\* \* \* \* \* \* \* \*

READ AND **REMOVE THIS PAGE** BEFORE PLACING

THE SPECIFICATION SECTION IN THE CONTRACT

\* \* \* \* \* \* \* \*

[DIVISION 8: DOORS AND WINDOWS]{.underline}

SECTION 08360 ‑ SECTIONAL OVERHEAD DOORS

USE: Furnishing and installing sectional overhead doors.

**NOTES TO SPECIFIER:**

A. Options within paragraphs are identified by enclosure in brackets;
blank spaces enclosed by brackets \[\_\_\_\_\_\] provide for information
to be inserted, as appropriate, to individual projects.

B. **TO AVOID CONFLICTING REQUIREMENTS AND COSTLY MISTAKES,** the
specifier must edit (delete, substitute or add to the text). The
remaining paragraphs must be renumbered.

C. DELETE FOR FINAL COPY: Notes to the Specifier, located between lines
of asterisks; all \[brackets\], [underlining]{.underline}, **boldface**,
and *italics*, within the paragraphs; and this page. (Open Reveal Codes
\[alt F3\] to do this accurately.)

D. [To Edit "(Footer B)":]{.underline} (Corel 8). **ENTIRE FOOTER SHOULD
BE BOLDED.** Click in the footer and delete the "Project Name (ftr B)"
text and replace it with the **Name of the Project (upper and lower
case)**. Replace date with current MM/YY (WITHOUT BRACKETS).

E. The Guide Specifications are intended to be continuously reviewed and
revised. User's technical comments are appreciated. Also, other related
or similar specification that are written "from scratch" that could
benefit others, or other questions can be sent to NSTC A/E Group, ST
110, or call (303) 987-6868.

**DRAWING DATA REQUIRED:**

**REQUIRED SPEC MODIFICATIONS:**

[GENERAL NOTES]{.underline}

A. Whenever entire articles, paragraphs or subparagraphs are not
applicable, the articles, paragraphs or subparagraphs should be deleted;
when necessary, reletter or renumber articles, paragraphs or
subparagraphs.

B. THIS GUIDE IS NOT INTENDED AS A SUBSTITUTE FOR READING THE ENTIRE
SECTION.

[TECHNICAL NOTES]{.underline}

A. 1.1A: Select applicable words.

B. 1.1B: Select or add applicable specification sections. Do not list
specification sections from Division 8.

C. 1.2: Select or add applicable references.

D. 1.3A-D: Select applicable words and insert appropriate data.

E. 1.4A: Select applicable section.

F. 1.4B: Inert number of copies of the manufacturer\'s descriptive data
required. Normally 5 copies are required. Distribution after review is
normally 1 copy to the COR, 3 copies to the Contractor, and 1 copy to
the project file.

G. 1.4C: Insert number of copies of the manufacturer\'s installation
instructions required. Normally 5 copies are required. Distribution
after review is normally 1 copy to the COR, 3 copies to the Contractor,
and 1 copy to the project file.

H. 1.4D: Insert number of shop drawings required. Normally 5 copies are
required. Distribution after review is normally 1 copy to the COR, 3
copies to the Contractor, and 1 copy to the project file.

I. 1.4E: Insert number of copies of Certificates of Conformance
required. Normally 3 copies are required. Distribution after review is
normally 1 copy to the COR, 1 copy to the Contractor, and 1 copy to the
project file.

J. 1.5B: Insert years experience required and select wording as
appropriate.

K. 2.1: Insert/Select applicable words.

L. 2.2A-Q

\* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \*

\* NOTICE TO DESIGNER!!

\*

\* Select Applicable Panel Paragraph

\* A, B, C, D, or E and insert appropriate

\* information \*

\* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \* \*

M. 2.2J: Select or insert applicable words. Delete when specifying
bottom of door safety edge for electric operation.

N. 2.2N: Select applicable words. NEMA Type 1 is \"general purpose\".
NEMA Type 4 is \"totally enclosed\".

O. 2.2P: Select applicable word and insert appropriate description of
radio control system required.

P. 2.3: Select and insert applicable words.

Q. 3.2A: Select applicable word.

R. 3.3A: Select applicable phrase.

S. 3.4B-D: Insert required tolerance.

T. 4.1 and 4.2: When a \"lump sum\" Contract is used, delete the title
\"PART 4: MEASUREMENT AND PAYMENT\", and both articles from this
specification section. Measurement and payment will be addressed in Part
4 of Section 01010.

