary mitigation for noise from fossil fuel generating stations is through good design, including enclosure of plant and machinery in noise-reducing buildings wherever possible and to minimise the potential for operations to create noise" and goes on to state that "Noise from gas turbines should be mitigated by attenuation of exhausts to reduce any risk of low-frequency noise transmission."
(paragraph 2.7.5).

## Table 8-1 Below Provides A Summary Of The Nps Advice Regarding Noise And 8.2.15 Vibration And How This Has Been Considered In This Chapter. Table 8-1: Summary Of Relevant Nps Advice Regarding Noise And Vibration

| Summary of NPS                       | Consideration within the Chapter    |
|--------------------------------------|-------------------------------------|
| NPS EN                               |                                     |
| -                                    |                                     |
| 1                                    |                                     |
| For descriptions of noise generating |                                     |
| aspects of the Proposed Development  |                                     |
| see                                  | Section 8.6.                        |

Paragraph 5.11.4 states: "Where 
noise impacts are likely to arise from 
the 
     proposed 
               development, 
                             the 
applicant should include the following 
in the noise assessment:

Noise Sensitive Premises have been 
identified in Table 8-5 - Monitoring 
Locations.

Information relating to the existing noise 
environment has been presented in 
Section 8.4.

Both 
       construction 
                     and 
                           operational 
impacts 
          have 
                 been 
                        presented 
                                    in 
Section 8.6.

·
A description of the noise generating 
aspects 
of 
the 
development proposal leading to noise impacts, including the identification of any distinctive, tonal, 
impulsive 
or 
low 
frequency characteristics of the noise;
The mitigation of construction and operational noise has been discussed in Section 8.7.

·
Identification of noise sensitive premises and noise sensitive areas that may be affected;
·
The 
characteristics 
of 
the 
existing noise environment;
·
A prediction of how the noise environment will change with the proposed development;
·
In the shorter term such as during the construction period;
·
In the longer term during the operating 
life 
of 
the 
infrastructure;
·
At particular times of the day, evening 
and 
night 
as 
appropriate;
·
An assessment of the effect of predicted changes in the noise;
·
Measures to be employed in mitigating noise.
The nature and extent of the noise assessment should be proportionate to the likely noise impact." Paragraph 5.11.5 states: "*The noise* Construction related traffic noise has 

Summary of NPS
Consideration within the Chapter 

been assessed in paragraphs 8.6.11– 
8.6.16

impact 
          of 
                ancillary 
                            activities 
associated with the development, 
such as increased road and rail traffic 
movements, 
              or 
                   other 
                          forms 
                                  of 
transportation, 
                 should 
                          also 
                                  be 
considered."

The effects of operational noise and its 
impact on human receptors can be 
found in paragraphs 8.6.20– 8.6.30

Paragraph 5.11.6 states: "Operational 
noise, 
        with 
               respect 
                         to 
                              human 
receptors, should be assessed using 
the principles of the relevant British 
Standards 
             and 
                   other 
                           guidance. 
Further information on assessment of 
particular noise sources may be 
contained in the technology-specific 
NPSs. In particular, for…electricity 
networks (EN-5) there is assessment 
guidance for specific features of 
those 
         technologies. 
                          For 
                                  the 
prediction, 
                assessment 
                                 and 
management of construction noise, 
reference should be made to any 
relevant British Standards and other 
guidance which also give examples of 
mitigation strategies."

Potential effects of noise on ecology and 
nature conservation are considered in 
Chapter 9: Ecology.

Paragraph 
            5.11.7 
                    states: 
                             "The 
applicant should consult EA and 
Natural England (NE), as necessary 
and in particular with regard to 
assessment of noise on protected 
species or other wildlife. The results 
of any noise surveys and predictions 
may 
        inform 
                 the 
                        ecological 
assessment. 
             The 
                   seasonality 
                                of 
potentially affected species in nearby 
sites may also need to be taken into 
account."

## Nps En-2

A noise assessment is included within this chapter.

Paragraph 2.7.2 states: "The ES 
should include a noise assessment as described in Section 5.11 in EN-1."
National Planning Policy Framework

 The revised National Planning Policy Framework (NPPF) (Ref 8-8) was published
8.2.16
in February 2019, replacing earlier versions published in July 2018 and March
2012.
 The NPPF states that;
8.2.17
"planning policies and decisions should contribute to and enhance the natural and local environment by…
e) preventing new and existing development from contributing to, being put at unacceptable risk from, or being adversely affected by, unacceptable levels of soil, air, water or noise pollution or land instability. Development should, wherever possible, help to improve local environmental conditions. (paragraph 
170)

·
Planning policies and decisions should also ensure that new development is appropriate for its location taking into account the likely effects (including cumulative effects) of pollution on health, living conditions and the natural environment, as well as the potential sensitivity of the site or the wider area to impacts that could arise from the development. In doing so they should:
§
mitigate and reduce to a minimum potential adverse impact resulting 
from noise from new development - and avoid noise giving rise to 
significant adverse impacts on health and the quality of life; [and]  
§
identify and protect tranquil areas which have remained relatively undisturbed by noise and are prized for their recreational and amenity value for this reason". (paragraph 180)
 With regards to 'adverse effects' and 'significant adverse effects' the NPPF refers
8.2.18
to the NPSE (Ref 8-10), which is described below.

## Noise Policy Statement For England

 The NPSE seeks to clarify the underlying principles and aims in existing policy
8.2.19
documents, legislation and guidance that relate to noise. The NPSE applies to all forms of noise, including environmental noise, neighbour noise and neighbourhood noise.
 The Statement sets out the long-term vision of the government's noise policy,
8.2.20
which is to:
"promote good health and a good quality of life through the effective management of noise within the context of policy on sustainable development" (paragraph 2.15).

 This long-term vision is supported by three aims:
8.2.21

·
"avoid significant adverse impacts on health and quality of life;
·
mitigate and minimise adverse impacts on health and quality of life; and
·
where possible, contribute to the improvements of health and quality of life." (paragraph 1.7)
 The long-term policy vision and aims are designed to enable decisions to be made
8.2.22
regarding what is an acceptable noise burden to place on society.
 The 'Explanatory Note' within the NPSE provides further guidance on defining
8.2.23
'significant adverse effects' and 'adverse effects' using the concepts:
·
No Observed Effect Level (NOEL) - the level below which no effect can be 
detected.  Below this level no detectable effect on health and quality of life due to noise can be established;
·
Lowest Observable Adverse Effect Level (LOAEL) - the level above which 
adverse effects on health and quality of life can be detected; and
·
Significant Observed Adverse Effect Level (SOAEL) - the level above which 
significant adverse effects on health and quality of life occur.
 The three aims can therefore be interpreted as follows:
8.2.24

·
the first aim is to avoid noise levels above the SOAEL;
·
the second aim considers situations where noise levels are between the LOAEL and SOAEL.  In such circumstances, all reasonable steps should be taken to mitigate and minimise the effects. However, this does not mean that such adverse effects cannot occur; and
·
the third aim seeks, where possible, to positively improve the health and 
quality of life through the pro-active management of noise, whilst also taking 
account of the guiding principles of sustainable development.  It is considered 
that the protection of quiet places and quiet times as well as the enhancement of the acoustic environment will assist with delivering this aim.
 The NPSE recognises that it is not possible to have single objective noise-based
8.2.25
measures that define the SOAEL, LOAEL and NOEL that are applicable to all sources of noise in all situations.  The levels are likely to be different for different noise sources, receptors and at different times of the day.
Planning Practice Guidance

 In March 2014, DCLG released its Planning Practice Guidance (PPG) (Ref 8-11)
8.2.26
web-based resource to support the NPPF. The guidance advises that local planning authorities' should consider:
·
whether or not a significant adverse effect is occurring or likely to occur;
·
whether or not an adverse effect is occurring or likely to occur; and
·
whether or not a good standard of amenity can be achieved.
 This guidance introduced the additional concepts of NOAEL (No Observed
8.2.27
Adverse Effect Level), and UAEL (Unacceptable Adverse Effect Level). Full details
of the PPG on effects are provided in **Table 8-2**.
 Factors to be considered in determining if noise is a concern are identified,
8.2.28
including the absolute noise level of the source, the existing ambient noise climate, time of day, frequency of occurrence, duration, character of the noise and cumulative impacts.
 With particular regard to mitigating noise impacts on residential development, the
8.2.29
guidance highlights that impacts may be partially offset if residents have access to a relatively quiet façade as part of their dwelling, or a relatively quiet amenity
space (private, shared or public).

| Perception                                | Examples of outcomes   |
|-------------------------------------------|------------------------|
| Increasing                                |                        |
| effect level                              |                        |
| Action                                    |                        |
| Not                                       |                        |
| noticeable                                |                        |
| No effect                                 |                        |
| No Observed                               |                        |
| Effect                                    |                        |
| No specific                               |                        |
| measures                                  |                        |
| required                                  |                        |
| No Observed                               |                        |
| Adverse Effect                            |                        |
| Noticeable                                |                        |
| and not                                   |                        |
| intrusive                                 |                        |
| No specific                               |                        |
| measures                                  |                        |
| required                                  |                        |
| Noise can be heard, but does not          |                        |
| cause any change in behaviour or          |                        |
| attitude. Can slightly affect the         |                        |
| acoustic character of the area but        |                        |
| not such that there is a perceived        |                        |
| change in the quality of life.            |                        |
| Lowest Observed Adverse Effect Level      |                        |
| Observed                                  |                        |
| Adverse Effect                            |                        |
| Noticeable                                |                        |
| and                                       |                        |
| intrusive                                 |                        |
| Mitigate                                  |                        |
| and reduce                                |                        |
| to a                                      |                        |
| minimum                                   |                        |
| Noise can be heard and causes             |                        |
| small changes in behaviour and/or         |                        |
| attitude,                                 | e.g.                   |
| television; speaking more loudly;         |                        |
| where                                     | there                  |
| ventilation, having to close windows      |                        |
| for some of the time because of the       |                        |
| noise. Potential for some reported        |                        |
| sleep                                     | disturbance.           |
| acoustic character of the area such       |                        |
| that there is a perceived change in       |                        |
| the quality of life.                      |                        |
| Significant Observed Adverse Effect Level |                        |
| Noticeable                                |                        |
| and                                       |                        |
| disruptive                                |                        |
| Significant                               |                        |
| Observed                                  |                        |
| Adverse Effect                            |                        |
| Avoid                                     |                        |
| The noise causes a material change        |                        |
| in behaviour and/or attitude,             | e.g.                   |
| avoiding certain activities during        |                        |
| periods of intrusion; where there is      |                        |
| no alternative ventilation, having to     |                        |
| keep windows closed most of the           |                        |
| Perception                            | Examples of outcomes   |
|---------------------------------------|------------------------|
| Increasing                            |                        |
| effect level                          |                        |
| Action                                |                        |
| time because of the noise. Potential  |                        |
| for sleep disturbance resulting in    |                        |
| difficulty                            | in                     |
| premature awakening and difficulty    |                        |
| in getting back to sleep. Quality of  |                        |
| life diminished due to change in      |                        |
| acoustic character of the area.       |                        |
| Unacceptable                          |                        |
| Adverse Effect                        | Prevent                |
| Noticeable                            |                        |
| and very                              |                        |
| disruptive                            |                        |
| Extensive and regular changes in      |                        |
| behaviour and/or an inability to      |                        |
| mitigate effect of noise leading to   |                        |
| psychological stress or physiological |                        |
| effects,                              | e.g.                   |
| deprivation/awakening;                | loss                   |
| appetite,                             | significant,           |
| definable harm,                       | e.g.                   |
| non                                   |                        |
| -                                     |                        |
| auditory.                             |                        |

## Local Development Plan Policy

 The Bassetlaw District - Local Development Framework (December 2011) (Ref 8-
8.2.30
12), has been reviewed.  Policy DM10: Renewable and Low Carbon Energy has been identified as relevant to the consideration of noise emissions from the Proposed Development in that the policy sets out a list of criteria against which proposals for renewable and low carbon energy infrastructure will need to demonstrate compliance with including those that:
·
"are compatible with tourism and recreational facilities; 
·
will not result in unacceptable impacts in terms of ….noise…; and
·
will not result in an unacceptable cumulative impact in relation to the factors above."
 The policy also states that large-scale renewable and low carbon energy
8.2.31
proposals must provide full details of arrangements for decommissioning and reinstatement of the site if/when it ceases to operate.
 BDC is currently in the early stages of preparing a new Local Plan for the District
8.2.32
and began consulting on a Draft Bassetlaw Local Plan (Ref 8-13) in January 2019. Although the draft Local Plan makes specific reference to the existing West Burton Power Station, there are no specific policies or objectives relating to noise or vibration.
 The Adopted Central Lincolnshire Local Plan, published in April 2017 (Ref 8-14)
8.2.33
includes policy LP26: Design and Amenity which makes clear that:
"All development…must achieve high quality sustainable design that contributes positively to local character, landscape and townscape, and supports diversity, equality and access for all".

 The Plan includes key environmental objective (Objective J.) 'to minimise pollution
8.2.34
(air, noise and light) and improve air quality'.
 It goes on to state that:
8.2.35
"Development proposals will be assessed against the following relevant design and amenity criteria:
The amenities which occupiers of neighbouring properties may reasonably expect to enjoy must not be unduly harmed by or as a result of development.  Proposals should demonstrate, where applicable, how the following matters have been considered, in relation to both the construction and life of the development:

·
m. Compatibility with neighbouring land uses; and
·
r. Adverse noise and vibration."
Other Guidance British Standard 7445-1:2003 and 7445-2:1991

 BS 7445 'Description and measurement of environmental noise' (Ref 8-15 and Ref
8.2.36
8-16) defines parameters, procedures and instrumentation required for noise measurement and analysis.
British Standard 5228:2009+A1:2014

 BS 5228-1 'Code of practice for noise and vibration control on construction and
8.2.37
open sites. Noise' (Ref 8-17) provides a 'best practice' guide for noise control, and includes Sound Power Level (SWL) data for individual plant as well as a calculation method for noise from construction activities. BS 5228-2 'Code of practice for noise and vibration control on construction and open sites. Vibration' (Ref 8-18) provides comparable 'best practice' for vibration control, including guidance on the human response to vibration.
British Standard 6472:2008

 BS 6472-1 'Guide to evaluation of human exposure to vibration in buildings Part 1:
8.2.38
Vibration sources other than blasting' (Ref 8-19) presents recommended frequency weighted vibration spectra (for continuous vibration) and vibration dose values (VDV) (for intermittent vibration) above which adverse comment is likely to occur in residential properties.
British Standard 7385:1993

 BS 7385-2 'Evaluation and measurement for vibration in buildings. Guide to
8.2.39
damage levels from groundborne vibration' (Ref 8-20) presents guide values for
transient and continuous vibration, above which there is a likelihood of cosmetic damage. The standard establishes the basic principles for carrying out vibration measurements and processing the data, with regard to evaluating vibration effects on buildings.
British Standard 4142:2014

 BS 4142 'Methods for rating and assessing industrial and commercial sound' (Ref
8.2.40
8-21) can be used for assessing the effect of sound of an industrial nature, including mechanical services plant sound.  The method compares the difference between 'rating level' of the industrial sound, with the 'background sound level' at the receptor position.  Within the operational noise assessment, the term 'sound' is used when applying the BS 4142 assessment method.
World Health Organisation

 The World Health Organisation's (WHO) 'Guidelines for Community Noise' (Ref 8-
8.2.41
22) recommend external daytime and evening environmental noise limits, and internal night-time limits to avoid sleep disturbance.
 The WHO 'Night Noise Guidelines for Europe' (Ref 8-23) recommend updated
8.2.42
guidelines on night-time noise limits to avoid sleep disturbance.
Calculation of Road Traffic Noise

 Department of Transport (DfT)/Welsh Office Memorandum 'Calculation of Road
8.2.43
Traffic Noise' (CRTN) (Ref 8-24) describes procedures for traffic noise calculation,
and is suitable for environmental assessments of schemes where road traffic noise may have an effect.
Design Manual for Road and Bridges 

 The Highways England 'Design Manual for Road and Bridges Volume 11 Section
8.2.44
3 Part 7 HD213/11 (Revision 1) Traffic Noise and Vibration' (DMRB) (Ref 8-25) provides guidance on the appropriate level of assessment to be used when assessing the noise and vibration effects arising from all road projects, including new construction, improvements and maintenance.  The guidance can also be used for assessing changes in traffic noise levels as a result of non-road projects such as the Proposed Development.
International Standards Organisation (ISO) 9613-2:1996

 ISO 9613-2:1996 'Attenuation of Sound during Propagation Outdoors, Part 2:
8.2.45
General Method of Calculation' (Ref 8-26) specifies an engineering method for
calculating the attenuation of sound during propagation outdoors in order to predict the levels of environmental noise at a distance from a variety of sources.

