All-in-one solution for residential heating

Keep the technical equipment outside. Only cosiness stays inside.

The new Daikin Altherma Monobloc Our promise...

... is to ensure that customers can depend on Daikin for the ultimate in comfort, so that they are free to focus on their own working and home lives.

We promise to dedicate ourselves to technological excellence, a design focus and the highest quality standards so that our customers can trust and rely on the comfort we deliver.

Our promise to the planet is absolute. Our products are at the forefront of low energy-usage and we will innovate to further reduce the environmental impact of our heating solutions.

From residential to collective heating solutions, from renovation to new build, we commit ourselves to answer all our customers’ needs.

Our heat pump DNA combined with our in-house combustion developments positions Daikin as a leader, for now and the decades to come. Contents

Introduction 2 Daikin Altherma low temperature monobloc 4 E(B/D)LQ-CV3 6 E(B/D)LQ011-016CV3/CW1 7 E(B/D)LQ011-016C3V3/C3W1 8 Options 9 Thermal stores and tanks 10 EKHWP-B/EKHWP-PB 12 EKHWS(U)-D 13 Always in control 14 Daikin Online Controller 14 EKRUCBL 15 EKRT1/EKRTWA 15 Supporting tools 18 Heating Solutions Navigator 19 Stand By Me 19 The reversible air-to-water heat pump monobloc system is the ideal system for users that have limited installation space inside. Delivering cutting-edge performance within the market’s most compact monobloc outdoor unit, Daikin Altherma low temperature monobloc offers heating and cooling, with an optional connection to provide domestic hot water.

A simple solution

The monobloc system combines all the features of heating and cooling (with optional domestic hot water) into one unit.

- Quiet and space-saving design that’s easy to commission and install
- All hydraulic components are combined into one outdoor unit
- Reliable operation is guaranteed, even with outdoor temperatures as low as -25°C
- Combine with an ECH₂O thermal store to provide thermal support
- Combine with a stainless steel tank for domestic hot water

High performance

- Improved seasonal efficiency ErP label up to A++
- High capacity at low ambient temperatures
- Connection to new stainless steel DHW tank (EKHWS(U)-D) with improved energy efficiency label B

Easy installation

- Sealed refrigerant means there is no need for refrigerant handling or F-gas qualifications
- Key hydraulic parts reduce the risk of installation errors and need for external parts such as expansion vessel, pump or isolation valves
- Fewer components lower the installation time and help maximise profits on the job

Year-round reliability

- Delivers higher heating capacity at low ambient temperatures
- Flow temperatures up to 55°C, perfect for new build applications using UFH
- Reliable operation is guaranteed, even with outdoor temperatures as low as -25°C
- Equipped with optional backup heater

Easy connection

- The LAN adapter allows to control the unit via the heating app The 5-7 kW range of Daikin Altherma monobloc

- Back-up heater less models

- Separate indoor wiring centre (control box)

- Separate back-up heater kit

The 11-16 kW range of Daikin Altherma monobloc

- Smaller casing
- Back-up heater less models and models with 3V integrated back-up heater for maximum installation flexibility
- 1 ph and 3 ph models
- Reversible and heating only models
- LAN Adapter connection
- A++ heating energy label (from G to A++)

* 36% compared to current monobloc Daikin Altherma low temperature monobloc

Reversible air to water monobloc system, ideal when indoor space is limited

› Compact reversible monobloc for space heating & cooling with optional domestic hot water › Compact heating only monobloc for space heating with optional domestic hot water › Fuss-free installation: only water connections required › Reliable operation even when -25°C outside thanks to frost protection features such as free hanging coil › COP up to 5