**REVISIONS OF THIS SECTION:**

CSI format, editorial changes: 12/01

Metric:

Technical Update: 08/92

SECTION 08360

SECTIONAL OVERHEAD DOORS

[PART 1: GENERAL]{.underline}

1.1 SUMMARY:

A. Section Includes: Furnishing and installing \[manual\] \[electric\]
overhead sectional doors with \[wood\] \[steel\] \[aluminum\] \[glass
fiber sheet\] \[insulated\] panels of \[flush\] \[stile and rail\]
design including operating hardware and supports.

1.2 REFERENCES:

A. American National Standards Institute:

ANSI A 135.4‑82 Basic Hardboard.

B. American Society for Testing and Materials:

ASTM A 123 E1 REV-89 Zinc (Hot‑Dip Galvanized) Coatings on Iron and
Steel Products

ASTM A 227/A 227M-91 Steel Wire, Cold‑Drawn for Mechanical Springs

ASTM A 229/A 229M-91 Steel Wire, Oil‑Tempered for Mechanical Springs

ASTM A 446/A 446M-91 Steel Sheet, Zinc‑Coated (Galvanized) by the Hot
Dip Process, Structural (Physical) Quality

ASTM A 526/A 526M-90 Steel Sheet, Zinc‑Coated (Galvanized) by the Hot
Dip Process, Commercial Quality

ASTM B 209‑90 Aluminum and Aluminum‑Alloy Sheet and Plate

ASTM B 221‑91 Aluminum and Aluminum‑Alloy Extruded Bars, Rods, Wire,
Shapes, and Tubes

ASTM B 221M E1-90 Aluminum and Aluminum‑Alloy Extruded Bars, Rods, Wire,
Shapes, and Tubes (Metric)

ASTM E 330‑90 Test Method for Structural Performance of Exterior
Windows, Curtain Walls, and Doors by Uniform Static Air Pressure
Difference

C. National Electric Manufacturer\'s Association:

NEMA ICS 1‑88 Industrial Control and Systems; (Revision 2 - January
1990)

NEMA MG 1‑87 Motors and Generators; (Revision 1 - January 1989)

D. National Association of Architectural Metal Manufacturers:

NAAMM Metal Finishes Manual for Architectural Metals and Metal Products
‑ 1975

1.3 SYSTEM DESCRIPTION:

A. Panels: \[Flush wood\] \[Stile and rail wood with \[[ ]{.underline}\]
infill panel\] \[Flush steel\] \[Stile and rail steel with \[[
]{.underline}\] infill panels\] \[flush aluminum\] \[Stile and rail
aluminum with \[aluminum\] \[glass fiber sheet\] \[[ ]{.underline}\]
infill panels;\] \[2\] \[1‑3/4\] inches thick.

B. Track: \[Standard lift\] \[High lift\] \[Low headroom\] track and
hardware.

C. Manual Operation: With \[pull rope\] \[chain hoist\] operation
requiring a maximum exertion of \[25\] lbs force.

D. Electric Operation: On \[[ ]{.underline}\] volt, \[[ ]{.underline}\]
phase, 60 Hz service to \[1/3\] \[1/2\] HP motor manually operable in
case of power failure, transit time of \[12\] inches per second.

1.4 SUBMITTALS:

A. General: Submittals shall be according to \[Section 01009 - General
Information and Requirements.\] \[and\] \[Section 01300 - Submittals.\]
\[and\] \[Section 01365 - Certificates of Conformance.\]

B. Manufacturer\'s Literature: Submit \[[ ]{.underline}\] copies of the
manufacturer\'s descriptive data for each type of overhead door and
operator to be used on this project.

C. Installation Instructions: Submit \[[ ]{.underline}\] copies of the
manufacturer\'s installation instructions for each type of overhead door
and operator to be used on this project.

D. Shop Drawings: Submit \[[ ]{.underline}\] copies of shop drawings for
each type of overhead door to be used on this project. Shop drawings
shall have the opening dimensions and tolerances, compont construction,
connections and details, anchorage methods and spacing, hardware and
locations, and installation details.

E. Certificates of Conformance: Submit \[[ ]{.underline}\] copies of
written certification from the manufacturer of the Contractor‑furnished
overhead doors and operators to be used on this project that they
conform to the requirements of this specification section.

1.5 QUALITY ASSURANCE

A. Manufacturer Qualifications: A company regularly engaged in overhead
door construction with three years minimum experience. The manufacturer
shall have parts and service available to correct deficiencies through
factory representatives, dealers, or factory certified maintenance
service shops.

B. Installer Qualifications: A company specializing in installing
overhead doors \[with \[[ ]{.underline}\] years \[documented\]
experience.\] \[approved by manufacturer.\]

C. Failure Criteria: Not limited to the following:

1\. Section joint weatherstripping loosening.

2\. Gap between bottom of closed door and floor slab.

3\. Motor operator malfunctioning.