ISO 4866-2:1996

 ISO 4866:2010 'Mechanical Vibration and Shock - Vibration of Fixed Structures –
8.2.46
Guidelines for the Measurement of Vibrations and Evaluation of Their Effects on
Structures' (Ref 8-27) establishes the principals for carrying out vibration
measurement and processing data with regard to evaluating vibration effects on structures.
8.3
Assessment Methodology and Significance Criteria
Consultation
 
The consultation undertaken with statutory consultees to inform this chapter,
8.3.1
including a summary of comments raised via the formal Scoping Opinion
(**Appendix 1B**: ES Volume II) and in response to the formal consultation is
summarised in **Table 8-3**.

Summary of Response
Consultee or organisation approached
Date and nature of consultation
How comments have been addressed in this Chapter
Secretary of State 
June 2017 (Scoping Opinion)
The 
choice 
of 
monitoring 
locations 
was informed by the annual West Burton noise 
monitoring 
programme, 
and 
supplemented through liaison with BDC and WLDC via the Scoping Opinion 
and 
subsequent engagement. 
The 
seven 
selected 
positions were chosen to be representative of 
the potentially worstaffected and closest NSR to the Site in each direction.
The 
Secretary 
of 
State agrees that the methodology 
and 
choice 
of 
noise 
receptors should be confirmed with the Bassetlaw 
District 
Council 
(BDC) 
Environmental Health Officer (EHO) and in so far as it relates to the 
Environmental 
Permit, 
with 
the 
Environment Agency (EA). The Secretary of State recommends that 
the 
Applicant 
take into account the noise 
monitoring 
locations set out by West Lindsey District Council (WLDC) in their 
scoping 
response. Summary of Response
Consultee or organisation approached
Date and nature of consultation
Detailed information should be provided on the construction and 
operational 
noise 
data 
and 
assumptions used to underpin 
the 
proposed 
noise 
modelling 
(for 
example atmospheric and 
ground 
parameters used in ISO 
9613-2 
calculations). The 
Secretary 
of 
State acknowledges the 
Applicant's 
intention 
to 
use 
BS4142:2014 criteria to assess a likely significant operational 
noise 
effect 
which 
is 
appropriate 
having 
had regard to the nature 
of 
the 
Proposed Development. 
The 
Secretary of State reminds the Applicant of the requirements in the Noise Policy Statement 
for 
England 
(NPSE), 
which suggests that noise 
assessment 
thresholds should be described in terms of the Lowest Observed Adverse Effect Level (LOAEL) 
and 
Significant Observed Adverse Effect Level (SOAEL). 
The 
Applicant 
should 
identify 
mitigation 
How comments have been addressed in this Chapter Full 
details 
of 
the 
assumptions 
made 
within the construction and operational noise predictions 
are 
provided 
in 
this 
chapter.
BS4142:2014 
has 
been used to assess the 
significance 
of 
operational noise, see paragraphs 
8.6.20–
8.6.30. AECOM's interpretation 
of 
the 
guidance 
provided 
within NPSE and BS 4142:2014 
with 
respect to assessment levels used to predict whether effects should be 
classified 
as 
significant is defined in paragraph 
8.3.44-
8.3.51 and through the combined use of Table 
8-**13, Table 8**-14 and 
Table 8-15.  
Summary of Response
Consultee or organisation approached
Date and nature of consultation
measures to address adverse effects. Scoping 
Report 
paragraph 
5.4.2 
states 
that 
annual 
noise 
surveys 
associated with WBA have 
been 
undertaken. 
The 
surveys include day, evening and night 15 minute 
noise 
measurements undertaken at noise sensitive 
receptors. 
Whilst the Secretary of State notes that the 
Applicant 
proposes to agree noise 
monitoring 
requirements with the BDC 
EHO, 
the 
Applicant would also need to provide a clear justification for any departure from the reference time intervals stated within BS 4142:2014. The 
noise 
assessment 
should 
state 
any 
assumptions made in relation to the rating level for operational noise sources and the range of likely operational conditions, 
allowing 
for diurnal variation. Scoping 
Report 
paragraph 
5.4.10 
states that the focus of the assessment 
How comments have been addressed in this Chapter Referenced 
in 
paragraph 8.6.25 and 
no departure from BS 4142:2014 methodology has been made.
The 
assumptions 
related 
to 
the 
prediction 
of 
rating 
levels 
for 
different 
assessment 
periods 
and 
operational 
configurations 
are 
presented in Section 8.6. Recommendations relating 
to 
the 
construction 
phase 
mitigation have been 
Summary of Response
Consultee or organisation approached
Date and nature of consultation
will 
be 
on 
recommendations for appropriate mitigation. 
The 
Secretary of State recommends 
that 
mitigation proposals are presented in the form of Construction Noise and Vibration Management 
Plans 
or 
as 
part 
of 
a 
Construction Environmental Management 
Plan 
(CEMP) and/or that the 
Applicant 
demonstrates 
that 
such 
mitigation 
is 
secured 
through 
appropriate requirements in the draft DCO. Operational 
noise 
mitigation measures should be addressed in the ES, including any 
measures 
to 
address the risk of low frequency noise emissions from gas turbine 
exhausts. 
Measures such as engineering 
design 
to 
reduce 
noise; 
layout of plant and equipment 
to 
minimise transmission; 
and 
any 
operational 
controls should be discussed. 
The 
Secretary of State recommends 
that 
operational 
noise 
requirements in the 
How comments have been addressed in this Chapter outlined 
in 
paragraphs 8.5.1 to 8.5.7, 
including 
reference 
to 
the 
Framework 
CEMP 
(Application 
Document Ref. 7.3).  
Implementation of the noise 
control 
measures is proposed to be secured by a Requirement 
of 
the 
draft DCO. The level of required attenuation 
predicted 
to be required based on 
the 
'worst-case' 
plant configuration and potential 
mitigation 
methods have been discussed 
in 
paragraphs 8.7.7 - 
8.7.18 and **Table 8**-31-
Table 8-34.
Summary of Response
Consultee or organisation approached
Date and nature of consultation
draft DCO are clearly distinguished 
from 
construction 
noise 
requirements. Consideration should be 
given 
to 
monitoring 
noise 
complaints 
during 
construction 
and 
when 
the 
development 
is 
operational. The results from the noise and vibration assessments should inform the terrestrial, aquatic/marine ecological assessments.
Bassetlaw District Council (BDC)
Email (4th May 2017)
Confirmation 
of 
proposed 
baseline 
monitoring Locations
West Lindsey District Council (WLDC)
Email (4th May 2017)
Confirmation 
of 
proposed 
baseline 
monitoring locations
How comments have been addressed in this Chapter It is proposed that monitoring of potential construction 
noise 
complaints would be included 
within 
the 
CEMP 
(paragraph 
8.5.3). The Framework CEMP 
(Application 
Document Ref. 7.3) includes provision for this measure. The 
assessment 
relating to impact on terrestrial ecology has been 
considered 
in 
Chapter 9: Ecology. Impacts on aquatic/ marine ecology have been scoped out of the assessment, 
given 
that outfalls to the 
River Trent are no 
longer proposed. Confirmation of BDC agreement 
to 
the 
proposed 
scope 
of 
baseline survey. Confirmation 
of 
agreement 
to 
the 
proposed 
scope 
of 
baseline 
survey.  
WLDC request for an additional location at the southern edge of Gainsborough 
was 
acknowledged and this location was included in 
survey 
- 
see 
Section 8.4.
Summary of Response
Consultee or organisation approached
Date and nature of consultation
How comments have been addressed in this Chapter
Planning Inspectorate
Meeting 4 July 2017
Construction 
noise 
assessment 
should 
be quantitative rather than qualitative and follow BS5228.
The construction noise assessment provided both 
at 
formal 
consultation (Preliminary Environmental Information 
Report 
(PEI)) stage and in this ES used quantitative prediction methods in accordance 
with 
BS5228.
Bassetlaw District Council (BDC)
Telephone and Email
(4- 6 
December 2017)
Confirmation was sought on the method used to derive representative background sound levels.  BDC were asked to respond with any comments in or objections to the proposed method set out in this chapter.  No such comments were received.
Bassetlaw District Council
March/April 2019
Provision of copies of final draft chapter and 
offer of pre-application meeting to each 
consultee to:
Environment Agency Lincolnshire County Council Nottinghamshire County Council
·
discuss final proposals and assessments;
·
obtain feedback prior to submission of 
Application; and
·
agree an approach to drafting of Statements of Common Ground (SoCG) prior to submission of the Application.
West Lindsey District Council
Further details on consultation undertaken can be found in the Consultation Report (**Application Document Ref. 7.1**).

Summary of Key Changes to Chapter 8 since Publication of the Preliminary Environmental Information (PEI) Report 

 
The PEI Report (Ref 8-28) was published for statutory consultation in September
8.3.2
2017, allowing consultees the opportunity to provide informed comment on the Proposed Development, the assessment process and preliminary findings through a consultation process, prior to the finalisation of this ES.
 
The key changes relevant to this chapter since the PEI Report was published are
8.3.3
summarised in **Table 8-4** below.

Table 8-4: Summary of key changes to chapter since publication of the PEI 
Report
Summary of change since PEI Report
Reason for change
Summary of change to chapter text in the ES
Presentation of worstcase scenario to align with Rochdale Envelope principles
used.
Alignment of assessment methodology.
The worst-case plant configuration based upon the ten scenarios presented at formal
consultation was derived and used as the basis for assessment and mitigation (operational noise text and
tables from paragraphs 8.6.20–8.6.31) and
operational noise mitigation requirements
set out in paragraphs 8.7.7– **8.7.18**Error!
Reference source not found..
Detailed consideration of the most representative way to determine the background sound levels for use in the
noise assessment and further engagement with BDC.
Table 8-23 in the PEI 
Report contained a range of values for the background sound level at 
each receptor - one level 
based on analysis of the full data set collected during the noise monitoring survey and the other based only on the measurements for periods when the receptor was downwind of the Site.
As there are no significant topographical features in the area surrounding the Proposed Development, the largest influence on sound propagation is wind
direction.  It is considered appropriate to base the assessment for each NSR on comparison of the downwind predicted levels from the Proposed Development with the background sound level measured with a similar wind direction, since this accounts for background sound levels arising from the existing WBA and WBB Power Stations.
The equivalent table in this ES chapter (Table 
8-24) and resultant 
mitigation tables (Table 
8-31-**Table 8**-34) have 
been updated so that the 
assessment for each receptor is based upon comparison of the downwind predicted levels
Summary of change since PEI Report
Reason for change
Summary of change to chapter text in the ES
with the background
sound level measured with a similar wind direction, to take account of background sound levels arising from the existing WBA and WBB Power Stations.  As described in
Table 8-3, BDC was 
asked to respond with any comments or objections to the proposed method set out in this chapter.  No such comments were received.
The PEI report did not assess the potential for impacts on aquatic species in the River Trent given the uncertainty at the time regarding whether outfalls were required.  Outfalls are no longer proposed; thereby the need to assess construction noise impacts on aquatic species is scoped out of this
assessment.
Updated design information regarding the feasibility of discharge of surface water on-Site to the existing drainage system of WBA Power Station. Discharge to the River Trent from the wider power station site will continue via the existing outfall structure and the rate of discharge into that system from the Proposed
Development will be controlled via the surface water drainage system.
The possibility of installing an outfall to the River Trent was presented in the PEI Report. Following formal consultation and further engineering design works, the potential surface water outfall options are now excluded from the Proposed Development and therefore the
proposed Order Limits, draft DCO and associated documentation exclude the need for a direct discharge to the river.
Update of relevant
paragraphs in Section 8.6
To reflect updated indicative construction programme.
Construction phase assessment year updated for road traffic related emissions.

## Assessment Methods

Baseline Sound Surveys

 
The location of potential NSR in proximity to the Site has been considered when
8.3.4
assessing the effects associated with noise and vibration levels from the construction, operational and decommissioning phases of the Proposed Development.
 
Key NSR locations have been selected which are considered to be representative
8.3.5
of the nearest and potentially most sensitive existing receptors to the Site. It is considered that if noise and vibration levels are suitably controlled at the key receptors identified, then noise and vibration levels will be suitably controlled at other sensitive receptors in the surrounding area.
 
In order to define existing sound conditions at NSR, long-term ambient sound
8.3.6
measurements have been undertaken at seven representative residential NSR locations around the existing West Burton Power Station site. The noise monitoring locations and protocol were discussed in advance and during the
surveys with BDC and WLDC. The seven locations are shown in **Table 8-5** and on Figure 8.1 (ES Volume III).

Monitoring location
National Grid Reference
Address
Distance/Direction from Site
Details
ML1
478832, 384556
Kent House, North Street, 
Sturton-le-
Steeple
1.4km SW
Located in the rear garden to the north of the residential property.
ML2
478585, 385365
Crossing Keepers Cottage, West Burton
1.9km SW
Located in the rear garden to the north of the residential property.
ML3
478934, 386410
Mill House Farm
1.1km W
Located in the rear garden to the south of the residential property.
ML4
479505, 387023
Manor Cottage, Bole
0.9km NW
Located in the rear garden to the south of the property.
ML5
482104, 387925
194 Lea Road, Gainsborough
2.3km E
Located in the rear garden to the west of the residential property.
Monitoring location
National Grid Reference
Address
Distance/Direction from Site
Details
ML6
482483, 387052
Green Lane, Lea
2.1km E
Located in the rear garden to the north of the residential property.
ML7
482779, 384625
Knaith Hall, Knaith
2.5km E
Located in the garden to the west of the residential property.

