record(mil1553,"CTL_MIL_02/A") {
		field(DESC, "MIL1553 on CTL02 - A")
		field(NMAX, "32")
		field(SCAN, "Passive")
		field(PHAS, "0")}
record(mil1553,"CTL_MIL_02/B") {
		field(DESC, "MIL1553 on CTL02 - B")
		field(NMAX, "32")
		field(SCAN, "Passive")
		field(PHAS, "1")}
record(mil1553,"CTL_MIL_02/C") {
		field(DESC, "MIL1553 on CTL02 - C")
		field(NMAX, "32")
		field(SCAN, "Passive")
		field(PHAS, "2")}
record(mil1553,"CTL_MIL_02/D") {
		field(DESC, "MIL1553 on CTL02 - D")
		field(NMAX, "32")
		field(SCAN, "Passive")
		field(PHAS, "3")}
record(longout,"CTL_MIL_02/DBG") {
		field(DESC, "MIL1553 on CTL02, debug")
		field(DTYP, "vxWorks Variable")
		field(OUT, "#@drv1553Debug")
		field(OMSL, "supervisory")
		field(SCAN, "Passive")
		field(VAL, "0")}
record(vme,"CTL_VME_02/A") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "0")}
record(vme,"CTL_VME_02/B") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "1")}
record(vme,"CTL_VME_02/C") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "2")}
record(vme,"CTL_VME_02/D") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "3")}
record(vme,"CTL_VME_02/E") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "4")}
record(vme,"CTL_VME_02/F") {
		field(DESC, "VME on CTL02")
		field(SCAN, "Passive")
		field(NMAX, "100")
		field(PHAS, "5")}
record(ai,"CTL_PROC_02/CPU") {
		field(DESC, "CPU usage for CTL02")
		field(DTYP, "VX stats")
		field(SCAN, "I/O Intr")
		field(INP, "@cpu")
		field(HOPR, "100.0")
		field(HIHI, "90.0")
		field(HIGH, "60.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")}
record(ai,"CTL_PROC_02/FD") {
		field(DESC, "FD usage for CTL02")
		field(DTYP, "VX stats")
		field(SCAN, "I/O Intr")
		field(INP, "@fd")
		field(HOPR, "100.0")
		field(HIHI, "90.0")
		field(HIGH, "60.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")}
record(ai,"CTL_PROC_02/MEM") {
		field(DTYP, "VX stats")
		field(DESC, "Memory usage for CTL02")
		field(SCAN, "I/O Intr")
		field(INP, "@memory")
		field(HOPR, "100.0")
		field(HIHI, "90.0")
		field(HIGH, "60.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")}
record(ao,"CTL_PROC_02/CPUSCAN") {
		field(DESC, "CPU scan for CTL02")
		field(DTYP, "VX stats")
		field(OUT, "@cpuScanPeriod")
		field(VAL, "10.0")
		field(PINI, "YES")}
record(ao,"CTL_PROC_02/FDSCAN") {
		field(DESC, "FD scan for CTL02")
		field(DTYP, "VX stats")
		field(OUT, "@fdScanPeriod")
		field(VAL, "10.0")
		field(PINI, "YES")}
record(ao,"CTL_PROC_02/MEMSCAN") {
		field(DESC, "Memory scan for CTL02")
		field(DTYP, "VX stats")
		field(OUT, "@memoryScanPeriod")
		field(VAL, "10.0")
		field(PINI, "YES")}
record(rm,"FPD_RM_02-01") {
		field(DESC, "Rack monitor on FPD_02-01")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R1")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-01/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-02") {
		field(DESC, "Rack monitor on FPD_02-02")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R2")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-02/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(rm,"FPD_RM_02-03") {
		field(DESC, "Rack monitor on FPD_02-03")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R3")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-03/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-04") {