______________________________________________________________________

**Single Unit**

| EBLQ/EDLQ | 05CV3 | 07CV3 | 05CV3 | 07CV3 | |-----------|-------|-------|-------|-------| | **Space heating** | | | | | | Average climate | General | ηs (Seasonal space heating efficiency) | % | 125 | | water outlet | 35°C | | | | | SCOP | 3.20 | 3.22 | 3.20 | 3.22 | | Seasonal space heating eff. class | A++ | A++ | A++ | A++ | | Average climate | General | ηs (Seasonal space heating efficiency) | % | 172 | | water outlet | 35°C | | | | | SCOP | 4.39 | 4.14 | 4.39 | 4.14 | | Seasonal space heating eff. class | A++ | A++ | A++ | A++ | | **Heating capacity** | Nom. kW | 4.40(1) / 4.03(2) | 7.00(1) / 6.90(2) | 4.40(1) / 4.03(2) | 7.00(1) / 6.90(2) | | **Cooling capacity** | Nom. kW | 3.88(1) / 3.99(2) | 5.20(1) / 5.15(2) | - | - | | **Power input** | Cooling Nom. kW | 0.950(1) / 1.93(2) | 1.37(1) / 2.69(2) | - | - | | Heating Nom. kW | 0.680(1) / 1.13(2) | 1.55(1) / 2.45(2) | 0.880(1) / 1.13(2) | 1.55(1) / 2.02(2) | | **COP** | 5.00(1) / 3.58(2) | 4.52(1) / 3.42(2) | 5.00(1) / 3.58(2) | 4.52(1) / 3.42(2) | | **EER** | 4.07(1) / 2.07(2) | 3.80(1) / 2.10(2) | - | - | | **Dimensions** | Unit HeightxWidthxDepth mm | 735x1,090x350 | | | | **Weight** | Unit kg | 76.0 | 80.0 | 76.0 | 80.0 | | **Operation range** | Heating Water side Min.—Max. °C | 15 ~55.0 | | | | Cooling Ambient Min.—Max. °CDB | 10.0~42.0 | - | - | - | | Water side Min.—Max. °C | 5.00~22.0 | - | - | - | | Domestic hot water Ambient Min.—Max. °CDB | -25.0~35.0 | - | - | - | | Water side Min.—Max. °C | 25~80 | - | - | - | | **Refrigerant** | Type | R-410A | | | | GWP | 2,088 | | | | | **Charge** | kg | 1.30 | 1.45 | 1.30 | 1.45 | | **Charge TCO2Eq** | 2.714 | 3.027 | 2.714 | 3.027 | | **Control** | Expansion valve (electronic type) | | | | | **Sound power level** | Heating Nom. dBA | 61 | 62 | 61 | 62 | | Cooling Nom. dBA | 63.0 | - | - | - | | **Sound pressure level** | Heating Nom. dBA | 48 | 49 | 48 | 49 | | Cooling Nom. dBA | 48 | 50 | - | - | | **Wiring centre** | EKCB07CV3 | EK2CB07CV3 | | | | **Casing** | Colour | White | | | | Material | Precoated sheet metal | | | | | **Dimensions** | Unit HeightxWidthxDepth mm | 360x340x970 | | | | **Weight** | Unit kg | 4.00 | | | | **Back-up heater kit** | EKMBUHC3V3 | EKMBUHC9W1 | | | | **Casing** | Colour | White | | | | Material | Precoated sheet metal | | | | | **Dimensions** | Unit HeightxWidthxDepth mm | 560x250x210 | | | | **Weight** | Unit kg | 11.0 | 13.0 | | |

(1) Cooling Ta 35°C - LWE 18°C (DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 35°C (DT = 5°C) (2) Cooling Ta 35°C - LWE 7°C (DT = 5°C); heating Ta DB/WB 7°C/6°C - LWC 45°C (DT = 5°C) (3) Contains fluorinated greenhouse gases Daikin Altherma low temperature monobloc without back-up heater

Reversible air to water monobloc system, ideal when indoor space is limited

- Monobloc all-in-one concept including hydraulic parts
- Separate indoor wiring center (control box)
- LAN Adapter connection
- Possible to combine with domestic hot water
- Energy efficient heating only system based on air-to-water heat pump technology
- A++ heating energy label (from G to A++)