 
All measurements were undertaken between Friday 14 July and Monday 24 July
8.3.7
2017.
 
Daytime relates to the period between 07:00 and 23:00 (with evening between
8.3.8
19:00 and 23:00), and night-time between 23:00 and 07:00.
 
All measurements were taken at approximately 1.2-1.5m above ground level
8.3.9
(AGL), with the exception of ML6, which was approximately 1.8m AGL (due to having to attach the microphone to a garden trellis), and in accordance with the requirements of British Standard BS 7445 (Ref 8-15). All monitoring locations were positioned at least 3.5m from any reflecting surface, other than the ground (i.e. free-field). Details of on-going activities and typical noise sources in the area were recorded during visits to the monitoring locations to set up and collect the measurement equipment.
Noise Survey Instrumentation

 Details of the instrumentation (sound level meters (SLMs)) used during the
8.3.10
surveys are presented in **Table 8-6** below:

Monitoring location
Manufactu rer
SLM model
SLM serial number
Microphone model
Microphone serial number
ML1
Rion
NL-52
01021278
Rion UC59
04334
ML2
Svantek
959
15606
GRAS 40AE
98114
ML3
B&K
2250
2827270
B&K 4189
2820205
ML4
Svantek
958
14693
GRAS 40AE
17973
ML5
Norsonic
Nor14 0
1403077
NOR1225
91924
ML6
B&K
2238
2381585
B&K 4188
2200371
Monitoring location
Manufactu rer
SLM model
SLM serial number
Microphone model
Microphone serial number
ML7
B&K
2250
2827271
B&K 4189
2820200

 All SLMs used were Class 1 precision instruments. Each was programmed to log a
8.3.11
number of parameters including LAeq, LA90 and LAmax values, in 15-minute
contiguous intervals.
 The calibration levels were checked prior to and following all measurements with a
8.3.12
Brüel & Kjær 4231 field calibrator (serial number 2217877). No significant drift, more than 0.2 dB, occurred. Full calibration details are available upon request.

## Meteorological Conditions

 Observations regarding weather conditions were made during the noise survey.  In
8.3.13
addition, a weather monitoring station was in operation at ML3. The weather station collected data relating to the wind speed (average and maximum), direction, precipitation and temperature.
 At the start of the survey period (Friday 14 July 2017), weather conditions were
8.3.14
observed to be dry with patchy cloud; wind blowing from a north-westerly direction with an average speed of approximately 2m/s and a maximum wind speed of approximately 4m/s. Road surfaces were noted to be dry and the ambient temperature was approximately 20°C.
 During the second site visit (Monday 17 July 2017) weather conditions were noted
8.3.15
to be dry with minimal cloud coverage and no wind. Road surfaces were noted to be dry and the ambient temperature was approximately 28°C.
 Upon collection of the survey (Monday 24 July 2017), weather conditions were
8.3.16
observed to be wet with thick cloud; wind blowing from a easterly direction with an average speed of approximately 1.8m/s and a max wind speed of approximately 2.2m/s. Road surfaces were noted to be wet and the ambient temperature was approximately 14°C.
 A daily overview of the data collected from the weather station has been presented
8.3.17
in **Table 8-7** below.

Date
Time Period
Ambient Rain Gauge (mm)
Wind Direction Average Degrees Clockwise from North
Range of 
15-minute 
Average Wind Speeds (m/s)
Friday 14th July 2017
16:30 - 
23:00
283
0.7 - 3.0
0.3
Date
Time Period
Ambient Rain Gauge (mm)
Wind Direction Average Degrees Clockwise from North
Range of 
15-minute 
Average Wind Speeds (m/s)
23:00 - 
07:00
200
0.6 - 2.0
0.1
07:00 - 
23:00
201
1.2 - 3.2
1.0
Saturday 15th July 2017
23:00 - 
07:00
212
1.0 - 2.9
0.0
07:00 - 
23:00
290
0.6 - 2.6
0.0
Sunday 16th July 2017
23:00 - 
07:00
233
0.2 - 1.3
0.0
07:00 - 
23:00
262
0.4 - 1.8
0.0
Monday 17th July 2017
23:00 - 
07:00
197
0.3 - 0.6
0.0
07:00 - 
23:00
79
0.3 - 2.0
0.0
Tuesday 18th July 2017
23:00 - 
07:00
44
0.5 - 1.9
0.0
07:00 - 
23:00
139
1.0 - 3.8
0.0
Wednesday 19th July 2017
23:00 - 
07:00
207
0.4 - 3.2
2.4
07:00 - 
23:00
269
1.1 - 3.3
10.3
Thursday 20th 
July 2017
23:00 - 
07:00
153
1.0 - 3.8
0.0
07:00 - 
23:00
151
2.2 - 5.1
0.0
Friday 21st July 2017
23:00 - 
07:00
133
0.6 - 3.4
11.2
07:00 - 
23:00
194
0.2 - 4.3
8.1
Saturday 22nd July 2017
23:00 - 
07:00
209
0.2 - 1.8
0.0
07:00 - 
23:00
287
0.4 - 2.0
2.3
Sunday 23rd July 2017
23:00 - 
07:00
215
1.2 - 2.3
0.1
Monday 24th July 2017
07:00 - 
13:00
310
2.0 - 5.1
0.0

 Overall, the meteorological conditions were within the limits considered suitable by
8.3.18
relevant standards for collecting sound level measurements, with the exception of some elevated wind speeds during Friday 21 July 2017 and elevated levels of
precipitation during Thursday 20 July 2017 daytime and Friday 21 July 2017 nighttime.  However, the measured levels are considered representative of a range of conditions prevailing at NSR within the study area.  No periods of baseline sound level data collection were therefore excluded from the assessment.

## Assessment Of Construction Noise Impacts

 At this stage in the project design development, before the appointment of a
8.3.19
construction contractor, site-specific details on the construction activities, programme and number or type of construction plant are not yet available. Therefore, detailed construction noise predictions at specific NSR have not been undertaken. Nevertheless, indicative construction noise predictions have been
undertaken using the calculation methods set out in BS 5228:2009+A1:2014 'Code of practice for noise and vibration control on construction and open sites' (Ref 8- 17), based upon construction information from other power stations projects and data provided by the Applicant relating to the construction phase of the Proposed Development.
 The calculation method provided in BS 5228 takes account of factors including the
8.3.20
number and types of equipment operating, their associated SWL, their modes of operation (% on-times within the working period), the distance to NSR, and the effects of any intervening ground cover or barrier/topographical screening. This allows prediction of the magnitude of impact.
 BS 5228 contains a number of example methodologies for identifying significant
8.3.21
construction noise effects based on fixed thresholds or noise level changes.
Taking into account this guidance, the threshold values detailed in **Table 8-8** have
been adopted in this chapter to define the SOAEL (the 'significant observed
adverse effect level', as defined in **Section 8.2**) and the LOAEL (the 'lowest
observable adverse effect level') for residential receptors.

| Time of Day         | SOAEL    | L               |
|---------------------|----------|-----------------|
| Aeq,                | T        |                 |
|                     |          |                 |
| dB (façade)         |          |                 |
| LOAEL               | L        |                 |
| Aeq,                | T        |                 |
| dB                  |          |                 |
| (façade)            |          |                 |
| Daytime (07:00      |          |                 |
| -                   |          |                 |
| 19:00) and          |          |                 |
| Saturdays (07:00    |          |                 |
| -                   |          |                 |
| 13:00)              |          |                 |
| 75                  | 65       |                 |
| 65                  | 55       | Evenings (19:00 |
| -                   |          |                 |
| 23:00 weekdays)     |          |                 |
| and Weekends (13:00 |          |                 |
| -                   |          |                 |
| 23:00               |          |                 |
| Saturdays and 07:00 |          |                 |
| -                   |          |                 |
| 23:00               |          |                 |
| Sundays)            |          |                 |
| Night               |          |                 |
| -                   |          |                 |
| time (23:00         |          |                 |
| -                   |          |                 |
| 07:00)              | 55       | 45              |

 The criterion for the SOAEL at residential receptors corresponds to the threshold
8.3.22
values for Category C in the BS 5228 example ABC method.  Similarly, the criterion for the LOAEL corresponds to the threshold values for Category A in the BS 5228 example ABC method.  In accordance with the NPPF and NPSE, it is
important to consider receptors that exceed the LOAEL and ensure adverse effects are mitigated and minimised.

 When considering exceedances of the SOAEL and LOAEL, other project-specific
8.3.23
factors have been taken into account, such as the existing ambient noise levels, number of receptors affected and the frequency and duration of the impact.
 Based upon the above, the magnitude of the impact of construction noise on
8.3.24
residential receptors has been classified in accordance with the descriptors in
Table 8-9.

Magnitude of  Impact
Daytime LAeq,T dB 
(façade)
Evening/Weekend 
LAeq,T dB (façade)
Night-time LAeq,T 
dB (façade)
High
> 80
> 70
> 60
Medium
>75-80
>65-70
>55-60
Low
>65-75
>55-65
>45-55
Very Low
≤ 65
≤ 55
≤ 45

Assessment of Daytime Construction Works Traffic on the Public Highway

 The Proposed Development will affect traffic flows on existing roads in the area
8.3.25
surrounding the Site during construction. The assessment focuses on the impact at existing residential properties located alongside the local road network.
 Construction traffic noise has been assessed by considering the increase in traffic
8.3.26
flows during the construction works, following the guidance of CRTN (Ref 8-24)
and DMRB (Ref 8-25).
 18-hour (06:00 - 24:00) Annual Average Weekday Traffic (AAWT) data have been
8.3.27
obtained for the assessed construction year 2029 'with' and 'without' construction traffic during the peak construction period, in order to determine if any existing roads are predicted to be subject to a potentially significant change in 18-hour traffic flows.  Basic Noise Level (BNL) calculations have been undertaken to predict the change in noise level between the 'with' and 'without' scenarios.
 The traffic data used within this assessment has been sourced from **Chapter 7**:
8.3.28
Traffic and Transport and its accompanying **Appendix 7A**: Transport Assessment
(ES Volume II). The data represents the peak traffic flow periods for assessment of the worst-case impacts; outside of these periods traffic flow and hence noise effects would be lower.
 The criteria for the assessment of traffic noise changes arising from construction
8.3.29
works have been taken from Table 3.1 of DMRB and are provided in Table 8-10
below.

Magnitude of impact
Change in traffic noise level LA10,18h 
dB
High
≥ 5
Medium
3 to <5
Low
1 to <3
Very low
<1

 DMRB advises that an increase in road traffic flows of 25% (where the traffic
8.3.30
speed and composition remain consistent) equates to an increase in road traffic
noise of 1 dB LA. A doubling of traffic flow would be required for an increase in 3 dB LA.
 It is generally accepted that changes in noise levels of 1 dB LA or less are
8.3.31
imperceptible, and changes of 1 to 3 dB LA are not widely perceptible.
Consequently, at the selected road traffic noise receptors the magnitude of the
predicted change in noise levels uses the scale shown in **Table 8-10** above with
respect to construction traffic. The criteria are based on the current guidance on short-term changes in traffic noise levels in DMRB.  The SOAEL is set at a change in traffic noise of +3 dB and the LOAEL at +1 dB.

## Assessment Of Construction Vibration Impacts

Impacts on Humans - Annoyance

 Vibration due to construction activities has the potential to result in adverse
8.3.32
impacts at nearby NSR. The transmission of ground-borne vibration is highly dependent on the nature of the intervening ground between the source and
receiver and the activities being undertaken. BS 5228-2: 2009+A1: 2014 'Code of Practice for Noise and Vibration Control on Construction and Open Sites - Vibration' (Ref 8-18) provides data on measured levels of vibration for various construction works, with particular emphasis on piling. Impacts are considered for both damage to buildings and annoyance to occupiers.
Table 8-11 details Peak Particle Velocity (PPV) vibration levels and provides a
8.3.33
semantic scale for the description of construction vibration effects on human receptors, based on guidance contained in BS 5228-2.

Peak Particle Velocity (PPV) level
Description
Magnitude of impact
>= 10 mm/s
Vibration is likely to be intolerable for any more than a very brief exposure to this level.
High
Peak Particle Velocity (PPV) level
Description
Magnitude of impact
Medium
1.0 to < 10 mm/s
It is likely that vibration of this level in residential environments will cause complaint, but can be tolerated if prior warning and explanation has been given to residents.
0.3 to < 1 mm/s
Vibration might be just perceptible in residential environments.
Low Very low
0.14 to < 0.3 mm/s
Vibration might be just perceptible in the most sensitive 
situations 
for 
most 
vibration 
frequencies associated with construction. At lower frequencies, people are less sensitive to vibration.

 For residential receptors and other high sensitivity receptors, the LOAEL is defined
8.3.34
as a PPV of 0.3mm/s (millimetres per second), this being the point at which construction vibration is likely to become perceptible. The SOAEL is defined as a PPV of 1.0mm/s, this being the level at which construction vibration can be tolerated with prior warning.
 At receptors above the SOAEL, further consideration of whether an effect is
8.3.35
significant is undertaken using professional judgement, taking account of the duration and frequency of the effect, as well as the time of evening/night that the effect would be experienced.
 In the absence of specific information on likely construction activities and plant, a
8.3.36
qualitative assessment based upon professional judgement has been undertaken
at this stage.  Given the significant distance to residential receptors, this qualitative judgement made is that no significant vibration (medium or high magnitude impacts) is expected to result at residential NSR from the proposed construction and therefore further assessment is scoped out.  However, further consideration is given to the occupants of adjacent buildings associated with WBA Power Station and WBB Power Station within the West Burton Power Station site.

## Impacts On Buildings

 In addition to human annoyance, building structures may be damaged by high
8.3.37
levels of vibration. The levels of vibration that may cause building damage are far in excess of those that may cause annoyance. Consequently, if vibration levels are controlled to those relating to annoyance (*i.e.* 1.0mm/s), then it is highly unlikely that buildings will be damaged by construction vibration levels.
 The criteria used in this assessment relate to the potential for cosmetic damage,
8.3.38
not structural damage. The principal concern is generally transient vibration, for example due to piling.
 BS 7385-2: 1993 'Evaluation and measurement for vibration in buildings - Part 2:
8.3.39
Guide to damage levels from groundborne vibration' (Ref 8-20) provides guidance on vibration levels likely to result in cosmetic damage and is referenced in BS 5228-2: 2009+A1:2014. Guide values for transient vibration, above which cosmetic
damage could occur, are given in **Table 8-12**.

Peak component particle velocity in frequency range of predominant pulse
Type of building
4Hz to 15Hz
15Hz and above
Reinforced 
or 
framed 
structures 
(industrial 
and 
50mm/s at 4Hz and above.
heavy commercial buildings). Unreinforced 
or 
light 
20mm/s 
at 
15Hz 
framed 
structures 
(residential 
or 
light 
increasing to 50mm/s at 40Hz and above.
commercial buildings).
15mm/s at 4Hz increasing to 20mm/s at 15Hz.