		field(DESC, "Rack monitor on FPD_02-04")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R4")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-04/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(rm,"FPD_RM_02-05") {
		field(DESC, "Rack monitor on FPD_02-05")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R5")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-05/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-06") {
		field(DESC, "Rack monitor on FPD_02-06")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C0 R6")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-06/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(rm,"FPD_RM_02-11") {
		field(DESC, "Rack monitor on FPD_02-11")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R1")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-11/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-12") {
		field(DESC, "Rack monitor on FPD_02-12")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R2")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-12/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(rm,"FPD_RM_02-13") {
		field(DESC, "Rack monitor on FPD_02-13")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R3")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-13/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-14") {
		field(DESC, "Rack monitor on FPD_02-14")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R4")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-14/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(rm,"FPD_RM_02-15") {
		field(DESC, "Rack monitor on FPD_02-15")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R5")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-15/FO")
		field(BWC0, "1")
		field(BMASK, "0x08")}
record(rm,"FPD_RM_02-16") {
		field(DESC, "Rack monitor on FPD_02-16")
		field(DTYP, "Rack Monitor")
		field(INP, "#@C1 R6")
		field(SCAN, "1 second")
		field(PHAS, "1")
		field(FLNK, "FPD_RMI_02-16/FO")
		field(BWC0, "1")
		field(BMASK, "0x09")}
record(fanout,"FPD_RMI_02-01/FO") {
		field(DESC, "FPD, 02-01 RMI Fanout, A1")
		field(SELM, "All")
		field(LNK01, "FPD_RM_TNA1_02-01/UP_POS")
		field(LNK02, "FPD_RM_TNA1_02-01/DN_POS")
		field(LNK03, "FPD_RM_TNA1_02-01/IN_POS")
		field(LNK04, "FPD_RM_TNA1_02-01/OUT_POS")}
record(ai,"FPD_RM_TNA1_02-01/UP_POS") {
		field(DESC, "FPD, Pot position in A1 UP")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-01.AD32 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA1_02-01/DN_POS") {
		field(DESC, "FPD, Pot position in A1 DOWN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-01.AD33 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA1_02-01/IN_POS") {
		field(DESC, "FPD, Pot position in A1 IN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-01.AD34 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA1_02-01/OUT_POS") {
		field(DESC, "FPD, Pot position in A1 OUT")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-01.AD35 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(fanout,"FPD_RMI_02-01/FO") {
		field(DESC, "FPD, 02-01 RMI Fanout, A1")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-01/BIN03")}