### Single Unit

| EBLQ/EDLQ | 011CV3 | 014CV3 | 016CV3 | 011CW1 | 014CW1 | 016CW1 | |-----------|--------|--------|--------|--------|--------|--------| | Space heating | | | | | | | | Average climate | General | General | General | General | General | General | | water outlet | water outlet | water outlet | water outlet | water outlet | water outlet | water outlet | | °C | °C | °C | °C | °C | °C | °C | | General ŋs (Seasonal space heating efficiency) | 120 | 123 | 119 | 120 | 123 | 119 | | SCOP | 3.09 | 3.16 | 3.06 | 3.09 | 3.16 | 3.06 | | Seasonal space heating eff. class | A+ | A+ | A+ | A+ | A+ | A+ | | Average climate | General | General | General | General | General | General | | water outlet | water outlet | water outlet | water outlet | water outlet | water outlet | water outlet | | °C | °C | °C | °C | °C | °C | °C | | General ŋs (Seasonal space heating efficiency) | 156 | 153 | 149 | 156 | 153 | 149 | | SCOP | 3.98 | 3.90 | 3.80 | 3.98 | 3.90 | 3.80 | | Seasonal space heating eff. class | A++ | A+ | A++ | A+ | A++ | A+ | | Heating capacity | Nom. kW | 11.2 (1) / 11.0 (2) | 14.5 (1) / 13.6 (2) | 16.0 (1) / 15.2 (2) | 11.2 (1) / 11.0 (2) | 14.5 (1) / 13.6 (2) | 16.0 (1) / 15.2 (2) | | Cooling capacity (only applicable to EBLQ) | Nom. kW | 12.4 (1) / 11.6 (2) | 12.8 (1) / 12.6 (2) | 13.9 (1) / 13.6 (2) | 12.4 (1) / 11.6 (2) | 12.8 (1) / 12.6 (2) | 13.9 (1) / 13.6 (2) | | Power input | Cooling Nom. kW | 3.18 (1) / 5.09 (2) | 3.16 (1) / 5.14 (2) | 3.56 (1) / 5.96 (2) | 3.18 (1) / 5.09 (2) | 3.16 (1) / 5.14 (2) | 3.56 (1) / 5.96 (2) | | Heating Nom. kW | 2.43 (1) / 3.30 (2) | 3.37 (1) / 4.30 (2) | 3.76 (1) / 4.66 (2) | 2.43 (1) / 3.30 (2) | 3.37 (1) / 4.30 (2) | 3.76 (1) / 4.66 (2) | | COP | 4.61 (1) / 3.55 (2) | 4.30 (1) / 3.32 (2) | 4.26 (1) / 3.26 (2) | 4.61 (1) / 3.55 (2) | 4.30 (1) / 3.32 (2) | 4.26 (1) / 3.26 (2) | | EER (only applicable to EBLQ) | 3.90 (1) / 2.28 (2) | 4.05 (1) / 2.45 (2) | 3.90 (1) / 2.28 (2) | 4.05 (1) / 2.45 (2) | 3.90 (1) / 2.28 (2) | 4.05 (1) / 2.45 (2) | | Dimensions | Unit HeightxWidthxDepth mm | 1,348x1,160x380 | 1,348x1,160x380 | 1,348x1,160x380 | 1,348x1,160x380 | 1,348x1,160x380 | 1,348x1,160x380 | | Weight | Unit kg | 151 | 154 | 151 | 154 | 151 | 154 | | Operation range (3) Heating | Ambient Min.—Max. °CWB | -25~35 | -25~35 | -25~35 | -25~35 | -25~35 | -25~35 | | Water side Min.—Max. °C | 25~35 | 25~35 | 25~35 | 25~35 | 25~35 | 25~35 | | Operation range (3) Cooling (only applicable to EBLQ) | Ambient Min.—Max. °CD | 10~46 | 10~46 | 10~46 | 10~46 | 10~46 | 10~46 | | Water side Min.—Max. °C | 5~22 | 5~22 | 5~22 | 5~22 | 5~22 | 5~22 | | Operation range (3) Domestic hot water (only applicable to EBLQ) | Ambient Min.—Max. °CDB | -25~35 | -25~35 | -25~35 | -25~35 | -25~35 | -25~35 | | Water side Min.—Max. °C | 25~80 | 25~80 | 25~80 | 25~80 | 25~80 | 25~80 | | Refrigerant | Type | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | | GWP | 2087.5 | 2087.5 | 2087.5 | 2087.5 | 2087.5 | 2087.5 | | Charge | kg | 3.40 | 3.40 | 3.40 | 3.40 | 3.40 | 3.40 | | Charge TCO2Eq | 710 | 710 | 710 | 710 | 710 | 710 | | Sound power level | Heating Nom. dBA | 64 | 66 | 64 | 66 | 64 | 66 | | Cooling Nom. dBA | 64 | 66 | 64 | 66 | 64 | 66 | | Sound pressure level | Heating Nom. dBA | 51 | 52 | 51 | 52 | 51 | 52 | | Cooling Nom. dBA | 50 | 52 | 50 | 52 | 50 | 52 | | Wiring centre | EKCB07CV3 | EK2CB07CV3 | EK2CB07CV3 | EK2CB07CV3 | EK2CB07CV3 | EK2CB07CV3 | | Casing Colour | White | White | White | White | White | White | | Material | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | | Dimensions | Unit HeightxWidthxDepth mm | 360x340x970 | 360x340x970 | 360x340x970 | 360x340x970 | 360x340x970 | 360x340x970 | | Weight | Unit kg | 4.00 | 4.00 | 4.00 | 4.00 | 4.00 | 4.00 | | Back-up heater kit | EKMBUHC3V3 | EKMBUHC9W1 | EKMBUHC9W1 | EKMBUHC9W1 | EKMBUHC9W1 | EKMBUHC9W1 | | Casing Colour | White | White | White | White | White | White | | Material | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | Precoated sheet metal | | Dimensions | Unit HeightxWidthxDepth mm | 560x250x210 | 560x250x210 | 560x250x210 | 560x250x210 | 560x250x210 | 560x250x210 | | Weight | Unit kg | 11.0 | 13.0 | 13.0 | 13.0 | 13.0 | 13.0 |