NOTE 1: Values referred to are at the base of the building.

NOTE 2: For un-reinforced or light framed structures and residential or light commercial buildings, a maximum displacement of 0.6mm (zero to peak) is not to be exceeded.

 BS 7385-2:1993 states that the probability of building damage tends to zero for
8.3.40
transient vibration levels less than 12.5mm/s PPV. For continuous vibration, such as from vibratory rollers, the threshold is around half this value.
 It is also noted that these values refer to the likelihood of cosmetic damage. ISO
8.3.41
4866:2010 defines three different categories of building damage:
·
cosmetic - formation of hairline cracks in plaster or drywall surfaces and in 
mortar joints of brick/concrete block constructions;
·
minor - formation of large cracks or loosening and falling of plaster or drywall 
surfaces or cracks through brick/block; and
·
major - damage to structural elements, cracks in support columns, loosening 
of joints, splaying of masonry cracks.
 BS 7385-2:1993 defines that minor damage occurs at a vibration level twice that of
8.3.42
cosmetic damage and major damage occurs at a vibration twice that of minor damage. Therefore, this guidance can be used to define the magnitude of impact
identified in **Table 8-13** below.

Magnitude of impact
Damage risk
Continuous vibration level ppv mm/s
High
Major
30
Medium
Minor
15
Low
Cosmetic
6
Very low
Negligible
<6

 In the absence of specific information on likely construction activities and plant, a
8.3.43
qualitative assessment based upon professional judgement has been undertaken. The qualitative judgement made at this stage, again given the significant distance to residential receptors, is that no significant vibration is expected to result from the proposed construction activities at nearby residential buildings and therefore further assessment of the effects of vibration on such buildings is scoped out. However, further consideration is given to the adjacent buildings within the West Burton Power Station site.

## Assessment Of Operational Noise Impacts

 The assessment of operational sound levels has been based upon calculations
8.3.44
using plant emissions data available at this stage. The data currently available includes: proposed plant equipment (provided by a range of equipment manufacturers), SWLs relating to the proposed plant, distance between the proposed plant and NSR and the acoustic screening offered by the existing landscape and existing West Burton Power Station buildings.
 Based upon the predicted sound levels, an assessment of potential impact at
8.3.45
nearby NSR has been undertaken using the guidance in BS 4142: 2014 'Methods for rating and assessing industrial and commercial sound' (Ref 8-21).
 A key aspect of the BS 4142:2014 assessment procedure is a comparison
8.3.46
between the *background sound level* in the vicinity of residential locations and the
rating level of the sound source under consideration.  The relevant parameters in
this instance are as follows:
·
background sound level - LA90,T - defined in the Standard as the "A-weighted 
sound pressure level that is exceeded by the residual sound for 90% of a given time interval, T, measured using time weighting F and quoted to the nearest whole number of decibels"; 
·
specific sound level - Ls (LAeq,Tr) - the "equivalent continuous A-weighted 
sound pressure level produced by the specific sound source at the assessment location over a given reference time interval, Tr"; and
·
rating level - LAr,Tr - the "specific sound level plus any adjustment made for the 
characteristic features of the sound".
 Whereas the previous version of BS 4142:1997 allowed for a single correction of
8.3.47
+5 dB to be made to the Specific Noise Level if one or more of the distinguishable, impulsive or irregular features were considered to be present, BS 4142:2014 allows for corrections to be applied based upon the presence or expected
presence of the following:
·
tonality: up to +6 dB correction;
·
impulsivity: up to +9 dB correction (this can be summed with tonality correction); and
·
other sound characteristics (neither tonal or impulsive but still distinctive): + 3 dB correction.
 Once any adjustments have been made, the *background sound level* and the
8.3.48
rating level are compared.  The standard states that:
·
"Typically, the greater the difference, the greater the magnitude of impact. 
·
A difference of around +10 dB or more is likely to be an indication of a significant adverse impact, depending upon the context.
·
A difference of around +5 dB is likely to be an indication of an adverse impact, depending upon the context.
·
The lower the rating level is to the measured background sound level, the less likely it is that the specific sound will have an adverse impact or a significant adverse impact.  Where the rating level does not exceed the background sound level, this is an indication of the specific sound source having a low impact, depending upon the context." (Section 11)
 Importantly, as suggested above, BS 4142:2014 requires that the *rating level* of
8.3.49
the sound source under assessment be considered in the context of the
environment, when defining the overall magnitude of the impact.
 BS 4142:2014 suggests that a one hour assessment period is considered during
8.3.50
the day and a 15-minute assessment period at night.
Table 8-14 illustrates the adopted magnitude of impact scale used in this
8.3.51
assessment based upon the numerical level difference. For BS 4142 assessment purposes the SOAEL is set at a rating level above the background sound level of +10 dB, and the LOAEL at +5 dB, although it should be remembered that the context assessment (including the absolute level of the sound under consideration) can vary the overall classification of effects.

services
Magnitude of impact
BS 4142 descriptor
Excess of rating level over background sound level (dB)
High
No BS 4142 descriptor for this magnitude level.
>15
Medium
Indication of a significant adverse effect, depending upon context.
 +10 approx.
Low
Indication of an adverse effect, depending upon context.
+5 approx. 
Very low
Indication of low impact, depending upon context.
≤ 0

Assessment of Operational Vibration Impacts

 No causes of potentially significant vibration associated with the Proposed
8.3.52
Development are known and therefore further assessment of operational vibration is scoped out of this assessment.
Significance Criteria

 Effects are classified based on the magnitude of the impact and the sensitivity or
8.3.53
value of the affected receptor.  The criteria for assigning the magnitude of impacts are outlined above for the various potential impacts during construction, operation and decommissioning, and these are followed by a scale of receptor sensitivity in
Table 8-15 and overall classification of effects matrix in **Table 8-16**.
Receptor Sensitivity

 In accordance with the principles of EIA, the sensitivity of existing receptors to
8.3.54
noise (or vibration) impacts during either construction or operational phases has
been defined in **Table 8-15**.

Sensitivity/value of resource/receptor
Description
Examples of receptor usage
Very high
Auditoria/studios. Specialist medical/teaching centres, or laboratories with highly sensitive equipment.
Receptors where noise or vibration will significantly affect the function of a receptor.
Residential. Quiet outdoor areas used for recreation.
High
Receptors where people or operations are
Sensitivity/value of resource/receptor
Description
Examples of receptor usage
Conference facilities. Schools/educational facilities in the
daytime. Hospitals/residential care homes. Libraries. Ecologically sensitive areas for example Special Protection Areas (SPAs).
particularly susceptible to
noise or vibration. Sensitive ecological receptors known to be vulnerable to the effects of noise or vibration.
Medium
Offices. Restaurants/retail. Sports grounds when spectator or noise is not a normal part of the event and where quiet conditions are necessary (*e.g.* tennis, golf).
Receptors
moderately sensitive to noise or vibration where it may cause some distraction or disturbance.
Low
Receptors where distraction or disturbance of people from noise or vibration is minimal.
Residences and other buildings not occupied during working hours. Factories and working environments with existing high noise levels. Sports grounds when spectator or noise is a normal part of the event.

Classification of Effects The following terminology has been used in the assessment to classify effects:
8.3.55

·
adverse - detrimental or negative effects to an environmental resource or 
receptor;
·
neutral - effects to an environmental resource or receptor that are neither 
adverse nor beneficial; or
·
beneficial - advantageous or positive effect to an environmental resource or 
receptor.
 The effect resulting from each individual potential impact type above is classified
8.3.56
according to the magnitude of the impact and the sensitivity or value of the affected receptor using the matrix presented in **Table 8-16** below, but where necessary also considering the context of the acoustic environment.

Magnitude of impact
High
Medium
Low
Very low
Sensitivity/value of resource/receptor
Very high
Major
Major
Moderate
Minor
Magnitude of impact
High
Medium
Low
Very low
Sensitivity/value of resource/receptor
High
Major
Moderate
Minor
Negligible
Medium
Moderate
Minor
Negligible
Negligible
Low
Minor
Negligible
Negligible
Negligible

 For the purposes of this assessment, negligible and minor effects are not
8.3.57
considered to be significant, whereas moderate and major effects are considered to be significant.
Extent of Study Area

 The extent of the study area has been defined to include the nearest
8.3.58
receptors/communities in each direction from the Site and alongside the transport corridors that may be affected by changes in road traffic flows during the construction 
and 
operational 
phases 
of 
the 
Proposed 
Development.
Representative NSR within this study area in all directions from the Site have been identified for the purposes of assessment, to ensure all effects are appropriately considered.
Rochdale Envelope

 The noise and vibration assessment has been undertaken with reference to the
8.3.59
Rochdale Envelope (i.e. the maximum parameters for the Proposed Development and in particular its main buildings and structures).  It is considered that the
potential variation in building locations and dimensions presented in **Chapter 4**:
The Proposed Development is unlikely to adversely affect the overall conclusions regarding the significance of residual noise effects, for reasons described below.
 The construction assessment has been based on the worst-case assumption of
8.3.60
activities occurring at the closest part of the Site to each receptor as shown in
Figure 4.1a and **Figure 4.1b** (ES Volume III).
 The operational assessment is based on the limits of deviation defined in Chapter
8.3.61
4: The Proposed Development and these relate to the Works Plans that accompany the Application (**Application Document Ref. 3.2**). These constrain
the design parameters of each element of the Proposed Development (and as for construction, in any event, mitigation will be integrated into the detailed design in order to meet agreed noise limits at the nearest NSR, in accordance with a
Requirement of the draft DCO (**Application Document Ref. 2.1**). Due to the
relatively small size of the Proposed Power Plant Site compared with the distances to NSR, there would be no significant effect with regard to predicted sound levels at NSR, no matter where operational plant is located on the Proposed Power Plant Site.

## Sources Of Information/Data

 The following sources of information that define the Proposed Development have
8.3.62
been reviewed and form the basis of the assessment of likely significant effects of noise and vibration:
·
construction plant and equipment from similar power station projects;
·
initial estimates of numbers of construction plant and equipment from the Applicant; 
·
construction noise data referenced from BS 5228;
·
indicative concept layout plans for the Proposed Power Plant Site (see Figures 4.1a and **4.1b** in ES Volume III) and the implications of the application of the Rochdale Envelope;
·
schedule of buildings and plant for the Proposed Development, including SWLs and internal reverberant sound pressure levels, provided by Original Equipment 
Manufacturers 
(OEMs) 
and 
also 
sourced 
from 
similar 
representative projects;
·
AAWT traffic data from **Appendix 7A:** Transport Assessment (ES Volume II);
·
Ordnance Survey mapping of the Site and surrounding area; and
·
aerial photography.
8.4
Baseline Conditions

## Existing Baseline Sound Survey Results

 
The processed results from each long-term sound survey position are provided in
8.4.1
Table 8-17 to **Table 8-23** below. The LA90 values presented represent the lowest
10th percentile of all 15-minute measurements within the time period.
Observations regarding the general baseline sound environment at each monitoring location are detailed after the tables.

| Date (2017)   | Time period   | L   |
|---------------|---------------|-----|
| Aeq           | ,T            |     |
| dB            |               |     |
| Highest       |               |     |
| L             |               |     |
| Amax,         | T             |     |
| dB            | L             |     |
| A90,          | T             |     |
| dB            |               |     |
| 15:30         |               |     |
| -             |               |     |
|               |               |     |
| 23:00*        |               |     |
| 46            | 78            | 39  |
| Monday 17     |               |     |
| July          |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         | 47            | 72  |
| Tuesday 18    | 07:00         |     |
| -             |               |     |
|               |               |     |
| 50            | 78            | 32  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq            | ,T            |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| July           | 23:00         |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 47            | 79  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 48             | 80            | 27  |
| Wednesday      |               |     |
| 19 July        |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 47             | 78            | 20  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 49            | 76  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 43            | 74  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 53             | 74            | 34  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 48             | 70            | 25  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 50            | 89  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 43            | 74  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 48             | 86            | 29  |
| Sunday 23      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 46             | 71            | 34  |
| Monday 24      |               |     |
| July           |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 13:00*         | 50            | 83  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 15:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00*         | 54            | 84  |
| Friday 14 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 53            | 86  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 54            | 84  |
| Saturday 15    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 55            | 91  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 54             | 88            | 39  |
| Sunday 16      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 48             | 77            | 26  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 57            | 90  |
| Monday 17      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 48            | 83  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 57             | 88            | 38  |
| Tuesday 18     |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 51             | 78            | 33  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 53            | 80  |
| Wednesday      |               |     |
| 19 July        |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 46            | 77  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 52             | 89            | 31  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 50             | 77            | 35  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 56            | 79  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 54            | 84  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 53             | 86            | 33  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 54            | 84  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 55            | 91  |
| Sunday 23      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 54             | 88            | 39  |
| Date (2017)   | Time period   | L   |
|---------------|---------------|-----|
| Aeq,          | T             |     |
| dB            |               |     |
| Highest       |               |     |
| L             |               |     |
| Amax,         | T             |     |
| dB            |               |     |
| L             |               |     |
| A90,          | T             |     |
| dB            |               |     |
| Monday 24     |               |     |
| July          |               |     |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 13:00*        | 48            | 77  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 16:30          |               |     |
| -              |               |     |
|                |               |     |
| 23:00*         |               |     |
| 49             | 75            | 34  |
| Friday 14 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 40             | 68            | 30  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 48            | 73  |
| Saturday 15    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 41            | 73  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 47             | 76            | 33  |
| Sunday 16      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 43             | 68            | 28  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 51            | 91  |
| Monday 17      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 43            | 61  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 55             | 84            | 38  |
| Tuesday 18     |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 60            | 34  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 49            | 75  |
| Wednesday      |               |     |
| 19 July        |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 44            | 75  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 52             | 74            | 34  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 60            | 34  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 48            | 72  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 47            | 70  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 47             | 71            | 34  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 40             | 69            | 31  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 46            | 67  |
| Sunday 23      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 45            | 65  |
| Monday 24      |               |     |
| July           |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 12:45*         |               |     |
| 51             | 73            | 40  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 17:30          |               |     |
| -              |               |     |
|                |               |     |
| 23:00*         | 44            | 88  |
| Friday 14 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 42            | 76  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 49             | 88            | 38  |
| Saturday 15    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 65            | 34  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 45            | 79  |
| Sunday 16      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 43            | 77  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 45             | 78            | 32  |
| Monday 17      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 46             | 84            | 36  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 52            | 86  |
| Tuesday 18     |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 46            | 78  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 48             | 86            | 39  |
| Wednesday      |               |     |
| 19 July        |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 44             | 78            | 36  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 48            | 80  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 45            | 68  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 52             | 80            | 40  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 50             | 79            | 38  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          | 49            | 79  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          | 47            | 78  |
| Sunday 23      |               |     |
| July           |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 20:15*         |               |     |
| 48             | 81            | 34  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)   | Time period   | L   |
|---------------|---------------|-----|
| Aeq,          | T             |     |
| dB            |               |     |
| Highest       |               |     |
| L             |               |     |
| Amax,         | T             |     |
| dB            |               |     |
| L             |               |     |
| A90,          | T             |     |
| dB            |               |     |
| 13:00         |               |     |
| -             |               |     |
|               |               |     |
| 23:00*        |               |     |
| 48            | 89            | 36  |
| Monday 17     |               |     |
| July          |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 40            | 66            | 29  |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 23:00         |               |     |
| 46            | 82            | 37  |
| Tuesday 18    |               |     |
| July          |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 39            | 78            | 27  |
| Date (2017)   | Time period   | L   |
|---------------|---------------|-----|
| Aeq,          | T             |     |
| dB            |               |     |
| Highest       |               |     |
| L             |               |     |
| Amax,         | T             |     |
| dB            |               |     |
| L             |               |     |
| A90,          | T             |     |
| dB            |               |     |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 23:00         |               |     |
| 51            | 88            | 35  |
| Wednesday     |               |     |
| 19 July       |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 43            | 80            | 29  |
| Thursday 20   |               |     |
| July          |               |     |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 11:00*        |               |     |
| 48            | 76            | 41  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 16:30          |               |     |
| -              |               |     |
|                |               |     |
| 23:00*         |               |     |
| 47             | 89            | 36  |
| Friday 14 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 72            | 30  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 47             | 82            | 35  |
| Saturday 15    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 40             | 82            | 31  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 45             | 75            | 35  |
| Sunday 16      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 45             | 83            | 33  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 45             | 82            | 36  |
| Monday 17      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 42             | 79            | 26  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 46             | 80            | 35  |
| Tuesday 18     |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 42             | 76            | 26  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 45             | 80            | 34  |
| Wednesday      |               |     |
| 19 July        |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 43             | 74            | 30  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 51             | 86            | 35  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 79            | 30  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 48             | 82            | 37  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 45             | 80            | 27  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 56             | 84            | 31  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 41             | 75            | 27  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 46             | 84            | 35  |
| Sunday 23      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 45             | 80            | 31  |
| Monday 24      |               |     |
| July           |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 11:45*         |               |     |
| 50             | 77            | 43  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