4\. Rail supports losing rigidity or loosening.

5\. Paint peeling or flaking.

[PART 2: PRODUCTS]{.underline}

2.1 MATERIALS:

A. Lumber: Softwood of \[[ ]{.underline}\] species, kiln dried,
preservative treated.

B. Plywood: \[Softwood\] \[Fir\] \[High density overlaid\] plywood with
\[ply\] \[lumber\] core, \[waterproof glue,\] \[1/4\] inch thick.

C. Hardboard: Shall be according to ANSI A 135.4 Class 1, \[smooth
faced\] \[smooth one face\] tempered hardboard, exterior use, \[1/4\]
inch thick.

D. Sheet Steel: Shall be according to ASTM \[A 526;\] \[A 446;\]
galvanized to \[1.25\] oz/sq ft \[flat.\] \[roll formed with \"v\"
groove for ribbed effect.\]

E. Aluminum Sheet: Shall be according to ASTM \[B 209;\] \[5005\] alloy,
\[H14\] temper, \[plain\] \[stucco embossed\] surfaces.

F. Aluminum Extrusions: Shall be according to ASTM \[B 221;\] \[6063\]
alloy, \[T6\] temper.

G. Glass Fiber Sheet: \[Opaque,\] \[Translucent,\] glass fibers bonded
in polyester resin \[with polyvinylchloride film coating,\] \[1/4\] inch
thick, \[[ ]{.underline}\] color \[as selected.\]

H. Insulation: \[Fibrous glass batt, unfaced;\] \[Rigid \[polystyrene\]
\[polyurethane\] same thickness as core framing members \[bonded to
facing\] which will provide a \"U\" factor of 0.14 or less.

I. Glass: \[\[Float glass,\] \[Wire glass,\] \[Tempered glass,\]
\[Polycarbonate,\] \[1/4\] inch \[See Specification Section [
]{.underline}\].

J. Glazing Material: \[Preformed neoprene.\]

K. Weatherstripping: Resilient \[and hollow\] \[rubber\] \[neoprene\]
\[vinyl\] strip.

L. Metal Primer Paint: \[Zinc chromate\] type.

M. Wood Primer Paint: \[Exterior alkyd\] type.

2.2 COMPONENTS:

A. Flush Wood Panels: Construction of lumber core and \[plywood\]
\[hardboard\] faces.

B. Panelled Wood Panels: Construction of lumber stiles and rails, and
\[plywood\] \[hardboard\] panel infill; stile and rail joints \[mortised
and tenoned;\] \[glued and steel dowelled;\] rabbeted weather joints at
meeting rails.

C. Flush Steel Panels: Outer steel sheet of \[16\] gage thick, \[flat\]
\[v‑grooved\] profile; inner \[steel\] sheet of \[16\] gage thick,
\[flat\] profile; core reinforcement of [ ]{.underline} gage thick sheet
steel roll formed to \[channel\] \"Z\" shaped; rabbeted weather joints
at meeting rails; insulated.

D. Flush Aluminum Panels: Outer aluminum sheet \[[ ]{.underline}\] inch
thick; inner aluminum sheet \[[ ]{.underline}\] inch thick; \[flat\]
profile; core reinforcement of \[[ ]{.underline}\] inch \[roll formed\]
\[extruded\] aluminum; rabbeted weather joints at meeting rails;
insulated.

E. Panelled Aluminum Panels: Construction of extruded aluminum stiles
and rails; \[[ ]{.underline}\] inch thick infill panels of \[sheet
aluminum;\] \[glass fiber sheet;\] stile and rail joints \[welded;\]
\[internally reinforced with cast aluminum brackets;\] \[rabbeted
weather joints at meeting rails.

F. Glazed Lights: \[[ ]{.underline}\] glazing for \[full panel width;\]
\[three\] glazed lights per panel;\] set in place with \[resilient
glazing channel.\] \[security glazing stops.\]

G. Track: \[13\] \[11\] gage thick by \[2\] \[3\] inch wide rolled
galvanized steel track, continuous, vertical mounted; galvanized steel
mounting brackets, \[1/4\] inch thick.

H. Hinge and Roller Assemblies: Heavy duty hinges and adjustable roller
holders of galvanized steel; floating hardened steel ball bearing
rollers, located at top and bottom of each panel at meeting joint.

I. Lock: Inside \[center\] \[side\] mounted, adjustable keeper, spring
activated latch bar with feature to keep in locked or retracted
position; interior \[and exterior\] handle; lock \[keyed alike.\]
\[keyed differently.\] \[master keyed.\] \[Five‑pin brass cylinder lock
with bars engaging tracks at [both]{.underline} jambs.\] \[Provide only
when door is specified without electric door opener.\] \[Key locks as
required by the authority having jurisdiction.\]

J. Door Panel Weatherstripping: At bottom of door panel, full width;
\[double\] contact resilient. Adjustable sealing strip on top section.

