Type,Manufacturer,Model,Fuel,Rating (kWe),Rating range (kWe),Rated min load (%),Range of rated min load  (%),Efficiency (LHV) (%),Range of efficiency (LHV) (%),Efficiency at FL (kJ/kWh) (HHV),Range of efficiency at FL (kJ/kWh) (HHV),Efficiency at 75% (kJ/kWh),Range of efficiency at 75% (kH/kWh) (HHV),Efficiency at 50% (kJ/kWh),Range of efficiency at 50%(kJ/kWh) (HHV),Useable thermal output (kJ/kWh),Range of useable thermal output (kJ/kWh),Exhaust Temp (C),Range of Exhaust Temp 2 (C),Cold start-up time (min),Range of cold start-up time (min),Min down time (min),Ramp rate up (kW/min),Range of load ramp rate (kW/min),Equipment costs ($/kW),Range of equip costs ($/kW),Installation costs ($/kW),Range of install costs ($/kW),Turnkey costs ($/kW),Range of turnkey costs ($/kW),Fuel costs ($/GJ),Fixed O&M ($/kWy),Range of fixed O&M ($/kWy),Variable O&M ($/kWh),Range of variable O&M ($/kWh),Lifetime,Range of lifetime,Lead time (mo),Range of lead time (mo),Length (m),Width (m),Height (m),Volume (m3),Range of volume (m3/kW),Footprint (m2),Range of footprint (m2/kW),Weight (kg),Range of weight (kg/kW),Noise level (dB),Range of noise level (dB),CO2 (g/kWh),Range of CO2 (g/kWh),CO (g/kWh),Range of CO (g/kWh),NOx (g/kWh),Range of NOx (g/kWh),SOx (g/kWh),Range of SOx (g/kWh),UHC (g/kWh),Range of UHC (g/kWh),PM-10 (g/kWh),Water requirements (l/kWh),Range of water require (l/kWh),Waste water production (l/kWh),Range of waste water prod (l/kWh),Hazardous materials,Voltage (V),Frequency (Hz),Data Source,Remarks
F.C. Hybrid Solid Oxide,,,N.G.,1233,225-2240,25,25,,,6067,5676-6457,6726,6446-7006,6810,6584-7037,865,570-1161,196.5,177-216,2,2,,,,1225,1150-1300,205,180-230,,,,37.5,25-50,0.0025,.002-.003,30,30,4.5,3-6 months,,,,,.51-.57,,.1-.11,,,60 at 9m,,318,318,0,0,0.025,.023-.027,0,0,0,0,0,0,0,0,0,Spent Desulfurizer Reagent,,,CADER Report,
F.C. Molten Carbonate,,,N.G.,1550,250-2850,27.5,25-30,,,7451,6905-7997,7549,6615-8483,8013,6436-9590,1688,1477-1899,227,77-377,1800,1200-2400,,146,7-285,1358,815-1900,268,100-435,,,,70,70,0.003,.003,32.5,30-35 years,18,12-24 months,,,,,.227-1.13,,.093-.372,,54-109,,60 at 9m-60 at 30m,382,356-408,0.0045,.0045,0.00091,.00091,0.0014,.0014,0,Negligible,0,0.24,0-.47,0.08,0-.17,None reported,,,CADER Report,
F.C. PEM,,,"N.G., Propane, Butane, Diesel",126.5,3-250,16.5,0-33,,,10158,10015-10300,9880,9743-10015,9514,9013-10015,2770,2110-3429,65.5,57-74,60,,,0.5,,4000,,1000,,5000,,,,,0.0275,.01-.045,20,15-25,1,,,,,,.13-.25,,.056-.28,,45-136,,50 at 2m - 65 at 3m,590,499-680,0,0,0,0,0,0,0,0,0,0.38,0-0.76,0,0,Batteries,,,CADER Report,
F.C. PEM,Avista labs,GEHomeGen,NG,4,4-10,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,12.5,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,www.avistalabs.com,
F.C. PEM,Ballard,,NG,1,1-10,,,,,,,,,,,,,,,,,,,,,,,,500,500-5000,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,www.ballard.com,
F.C. PEM,Ballard,,"NG, HD-5 propane",212,,,,,,8327,,,,,,4025,,,,,,,,,,,,,1800,,,,,,,,,12,,7.3,2.4,2.7,49,,,,20412,,<60 at 9m,80 at 1 m,,,0.259,0.172-.345,0.135,.09-.18,,,0,,0,114,,,,,480,60,Ballard and EPRI TR-106620-R1,"Outlet T=75C for water, emissions output T=177C"
F.C. PEM,DAIS-Analytic,RPG-3K,NG,3,3-10,,,40,,9477.8,,,,10662.5,,6kw,,,,,,60,7kw/15min = .47,,,,,,300,300-1000,,,,,,12.5,,,,0.9,0.9,1.7,1.4,,,,,,,,40% of flow rate,,5ppm,,,,0,,,,,1 gall/day for CHP,,2-3mL/min,,,240/120V,60,www.daisanalytic.com,
F.C. PEM,Energy Partners,not Determined,NG,10,5-10,,,>35,,,,,,,,,,,,,,15,5kw/15min = .33,,,,,,,,,,,,,5.7,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,www.energypartners.com,
F.C. PEM,IDATECH,not determined,methanol,3,1-15,,,,,,,,,,,1260,kw thermal/kw electric,,,,,,12kw/2min = 6,,,,,,($10000 total)              $666.00/kw,666-2000,.075/kwh,83,,,,n/a,,,,1,0.9,0.9,0.81,,,,363,,50 at 3,,<5ppm,,<1ppm,,,,,,,,,,,,,,240/120V,60,"David J. Edlund fuel cells ""Powerline"" Mar/Ap. 1999",
F.C. PEM,ONSI,not determined,"NG, propane",5,5-10,38,36-39,32,30-34,,,,,,,4000,kW thermal/kW electric,,,,,,,,,,,,,,,,,,,,,,,1.02,0.61,1.02,0.63,,,,not determined,,60 at 9m,,,,,,,,,,,,,,,,,,200/100V,50,"IFC, LLC",grid connected or independent
F.C. PEM,Plug Power,,"NG, propane, methanol",7,7-15,,,40,,,,,,,,,,93,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,"Annual Report for fiscal yr. 99 Mar 30, 2000 www.plugpower.com",
F.C. Phosphoric Acid,,,"N.G., Propane",200,,0,,,,9970,,9970,,9970,,3825,3693-3956,90.5,60-121,180,,,,80 kW instantaneous step,3000,,600,450-750,,,,,,0.009,.008-.01,20,,7,,,,,,1.13,,.37,,91,62 at 9m,,513,,0.01,,0.007,,0,,0.00018,,0,0,,0,,None reported,,,CADER Report,
F.C.PEM,H-Power Corp.,,"NG, propane,methanol",3,3-10,,,30 fuel to energy,70 w/CHP,10550,,,,,,528,,,,,,,.47,,,,1713,,800,800-2666,,,,0.015,,5,,,,1.5,1.2,0.96,1.7,,,,N/A,,<60 at 9m,,n/a,,<10ppm,,,,,,,,,,,,,,120,,www.hpower.com,
MCFC,Fuel Cell Energy,,NG,250,125-250,,,45 electrical,77CHP,,,,,,,,,371,,1440,1440-2880,,125kw/3sec = 2500,,,,,,4000,4000-5000,3.8,200,,0,,3-7,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,,www.fce.com,