| Date (2017)   | Time period   | L   |
|---------------|---------------|-----|
| Aeq,          | T             |     |
| dB            |               |     |
| Highest       |               |     |
| L             |               |     |
| Amax,         | T             |     |
| dB            |               |     |
| L             |               |     |
| A90,          | T             |     |
| dB            |               |     |
| 15:30         |               |     |
| -             |               |     |
|               |               |     |
| 23:00*        |               |     |
| 49            | 77            | 33  |
| Monday 17     |               |     |
| July          |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 44            | 65            | 21  |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 23:00         |               |     |
| 48            | 73            | 39  |
| Tuesday 18    |               |     |
| July          |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 42            | 60            | 24  |
| 07:00         |               |     |
| -             |               |     |
|               |               |     |
| 23:00         |               |     |
| 53            | 89            | 38  |
| Wednesday     |               |     |
| 19 July       |               |     |
| 23:00         |               |     |
| -             |               |     |
|               |               |     |
| 07:00         |               |     |
| 41            | 61            | 29  |
| Date (2017)    | Time period   | L   |
|----------------|---------------|-----|
| Aeq,           | T             |     |
| dB             |               |     |
| Highest        |               |     |
| L              |               |     |
| Amax,          | T             |     |
| dB             |               |     |
| L              |               |     |
| A90,           | T             |     |
| dB             |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 51             | 87            | 38  |
| Thursday 20    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 44             | 68            | 30  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 51             | 74            | 42  |
| Friday 21 July |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 45             | 67            | 27  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 47             | 78            | 35  |
| Saturday 22    |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 39             | 60            | 20  |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 23:00          |               |     |
| 44             | 78            | 34  |
| Sunday 23      |               |     |
| July           |               |     |
| 23:00          |               |     |
| -              |               |     |
|                |               |     |
| 07:00          |               |     |
| 43             | 65            | 32  |
| Monday         |               |     |
| 24July         |               |     |
| 07:00          |               |     |
| -              |               |     |
|                |               |     |
| 13:00*         |               |     |
| 48             | 63            | 44  |

* Note - this period does not cover the full 16-hr day period and therefore may not be directly comparable with other complete time periods.

## Observations Of General Baseline Sound Environment

North Street, Sturton-le-Steeple (ML1)

 
The dominant sound source at this location during the daytime was noted to be
8.4.2
road traffic noise from Cross Street, Station Road and Gainsborough Road. Some additional (low level) noise was audible, potentially attributed to the maintenance of the WBB Power Station.
Crossing Keepers Cottage, West Burton (ML2)

 
The dominant sound source at this location during the daytime was noted to be
8.4.3
road traffic noise from Gainsborough Road (west). Mill House Farm, West Burton (ML3)
 
The dominant sound source at this location during the daytime was noted to be
8.4.4
road traffic noise from Gainsborough Road. In addition, electrical sound from the nearby electricity pylons was audible.
Manor Cottage, Bole (ML4)

 
The dominant sound source at this location during the daytime was noted to be
8.4.5
road traffic noise from Sturton Road. 194 Lea Road, Gainsborough (ML5)
 
The dominant sound source at this location during the daytime was noted to be
8.4.6
road traffic noise from Lea Road. Occasional dog barking was also noted at the neighbouring property.
Green Lane, Lea (ML6)

 
The dominant sound source at this location during the daytime was noted to be
8.4.7
road traffic noise from Gainsborough Road (east).
Knaith Hall, Knaith (ML7)

 
The dominant sound source at this location during the daytime was noted to be
8.4.8
road traffic noise from Gainsborough Road (east). During the setup of equipment, a gardener was present (using power tools).

## Representative Background Sound Levels

 
Representative background sound levels have been established for daytime and
8.4.9
night-time periods, based upon review and comparison of the modal and lowest
10th percentile of all 15-minute interval results throughout the daytime and nighttime periods surveyed.
 The area around the Site is very flat and the potential NSR are located all around
8.4.10
the Site at distances of approximately 1km to over 2km.  There are very few existing sources of background sound, particularly at night.
 As there are no significant topographical features in the area, the largest influence
8.4.11
on sound propagation is wind direction.  When a receptor is downwind of a source, sound propagation will be 10-15 dB higher than when it is upwind.  Therefore at each NSR, the background sound level varies depending on whether it is upwind or downwind of the major sound sources.  This applies to sound both from the existing background sources and the Proposed Development.
 Background 
sound measurements 
were 
undertaken 
over 
an 
extended
8.4.12
period.  During the survey, wind direction was also monitored to determine whether this had a significant effect on the results.  It was found that the background sound level for each NSR derived from the periods when it was downwind of the Site were slightly higher than those derived from the dataset as a whole (between 1 and 5 dB).  This is because the most significant background sound sources are the existing WBA and WBB Power Stations and when the wind was blowing in the opposite direction for each receptor, the contribution from the existing Power Stations will have been reduced.
 As the Proposed Power Plant Site is to be located immediately north of the
8.4.13
operational WBB Power Station, any sound emitted by the Proposed Development would be subject to the same wind propagation effects as the existing sounds emitted.  The sound predictions in the assessment are based on the ISO 9613 method, which assumes gentle downwind conditions.  Therefore, the predicted levels will only actually be experienced at each NSR when it is downwind of the Proposed Power Plant.  Consequently, it is appropriate to compare these predicted levels with background sound levels measured in similar conditions.
 There is no reliable method of predicting upwind propagation as there are too
8.4.14
many variables.  However as stated above, the upwind sound levels from an individual sound source will generally be 10-15 dB lower than the downwind sound levels.  The difference between the upwind and downwind background sound levels at the receptors was smaller than this (at 1-5 dB) as they have contributions from sources located all around them.  So the potential impact of the Proposed Development would be at its greatest in downwind conditions.
 As a result, the wind direction has also been taken into consideration in the
8.4.15
analysis of the data to produce a representative *background sound level* for each
NSR.  The wind direction data was gathered by a portable monitor alongside one of the sound level meters during the baseline sound survey.  This information was used to analyse and refine the measured results from all seven NSR.  The results produced by the analysis and refinement were consistent with the locations of the major sound sources listed for each location and, in view of the very flat nature of the land around the Site, it is assumed that the wind direction measured at the single location was representative for all.
Table 8-24 summarises the defined representative *background sound levels* taken
8.4.16
forward for the NSR adjacent to each monitoring location within the BS 4142 assessment.

| Receptor      |   ML1  |   ML2  |   ML3  |   ML4  |   ML5  |   ML6  |
|---------------|--------|--------|--------|--------|--------|--------|
| Daytime       |        |        |        |        |        |        |
| L             |        |        |        |        |        |        |
| A90           |        |        |        |        |        |        |
| dB (07:00-    |        |        |        |        |        |        |
| 23:00)        |        |        |        |        |        |        |
| 31            |     34 |     37 |     37 |     36 |     35 |     36 |
| Night-time    |        |        |        |        |        |        |
| L             |        |        |        |        |        |        |
| A90           |        |        |        |        |        |        |
| dB            |        |        |        |        |        |        |
| (23:00-07:00) |        |        |        |        |        |        |
| 26            |     33 |     34 |     34 |     29 |     29 |     24 |

 Up to 20 battery storage units were constructed within the footprint of WBB Power
8.4.17
Station and commenced operation in January 2018. The development includes a central control unit and associated cabling to connect the battery units to the existing 6.6 kV station switchboard.  The battery units are arranged in pairs that measure 17.6m by 5.3m and are 2.9m in height.
 A noise impact assessment was undertaken for the battery project (Ref 8-29).
8.4.18
Assessments made in accordance with BS 4142:2014 predicted that the noise generated from operation of the battery units would be unlikely to be noticeable (+0.1 dB - +0.2 dB) at the NSR used for the purposes of this chapter, which would be below the threshold of an adverse effect.  The current baseline at local NSR is therefore unlikely to be affected by the battery project and no further consideration has been given in this chapter to the development.
 No other developments, including those recently consented on the wider West
8.4.19
Burton Power Station site, are considered to have likely materially changed the
reported baseline for the purposes of this assessment.

## Future Baseline

 In the absence of the Proposed Development, future baseline sound levels at NSR
8.4.20
will depend largely on traffic flows on surrounding road/rail networks and the future operations at other industrial and commercial premises in the area. It is anticipated that WBA Power Station would close by 2025 under current legislation; potentially resulting in a reduction in future baseline at properties within the Site vicinity, compared with current periods when the existing coal fired power station is in operation.  WBB Power Station is assumed to remain operational in the future baseline scenario.

## 8.5 Development Design And Impact Avoidance Construction Noise

 
Construction activities will be undertaken during 0700 and 1900 hours on Monday
8.5.1
to Friday and 0800 and 1800 hours on a Saturday), although some works may take place outside of core working hours, provided they do not exceed a noise limit at locations to be agreed with BDC.
 
Measures to mitigate noise will be implemented during the construction phase of
8.5.2
the Proposed Development in order to minimise impacts at local residential NSR, particularly with respect to activities required outside of core working hours. The
appointed contractor(s) will produce a Construction Environmental Management Plan (CEMP) that would provide details of proposed environmental control measures, including measures related to noise.  A Framework CEMP is included
as **Application Document Ref. 7.3** and contains the impact avoidance measures
as outlined in this section.  It is proposed that the final CEMP will be secured by a
Requirement of the draft DCO (**Application Document Ref. 2.1**) and submitted
for approval by the local planning authority prior to construction.  The appointed contractor will then implement the approved CEMP.
 
Mitigation measures for inclusion within the CEMP include, but are not limited to:
8.5.3
·
abiding by construction noise limits at locations to be agreed with BDC;
·
ensuring that all appropriate processes are in place to minimise noise before works begin and ensuring that BPM are being achieved throughout the construction programme, including the use of localised screening around significant noise producing plant and activities;
·
ensuring that modern plant is used, complying with the applicable UK noise 
emission requirements;
·
selection of inherently quiet plant where possible;
·
hydraulic techniques for breaking to be used in preference to percussive techniques where reasonably practicable;
·
if piling is required, use of lower noise piling (such as rotary bored or hydraulic jacking) rather than driven piling techniques where reasonably practicable; 
·
off-site pre-fabrication where reasonably practicable;
·
all plant and equipment being used for the works to be properly maintained, silenced where appropriate, operated to prevent excessive noise, and switched off when not in use;
·
all contractors to be made familiar with current legislation and the guidance in 
BS 5228 (Parts 1 and 2) (Ref 8-17 and Ref 8-18), which should form a 
prerequisite of their appointment;
·
loading and unloading of vehicles, dismantling of site equipment such as scaffolding or moving equipment or materials around the Site, to be conducted in such a manner as to minimise noise generation as far as reasonably practicable;
·
all vehicles used on-Site shall incorporate broadband reversing warning 
devices as opposed to the typical tonal reversing alarms to minimise noise disturbance where reasonably practicable;
·
appropriate routing of construction traffic on public roads and along access tracks (see **Chapter 7:** Traffic and Transport); 
·
provision of information to BDC and local residents to advise of potential noisy works that are due to take place; and
·
monitoring of noise complaints, and reporting to the Applicant for immediate investigation and action.
 
Method Statements regarding construction management, traffic management and
8.5.4
overall site management will be prepared in accordance with best practice and relevant British Standards, to help to minimise impacts of construction works.  One of the key aims of such Method Statements would be to minimise noise disruption to local residents during the construction phase, as far as reasonably practicable.
 
Consultation and communication with the local community throughout the
8.5.5
construction period would serve to publicise the works schedule, giving notification to residents regarding periods when higher levels of noise may occur during specific operations, and providing lines of communication where complaints can be addressed.
 
The selected contractor would be encouraged to be a member of the 'Considerate
8.5.6
Constructors Scheme' which is an initiative open to all contractors undertaking
building work.
 
A detailed noise assessment would be carried out once the contractor is appointed
8.5.7
and further details of construction methods are known, in order to identify specific mitigation measures for the Proposed Development (including construction traffic). The control of noise, including monitoring during construction is proposed to be
secured by a Requirement of the draft DCO (**Application Document Ref. 2.1**).

## Operational Noise

 
The selection of the Proposed Power Plant Site and development of the indicative
8.5.8
concept layout have already included consideration of potential noise effects and proximity to NSR, with plant being located close to WBB Power Station, in order to increase the distance between plant and the NSR.  During the detailed design stage, further options to mitigate potential significant noise effects by design will be explored.
 
Several options for configuration of generation plant and equipment have been
8.5.9
considered within the Rochdale Envelope assessed. Preliminary modelling has shown that options are available that are capable of meeting applicable threshold noise levels.
 The Proposed Development would be operated in accordance with an
8.5.10
Environmental Permit issued and regulated by the Environment Agency. This will require operational noise from the generating station to be controlled through the use of BAT, which will be determined through the Environmental Permit application. It is proposed that operational noise will also be secured by a
Requirement of the draft DCO (**Application Document Ref. 2.1**).
8.6
Likely Impacts and Effects

## Construction Noise And Vibration

 
This section discusses the potential noise and vibration effects on sensitive
8.6.1
receptors during the construction phase of the Proposed Development.
 