record(mbbiDirect,"FPD_RMI_02-01/BIN03") {
		field(DESC, "FPD, 02-01 RMI BIN03 array, A1")
		field(INP, "FPD_RM_02-01.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-01_BIN03/FO")}
record(fanout,"FPD_RMI_02-02/FO") {
		field(DESC, "FPD, 02-02 RMI Fanout, A1")
		field(SELM, "All")
		field(LNK01, "FPD_RMI_02-02/BIN00")
		field(LNK02, "FPD_RMI_02-02/BIN03")}
record(mbbiDirect,"FPD_RMI_02-02/BIN00") {
		field(DESC, "FPD, 02-02 RMI BIN00 array, A1")
		field(INP, "FPD_RM_02-02.BIN00 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-02_BIN00/FO")}
record(mbbiDirect,"FPD_RMI_02-02/BIN03") {
		field(DESC, "FPD, 02-02 RMI BIN03 array, A1")
		field(INP, "FPD_RM_02-02.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-02_BIN03/FO")}
record(fanout64,"FPD_RMI_02-02_BIN00/FO") {
		field(DESC, "FPD, 02-02 BIN00 Alarm Fanout, A1")
		field(LNK01, "FPD_RM_TNA1_02-02/AL_SMO")}
record(bi,"FPD_RM_TNA1_02-02/AL_SMO") {
		field(DESC, "FPD, A1 Smoke Alarm")
		field(INP, "FPD_RMI_02-02/BIN00.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-01_BIN03/FO") {
		field(DESC, "FPD, 02-01 BIN03 Alarm Fanout, A1")
		field(LNK01, "FPD_RM_TNA1_02-01/UP_AL_CBL")
		field(LNK02, "FPD_RM_TNA1_02-01/UP_AL_MEC")
		field(LNK03, "FPD_RM_TNA1_02-01/UP_AL_DRV")
		field(LNK04, "FPD_RM_TNA1_02-01/DN_AL_CBL")
		field(LNK05, "FPD_RM_TNA1_02-01/DN_AL_MEC")
		field(LNK06, "FPD_RM_TNA1_02-01/DN_AL_DRV")}
record(bi,"FPD_RM_TNA1_02-01/UP_AL_CBL") {
		field(DESC, "FPD, A1 UP Cable Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-01/UP_AL_MEC") {
		field(DESC, "FPD, A1 UP Mechanical Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-01/UP_AL_DRV") {
		field(DESC, "FPD, A1 UP Driver Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-01/DN_AL_CBL") {
		field(DESC, "FPD, A1 DOWN Cable Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-01/DN_AL_MEC") {
		field(DESC, "FPD, A1 DOWN Mechanical Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-01/DN_AL_DRV") {
		field(DESC, "FPD, A1 DOWN Driver Alarm")
		field(INP, "FPD_RMI_02-01/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-02_BIN03/FO") {
		field(DESC, "FPD, 02-02 BIN03 Alarm Fanout, A1")
		field(LNK01, "FPD_RM_TNA1_02-02/IN_AL_CBL")
		field(LNK02, "FPD_RM_TNA1_02-02/IN_AL_MEC")
		field(LNK03, "FPD_RM_TNA1_02-02/IN_AL_DRV")
		field(LNK04, "FPD_RM_TNA1_02-02/OUT_AL_CBL")
		field(LNK05, "FPD_RM_TNA1_02-02/OUT_AL_MEC")
		field(LNK06, "FPD_RM_TNA1_02-02/OUT_AL_DRV")}
record(bi,"FPD_RM_TNA1_02-02/IN_AL_CBL") {
		field(DESC, "FPD, A1 IN Cable Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-02/IN_AL_MEC") {
		field(DESC, "FPD, A1 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-02/IN_AL_DRV") {
		field(DESC, "FPD, A1 IN Driver Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-02/OUT_AL_CBL") {
		field(DESC, "FPD, A1 OUT Cable Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-02/OUT_AL_MEC") {
		field(DESC, "FPD, A1 OUT Mechanical Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA1_02-02/OUT_AL_DRV") {
		field(DESC, "FPD, A1 OUT Driver Alarm")
		field(INP, "FPD_RMI_02-02/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout,"FPD_RMI_02-03/FO") {
		field(DESC, "FPD, 02-03 RMI Fanout, A2")
