\* \* \* \* \* \* \* \* \* \*

READ AND **REMOVE THIS PAGE** BEFORE PLACING

THE SPECIFICATION SECTION IN THE CONTRACT

\* \* \* \* \* \* \* \* \* \*

[DIVISION 16: ELECTRICAL]{.underline}

SECTION 16520 - EXTERIOR LUMINAIRES

USE: Furnishing and installing exterior lighting fixtures, ballasts, and
lamps.

**NOTES TO SPECIFIER:**

A. Options within paragraphs are identified by enclosure in brackets;
blank spaces enclosed by brackets \[\_\_\_\_\_\] provide for information
to be inserted, as appropriate, to individual projects.

B. **TO AVOID CONFLICTING REQUIREMENTS AND COSTLY MISTAKES,** the
specifier must edit (delete, substitute or add to the text). The
remaining paragraphs must be renumbered.

C. DELETE FOR FINAL COPY: Notes to the Specifier, located between lines
of asterisks; all \[brackets\], [underlining]{.underline}, **boldface**,
and *italics*, within the paragraphs; and this page. (Open Reveal Codes
\[alt F3\] to do this accurately.)

D. [To Edit "(Footer B)":]{.underline} (Corel 8). **ENTIRE FOOTER SHOULD
BE BOLDED.** Click in the footer and delete the "Project Name (ftr B)"
text and replace it with the **Name of the Project (upper and lower
case)**. Replace date with current MM/YY (WITHOUT BRACKETS).

E. The Guide Specifications are intended to be continuously reviewed and
revised. User's technical comments are appreciated. Also, other related
or similar specification that are written "from scratch" that could
benefit others, or other questions can be sent to NSTC A/E Group, ST
110, or call (303) 987-6868.

**DRAWING DATA REQUIRED:**

**REVISIONS OF THIS SECTION:**

CSI format, editorial changes: 12/01

Metric:

Technical Update: 2/97

**SECTION 16520**

**EXTERIOR LUMINAIRES**

**[PART 1: GENERAL]{.underline}**

**1.1 SUMMARY**

** A. Section Includes: \[Furnishing\] \[and\] \[installing\] exterior
luminaires (lighting fixtures), ballasts, and lamps. The \"type\" letter
used for reference to various fixtures corresponds to the alphabetical
letter used to identify fixtures on the drawings.**

**1.2 DEFINITIONS**

** A. Lighting Fixtures Mounting Height: The distance from the ground
level to the following points:**

**  1. For Wall Mounting: To the center of the outlet box.**

** 2. For Eave or Pole Mounting: To the lowest point on the fixture.**

**1.3 SUBMITTALS**

** A. General: Submittals shall be according to \[Section 01009 -
General Information and Requirements.\] \[Section 01300 - Submittals.\]
\[Section 01365 - Certificates of Conformance.\]**

** B. Manufacturer\'s Literature: Submit \[\_\_\_\] copies of the
manufacturer\'s technical data for the light fixtures to be used on this
project.**

** C. Photometric Data: Submit \[\_\_\_\] copies of light distribution
(isofootcandle) curves, candlepower distribution tables and
manufacturer\'s recommended spacing/mounting height data for all
lighting fixtures \[except the following:**

**  1. Type \[\_\_\_\]**

** 2. Type \[\_\_\_\]**

** D. Shop Drawings: Submit \[\_\_\_\] copies of shop drawings for the
lighting fixtures to be used on this project showing dimensions,
construction details, installation details, accessories, and, where
applicable, suspension and lowering mechanisms, for the following
lighting fixtures:**

**  1. Type \[\_\_\_\]**

** 2. Type \[\_\_\_\]**

**1.4 QUALITY ASSURANCE**

** A. Labeling Requirements: Lighting fixtures and ballasts shall be
Underwriters Laboratories, Inc. (UL) listed and labeled. Fluorescent
ballasts shall be CBM/ETL labeled. UL listing and labeling will not be
required if it can be shown that fixtures and ballasts meet the
requirements of another nationally recognized testing laboratory
(NRTL).**

**[PART 2: PRODUCTS]{.underline}**

**2.1 MATERIALS**

** A. General: Lighting fixtures and accessories shall be constructed of
the manufacturer\'s standard materials, as listed in published product
information; types and sizes shall be as indicated or as required for
the installation.**