Noise levels experienced by local receptors during such works depend upon a
8.6.2
number of variables, the most significant of which are:
·
the noise generated by plant or equipment used on-Site, generally expressed 
as SWL or the vibration generated by the plant;
·
the periods of use of the plant on-Site, known as its on-time; 
·
the distance between the noise/vibration source and the receptor;
·
the noise attenuation due to ground absorption, air absorption and barrier effects; 
·
in some instances, the reflection of noise due to the presence of hard surfaces such as the sides of buildings; and
·
the time of day or night the works are undertaken.
 
Residential NSR are located at distance in different directions around the Site. The
8.6.3
closest residential NSR to the West Burton Power Station site include Manor Cottage, Bole, located approximately 1.2km to the west, and Mill House Farm located approximately 1.3km to the west of the Proposed Power Plant Site.
 
Predicted noise levels during construction of the Proposed Development have
8.6.4
been based upon construction methods used for other power stations in the UK, and supplemented by information provided by the Applicant.  As a conservative approach, it is assumed that all plant and activities are taking place at the closest point within the Proposed Power Plant Site to each NSR, whereas in reality, this will not occur for any significant duration, if at all.  Also no screening provided by buildings within the West Burton Power Station site or soft ground attenuation have been taken into account.
 
The predicted levels apply to core weekday daytime working hours (07:00 –
8.6.5
19:00).
 
A summary of noise predictions at NSR locations around the Site (using the
8.6.6
closest NSR to the Proposed Development construction works in the vicinity of the
baseline sound survey locations) are presented in **Table 8-25**.  Facade noise
levels have been predicted to allow subsequent comparison with Construction
Noise SOAEL and LOAEL for residential receptors as detailed in **Table 8-8**.
 
As advised by BS 5228 (Ref 8-17), noise levels predicted at distances over 300m
8.6.7
(which all NSR exceed) should be treated with caution due to the increasing importance of meteorological effects.

Predicted free-field noise level for daytime construction activity
dB LAeq,12h
Receptor
Site Preparation
Piling and foundation
Electrical & Gas connection enabling works
Building & General Site Activities
Fit out
Landscaping
ML1 - North Street, Sturton-le-
Steeple - to east of
54
52
53
52
51
33
ML2 - Crossing Keepers 
Cottage, West Burton
55
52
53
54
51
33
ML3 - Mill House Farm
55
55
56
57
54
36
ML4 - Manor Cottage, Bole
56
57
58
59
56
38
ML5 - Causeway Lane
51
51
52
53
50
32
ML6 - Green Lane, Lea
51
51
52
53
50
32
ML7 - Knaith Hall, Knaith
49
49
49
50
47
29

## Construction Noise Effects

 
The effects of the predicted daytime construction noise levels (as presented in
8.6.8
Table 8-25 have been compared against the absolute construction noise limit
values in **Table 8-8** and using the semantic scales in **Table 8-9**, the classification
of effects is summarised in **Table 8-26** below.

Predicted Effect - Construction of the Proposed Development
Receptor
Site Preparation
Piling and foundation
Electrical & Gas connection enabling works
Building & General Site Activities
Fit out
Landscaping Negligible (not significant)
ML1 - North Street, Sturton-le-Steeple
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
ML2 - Crossing 
Keepers Cottage, West Burton
Negligible (not significant)
Negligible (not significant)
ML3 - Mill House Farm
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
ML4 - Manor Cottage, 
Bole
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible(not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
ML5 - Causeway Lane 
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
ML6 - Green Lane, 
Lea
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
ML7 - Knaith Hall, 
Knaith
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)
Negligible (not significant)

 
Construction noise effects at all NSR during construction of the Proposed
8.6.9
Development are predicted to be negligible (not significant) during the daytime period, due largely to the distances between the construction works and NSR.
 It may be necessary for some construction activities to take place continuously
8.6.10
over day, evening and night periods during peak construction times of the Proposed Development, although the exact nature of the works is unknown. SOAEL and LOAEL threshold values during non-weekday daytime periods have
been defined in **Table 8-8**. Comparison of the predicted daytime noise levels
against the lower limit values for evening, weekend and particularly night-time working indicate potential minor adverse (not significant) effects at NSR during evening and weekend working, but potential for moderate adverse (significant)
effects at some NSR during night-time working, if the same intensity of working as for the daytime is assumed. Therefore, construction activities taking place during night-time hours will need to be planned, managed and mitigated appropriately, so as not to exceed the SOAEL threshold values and reduce levels towards the LOAEL (or less) where practical. Provided the SOAEL threshold values are not exceeded, construction activities outside of core working hours would be considered as having a minor adverse effect or less (not significant).  Potential measures to ensure that appropriate mitigation is in place during the works are
discussed in **Section 8.5**, whilst additional measures related night-time working are detailed in **Section 8.7**.

## Construction Traffic Noise

 HGVs delivering construction materials would access the West Burton Power
8.6.11
Station site from the existing site entrance located off the C2 Gainsborough Road, with all HGVs arriving and departing to/from the north via the A620 and onwards to
the A631. Data have been used from **Appendix 7A:** Transport Assessment (ES
Volume II) for the assumed typical traffic flows associated with construction.
 2029 is assumed to be the year with the peak traffic flows related to the
8.6.12
construction of the Proposed Development. **Table 8-27** presents the predicted
2029 Baseline and Committed Development Traffic Flows, and Table 8-28
presents 2029 Baseline, Committed Development and Construction Traffic Flows combined.
Table 8-27: Scenario 1 - 2029 Baseline and Committed Development traffic flows

Total HGVs
Percentage HGV
Average Speed
Location
Flow
Total Vehicles (AAWT)
Total 2-
Way
3,211
481
15.0%
64kph
Gainsborough Road (South of Power Station Entrance)
Total HGVs
Percentage HGV
Average Speed
Location
Flow
Total Vehicles (AAWT)
Total 2-
Way
3,527
504
14.3%
82kph
Sturton Road (North of Power Station Entrance)
Total 2-
Way
5,636
771
13.7%
80kph
A620 Gainsborough Road A620 Saundby Road
Total 2-
Way
8,804
1,166
13.2%
71kph
Total HGVs
Percentage HGV
Average Speed
Location
Flow
Total Vehicles (AAWT)
Gainsborough Road (South of Power Station Entrance)
Total 
2-
Way
3,231
481
14.9%
64kph
Sturton Road (North of Power Station Entrance)
Total 
2-
Way
3,845
616
16.0%
82kph
A620 Gainsborough Road
Total 
2-
Way
5,656
771
13.6%
80kph
A620 Saundby Road
Total 
2-
Way
9,102
1,278
14.0%
71kph

 The potential changes in road traffic noise along these roads as a result of
8.6.13
construction traffic relating to the Proposed Development have been considered
by calculating the BNL at 10m from the road and comparing the change Table 8- 29 presents the results of the BNL change assessment.

Effect
Link
Predicted BNL, LA10, 18hr dB
Change in BNL, dB (Scenario 2 minus Scenario 1)
Scenario 1 2029 Baseline and Committed Development
Scenario 2 2029 Baseline, Committed Development and Construction Traffic
65.3
65.3
0
Negligible (not significant) 
Gainsborough Road (South of Power Station Entrance) Sturton Road (North of Power Station Entrance)
68.0
68.7
+0.7
Negligible (not significant)
A620 Gainsborough Road
69.8
69.8
0
Negligible (not significant)
A620 Saundby Road
70.0
70.2
+0.2
Negligible (not significant)

 The above predictions assume that all roads are laid with impervious bitumen
8.6.14
(such as hot rolled asphalt) with a 2mm texture depth and that the road surface remains unchanged with and without construction traffic.
Table 8-29 shows either no change or very low magnitude of noise impact is
8.6.15
expected due to changes in traffic flows along all the assessed routes during construction of the Proposed Development.  This will result in no change or negligible adverse effects (not significant) at local residential NSR. Based upon the above, no further specific mitigation measures are proposed in addition to those
listed in **Section 8.5**.
 The construction noise management measures listed within **Section 8.5**, which
8.6.16
will be further developed as the project progresses and more details of the construction phase are known, will assist in minimising the potential for adverse effects due to construction traffic noise at nearby NSR.

## Construction Vibration Effects

 The magnitude of impact at different receptors will be dependent upon a number
8.6.17
of factors, including distance between the works and receptors, ground conditions, the nature and method of works required close to receptors and the specific activities being undertaken at any given time.
 There are no residential receptors within close proximity to the Proposed
8.6.18
Development which have the potential to be affected by construction vibration. However, 
there 
is 
the 
potential 
for 
some 
vibration 
impacts 
upon
buildings/structures within the West Burton Power Station site. Whilst it is
considered unlikely that most typical construction working routines would generate levels of vibration above which building damage would be expected to be sustained (subject to final plant and working requirements), there is the potential that vibration impacts could cause annoyance to occupants and exceed the
LOAEL and SOAEL set out in **Section 8.3**.  The need for piling, and the type of
any piling potentially required is not yet confirmed.
 If piling, heavy earthworks, vibratory rollers or other significant vibration producing
8.6.19
operations are proposed in close proximity to any existing sensitive buildings, further consideration will be given to potential impacts, once the contractor is appointed and the construction methods and requirements are developed.  As the construction of the Proposed Development and the use of many of the existing buildings within the West Burton Power Station site are both within the control of the Applicant, any identified issues can be effectively managed by the Applicant and their contractor.  Potential measures to ensure that appropriate mitigation is in
place during the works are discussed in **Section 8.5** and **Section 8.7**.
Operational Noise
 The preferred configuration of the Proposed Development is yet to be decided.
8.6.20
Therefore, noise modelling has been undertaken for a number of different potential operational scenarios of plant configuration, in order to give a view of the range of sound levels that could be produced by various unmitigated and mitigated options for the purposes of determining a representative worst-case.  In the PEI Report (Ref 8-28), results for ten scenarios assessed were presented.  However, in order to simplify the assessment, the worst-case configuration, which comprises five
smaller OCGTs, is presented in this section, whilst the need for and effects of
proposed mitigation measures are discussed in **Section 8.7**.
 The indicative locations of operational equipment were taken from Figure 4.1b
8.6.21
(ES Volume III).  Input SWL data was either provided by typical equipment manufacturers or taken from AECOM's archive of data for similar installations. The SWL data was provided for various source components.  The typical source components included the following (noting some minor differences in the data provided by each manufacturer):
·
gas turbine (GT) enclosure;
·
diffuser enclosure;
·
generator enclosure;
·
auxiliaries enclosure;
·
air duct;
·
air intake inlet;
·
air intake body;
·
stack body upstream silencer;
·
stack body downstream silencer; and
·
stack outlet.
 The assessment described below sets out the predicted noise impacts and effects
8.6.22
associated with operation of the Proposed Development, which would be longterm.
 The following assumptions have been made when undertaking the operational
8.6.23
noise modelling and assessment:
·
the Proposed Development would operate to meet market demand and therefore operate intermittently at times of peak demand or system need as discussed in **paragraph 8.6.24**. However, the BS 4142 assessment method 
(Ref 8-21) is based upon reference periods of 1 hour during the day and 15 
minutes at night.  Therefore the assessment only considers the sound averaged over the worst hour of the daytime or worst 15 minutes of the night. When the Proposed Development is operational, the sound produced by the plant would be relatively constant in nature and each period of operation is assumed to be longer than one hour.  As a result, the intermittent nature of the operation does not have an impact on the assessment.  
·
a +3 dB correction has been applied to the specific sound levels predicted from the Proposed Development, on the basis that the sound emissions may be distinctive above the residual acoustic environment, through its expected cyclical operation, potentially each day.  This is considered conservative in the context of the prevailing noise environment, which includes road traffic noise and some noise from WBA Power Station and WBB Power Station;
·
corrections for tonality, impulsivity, and intermittency have not been applied, on the assumption that these potential features will be designed out of the Proposed Development during the detailed design phase by the selection of appropriate plant, building cladding louvres and silencers/attenuators;  
·
the SWLs provided by manufacturers for all principal sound emitting enclosure/elements (air inlet filters, electrical buildings, transformers, workshops etc.) are understood to be external radiated SWL; and
·
prediction methodologies have been based on ISO 9613:2.
 Operation of the plant is to be driven by the dynamics of the energy market; as a
8.6.24
result the plant could run for shorter or longer periods, at any time of day, up to the maximum allowed under its Environmental Permit, which is currently anticipated to be up to 1,500 hours/year on a rolling 5 year average.
 The plant would be expected to generally operate during periods of peak demand
8.6.25
for relatively short periods, typically a few hours at a time. However, it is not possible to predict what the maximum operating period would be or how many periods could occur during a single day. Therefore, to inform a worst-case
assessment, continual operation has been assumed. In accordance with BS 4142:2014 (Ref 8-21) the daytime assessment considers a 1-hour period and the night-time assessment considers a 15-minute period.
 In the absence of any additional mitigation, the predicted free-field operational
8.6.26
specific sound levels at the NSR around the Proposed Development, for the worstcase plant configuration (up to five OCGTs), are presented in **Table 8-30**.