		field(SELM, "All")
		field(LNK01, "FPD_RM_TNA2_02-03/UP_POS")
		field(LNK02, "FPD_RM_TNA2_02-03/DN_POS")
		field(LNK03, "FPD_RM_TNA2_02-03/IN_POS")
		field(LNK04, "FPD_RM_TNA2_02-03/OUT_POS")}
record(ai,"FPD_RM_TNA2_02-03/UP_POS") {
		field(DESC, "FPD, Pot position in A2 UP")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-03.AD32 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA2_02-03/DN_POS") {
		field(DESC, "FPD, Pot position in A2 DOWN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-03.AD33 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA2_02-03/IN_POS") {
		field(DESC, "FPD, Pot position in A2 IN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-03.AD34 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNA2_02-03/OUT_POS") {
		field(DESC, "FPD, Pot position in A2 OUT")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-03.AD35 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(fanout,"FPD_RMI_02-03/FO") {
		field(DESC, "FPD, 02-03 RMI Fanout, A2")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-03/BIN03")}
record(mbbiDirect,"FPD_RMI_02-03/BIN03") {
		field(DESC, "FPD, 02-03 RMI BIN03 array, A2")
		field(INP, "FPD_RM_02-03.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-03_BIN03/FO")}
record(fanout,"FPD_RMI_02-04/FO") {
		field(DESC, "FPD, 02-04 RMI Fanout, A2")
		field(SELM, "All")
		field(LNK01, "FPD_RMI_02-04/BIN00")
		field(LNK02, "FPD_RMI_02-04/BIN03")}
record(mbbiDirect,"FPD_RMI_02-04/BIN00") {
		field(DESC, "FPD, 02-04 RMI BIN00 array, A2")
		field(INP, "FPD_RM_02-04.BIN00 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-04_BIN00/FO")}
record(mbbiDirect,"FPD_RMI_02-04/BIN03") {
		field(DESC, "FPD, 02-04 RMI BIN03 array, A2")
		field(INP, "FPD_RM_02-04.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-04_BIN03/FO")}
record(fanout64,"FPD_RMI_02-04_BIN00/FO") {
		field(DESC, "FPD, 02-04 BIN00 Alarm Fanout, A2")
		field(LNK01, "FPD_RM_TNA2_02-04/AL_SMO")}
record(bi,"FPD_RM_TNA2_02-04/AL_SMO") {
		field(DESC, "FPD, A2 Smoke Alarm")
		field(INP, "FPD_RMI_02-04/BIN00.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-03_BIN03/FO") {
		field(DESC, "FPD, 02-03 BIN03 Alarm Fanout, A2")
		field(LNK01, "FPD_RM_TNA2_02-03/UP_AL_CBL")
		field(LNK02, "FPD_RM_TNA2_02-03/UP_AL_MEC")
		field(LNK03, "FPD_RM_TNA2_02-03/UP_AL_DRV")
		field(LNK04, "FPD_RM_TNA2_02-03/DN_AL_CBL")
		field(LNK05, "FPD_RM_TNA2_02-03/DN_AL_MEC")
		field(LNK06, "FPD_RM_TNA2_02-03/DN_AL_DRV")}
record(bi,"FPD_RM_TNA2_02-03/UP_AL_CBL") {
		field(DESC, "FPD, A2 UP Cable Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-03/UP_AL_MEC") {
		field(DESC, "FPD, A2 UP Mechanical Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-03/UP_AL_DRV") {
		field(DESC, "FPD, A2 UP Driver Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-03/DN_AL_CBL") {
		field(DESC, "FPD, A2 DOWN Cable Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-03/DN_AL_MEC") {
		field(DESC, "FPD, A2 DOWN Mechanical Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-03/DN_AL_DRV") {
		field(DESC, "FPD, A2 DOWN Driver Alarm")
		field(INP, "FPD_RMI_02-03/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-04_BIN03/FO") {
		field(DESC, "FPD, 02-04 BIN03 Alarm Fanout, A2")