(1) Condition 1: cooling Ta 35°C - LWE 18°C (DT = 5°C), heating Ta DB/WB 7°C/6°C - LWC 35°C (DT = 5°C) | (2) Condition 2: cooling Ta 35°C - LWE 7°C (DT = 5°C), heating Ta DB/WB 7°C/6°C - LWC 45°C (DT = 5°C) | (3) Including back-up heater and/or booster heater, see details in databook. Daikin Altherma low temperature monobloc with integrated back-up heater

Reversible air to water monobloc system, ideal when indoor space is limited

- Monobloc all-in-one concept including hydraulic parts
- Separate indoor wiring center (control box)
- LAN Adapter connection
- Possible to combine with domestic hot water
- Energy efficient heating only system based on air-to-water heat pump technology
- A++ heating energy label (from G to A++)

______________________________________________________________________

### Single Unit

| Space heating | EBLQ/EDLQ | 011C3V3 | 014C3V3 | 016C3V3 | 011C3W1 | 014C3W1 | 016C3W1 | |---------------|-----------|---------|---------|---------|---------|---------|---------| | Average climate water outlet | General | 55°C | 120 | 123 | 119 | 120 | 123 | 119 | | | General | 3.09 | 3.16 | 3.06 | 3.09 | 3.16 | 3.06 | | Average climate water outlet | General | 156 | 153 | 149 | 156 | 153 | 149 | | | General | 3.98 | 3.90 | 3.80 | 3.98 | 3.90 | 3.80 | | Heating capacity | Nom. kW | 11.2 (1) / 11.0 (2) | 14.5 (1) / 13.6 (2) | 16.0 (1) / 15.2 (2) | 11.2 (1) / 11.0 (2) | 14.5 (1) / 13.6 (2) | 16.0 (1) / 15.2 (2) | | Cooling capacity | Nom. kW | 12.4 (1) / 11.6 (2) | 12.8 (1) / 12.6 (2) | 13.9 (1) / 13.6 (2) | 12.4 (1) / 11.6 (2) | 12.8 (1) / 12.6 (2) | 13.9 (1) / 13.6 (2) | | Power input | Cooling Nom. kW | 3.18 (1) / 3.09 (2) | 3.36 (1) / 3.14 (2) | 3.56 (1) / 3.56 (2) | 3.18 (1) / 3.09 (2) | 3.36 (1) / 3.14 (2) | 3.56 (1) / 3.56 (2) | | | Heating Nom. kW | 2.43 (1) / 3.10 (2) | 3.37 (1) / 4.10 (2) | 3.76 (1) / 4.66 (2) | 2.43 (1) / 3.10 (2) | 3.37 (1) / 4.10 (2) | 3.76 (1) / 4.66 (2) | | COP | 4.61 (1) / 3.55 (2) | 4.30 (1) / 3.32 (2) | 4.26 (1) / 3.26 (2) | 4.61 (1) / 3.55 (2) | 4.30 (1) / 3.32 (2) | 4.26 (1) / 3.26 (2) | | EER (only applicable to EBLQ) | 3.90 (1) / 2.28 (2) | 4.05 (1) / 2.45 (2) | 3.90 (1) / 2.28 (2) | 3.90 (1) / 2.28 (2) | 4.05 (1) / 2.45 (2) | 3.90 (1) / 2.28 (2) | | SEER (only applicable to EBLQ) | 3.85 | 3.89 | 3.90 | 3.85 | 3.89 | 3.90 |