Location
Reference
Up to five OCGTs
Kent House, North Street, Sturton-le-
Steeple
ML1
41
Crossing Keepers Cottage, West Burton
ML2
42
Mill House Farm
ML3
47
Manor Cottage, Bole
ML4
50
194 Lea Road, Gainsborough
ML5
39
Green Lane, Lea
ML6
41
Knaith Hall, Knaith
ML7
37

 The daytime BS 4142 assessments results for receptors ML1-ML7 are presented
8.6.27
in **Table 8.31** below. The values presented are the differences between the range
of representative *background sound level* at each NSR and the predicted rating
level (the specific Sound Level LAeq,T plus a +3 dB correction for a potentially
distinctive character).  Positive values in the table indicate an excess of the rating level over the *background sound level*.

background sound level, without mitigation
| Location               | Reference        |
|------------------------|------------------|
| Classification         |                  |
| of Effect              |                  |
| (unmitigated)          |                  |
| Up to five OCGTs       |                  |
| -                      |                  |
|                        |                  |
| Excess of rating level |                  |
| over  background sound |                  |
| level (dB)             |                  |
| Kent House,            |                  |
| North Street,          |                  |
| Sturton                |                  |
| -                      |                  |
| le                     |                  |
| -                      |                  |
| ML1                    | 13 (Medium/High) |
| Moderate/major         |                  |
| (significant)          |                  |
| Location                                                                 | Reference            |
|--------------------------------------------------------------------------|----------------------|
| Classification                                                           |                      |
| of Effect                                                                |                      |
| (unmitigated)                                                            |                      |
| Up to five OCGTs                                                         |                      |
| -                                                                        |                      |
|                                                                          |                      |
| Excess of rating level                                                   |                      |
| over  background sound                                                   |                      |
| level (dB)                                                               |                      |
| Steeple                                                                  |                      |
| ML2                                                                      | 11 (Medium)          |
| Moderate                                                                 |                      |
| (significant)                                                            |                      |
| Crossing                                                                 |                      |
| Keepers                                                                  |                      |
| Cottage, West                                                            |                      |
| Burton                                                                   |                      |
| Mill House                                                               |                      |
| Farm                                                                     |                      |
| ML3                                                                      | 13 (Medium/High)     |
| Moderate/major                                                           |                      |
| (significant)                                                            |                      |
| Manor                                                                    |                      |
| Cottage, Bole                                                            |                      |
| ML4                                                                      | 16 (High)            |
| Major                                                                    |                      |
| (significant)                                                            |                      |
| 194 Lea Road,                                                            |                      |
| Gainsborough                                                             |                      |
| ML5                                                                      | 6 (Low)              |
| Minor (not                                                               |                      |
| significant)                                                             |                      |
| Green Lane,                                                              |                      |
| Lea                                                                      |                      |
| ML6                                                                      | 9 (Medium)           |
| Moderate                                                                 |                      |
| (significant)                                                            |                      |
| Knaith Hall,                                                             |                      |
| Knaith                                                                   |                      |
| ML7                                                                      | 4 (Low)              |
| Minor (not                                                               |                      |
| significant)                                                             |                      |
| The night-time BS 4142 assessment results for ML1 - ML7 are presented in |                      |
| Table                                                                    |                      |
| 8.6.28                                                                   |                      |
| 8-32                                                                     |                      |
| .                                                                        |                      |
| Table 8                                                                  |                      |
| -                                                                        |                      |
| 32                                                                       | : BS 4142 worst      |
| -                                                                        |                      |
| case night                                                               |                      |
| -                                                                        |                      |
| time excess of                                                           | rating level         |
| background sound level                                                   | , without mitigation |
| Location                                                                 |                      |
| Reference                                                                |                      |
| Effect                                                                   |                      |
| (unmitigated)                                                            |                      |
| Up to five OCGTs                                                         |                      |
| -                                                                        |                      |
| Excess of rating level                                                   |                      |
| over  background                                                         |                      |
| sound level (dB)                                                         |                      |
| ML1                                                                      | 18 (High)            |
| Kent House,                                                              |                      |
| North Street,                                                            |                      |
| Sturton                                                                  |                      |
| -                                                                        |                      |
| le                                                                       |                      |
| -                                                                        |                      |
| Steeple                                                                  |                      |
| ML2                                                                      | 12 (Medium/High)     |
| Moderate/major                                                           |                      |
| (significant)                                                            |                      |
| Crossing                                                                 |                      |
| Keepers                                                                  |                      |
| Cottage, West                                                            |                      |
| Burton                                                                   |                      |
| Mill House                                                               |                      |
| Farm                                                                     |                      |
| ML3                                                                      | 16 (High)            |
| Manor                                                                    |                      |
| Cottage, Bole                                                            |                      |
| ML4                                                                      | 19 (High)            |
| 194 Lea Road,                                                            |                      |
| Gainsborough                                                             |                      |
| ML5                                                                      | 13 (Medium/High)     |
| Moderate/major                                                           |                      |
| (significant)                                                            |                      |
| Green Lane,                                                              |                      |
| ML6                                                                      | 15 (High)            |
Lea Knaith Hall, Knaith
ML7
16 (High)
Major (significant)

 In accordance with **Table 8-14** , the values in **Table 8-31** and **Table 8-32** for the
8.6.29
worst-case scenario produce a range of impact magnitudes from low to high adverse at the seven NSR. This would result in effects between minor (not
significant) to major adverse (significant) in accordance with **Table 8-16**.
 On the basis of the above results and a desire to reduce sound levels to the
8.6.30
LOAEL (no greater than +5 dB excess of rating level over background sound level), potential mitigation options to reduce sound levels have been considered
and are discussed in **Section 8.7**.

## Decommissioning

 The potential impacts and effects would require further consideration at the
8.6.31
decommissioning stage of the Proposed Development, but potential measures to ensure that appropriate mitigation is in place during such works are detailed in
Section 
8.5. 
The 
predicted 
noise 
and 
vibration 
effects 
of 
eventual
decommissioning of the Proposed Development are considered to be comparable to, or less than those assessed for construction activities, and thus effects are not anticipated to be significant.

## 8.7 Mitigation And Enhancement Measures Construction

 
It is predicted that there is the potential for no more than negligible adverse (not
8.7.1
significant) noise effects at residential NSR during construction works during
daytime working hours and minor adverse (not significant) noise effects if work were to take place at the same intensity during evenings and/or weekends. Therefore, no further specific mitigation measures have been identified for these
time periods beyond those reported in **Section 8.5** and included in the Framework
CEMP (**Application Document Ref. 7.3**). In the event that construction activities
are required at night-time, levels in excess of the SOAEL for night-time (55 dB) could occur at ML4 and ML3 (depending on the nature of activities undertaken and intensity of working).  This could result in a moderate adverse (significant) noise effect at these NSR in the absence of additional mitigation.  Measures would therefore be put in place to control activities at night-time so as not to exceed the SOAEL or relevant noise limit at locations to be agreed with BDC.  It is proposed
that this would be secured by a Requirement in the draft DCO (Application
Document Ref. 2.1).
 
There is the potential for some vibration effects at buildings, primarily at the
8.7.2
existing buildings within the West Burton Power Station site, during construction of the Proposed Development depending upon the requirement for, and nature of,
piling and other vibration emitting activities. As the construction of the Proposed Development and the use of many of the existing buildings within the West Burton Power Station site are both within the control of the Applicant, any identified issues can be effectively managed by the Applicant and their contractor.

 
Control of construction noise and vibration is proposed to be secured by a
8.7.3
Requirement of the draft DCO (**Application Document Ref. 2.1**). Furthermore, if
piling is required, this will be subject to a piling and penetrative foundation design method statement, informed by a risk assessment, which will be submitted to and, after consultation with the Environment Agency, approval sought from BDC.  It is proposed that this would be secured by a Requirement of the draft DCO
(**Application Document Ref. 2.1**).
 
The preferred approach for controlling construction noise and vibration is to reduce
8.7.4
levels at source where possible, but with due regard to practicality. Sometimes a greater noise or vibration level may be acceptable if the overall construction time, and therefore length of disruption, is reduced.
 
The list of noise control measures presented within **Section 8.5** provides a
8.7.5
detailed, but not exhaustive list of construction noise and vibration management
measures that are outlined in the Framework CEMP (Application Document Ref.
7.3).
 
Residual noise and vibration effects after mitigation are described in **Section 8.9**.
8.7.6
Operational Noise 
 
The operational assessment has assumed that potential sound of a tonal,
8.7.7
impulsive or intermittent nature (according to BS4142: 2014) will be designed out of the Proposed Development during the detailed design phase through the selection of appropriate plant, building cladding, louvres and silencers/attenuators
as necessary.  However, a +3 dB correction has been applied to the Specific Sound Levels predicted from the Proposed Development, on the basis that the sound emissions have the potential to be distinctive above the residual acoustic environment.
 
For the purposes of assessment, the 'mode' (as advocated in BS 4142:2014 (Ref
8.7.8
8-21)) has been considered alongside the 10th percentile of the measured
LA90,15mins values to determine representative background sound levels.  Based on
the profile of the obtained noise monitoring results, background sound levels equal to or lower than the mode have been assigned as 'representative' in this
assessment, which are more conservative than the use of the 10th percentile of the
measured values.  Therefore, conservative ('worst-case') assessment results are provided.
 
Based on the worst-case results presented in **Table 8-31** and **Table 8-32**,
8.7.9
mitigation would be required to achieve operational sound levels below the SOAEL
and LOAEL at all assessed NSR. **Table 8-33** and **Table 8-34** outline the overall
attenuation required to achieve the daytime and night-time LOAEL criterion of rating level no greater than +5 dB above the defined representative background sound level at each NSR.

Location
Reference
Up to five OCGT required attenuation to achieve daytime LOAEL (operation)
Kent House, North Street, Sturton-le-
Steeple
ML1
8
Crossing Keepers Cottage, West Burton
ML2
6
Mill House Farm
ML3
8
Manor Cottage, Bole
ML4
11
194 Lea Road, Gainsborough
ML5
1
Green Lane, Lea
ML6
4
Knaith Hall, Knaith
ML7
0
| Location                          |   Reference |
|-----------------------------------|-------------|
| Up to five OCGTs -                |             |
| required attenuation to           |             |
| achieve night-time                |             |
| LOAEL (operation)                 |             |
| Kent House, North Street, Sturton |             |
| -                                 |             |
| le                                |             |
| -                                 |             |
| Steeple                           |             |
| ML1                               |          13 |
| Crossing Keepers Cottage, West    |             |
| Burton                            |             |
| ML2                               |           7 |
| Mill House Farm                   |             |
| ML3                               |          11 |
| Manor Cottage, Bole               |             |
| ML4                               |          14 |
| 194 Lea Road, Gainsborough        |             |
| ML5                               |           8 |
| Green Lane, Lea                   |             |
| ML6                               |          10 |
| Knaith Hall, Knaith               |             |
| ML7                               |          11 |

 In light of the required attenuation to achieve the defined noise criteria, further
8.7.10
appraisal by plant engineers has been undertaken.  This has evaluated the main potential noise sources associated with the operational plant and identified potential design and embedded mitigation options that, in combination, could reduce predicted sound levels at nearby NSR to below the LOAEL criteria.  The potential mitigation measures include:
·
reducing the breakout noise from the GTs, generator and accessories through use of enhanced enclosures, or potentially containing them within a building;
·
reducing the air inlet noise emissions by addition of further in-line attenuation; 
·
reducing the stack outlet noise emissions by addition of silencers or sound proofing panels; 
·
reducing fin fan cooler noise emissions by screening, re-sizing, fitting low 
noise fans or attenuation;
·
screening or enclosing the transformers or other equipment; 
·
use of screening or bunding to shield receptors from noise sources; or
·
orientation of plant within the Site to provide screening of low level noise sources by other buildings and structures, or orientating fans and the air inlets away from sensitive receptors.
 An engineering appraisal was undertaken to assess the reduction in sound levels
8.7.11
that could be achieved by application of the mitigation measures listed above. Through discussion with one of the manufacturers, it was concluded that the sound power emissions from the major source components in the unmitigated
scenario could be practically reduced by the amounts given in Table 8-35.
Table 8-35: Practical sound power reductions for worst-case source components provided by a manufactures

| Source component     |   Practical sound power level (SWL)  |
|----------------------|--------------------------------------|
| reduction from worst |                                      |
| -                    |                                      |
| case scenario        |                                      |
| Air intake           |                                   15 |
| GT Enclosure         |                                   15 |
| Stack                |                                   16 |
| Fin Fan Cooler       |                                   10 |
| Main transformer     |                                   10 |

 By application of those mitigation measures to the manufacturer's worst-case data,
8.7.12
the mitigated *specific sound levels* given in **Table 8-36** are predicted.
Table 8-36: Predicted operational *specific sound levels* LAeq,T - Proposed Power Plant Site with mitigation

| Location                          | Reference   |
|-----------------------------------|-------------|
| Up to five OCGTs                  |             |
| -                                 |             |
|                                   |             |
| predicted operational             |             |
| specific sound levels             |             |
| L                                 |             |
| Aeq,T                             |             |
| Kent House, North Street, Sturton |             |
| -                                 |             |
| le                                |             |
| -                                 |             |
| Steeple                           |             |
| ML1                               | 21          |
| Crossing Keepers Cottage, West    |             |
| ML2                               | 23          |
| Location                                                                                 | Reference         |
|------------------------------------------------------------------------------------------|-------------------|
| Up to five OCGTs                                                                         |                   |
| -                                                                                        |                   |
|                                                                                          |                   |
| predicted operational                                                                    |                   |
| specific sound levels                                                                    |                   |
| L                                                                                        |                   |
| Aeq,T                                                                                    |                   |
| Burton                                                                                   |                   |
| Mill House Farm                                                                          | ML3               |
| Manor Cottage, Bole                                                                      | ML4               |
| 194 Lea Road, Gainsborough                                                               | ML5               |
| Green Lane, Lea                                                                          | ML6               |
| Knaith Hall, Knaith                                                                      | ML7               |
| The daytime BS 4142 assessment results for these mitigated predictions at                | 8.7.13            |
| receptors ML1-ML7 are presented in                                                       |                   |
| Table 8-37                                                                               |                   |
| below. The values presented are                                                          |                   |
| the differences between the range of representative                                      |                   |
| background sound level                                                                   |                   |
| at                                                                                       |                   |
| each NSR and the predicted                                                               |                   |
| rating level                                                                             |                   |
| (the specific Sound Level                                                                |                   |
| L                                                                                        |                   |
| Aeq,T                                                                                    |                   |
| plus a                                                                                   |                   |
| +3 dB correction for a potentially distinctive character).  Positive values in the table |                   |
| indicate an excess of the                                                                |                   |
| rating level                                                                             |                   |
| over the                                                                                 |                   |
| background sound level, whilst                                                           |                   |
| negative values indicate that the                                                        |                   |
| rating level                                                                             |                   |
| is below the                                                                             |                   |
| background sound level                                                                   |                   |
| .                                                                                        |                   |
| Table 8                                                                                  |                   |
| -                                                                                        |                   |
| 37:                                                                                      |                   |
| level                                                                                    | , with mitigation |
| Location                                                                                 | Ref.              |
| Classification of                                                                        |                   |
| Effect (mitigated)                                                                       |                   |
| Up to five OCGTs                                                                         |                   |
| -                                                                                        |                   |
| Excess of rating                                                                         |                   |
| level over                                                                               |                   |
| background                                                                               |                   |
| sound level (dB)                                                                         |                   |
| Kent House, North Street,                                                                |                   |
| Sturton                                                                                  |                   |
| -                                                                                        |                   |
| le                                                                                       |                   |
| -                                                                                        |                   |
| Steeple                                                                                  |                   |
| ML1                                                                                      |                   |
| -                                                                                        |                   |
| 7 (Very low)                                                                             |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| Crossing Keepers Cottage,                                                                |                   |
| West Burton                                                                              |                   |
| ML2                                                                                      |                   |
| -                                                                                        |                   |
| 7 (Very low)                                                                             |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| Mill House Farm                                                                          | ML3               |
| -                                                                                        |                   |
| 6 (Very low)                                                                             |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| Manor Cottage, Bole                                                                      | ML4               |
| -                                                                                        |                   |
| 3 (Very low)                                                                             |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| 194 Lea Road,                                                                            |                   |
| Gainsborough                                                                             |                   |
| ML5                                                                                      |                   |
| -                                                                                        |                   |
| 13 (Very low)                                                                            |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| Green Lane, Lea                                                                          | ML6               |
| -                                                                                        |                   |
| 11 (Very low)                                                                            |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |
| Knaith Hall, Knaith                                                                      | ML7               |
| -                                                                                        |                   |
| 15 (Very low)                                                                            |                   |
| Negligible adverse                                                                       |                   |
| (not significant)                                                                        |                   |

 The night-time BS 4142 assessment results for ML1 - ML7 are presented in Table
8.7.14
8-38.

level, with mitigation
Location
Ref.
Classification of Effect (mitigated)
Up to five 
OCGTs - Excess 
of rating level over background sound level (dB)
Kent House, North Street, 
Sturton-le-Steeple
ML1
-2 (Very low)
Negligible adverse (not significant) 
Crossing Keepers Cottage, West Burton
ML2
-6 (Very low)
Negligible adverse (not significant) 
Mill House Farm
ML3
-3 (Very low)
Negligible adverse (not significant) 
Manor Cottage, Bole
ML4
0 (Very low)
Negligible adverse (not significant) 
194 Lea Road, Gainsborough
ML5
-6 (Very low)
Negligible adverse (not significant) 
Green Lane, Lea
ML6
-5 (Very low)
Negligible adverse (not significant) 
Knaith Hall, Knaith
ML7
-3 (Very low)
Negligible adverse (not significant) 

 In accordance with **Table 8-14**, on this basis, the use of a combination of such
8.7.15
mitigation measures would result in a very low magnitude of impact at each of the NSR. This would result in negligible (not significant) noise effects at NSR in
accordance with **Table 8-15** and **Table 8-16**.
 As the Proposed Development design progresses to the detailed design stage, the
8.7.16
existing noise model will be refined and additional acoustic assessment will be undertaken in consultation with the design engineers, to determine the most appropriate mitigation options in accordance with BAT.  The findings of the further assessment will inform the design to ensure that rating levels meet with a target of no greater than +5 dB above the representative background sound level at each NSR, resulting in no more than a low magnitude of impact and no greater than a minor adverse effect which would not be significant.  Operational noise is
proposed to be secured by a Requirement in the draft DCO (Application
Document Ref. 2.1), with the levels and the approach to monitoring of noise
effects to be agreed with BDC in consultation with WLDC.