		field(LNK01, "FPD_RM_TNA2_02-04/IN_AL_CBL")
		field(LNK02, "FPD_RM_TNA2_02-04/IN_AL_MEC")
		field(LNK03, "FPD_RM_TNA2_02-04/IN_AL_DRV")
		field(LNK04, "FPD_RM_TNA2_02-04/OUT_AL_CBL")
		field(LNK05, "FPD_RM_TNA2_02-04/OUT_AL_MEC")
		field(LNK06, "FPD_RM_TNA2_02-04/OUT_AL_DRV")}
record(bi,"FPD_RM_TNA2_02-04/IN_AL_CBL") {
		field(DESC, "FPD, A2 IN Cable Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-04/IN_AL_MEC") {
		field(DESC, "FPD, A2 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-04/IN_AL_DRV") {
		field(DESC, "FPD, A2 IN Driver Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-04/OUT_AL_CBL") {
		field(DESC, "FPD, A2 OUT Cable Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-04/OUT_AL_MEC") {
		field(DESC, "FPD, A2 OUT Mechanical Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNA2_02-04/OUT_AL_DRV") {
		field(DESC, "FPD, A2 OUT Driver Alarm")
		field(INP, "FPD_RMI_02-04/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout,"FPD_RMI_02-11/FO") {
		field(DESC, "FPD, 02-11 RMI Fanout, P1")
		field(SELM, "All")
		field(LNK01, "FPD_RM_TNP1_02-11/UP_POS")
		field(LNK02, "FPD_RM_TNP1_02-11/DN_POS")
		field(LNK03, "FPD_RM_TNP1_02-11/IN_POS")
		field(LNK04, "FPD_RM_TNP1_02-11/OUT_POS")}
record(ai,"FPD_RM_TNP1_02-11/UP_POS") {
		field(DESC, "FPD, Pot position in P1 UP")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-11.AD32 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP1_02-11/DN_POS") {
		field(DESC, "FPD, Pot position in P1 DOWN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-11.AD33 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP1_02-11/IN_POS") {
		field(DESC, "FPD, Pot position in P1 IN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-11.AD34 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP1_02-11/OUT_POS") {
		field(DESC, "FPD, Pot position in P1 OUT")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-11.AD35 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(fanout,"FPD_RMI_02-11/FO") {
		field(DESC, "FPD, 02-11 RMI Fanout, P1")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-11/BIN03")}
record(mbbiDirect,"FPD_RMI_02-11/BIN03") {
		field(DESC, "FPD, 02-11 RMI BIN03 array, P1")
		field(INP, "FPD_RM_02-11.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-11_BIN03/FO")}
record(fanout,"FPD_RMI_02-12/FO") {
		field(DESC, "FPD, 02-12 RMI Fanout, P1")
		field(SELM, "All")
		field(LNK01, "FPD_RMI_02-12/BIN00")
		field(LNK02, "FPD_RMI_02-12/BIN03")}
record(mbbiDirect,"FPD_RMI_02-12/BIN00") {
		field(DESC, "FPD, 02-12 RMI BIN00 array, P1")
		field(INP, "FPD_RM_02-12.BIN00 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-12_BIN00/FO")}
record(mbbiDirect,"FPD_RMI_02-12/BIN03") {
		field(DESC, "FPD, 02-12 RMI BIN03 array, P1")
		field(INP, "FPD_RM_02-12.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-12_BIN03/FO")}
record(fanout64,"FPD_RMI_02-12_BIN00/FO") {
		field(DESC, "FPD, 02-12 BIN00 Alarm Fanout, P1")
		field(LNK01, "FPD_RM_TNP1_02-12/AL_SMO")}
record(bi,"FPD_RM_TNP1_02-12/AL_SMO") {
		field(DESC, "FPD, P1 Smoke Alarm")
		field(INP, "FPD_RMI_02-12/BIN00.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-11_BIN03/FO") {
		field(DESC, "FPD, 02-11 BIN03 Alarm Fanout, P1")