### Dimensions

| Unit | Height x Width x Depth mm | 1,348 x 1,160 x 380 | |------|---------------------------|----------------------|

### Weight

| Unit | kg | 157 | 160 | |------|----|-----|-----|

### Operation range (3)

- Heating: Ambient Min.~Max. °CWB 25~35
- Water side Min.~Max. °C 25~55
- Cooling: Ambient Min.~Max. °CDB 10~46
- Water side Min.~Max. °C 5~22
- Domestic hot water: Ambient Min.~Max. °CDB 25~35
- Water side Min.~Max. °C 25~80

### Refrigerant

- Type: R-410A
- GWP: 2087.5
- Charge kg: 3.40
- Charge TCO2Eq: 7.10

### Sound power level

- Heating Nom. dBA: 64
- Cooling Nom. dBA: 64

### Sound pressure level

- Heating Nom. dBA: 51
- Cooling Nom. dBA: 50

### Wiring centre

- EKCB07C3V3
- EK2CB07C3V3

### Casing

- Colour: White
- Material: Precoated sheet metal

### Dimensions

| Unit | Height x Width x Depth mm | 360 x 340 x 970 | |------|---------------------------|------------------|

### Weight

| Unit | kg | 4.00 |

______________________________________________________________________

(1) Condition 1: cooling Ta 35°C - LWE 18°C (DT = 5°C), heating Ta DB/WB 7°C/6°C - LWC 35°C (DT = 5°C) | (2) Condition 2: cooling Ta 35°C - LWE 7°C (DT = 5°C), heating Ta DB/WB 7°C/6°C - LWC 45°C (DT = 5°C) | (3) Including back-up heater and/or booster heater, see details in databook. | Type | Material name | Daikin Altherma LT monobloc | Illustration | |-------------------------------|---------------|-----------------------------|--------------| | Controls | | 5-7 kW | 11-16 kW BUH-less | 11-16 kW with 3V BUH | | LAN adapter | BRP069A62 | • | • | • | | LAN adapter + PV solar connection | BRP069A61 | • | • | • | | Remote user interface (DE, FR, NL, IT) | EKRUCBL1 | • | • | • | | Remote user interface (EN, ES, EL, PT) | EKRUCBL3 | • | • | • | | Remote user interface (EN, SV, NO, FI) | EKRUCBL2 | • | • | • | | Remote user interface (EN, TR, PL, RO) | EKRUCBL4 | • | • | • | | Remote user interface (DE, CS, SL, SK) | EKRUCBL5 | • | • | • | | Remote user interface (EN, HR, HU, BG) | EKRUCBL6 | • | • | • | | Remote user interface (EN, DE, RU, DA) | EKRUCBL7 | • | • | • | | Simplified user interface | EKRUCBSB | • | • | • | | Room thermostat (wired) | EKRTWA | • | • | • | | Room thermostat (wireless) | EKRT1R | • | • | • | | Adapter | EKRP1HBAA | • | • | • | | Back-up heater | EKMBUHC3V3/C9W1 | • | • | • | | Bottom plate heater | EKBPHTH16A | • | • | • | | Drain | EKDK04 | • | • | • | | Remote sensor for OU | EKRSCA1 | • | • | • | | External sensor | EKRTETS | • | • | • | | Remote sensor for IU | KRC501-1 | • | • | • | | Wiring centre | EKCB07CAV3 | • | • | • | | Option box | EK2CB07CAV3 | • | • | • | | By pass | EKMBHBP1 | • | • | • | | Bizone | BZKA7V3 | • | • | • | | Others | EKPCCCAB3 | • | • | • | Thermal stores and tanks Hot water heating installation options

Why choose a thermal store or domestic hot water tank

Whether you only need hot water or you want to combine your hot water with solar systems, we offer you the best solutions to the highest levels of comfort, energy efficiency and reliability.

