\* \* \* \* \* \* \* \*

READ AND **REMOVE THIS PAGE** BEFORE PLACING

THE SPECIFICATION SECTION IN THE CONTRACT

\* \* \* \* \* \* \* \*

[DIVISION 8: DOORS AND WINDOWS]{.underline}

SECTION 08708 ‑ FINISH HARDWARE

USE: Furnishing and installing finish hardware for doors listed in Door
Schedule.

**NOTES TO SPECIFIER:**

A. Options within paragraphs are identified by enclosure in brackets;
blank spaces enclosed by brackets \[\_\_\_\_\_\] provide for information
to be inserted, as appropriate, to individual projects.

B. **TO AVOID CONFLICTING REQUIREMENTS AND COSTLY MISTAKES,** the
specifier must edit (delete, substitute or add to the text). The
remaining paragraphs must be renumbered.

C. DELETE FOR FINAL COPY: Notes to the Specifier, located between lines
of asterisks; all \[brackets\], [underlining]{.underline}, **boldface**,
and *italics*, within the paragraphs; and this page. (Open Reveal Codes
\[alt F3\] to do this accurately.)

D. [To Edit "(Footer B)":]{.underline} (Corel 8). **ENTIRE FOOTER SHOULD
BE BOLDED.** Click in the footer and delete the "Project Name (ftr B)"
text and replace it with the **Name of the Project (upper and lower
case)**. Replace date with current MM/YY (WITHOUT BRACKETS).

E. The Guide Specifications are intended to be continuously reviewed and
revised. User's technical comments are appreciated. Also, other related
or similar specification that are written "from scratch" that could
benefit others, or other questions can be sent to NSTC A/E Group, ST
110, or call (303) 987-6868.

**DRAWING DATA REQUIRED:**

**REQUIRED SPEC MODIFICATIONS:**

[GENERAL NOTES]{.underline}

A. Whenever entire articles, paragraphs, or subparagraphs are not
applicable, the articles, paragraphs, or subparagraphs should be
deleted; when necessary, reletter or renumber articles, paragraphs, or
subparagraphs.

B. THIS GUIDE IS NOT INTENDED AS A SUBSTITUTE FOR READING THE ENTIRE
SECTION.

[TECHNICAL NOTES]{.underline}

A. 1.1B: Select or add applicable specification sections. Do not list
specification sections from Division 8.

B. 1.2: Select or add applicable references.

C. 1.4A: Select applicable phrase.

D. 1.4B: Insert number of copies of the manufacturer\'s descriptive data
required. Normally 5 copies are required. Distribution after review is
normally 1 copy to the CO, 3 copies to the Contractor, and 1 copy to the
project file.

E. 1.4C: Insert number of copies of installation instructions required.
Normally 5 copies are required. Distribution after review is normally 1
copy to the CO, 5 copies to the Contractor, and 1 copy to the project
file.

F. 1.4D: Insert number of copies of the manufacturer\'s operating and
maintenance instructions required. Normally 5 copies are required.
Distribution after review is normally 1 copy to the CO, 3 copies to the
Contractor, and 1 copy to the project file.

G. 1.4E: Insert number of copies of hardware schedule required. Normally
5 copies are required. Distribution after review is normally 1 copy to
the CO, 3 copies to the Contractor, and 1 copy to the project file.

H. 4.1 and 4.2: When a \"lump sum\" Contract is used, delete the title
PART 4: MEASUREMENT AND PAYMENT, and both articles from this
specification section. Measurement and payment will be addressed in Part
4 of Section 01010.

**REVISIONS OF THIS SECTION:**

CSI format, editorial changes: 12/01

Metric:

Technical Update: 01/94

SECTION 08708

FINISH HARDWARE

[PART 1: GENERAL]{.underline}

1.1 SUMMARY:

A. Section Includes: Furnishing and installing finish hardware on doors
as noted in the Door Schedule.

1.2 REFERENCES:

A. American National Standards Institute:

ANSI A 156.1-88 Butts and Hinges

ANSI A 156.2-89 Bored and Preassembled Locks and Latches

ANSI A 156.3-89 Exit Devices and Directory of Certified Exit Devices

ANSI A 156.4-86 Door Controls - Closers

ANSI A 156.5-84 Auxiliary Locks and Associated Products

ANSI A 156.6-86 Architectural Door Trim

ANSI A 156.7-88 Template Hinge Dimensions

ANSI A 156.8-88 Door Controls - Overhead Holders

ANSI A 156.14-91 Sliding and Folding Door Hardware

ANSI A 156.15-86 Closer Holder Release Devices

ANSI A 156.16-89 Auxilliary Hardware

ANSI A 156.18-87 Materials and Finishes

ANSI A 156.21-89 Thresholds

B. Door and Hardware Institute:

DHI Recommended Locations for Builder\'s Hardware for Standard Steel
Doors and Frames