K. Jamb Weatherstripping: Roll formed \[steel\] \[aluminum\] fitted full
height of jamb with integral resilient weatherstripping in moderate
contact with door panels.

L. Lift Mechanism: Heavy‑duty torsion springs on continuous, ball
bearing solid cross head or shaft, with braided galvanized steel lift
cables having a minimum safety factor of 5 to 1.

M. Hood: \[20\] gage thick sheet steel, internally reinforced for
stiffening; enclosed cross head shaft, top, front, and ends, including
chain pulley \[and motor.\]

N. Electric Operator: \[NEMA Type \[1\] \[4\]\] \[UL approved\] motor;
\[\[side\] \[center\] mounted on cross head shaft;\] \[center mounted
draw bar assembly;\] adjustable safety friction clutch; brake system
actuated by independent voltage solenoid controlled by motor starter;
enclosed gear driven limit switch; enclosed magnetic cross line
reversing starter, mounting brackets and hardware.

O. Control Station: Standard \[three\] \[one\] button (open‑close‑stop)
\[momentary\] \[continuous hold\] type control for each electric
operator; \[24\] volt circuit; \[surface\] \[recess\] mounted. \[Include
key operated switch located at \[inside door jamb.\] \[exterior location
indicated.\]

P. Radio Control Loop Detector \[and Treadle:\] \[[ ]{.underline}.\]

Q. Safety Edge: At bottom of door panel, full width;
\[electromechanical\] \[pneumatic\] sensitized type, wired to \[stop\]
\[reverse\] door upon striking object; hollow \[neoprene\] \[rubber\]
covered to provide weatherstrip seal.

2.3 FINISHES:

A. Exterior \[Wood:\] \[Steel:\] \[Painted with primer.\] \[Prepared for
\[paint\] \[transparent\] finish.\]

B. Interior \[Wood:\] \[Steel:\] \[Painted with primer.\] \[Prepared for
\[paint\] \[transparent\] finish.\]

C. Precoated \[Steel:\] \[Aluminum:\] Shop precoated with \[[
]{.underline}\] coating of \[[ ]{.underline}\] color.

D. Anodized Aluminum: \[[ ]{.underline}\] with \[[ ]{.underline}\]
color.

E. Glass Fiber Sheet: \[[ ]{.underline}\] color.

[PART 3: EXECUTION]{.underline}

3.1 EXAMINATION:

A. Verification of Conditions: Verify that wall openings are ready to
receive work and opening dimensions and tolerances are within limits.

3.2 PREPARATION:

A. Requirements: Prepare opening to permit correct installation of door
unit and air and vapor barrier seal. Apply \[sealer.\] \[conditioner.\]

3.3 INSTALLATION:

A. Requirements: Doors shall be installed \[according to the
manufacturer\'s instructions\] \[by the manufacturer or his authorized
representative, according to approved installation drawings and
instructions.\]

B. Anchors: Use anchorage devices to securely fasten assembly to wall
construction and building framing without distortion or stress.

C. Bracing: Securely brace door tracks suspended from structure. Secure
tracks to structural members only.

D. Alignment: Fit and align door assembly including hardware, level and
plumb, to provide smooth operation.

E. Electrical Service: Coordinate installation of electrical service.
Complete wiring from disconnect to unit components.

F. Sealants: Coordinate installation of sealants and backing materials
at frame perimeter according to Section 07920 ‑ Sealants and Caulking.

G. Trim: Install perimeter trim and \[closures.\]

H. Glass: Install glass and glazing watertight.

3.4 TOLERANCES:

A. General: Maintain dimension tolerances and alignment with adjacent
work.

B. Variation from Plumb: \[1/16\] inch maximum.

C. Variation from Level: \[1/16\] inch maximum.

D. Longitudinal or Diagonal Warp: Plus or minus \[1/8\] inch \[[
]{.underline}\] from 10 feet straight edge.

3.5 ADJUSTING:

A. Requirements: Doors shall be weathertight, free of distortion,
lubricated and adjusted to operate freely.

3.6 CLEANING:

A. Requirements: Clean doors, frames \[and glass.\] Remove labels and
visible markings.

[PART 4: MEASUREMENT AND PAYMENT]{.underline}

4.1 METHOD OF MEASUREMENT:

A. Units: The work described in this section will not be measured for
payment.

4.2 BASIS OF PAYMENT:

A. Payment: No direct payment for the work described under this section
will be made. The Contractor shall include consideration for this item
in the bid price for other items of the Contract.

END OF SECTION