✅ Domestic hot water tanks

Stainless steel tanks

Comfort

› Available in 150, 180, 200, 250 and 300 litres in stainless steel EKHWS(U)-D

Efficiency

› High-quality insulation keeps heat loss to a minimum › Efficient temperature heating: from 10°C to 50°C in only 60 minutes › Available as an integrated solution or separate tank

Reliability

› At necessary intervals, the unit can heat up water up to 60°C to prevent the risk of bacteria growth The ECH₂O thermal store range

ECH₂O thermal store: additional hot water comfort

Combine your monobloc with a thermal store to achieve the ultimate comfort at home. › Fresh water principle: receive domestic hot water on demand while eliminating the risk of contamination and sedimentation › Optimal domestic hot water performance: the low temperature evolution enables high tapping performance › Fit for the future: possibility to integrate with renewable solar energy and other heat sources, e.g. fireplace › Lightweight and robust build of the unit combined with the cascade principle offers flexible installation options

Efficiency › Fit for the future: maximise renewable energy sources › Intelligent Heat Storage Management: ensures continuous heating during defrost mode, and uses stored heat for space heating › High-quality insulation keeps heat loss to a minimum

Reliability › Maintenance-free tank: no corrosion, anode, scale or lime deposits, and no water loss through the safety valve

Pressureless (drain-back) solar system › The solar collectors are only filled with water when sufficient heating is provided by the sun › The pumps in the control and pump unit switch on briefly and fill the collectors with storage tank water › After filling, water circulation is maintained by the remaining pump

Monthly energy consumption of an average detached house

- Utilisation of solar energy for domestic hot water and central heating
- Heat pump (environmental heat)
- Auxiliary energy (electricity)

## Thermal store

**Plastic domestic hot water tank with solar support**

- Tank designed for connection with pressurised thermal solar system
- Tank designed for connection with drainback thermal solar system
- Available in 300 and 500 liters
- Large hot water storage tank to provide domestic hot water at any time
- Heat loss is reduced to a minimum thanks to the high quality insulation
- Space heating support possible (500l tank only)

### Accessory EKHWP 300B 500B 300PB 500PB

| Casing | Colour | Material | |--------|--------|----------| | | Traffic white (RAL9016) / Dark grey (RAL7011) | Impact resistant polypropylene |

| Dimensions | Unit | Width mm | Depth mm | Height mm | Weight Unit | Empty kg | |------------|------|----------|----------|-----------|-------------|---------| | | | 595 | 615 | 1,650 | 58 | 82 | | | | 790 | 790 | 1,660 | 82 | 89 |

| Tank | Water volume l | Material | |------|----------------|----------| | | 294 | Polypropylene |

| Heat exchanger | Domestic hot water | Quantity | Tube material | Face area m² | Internal coil volume l | Operating pressure bar | Average specific thermal output W/K | |----------------|--------------------|----------|---------------|--------------|------------------------|------------------------|-----------------------------------| | | | 1 | Stainless steel (DIN 1.4404) | 5.600 | 271 | 6 | 2,790 | | | | | | 5.800 | 281 | | 2,825 | | | | | | 5.600 | 271 | | 2,790 | | | | | | 5.900 | 281 | | 2,825 |

| Charging | Quantity | Tube material | Face area m² | Internal coil volume l | Operating pressure bar | Average specific thermal output W/K | |----------|----------|---------------|--------------|------------------------|------------------------|-----------------------------------| | | 1 | Stainless steel (DIN 1.4404) | 3 | 13 | 3 | 1,300 | | | | | 4 | 18 | 3 | 1,800 | | | | | 3 | 13 | 3 | 1,300 | | | | | 4 | 18 | 3 | 1,800 |

| Pressurised solar heating | Average specific thermal output W/K | Quantity | Tube material | Face area m² | Internal coil volume l | Operating pressure bar | Average specific thermal output W/K | |---------------------------|-----------------------------------|----------|---------------|--------------|------------------------|------------------------|-----------------------------------| | | | 1 | Stainless steel (DIN 1.4404) | - | - | - | - | | | | | | - | - | - | - | | | | | | - | - | - | - | | | | | | - | - | - | - |