C. International Conference of Building Officials (ICBO):

UBC‑1994 Uniform Building Code

D. National Fire Protection Association:

NFPA 101‑94 Code for Safety to Life from Fire in Buildings and
Structures

E. Underwriters\' Laboratories, Inc.:

UL 969‑89 UL Standard for Safety Marking and Labeling Systems Third
Edition

1.3 SYSTEM DESCRIPTION:

A. Performance Requirements: Doors, when latched, shall fit snugly
against silencers. There shall be no movement of the door possible when
door is latched; however, there shall also be no extra force required to
latch the door.

1.4 SUBMITTALS:

A. General: Submittals shall be according to \[Section 01009 - General
Information and Requirements.\] \[and\] \[Section 01300 ‑ Submittals.\]
\[and\] \[Section 01365 - Certificates of Conformance.\]

B. Manufacturer\'s Literature: Submit \[\_\_\] copies of the
manufacturer\'s descriptive data for the finish hardware to be used on
this project.

C. Installation Instructions: Submit \[\_\_\] copies of the
manufacturer\'s installation instructions for the finish hardware to be
used on this project.

D. Operating and Maintenance Instructions: Submit \[[ ]{.underline}\]
copies of manufacturer\'s operating and maintenance instructions for
finish hardware to be used on this project.

E. Hardware Schedule: Submit \[[ ]{.underline}\] copies of the schedule
covering hardware for all personnel doors. Coordinate hardware with
doors, frames, and related work to ensure proper size, weight, hand
function, and finish. Organize schedule into \"sets\" indicating every
item required for each door and frame. Furnish approved hardware
template to each fabricator of doors and frames requiring factory
preparation for hardware installation. Include the following:

1\. Name and manufacturer for each item.

2\. Type, style, function, size, and finish for each item.

3\. Hardware location cross‑referenced to floor plans.

4\. Explanation of schedule abbreviations, symbols, and codes.

5\. Door and frame sizes, and materials.

6\. Keying information.

1.5 QUALITY ASSURANCE:

A. Hardware Consultant: The Contractor shall have a hardware supplier
who has an employee who is a member of the American Society of Hardware
Consultants with the technical experience to correctly interpret these
Contract documents and efficiently service the hardware portion of this
Contract. This representative shall be available, subject to call by the
Contracting Officer. \[This representative shall make a personal
inspection of the hardware after application and before final
inspection, to see that the hardware is properly installed and in good
working order. In case of faulty installation, he shall inform the
Contractor and the Contracting Officer, and suggest proper
corrections.\]

B. Labeling Requirements: Provide UL label on exit devices required on
fire‑rated doors.

C. Product Uniformity: The warranty for all components and type of
hardware (butts, locksets, closers, and other items necessary to
complete the intended application) shall be covered by a single
manufacturer.

D. Failure Criteria: Not limited to the following:

1\. Units coming loose from their mounts.

2\. Units becoming non‑functional.

3\. Units\' finish becoming tarnished through normal use.

1.6 SEQUENCING AND SCHEDULING:

A. Readiness: Doors shall have been previously primed and shall be ready
for application of hardware prior to application of finish coats.

1\. Do not install hardware until areas routed or drilled for hardware
have been painted. Do not install hardware until complete door has been
painted, including tops and bottoms.

1.7 MAINTENANCE:

A. Specialized Maintenance Tool Set: Furnish a complete set which will
be required for future adjustment, maintenance, removal, and replacement
of hardware.