		field(LNK01, "FPD_RM_TNP1_02-11/UP_AL_CBL")
		field(LNK02, "FPD_RM_TNP1_02-11/UP_AL_MEC")
		field(LNK03, "FPD_RM_TNP1_02-11/UP_AL_DRV")
		field(LNK04, "FPD_RM_TNP1_02-11/DN_AL_CBL")
		field(LNK05, "FPD_RM_TNP1_02-11/DN_AL_MEC")
		field(LNK06, "FPD_RM_TNP1_02-11/DN_AL_DRV")}
record(bi,"FPD_RM_TNP1_02-11/UP_AL_CBL") {
		field(DESC, "FPD, P1 UP Cable Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-11/UP_AL_MEC") {
		field(DESC, "FPD, P1 UP Mechanical Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-11/UP_AL_DRV") {
		field(DESC, "FPD, P1 UP Driver Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-11/DN_AL_CBL") {
		field(DESC, "FPD, P1 DOWN Cable Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-11/DN_AL_MEC") {
		field(DESC, "FPD, P1 DOWN Mechanical Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-11/DN_AL_DRV") {
		field(DESC, "FPD, P1 DOWN Driver Alarm")
		field(INP, "FPD_RMI_02-11/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-12_BIN03/FO") {
		field(DESC, "FPD, 02-12 BIN03 Alarm Fanout, P1")
		field(LNK01, "FPD_RM_TNP1_02-12/IN_AL_CBL")
		field(LNK02, "FPD_RM_TNP1_02-12/IN_AL_MEC")
		field(LNK03, "FPD_RM_TNP1_02-12/IN_AL_DRV")
		field(LNK04, "FPD_RM_TNP1_02-12/OUT_AL_CBL")
		field(LNK05, "FPD_RM_TNP1_02-12/OUT_AL_MEC")
		field(LNK06, "FPD_RM_TNP1_02-12/OUT_AL_DRV")}
record(bi,"FPD_RM_TNP1_02-12/IN_AL_CBL") {
		field(DESC, "FPD, P1 IN Cable Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-12/IN_AL_MEC") {
		field(DESC, "FPD, P1 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-12/IN_AL_DRV") {
		field(DESC, "FPD, P1 IN Driver Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-12/OUT_AL_CBL") {
		field(DESC, "FPD, P1 OUT Cable Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-12/OUT_AL_MEC") {
		field(DESC, "FPD, P1 OUT Mechanical Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP1_02-12/OUT_AL_DRV") {
		field(DESC, "FPD, P1 OUT Driver Alarm")
		field(INP, "FPD_RMI_02-12/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout,"FPD_RMI_02-13/FO") {
		field(DESC, "FPD, 02-13 RMI Fanout, P2")
		field(SELM, "All")
		field(LNK01, "FPD_RM_TNP2_02-13/UP_POS")
		field(LNK02, "FPD_RM_TNP2_02-13/DN_POS")
		field(LNK03, "FPD_RM_TNP2_02-13/IN_POS")
		field(LNK04, "FPD_RM_TNP2_02-13/OUT_POS")}
record(ai,"FPD_RM_TNP2_02-13/UP_POS") {
		field(DESC, "FPD, Pot position in P2 UP")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-13.AD32 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP2_02-13/DN_POS") {
		field(DESC, "FPD, Pot position in P2 DOWN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-13.AD33 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP2_02-13/IN_POS") {
		field(DESC, "FPD, Pot position in P2 IN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-13.AD34 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TNP2_02-13/OUT_POS") {
		field(DESC, "FPD, Pot position in P2 OUT")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-13.AD35 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(fanout,"FPD_RMI_02-13/FO") {
		field(DESC, "FPD, 02-13 RMI Fanout, P2")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-13/BIN03")}
record(mbbiDirect,"FPD_RMI_02-13/BIN03") {