| Auxiliary solar heating | Average specific thermal output W/K | Quantity | Tube material | Face area m² | Internal coil volume l | Operating pressure bar | Average specific thermal output W/K | |-------------------------|-----------------------------------|----------|---------------|--------------|------------------------|------------------------|-----------------------------------| | | | 1 | Stainless steel (DIN 1.4404) | - | - | - | - | | | | | | - | - | - | - | | | | | | - | - | - | - | | | | | | - | - | - | - | Domestic hot water tank

Stainless steel domestic hot water tank

- Available in 150, 180, 200, 250 and 300l
- Energy efficiency class B
- Low standing losses (1.08 - 1.63 kWh/24h)
- Pre plumbed model (SU) for UK

| Accessory | EKHWS(U) | 150D3V3 | 180D3V3 | 200D3V3 | 250D3V3 | 300D3V3 | |--------------------|----------|---------|---------|---------|---------|---------| | Casing | Colour | Neutral white | Epoxy coated steel / Epoxy-coated mild steel | | Material | | | | | | | | Dimensions | Unit | Height | Tank | mm | 1,000 | 1,164 | 1,264 | 1,535 | 1,745 | | Weight | Unit | Empty | kg | 45 | 50 | 53 | 58 | 63 | | Tank | Water volume | I | 145 | 174 | 192 | 242 | 292 | | Material | Stainless steel (EN 1.4521) | | Maximum water temperature | °C | 75 | | Insulation Heat loss | kWh/24h | 1.1 | 1.2 | 1.3 | 1.4 | 1.6 | | Energy efficiency class | B | | | Standing heat loss | W | 45 | 50 | 55 | 60 | 68 | | Storage volume | I | 145 | 174 | 192 | 242 | 292 | | Heat exchanger | Domestic hot water | Quantity | 1 | | Tube material | Stainless steel (EN 1.4521) | | Face area | m² | 1.050 | 1.400 | 1.800 | | Internal coil volume | I | 4.9 | 6.5 | 8.2 | | Operating pressure | bar | 10 | | Booster heater | Capacity | kW | 3 | | Power supply | Phase/Frequency/Voltage | Hz/V | 1~/50/230 | Always in control

Daikin Online Controller

The Daikin Online Controller application can control and monitor the status of your heating system and allows you to:

Monitor › The status of your heating system › Your energy consumption graphs

Schedule › Schedule the set temperature and operation mode › with up to 6 actions per day for 7 days › Enable holiday mode › View in intuitive mode

Control \*\* › The operation mode and set temperature › Remotely control your system and domestic hot water

\*Control via the app › Room thermostat control for space heating and domestic hot water › Leaving water temperature control for domestic hot water › External control for domestic hot water

Daikin Online Heating Control

The Daikin Online Control Heating app is a multifaceted programme that allows customers to control and monitor the status of their heating system.

Main features › Equipped with GDPR (data protection) › Remote firmware update of LAN Adapter › Control over multiple unit locations **EKRUCBL**

**Control**

- Manage space heating, cooling, domestic hot water and among others, booster mode
- User-friendly remote control with contemporary design
- Easy to use with direct accessibility to all main functions

**Comfort**

- An additional user interface can include a room thermostat in the space to be heated
- Easy commissioning: intuitive interface for advanced menu settings

* only in combination with EKRTETS

______________________________________________________________________

**EKRTR1/EKRTWA**

**Control** The LCD screen of the room thermostat presents the necessary information regarding the setting of the Daikin Altherma system.

**Comfort** An external sensor (EKRTETS) can be placed between the underfloor heating and the floor, as an alternative to the wireless room thermostat.