## Decommissioning

 Consistent with construction mitigation, it has been assumed that relevant best
8.7.17
practice mitigation measures would be in place during any decommissioning
works.  No additional mitigation has been identified as necessary for the decommissioning phase of the Proposed Development.

 Residual effects after mitigation are described in **Section 8.9**.

8.7.18

8.8
Limitation or Difficulties
Construction
 
Detailed construction information is not yet available (given that the construction
8.8.1
contractor has not yet been appointed). Therefore, this assessment draws upon the experience and assessments undertaken for other similar projects. The
assessment is quantitative, but indicative, although it is considered to be robust.
Construction noise thresholds (limit values) have been provided in **Table 8-8**,
which are to be applied at local NSR.  Further assessment has been identified as being required pre-construction, to ensure that appropriate mitigation measures are developed to achieve the threshold values, once the contractor is appointed.  It
is proposed to secure this (and other mitigation measures detailed in **Section 8.7**) by a Requirement of the draft DCO (**Application Document Ref. 2.1**), which will
ensure that construction noise and vibration is minimised.  Construction noise impacts will be further minimised through the use of the CEMP.

## Operation

 
Assumptions made during the noise modelling, and assessment of the Proposed
8.8.2
Development operation, are presented in **paragraph 8.6.23**.  It is considered that
the assumptions made result in the assessment being conservative.
 
Given the large extent of sound level data obtained during the noise surveys,
8.8.3
significantly different 'representative' background sound level values can be obtained using different statistical analysis methods. The example analysis used in
BS 4142:2014 is the 'mode'. In this assessment the mode has been considered
alongside the 10th percentile of the measured LA90,15mins values.  As a result,
background sound levels equal to or lower than the mode have been assigned as 'representative' in this assessment.  Therefore, conservative ('worst-case') assessment results are provided.
 
The preferred configuration of the Proposed Development is yet to be decided.
8.8.4
Therefore, the operational noise modelling undertaken has considered a representative worst-case which comprises up to five smaller OCGTs, assessing both unmitigated and mitigated scenarios. Given the requirement for additional mitigation measures, further assessment will be undertaken at the detailed design stage to control noise emissions in order to meet the appropriate noise limits at nearby NSR.
 
Construction and operational noise management measures provided in this
8.8.5
chapter, including noise monitoring of the Proposed Development, are proposed to
be secured by a Requirement of the draft DCO (**Application Document Ref. 2.1**).
These proposals would be agreed with BDC, in consultation with WLDC in relation to operational noise, including the definition of agreed noise limits at the nearest NSR or other locations as agreed with the authorities.

8.9
Summary of Likely Significant Residual Effects 
 
A summary of the residual effects, assuming the implementation of appropriate
8.9.1
mitigation to reduce noise and vibration during construction, operation and
decommissioning phases, is presented in **Table 8-39** below.

| Mitigation                         | Residual Effect   |
|------------------------------------|-------------------|
| (unmitigated)                      |                   |
| Negligible adverse at              |                   |
| the nearest residential            |                   |
| NSR (not significant).             |                   |
| Noise impact during                |                   |
| construction of the                |                   |
| Proposed                           |                   |
| Development                        |                   |
| (daytime).                         |                   |
| Short                              |                   |
| -                                  |                   |
| term                               |                   |
| (3                                 |                   |
| -                                  |                   |
| 4 years)                           |                   |
| Negligible (daytime) not           |                   |
| significant.                       |                   |
| Further detailed assessment and    |                   |
| preparation of a construction      |                   |
| noise control scheme (including    |                   |
| agreed noise limits) once          |                   |
| contractor appointed in            |                   |
| accordance with a Requirement      |                   |
| of the draft DCO (                 | Application       |
| Document Ref. 2.1                  | ).                |
| Short                              |                   |
| -                                  |                   |
| term                               |                   |
| (3                                 |                   |
| -                                  |                   |
| 4 years)                           |                   |
| Minor adverse                      |                   |
| (evenings/weekends) and            |                   |
| not significant.                   |                   |
| Minor adverse                      |                   |
| (evenings/weekends)                |                   |
| and not significant.               |                   |
| Further detailed assessment and    |                   |
| preparation of a construction      |                   |
| noise control scheme (including    |                   |
| agreed noise limits) once          |                   |
| contractor appointed in            |                   |
| accordance with a Requirement      |                   |
| of the draft DCO (                 | Application       |
| Document Ref. 2.1                  | ).                |
| Noise impact during                |                   |
| construction of the                |                   |
| Proposed                           |                   |
| Development                        |                   |
| (evenings/weekends),               |                   |
| where works are                    |                   |
| required, are                      |                   |
| proposed to be                     |                   |
| secured by a                       |                   |
| Requirement of the                 |                   |
| draft DCO                          |                   |
| (                                  | Application       |
| Document Ref. 2.1                  | ).                |
| Minor adverse (night               |                   |
| -                                  |                   |
| time) and not                      |                   |
| significant.                       |                   |
| Short                              |                   |
| -                                  |                   |
| term                               |                   |
| (3                                 |                   |
| -                                  |                   |
| 4 years)                           |                   |
| Moderate adverse (night            |                   |
| -                                  |                   |
| time) and significant              |                   |
| Proposals would be put in place    |                   |
| to control construction activities |                   |
| at night                           |                   |
| -                                  |                   |
| time so as not to exceed           |                   |
| the SOAEL or relevant noise        |                   |
| Noise impact during                |                   |
| construction of the                |                   |
| Proposed                           |                   |
| Development (night                 |                   |
| -                                  |                   |
| Mitigation                       | Residual Effect           |
|----------------------------------|---------------------------|
| (unmitigated)                    |                           |
| limit to be agreed with BDC.  A  |                           |
| Requirement of the draft DCO is  |                           |
| proposed to secure this          |                           |
| (                                | Application Document Ref  |
| 2.1                              | ).                        |
| time), where works               |                           |
| are required, is                 |                           |
| proposed to be                   |                           |
| secured by a                     |                           |
| Requirement of the               |                           |
| draft DCO                        |                           |
| (                                | Application               |
| Document Ref 2.1                 | ).                        |
| Negligible adverse (not          |                           |
| significant)                     |                           |
| Noise impacts due to             |                           |
| construction traffic on          |                           |
| public highways.                 |                           |
| Short                            |                           |
| -                                |                           |
| term                             |                           |
| (3                               |                           |
| -                                |                           |
| 4 years)                         |                           |
| No change or negligible          |                           |
| adverse (not significant)        |                           |
| during 'worst                    |                           |
| -                                |                           |
| case' period                     |                           |
| of construction traffic.         |                           |
| No further mitigation considered |                           |
| necessary, unless number of      |                           |
| proposed construction vehicle    |                           |
| movements changes.               |                           |
| Operation of the                 |                           |
| Proposed                         |                           |
| Development.                     |                           |
| Negligible/ minor                |                           |
| adverse (not                     |                           |
| significant)                     |                           |
| Application of practical sound   |                           |
| mitigation to the turbine        |                           |
| (enclosure, inlets and exhaust), |                           |
| the cooling equipment and the    |                           |
| transformers during the detailed |                           |
| design will control sound        |                           |
| emissions to result in a low or  |                           |
| very low magnitude of impact.    |                           |
| Long                             |                           |
| -                                |                           |
| term                             | Based on the worst        |
| -                                |                           |
| case                             |                           |
| assessment of up to five         |                           |
| OCGT units without               |                           |
| additional mitigation, the       |                           |
| impact magnitude ranges          |                           |
| from low to high at the          |                           |
| seven receptor locations.        |                           |
| This would result in effects     |                           |
| between minor (not               |                           |
| significant) to major            |                           |
| adverse (significant) if         |                           |
| noise is not controlled          |                           |
| further.                         |                           |
| As design progresses,            |                           |
| preparation of operational noise |                           |
| control proposals (including     |                           |
| agreed noise limits) will be     |                           |
| undertaken in accordance with a  |                           |
| Requirement of the draft DCO     |                           |
| (                                | Application Document Ref. |
| Mitigation                      | Residual Effect                                                                                                        | Predicted Impact   |
|---------------------------------|------------------------------------------------------------------------------------------------------------------------|--------------------|
| (unmitigated)                   |                                                                                                                        |                    |
| 2.1                             | ).                                                                                                                     |                    |
| Noise impacts during            |                                                                                                                        |                    |
| decommissioning of              |                                                                                                                        |                    |
| the Proposed                    |                                                                                                                        |                    |
| Development.                    |                                                                                                                        |                    |
| Further assessment              |                                                                                                                        |                    |
| would need to confirm           |                                                                                                                        |                    |
| the potential level of          |                                                                                                                        |                    |
| effect at NSR, although         |                                                                                                                        |                    |
| they may be expected            |                                                                                                                        |                    |
| to be similar to those          |                                                                                                                        |                    |
| during construction.            |                                                                                                                        |                    |
| Short                           |                                                                                                                        |                    |
| -                               |                                                                                                                        |                    |
| term                            | As detailed above for                                                                                                  |                    |
| construction effects.           |                                                                                                                        |                    |
| Further detailed assessment and |                                                                                                                        |                    |
| Decommissioning Environmental   |                                                                                                                        |                    |
| Management Plan (DEMP),         |                                                                                                                        |                    |
| particularly regarding working  |                                                                                                                        |                    |
| outside of daytime working      |                                                                                                                        |                    |
| hours, in accordance with a     |                                                                                                                        |                    |
| Requirement of the draft DCO    |                                                                                                                        |                    |
| (                               | Application Document Ref.                                                                                              |                    |
| 2.1                             | ).                                                                                                                     |                    |
|                                 | The residual noise and vibration effects from the Proposed Development are therefore considered to be not significant. | 8.9.2              |

## 8.10 References

Ref 8-1
Her Majesty's Stationary Office (1990) Environmental Protection Act
1990.
Ref 8-2
Her Majesty's Stationary Office (1974) *Control of Pollution Act 1974*.
Ref 8-3
Her Majesty's Stationary Office (2016) Environmental Permitting
(England and Wales) Regulations 2016.
Ref 8-4
Environment Agency (2002a) Integrated Pollution Prevention and 
Control (IPPC) H3 document Horizontal Guidance for Noise Part 2 - 
Noise assessment and Control.
Ref 8-5
Environment Agency (2002b) Integrated Pollution Prevention and 
Control (IPPC) H3 document Horizontal Guidance for Noise Part 1 - 
Regulation and Permitting.
Ref 8-6
Department of Energy & Climate Change (2011) Overarching National
Policy Statement for Energy EN -1.
Ref 8-7
Department of Energy & Climate Change (2011) National Policy
Statement for Fossil Fuel Electricity Generating infrastructure EN -2.
Ref 8-8
Ministry of Housing, Communities and Local Government (2019)
National Planning Policy Framework.
Ref 8-9
Office of the Deputy Prime Minister (1994) Planning Policy Guidance
(PPG) 24 - Planning and Noise.
Ref 8-10 
Department for Environment, Food & Rural Affairs (2010) Noise Policy
Statement for England (NPSE).
Ref 8-11 
Department for Communities and Local Government (DCLG) (2014)
Planning Practice Guidance.
Ref 8-12 
Bassetlaw District Council (2011) The Bassetlaw District Council –
Local Development Framework.
Ref 8-13 
Bassetlaw District Council (2019) The Bassetlaw District Council –
Draft Local Plan.
Ref 8-14 
West Lindsey District Council (2017) Central Lincolnshire Local Plan.
Ref 8-15 
British Standards Institute (2003) BS 7445-1 - Description and
measurement of environmental noise. Guide to quantities and procedures.
Ref 8-16 
British Standards Institute (1991) BS 7445-2 - Description and
measurement of environmental noise. Guide to the acquisition of data pertinent to land use.
Ref 8-17 
British Standards Institute (2014) BS 5228-1:2009+A1:2014 - Code of
practice for noise and vibration control on construction and open sites. Part 1: Noise.
Ref 8-18 
British Standards Institute (2014) BS 5228-2:2009+A1:2014 - 'Code
of practice for Noise and Vibration control on construction and open sites. Part 2:Vibration.'
Ref 8-19 
British Standards Institute (2008) BS 6472-1 - Guide to evaluation of
human exposure to vibration in buildings. Vibration sources other than blasting.
Ref 8-20 
British Standards Institute (1993) BS 7385-2 - Evaluation and
measurement for vibration in buildings. Guide to damage levels from groundborne vibration.
Ref 8-21 
British Standards Institute (2014) BS 4142 - Methods for rating and
assessing industrial and commercial sound.
Ref 8-22 
World Health Organisation (1999) Guidelines for Community Noise.
Ref 8-23 
World Health Organisation (2009) Night Noise Guidelines for Europe.
Ref 8-24 
Department of Transport/Welsh Office (1998) Calculation of Road
Traffic Noise (CRTN).
Ref 8-25 
Highways Agency (2011) Design Manual for Road and Bridges
Volume 11 Section 3 Part 7 HD213/11 (Revision 1) Traffic Noise and Vibration.
Ref 8-26 
International Standards Organisation (1996) ISO 9613-2 - Attenuation
of Sound during Propagation Outdoors, Part 2: General Method of Calculation.
Ref 8-27 
International Standards Organisation (2010)
ISO 4866:2010 –
Vibration of Fixed Structures - Guidelines for the Measurement of Vibrations and Evaluation of Their Effects on Structures.
Ref 8-28
AECOM (2017) *Preliminary Environmental Information (PEI) Report*, 
September 2017.
Ref 8-29
Spectrum Acoustic Consultants (2016) West Burton CCGT Power 
Station Noise Impact Assessment of Proposed 49MW Enhanced Frequency Response Unit.