		field(DESC, "FPD, 02-13 RMI BIN03 array, P2")
		field(INP, "FPD_RM_02-13.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-13_BIN03/FO")}
record(fanout,"FPD_RMI_02-14/FO") {
		field(DESC, "FPD, 02-14 RMI Fanout, P2")
		field(SELM, "All")
		field(LNK01, "FPD_RMI_02-14/BIN00")
		field(LNK02, "FPD_RMI_02-14/BIN03")}
record(mbbiDirect,"FPD_RMI_02-14/BIN00") {
		field(DESC, "FPD, 02-14 RMI BIN00 array, P2")
		field(INP, "FPD_RM_02-14.BIN00 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-14_BIN00/FO")}
record(mbbiDirect,"FPD_RMI_02-14/BIN03") {
		field(DESC, "FPD, 02-14 RMI BIN03 array, P2")
		field(INP, "FPD_RM_02-14.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-14_BIN03/FO")}
record(fanout64,"FPD_RMI_02-14_BIN00/FO") {
		field(DESC, "FPD, 02-14 BIN00 Alarm Fanout, P2")
		field(LNK01, "FPD_RM_TNP2_02-14/AL_SMO")}
record(bi,"FPD_RM_TNP2_02-14/AL_SMO") {
		field(DESC, "FPD, P2 Smoke Alarm")
		field(INP, "FPD_RMI_02-14/BIN00.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-13_BIN03/FO") {
		field(DESC, "FPD, 02-13 BIN03 Alarm Fanout, P2")
		field(LNK01, "FPD_RM_TNP2_02-13/UP_AL_CBL")
		field(LNK02, "FPD_RM_TNP2_02-13/UP_AL_MEC")
		field(LNK03, "FPD_RM_TNP2_02-13/UP_AL_DRV")
		field(LNK04, "FPD_RM_TNP2_02-13/DN_AL_CBL")
		field(LNK05, "FPD_RM_TNP2_02-13/DN_AL_MEC")
		field(LNK06, "FPD_RM_TNP2_02-13/DN_AL_DRV")}
record(bi,"FPD_RM_TNP2_02-13/UP_AL_CBL") {
		field(DESC, "FPD, P2 UP Cable Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-13/UP_AL_MEC") {
		field(DESC, "FPD, P2 UP Mechanical Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-13/UP_AL_DRV") {
		field(DESC, "FPD, P2 UP Driver Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-13/DN_AL_CBL") {
		field(DESC, "FPD, P2 DOWN Cable Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-13/DN_AL_MEC") {
		field(DESC, "FPD, P2 DOWN Mechanical Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-13/DN_AL_DRV") {
		field(DESC, "FPD, P2 DOWN Driver Alarm")
		field(INP, "FPD_RMI_02-13/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-14_BIN03/FO") {
		field(DESC, "FPD, 02-14 BIN03 Alarm Fanout, P2")
		field(LNK01, "FPD_RM_TNP2_02-14/IN_AL_CBL")
		field(LNK02, "FPD_RM_TNP2_02-14/IN_AL_MEC")
		field(LNK03, "FPD_RM_TNP2_02-14/IN_AL_DRV")
		field(LNK04, "FPD_RM_TNP2_02-14/OUT_AL_CBL")
		field(LNK05, "FPD_RM_TNP2_02-14/OUT_AL_MEC")
		field(LNK06, "FPD_RM_TNP2_02-14/OUT_AL_DRV")}
record(bi,"FPD_RM_TNP2_02-14/IN_AL_CBL") {
		field(DESC, "FPD, P2 IN Cable Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-14/IN_AL_MEC") {
		field(DESC, "FPD, P2 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-14/IN_AL_DRV") {
		field(DESC, "FPD, P2 IN Driver Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-14/OUT_AL_CBL") {
		field(DESC, "FPD, P2 OUT Cable Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-14/OUT_AL_MEC") {
		field(DESC, "FPD, P2 OUT Mechanical Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TNP2_02-14/OUT_AL_DRV") {
		field(DESC, "FPD, P2 OUT Driver Alarm")
		field(INP, "FPD_RMI_02-14/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout,"FPD_RMI_02-05/FO") {
		field(DESC, "FPD, 02-05 RMI Fanout, Dipoles")
		field(SELM, "All")
		field(LNK01, "FPD_RM_TND1_02-05/IN_POS")
		field(LNK02, "FPD_RM_TND2_02-05/IN_POS")}