**General features**

- Several languages possible depending on the model, including: English, German, Dutch, Spanish, Italian, French, Greek, Russian, etc.
- Set the temperature of the room based on measurements from the built-in or external sensor
- Off function (with integrated frost-protection function)
- Holiday function mode
- Comfort and reduced function modes
- Time (day and month)
- Programmable weekly timer with 2 user defined and 5 preset programmes, with up to 12 actions per day
- Keylock function
- Set limits: the installer can change the upper and lower limits
- Floor temperature protection

### EKRTWA/EKRTR

**Wired remote control for Heating**

| Dimensions | EKRTR | EKRTWA | |------------|-------|--------| | Unit | | 87/125/34 | | Thermostat | Height/Width/Depth mm | 87/125/34 | | Receiver | Height/Width/Depth mm | 170/50/28 | | Weight | g | 215 | | Thermostat | g | 210 | | Receiver | g | 125 | | Ambient temperature | Min./Max. °C | -20/60 | | Operation | Min./Max. °C | 0/50 | | Temperature setting range | Heating Min./Max. °C | 4/37 | | Cooling | Min./Max. °C | 4/37 | | Clock | Yes | | | Regulation function | Proportional band | | | Power supply | Voltage V | Battery powered 3x AA-LR6 (alkaline) | | Thermostat | Voltage V | - | | Receiver | Voltage V | 230 | | Frequency | Hz | 50 | | Phase | 1~ | - | | Connection | Type | Wired | | Thermostat | Wireless | - | | Receiver | Wired | - | | Maximum distance to receiver | Indoor m | approx. 30m | | Outdoor m | approx. 100m | - | | Control systems | Class of temperature control | IV | | Contribution to seasonal space heating efficiency | % | 2.0 | Supporting tools

Heating Solutions Navigator

HSN provides the best fit solution for your customers home:

› User-friendly interface showcases the wide array of Daikin Heating Solutions available › Estimation of the required heat load from a simple intuitive approach to a deeper detailed room-by-room calculation › Country specific elements are taken into account › Create custom made piping & wiring diagrams › Link to flue gas selection tool for gas based solutions › Set the configuration of your installation › Overview of all the options specifically for your installation › Quick link to the installation specific literature › Compare economic and ecological benefit of the Daikin solution against a conventional heating installation. › Storage of all your leads on you Stand By Me account › Easy conversion from lead to installation to invite your end user for extra after-sales services

Want to know more about our Heating Solutions Navigator?

› Have a look at our video on https://www.youtube.com/watch?v=RomRf4W6Ci8! Stand By Me, my climate of security

With your customer’s new Daikin installation and Stand By Me service programme, you can rest assured they are benefiting from the best comfort, energy efficiency, usability and service available on the market.

**After-sales services**

Stand By Me offers after-sales services such as warranty extensions and maintenance contracts:

- warranty extension on parts and/or labour
- starts on commissioning date

**Quick follow-up by Daikin service partners**

Daikin service partners are automatically linked with their customer after registration on [www.standbyme.daikin.eu](http://www.standbyme.daikin.eu).

A notification is sent when a customer purchases a maintenance contract.

Your customer is guaranteed:

- quick and reliable service
- complete installation logbook including registration documents, maintenance deadlines, repair reports etc.

**Key account portal**

The key account portal is the perfect solution for large accounts:

- keep track of all your installations
- project management
- remote metering (UK only)

› For more details about the Stand By Me services in your country, contact your local Daikin office.

**Business portal**

› Learn more about Daikin’s units on our extranet portal: [my.daikin.eu](http://my.daikin.eu) › Receive information in a matter of seconds using our powerful search tool › Customise search options to only see information that is relevant for you › Accessible via a mobile device or computer

**E-care app**

**NEW**

**All-in-one app for the dealer**

› Register your installation on Stand By Me via simple QR code scanning › Quick configuration of your heat pump in only 7 steps › Diagnosis of malfunction by QR code scanning and error code input

› Learn more about Daikin’s units on our extranet portal: [my.daikin.eu](http://my.daikin.eu) › Receive information in a matter of seconds using our powerful search tool › Customise search options to only see information that is relevant for you › Accessible via a mobile device or computer The present publication is drawn up by way of information only and does not constitute an offer binding upon Daikin Europe N.V. Daikin Europe N.V. has compiled the content of this publication to the best of its knowledge. No express or implied warranty is given for the completeness, accuracy, reliability or fitness for particular purpose of its content and the products and services presented therein. Specifications are subject to change without prior notice. Daikin Europe N.V. explicitly rejects any liability for any direct or indirect damage, in the broadest sense, arising from or related to the use and/or interpretation of this publication. All content is copyrighted by Daikin Europe N.V.