[PART 2: PRODUCTS]{.underline}

2.1 MATERIALS:

A. Door Hardware: Shall comply with the followings standards:

1\. Butts and Hinges ANSI A 156.1

2\. Locks and Trim ANSI A 156.2

3\. Exit Devices ANSI A 156.3

4\. Closers ANSI A 156.4

5\. Auxiliary Locks ANSI A 156.5

6\. Architectural Door Trim ANSI A 156.6

7\. Template Hinge Dimensions ANSI A 156.7

8\. Overhead Holders ANSI A 156.8

9\. Closer Holder Release Devices ANSI A 156.15

10\. ab Auxiliary Hardware ANSI A 156.16

11\. ab Materials and Finishes ANSI A 156.18

12\. ab Sliding and Folding Door Hardware ANSI A 156.14

13\. ab Thresholds ANSI A 156.21

B. Fastenings: Finish hardware shall be furnished with necessary screws,
bolts or other fastenings of suitable size and type to anchor the
hardware in position for heavy use and long life, and shall harmonize
with the hardware as to material and finish. These fastenings shall be
furnished where necessary with expansion shields, sex bolts, toggle
bolts, or other approved anchors according to the material to which it
is applied and according to the manufacturer\'s written instructions.

C. Keys: Provide two keys for each lock furnished. Die stamp each key
with numbers of lock change and set symbol number or letter. Keys shall
be turned in to the Contracting Officer, who will issue a receipt for
them.

D. Keying: Locks shall be keyed alike in groups, master‑keyed and grand
master‑keyed, as approved by the local governing authority. Furnish five
master keys for each set and five grand master keys direct by registered
mail from lock manufacturer to the Contracting Officer properly marked
for easy identification.

E. Key Security: For security purposes, keying must be done by the lock
manufacturer and permanent records maintained by this manufacturer.
Keying chart from manufacturer shall be made available to the
Government.

[PART 3: EXECUTION]{.underline}

3.1 PREPARATION:

A. General: Mortised items shall be fitted and then removed and placed
in their original packages until painters have completed their work.

B. Blocking: Provide solid blocking for wall stops.

3.2 INSTALLATION:

A. General: Install each hardware item in compliance with the
manufacturer\'s instructions. Wherever cutting and fitting are required
to install hardware on surfaces which will be painted or finished at a
later time, install each item completely and then remove and store in a
secure place. After completion of the finishes, reinstall each item. Do
not install surface‑mounted items until finishes have been completed on
the substrate.

B. Location: Install the required hardware on the appropriate door
according to the approved hardware schedule.

C. Cylinder Cores: Remove construction cores from cylinders and replace
with permanent cores in the presence of the Contracting Officer.
Demonstrate that tagged keys operate respective locks. Deliver tagged
keys to the Contracting Officer upon acceptance of each core cylinder
installation.

D. Installation: Manuals accompanying the hardware shall be consulted
and their instructions strictly adhered to.

1\. Mounting Heights: Mount units at heights identified by the Door and
Hardware Institute, except as otherwise indicated.

2\. Install each hardware item in compliance with the manufacturer\'s
instructions. Wherever cutting and fitting are required to install
hardware on surfaces which will be painted or finished at a later time,
install each item completely and then remove and store in a secure
place. After completion of the finishes, reinstall each item. Do not
install surface-mounted items until finishes have been completed on the
substrate.

E. Silencers: Door frames shall receive rubber door silencers; single
doors shall receive three per door; double doors shall receive two per
opening.

1\. Doors, when latched, shall fit snugly against silencers. There shall
be no movement of the door possible when door is latched; however, there
shall also be no extra force required to latch the door.

2\. Apply single door silencers to jamb stop strip and apply double door
silencers to header stop strip near the center of opening.

F. Fasteners: Use fastening devices as needed to securely anchor
hardware according to manufacturer\'s published templates. Self‑tapping
sheet metal screws are not acceptable. Closers and exit devices on wood
doors shall be through‑bolted.

303 ADJUSTING:

A. General: Wherever hardware installation is made more than one month
prior to acceptance or occupancy, make a final check and adjustment of
hardware items during the week prior to acceptance or occupancy. Clean
and lubricate operating items as necessary to restore proper function
and finish of hardware and doors. Adjust door-control devices to
compensate for final operation of heating and ventilating equipment.
Adjust and check each operating item of hardware and each door to insure
proper operation or function of every unit. Replace units which cannot
be adjusted to operate freely and smoothly.

3.4 DEMONSTRATION:

A. Requirements: Instruct designated Government personnel in proper
adjustment and maintenance of hardware and hardware finishes.

[PART 4: MEASUREMENT AND PAYMENT]{.underline}

4.1 METHOD OF MEASUREMENT:

A. Units: The work described in this section will not be measured for
payment.

4.2 BASIS OF PAYMENT:

A. Payment: No direct payment for the work described under this section
will be made. The Contractor shall include consideration for this item
in the bid price for other items of the Contract.

END OF SECTION