Hyundai Solar Module

Black-Black MG-Series

Poly-crystalline Type HiS-M230MG (BK) | HiS-M235MG (BK) | HiS-M240MG (BK)

Mono-crystalline Type HiS-S240MG (BK) | HiS-S245MG (BK) | HiS-S250MG (BK)

Mechanical Characteristics

| Dimensions | 983 mm (38.7") (W) × 1,645 mm (64.76") (L) × 35 mm (1.38") (H) | |------------------|------------------------------------------------------------------| | Weight | Approx. 19.0 kg (41.9 lbs) | | Solar cells | 60 cells in series (6 × 10 matrix) | | Output cables | 4 mm² (12AWG) cables with polarized weatherproof connectors, IEC certified (UL listed), Length 1.0 m (39.4") | | Junction box | IP65, weatherproof, IEC certified (UL listed) | | Bypass diodes | 3 bypass diodes to prevent power decrease by partial shade | | Construction | Front: High transmission low-iron tempered glass, 3.2 mm (0.126") Encapsulant: EVA Back Sheet: Weatherproof film (Black) | | Frame | Clear anodized aluminum alloy type 6063 (Black) |

High Quality

- IEC 61215 (Ed.2) and IEC 61730 by TÜV Rheinland
- UL listed (UL 1703), Class C Fire Rating
- Output power tolerance +3/-0 %
- ISO 9001:2000 and ISO 14001:2004 Certified
- Advanced Mechanical Test (5,400 Pa) Passed (IEC) / Mechanical Load Test (40 lbs/ft²) Passed (UL)

Fast and Inexpensive Mounting

- Delivered ready for connection
- Pre-confectioned cables
- IEC (UL) certified and weatherproof connectors
- Integrated bypass diodes

Limited Warranty

- 10 years for product defect
- 10 years for 90 % of warranted min. power
- 25 years for 80 % of warranted min. power

※ Important Notice on Warranty The warranties apply only to the PV modules with Hyundai Heavy Industries Co., Ltd’s logo (shown below) and product serial number on it. Electrical Characteristics

### Poly-crystalline Type

| Nominal output (Pmpp) | W | 230 | 235 | 240 | |-----------------------|---|-----|-----|-----| | Voltage at Pmax (Vmpp) | V | 30.1 | 30.3 | 30.5 | | Current at Pmax (Impp) | A | 7.7 | 7.8 | 7.9 | | Open circuit voltage (Voc) | V | 37.1 | 37.4 | 37.7 | | Short circuit current (Isc) | A | 8.2 | 8.3 | 8.3 | | Output tolerance | % | +3/-0 | | No. of cells & connections | pcs | 60 in series | | Cell type | - | 6" Poly-crystalline silicon | | Module efficiency | % | 14.2 | 14.5 | 14.8 | | Temperature coefficient of Pmpp | %/K | -0.43 | -0.43 | -0.43 | | Temperature coefficient of Voc | %/K | -0.32 | -0.32 | -0.32 | | Temperature coefficient of Isc | %/K | 0.048 | 0.048 | 0.048 |

※ All data at STC (Standard Test Conditions). Above data may be changed without prior notice.

### Mono-crystalline Type

| Nominal output (Pmpp) | W | 240 | 245 | 250 | |-----------------------|---|-----|-----|-----| | Voltage at Pmax (Vmpp) | V | 30.1 | 30.3 | 30.5 | | Current at Pmax (Impp) | A | 8.0 | 8.1 | 8.2 | | Open circuit voltage (Voc) | V | 37.3 | 37.4 | 37.5 | | Short circuit current (Isc) | A | 8.5 | 8.6 | 8.7 | | Output tolerance | % | +3/-0 | | No. of cells & connections | pcs | 60 in series | | Cell type | - | 6" Mono-crystalline silicon | | Module efficiency | % | 14.8 | 15.2 | 15.5 | | Temperature coefficient of Pmpp | %/K | -0.45 | -0.45 | -0.45 | | Temperature coefficient of Voc | %/K | -0.33 | -0.33 | -0.33 | | Temperature coefficient of Isc | %/K | 0.032 | 0.032 | 0.032 |

※ All data at STC (Standard Test Conditions). Above data may be changed without prior notice.

### Module Diagram

[unit: mm, inch]

### I-V Curves

| Nominal Operating Cell Temperature | 46°C ± 2 | | Operating Temperature | -40 - 85°C | | Maximum System Voltage | DC 1,000 V (IEC) DC 600 V (UL) | | Maximum Reverse Current | 15 A |

### Installation Safety Guide

- Only qualified personnel should install or perform maintenance.
- Be aware of dangerous high DC voltage.
- Do not damage or scratch the rear surface of the module.
- Do not handle or install modules when they are wet.