record(ai,"FPD_RM_TND1_02-05/IN_POS") {
		field(DESC, "Pot position in A1 UP")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-05.AD32 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(ai,"FPD_RM_TND2_02-05/IN_POS") {
		field(DESC, "Pot position in A1 DOWN")
		field(DTYP, "Raw Soft Channel")
		field(INP, "FPD_RM_02-05.AD33 NPP MS")
		field(SCAN, "Passive")
		field(LINR, "LINEAR")
		field(ROFF, "2048")
		field(ASLO, "0.0048828125")
		field(AOFF, "0.0")
		field(EGUL, "0.0")
		field(ESLO, "2.7917")
		field(SMOO, "0.0")
		field(EGU, "mm")
		field(HIHI, "40.0")
		field(HIGH, "35.0")
		field(HHSV, "MAJOR")
		field(HSV, "MINOR")
		field(LOLO, "0.01")
		field(LLSV, "MAJOR")
		field(PREC, "2")}
record(fanout,"FPD_RMI_02-05/FO") {
		field(DESC, "FPD, 02-05 RMI Fanout, Dipoles")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-05/BIN03")}
record(mbbiDirect,"FPD_RMI_02-05/BIN03") {
		field(DESC, "FPD, 02-05 RMI BIN03 array, Dipoles")
		field(INP, "FPD_RM_02-05.BIN03 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-05_BIN03/FO")}
record(fanout,"FPD_RMI_02-06/FO") {
		field(DESC, "FPD, 02-06 RMI Fanout, Dipoles")
		field(SELM, "All")
		field(LNK1, "FPD_RMI_02-06/BIN00")}
record(mbbiDirect,"FPD_RMI_02-06/BIN00") {
		field(DESC, "FPD, 02-06 RMI BIN00 array, Dipoles")
		field(INP, "FPD_RM_02-06.BIN00 NPP MS")
		field(SCAN, "Passive")
		field(FLNK, "FPD_RMI_02-06_BIN00/FO")}
record(fanout64,"FPD_RMI_02-06_BIN00/FO") {
		field(DESC, "FPD, 02-06 BIN00 Alarm Fanout, Dipoles")
		field(LNK01, "FPD_RM_TNDI_02-06/AL_SMO")}
record(bi,"FPD_RM_TNDI_02-00/AL_SMO") {
		field(DESC, "FPD, Dipoles Smoke Alarm")
		field(INP, "FPD_RMI_02-06/BIN00.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(fanout64,"FPD_RMI_02-05_BIN03/FO") {
		field(DESC, "FPD, 02-05 BIN03 Alarm Fanout, Dipoles")
		field(LNK01, "FPD_RM_TND1_02-05/IN_AL_CBL")
		field(LNK02, "FPD_RM_TND1_02-05/IN_AL_MEC")
		field(LNK03, "FPD_RM_TND1_02-05/IN_AL_DRV")
		field(LNK04, "FPD_RM_TND2_02-05/IN_AL_CBL")
		field(LNK05, "FPD_RM_TND2_02-05/IN_AL_MEC")
		field(LNK06, "FPD_RM_TND2_02-05/IN_AL_DRV")}
record(bi,"FPD_RM_TND1_02-05/IN_AL_CBL") {
		field(DESC, "FPD, D1 IN Cable Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.B0 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TND1_02-05/IN_AL_MEC") {
		field(DESC, "FPD, D1 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.B4 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TND1_02-05/IN_AL_DRV") {
		field(DESC, "FPD, D1 IN Driver Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.B5 NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TND2_02-05/IN_AL_CBL") {
		field(DESC, "FPD, D2 IN Cable Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.B8 NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TND2_02-05/IN_AL_MEC") {
		field(DESC, "FPD, D2 IN Mechanical Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.BC NPP MS")
		field(ZNAM, "OK")
		field(ONAM, "Failed")
		field(OSV, "MAJOR")
		field(SCAN, "Passive")}
record(bi,"FPD_RM_TND2_02-05/IN_AL_DRV") {
		field(DESC, "FPD, D2 IN Driver Alarm")
		field(INP, "FPD_RMI_02-05/BIN03.BD NPP MS")
		field(ZNAM, "Failed")
		field(ONAM, "OK")
		field(ZSV, "MAJOR")
		field(SCAN, "Passive")}