** B. Lamp Requirements: Lighting fixtures shall be furnished complete
with lamps of the quantity and type specified.**

** C. Photometrics: Shall be the published certified results of tests by
an independent photometric testing laboratory.**

** D. Lighting Fixture Mounting Arms: Shall be of the type and length
indicated. In addition, mounting arm shall be compatible with the type
of fixture and pole supplied.**

** E. Lamp Wattage Label: Each incandescent fixture shall be indelibly
stamped or labeled to show the manufacturers\' restriction on the
largest wattage of lamp permissible.**

**\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\***

**BELOW PARAS ARE EXAMPLES ONLY. EDIT TO SUIT PROJECT.**

**\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\***

** F. Incandescent Fixtures: Shall be as follows:**

**  1. Type K lighting fixture: Shall be recessed, 12 inches square
(nominal) with polished reflector, Fresnel glass lens, and white
finished trim frame suitable for installation in a gypsum board ceiling.
Fixture shall be UL listed for use in damp locations. Fixture shall be
equipped with a side mounted pre-wired junction box UL listed for
through branch circuit wiring. Unit shall be rated 150 watts (minimum),
120V, and shall be lamped with one 100 watt, A21 lamp.**

** 2. Type M lighting fixture: Shall be a two-lamp floodlight suitable
for use in wet locations. Lampholders shall be gasketed and shall be
suitable for 150 watt PAR lamps. Furnish and install two 150 watt PAR 38
lamps.**

** G. Fluorescent Fixtures: Shall be as follows:**

**  1. General: Unless otherwise specified, body, reflectors, wiring
cover, end caps, door frame, hinges and latches shall be steel, not less
than 24 ga for wiring cover and 22 ga for all other parts. Body and
reflectors shall be die formed and shall have embossed ribs or flanges
for rigidity. Steel parts shall be pretreated with a multi-stage
phosphate (or other similar) under-finish to enhance paint adhesion and
corrosion resistance. Steel parts shall be finished white with a high
gloss baked enamel or baked dry polyester powder coating of 85%
(minimum) reflectance.**

** 2. Ballast: Unless otherwise specified, ballasts shall be rapid
start, high power factor, Class P with A sound rating and catalog-listed
suitable for cold weather (-20 degrees F) operation.**

** 3. Type F Lighting Fixture: Shall be a wall mounted linear
fluorescent unit with high impact acrylic opal diffuser. Housing shall
be factory bronze finished extruded aluminum 4 inch x 5 inch x 50 inch
long (nominal) mounted parallel to wall on 6 inch (nominal) arms.
Diffuser shall be aimed down. Fixture shall be suitable for operation at
120V and shall include one F40 CW (35 watt nominal) fluorescent lamp.
Fixture shall be suitable for use in wet locations.**

** H. H-I-D Fixtures: Shall be as follows:**

**  1. Type L Lighting Fixture: Shall be a wall mounted unit with a
one-piece die-cast aluminum housing and a gasketed precision molded
prismatic polycarbonate refractor. Housing shall contain a HPF reactor
ballast designed to operate at 120V and shall contain aluminum reflector
on top and back. Fixture shall mount on standard 4 inch outlet box with
at least 2 bolts. Fixture shall be lamped with one 150 watt high
pressure sodium lamp. Finish shall be factory bronze.**

** 2. Type N lighting fixture shall be a pole mounted \"cobra head\"
unit mounted on a wood pole. Housing shall be precision die-cast
aluminum and is to be furnished complete with power module to which are
attached the major electrical components; power door is to be held by a
single captive screw. Fixture shall be prewired; power module shall be
removable through the use of quick disconnect plugs. Optical assembly
shall consist of a die-cast aluminum lens holder with aluminum
reflector, a heat and impact resistant flat glass lens and a porcelain
mogul base screw shell socket. Socket holder shall be adjustable. The
optical assembly shall contain an activated charcoal filter. Reflector
shall be designed to produce an ANSI, IES M-C-III light distribution.
Ballast shall be of the regulator type suitable for use at 120V. Fixture
shall be lamped with one 250 watt high pressure sodium lamp. Mounting
arm shall be 4 ft long, 2 in. pipe size suitable for mounting on a wood
pole. Pole shall be pressure treated wood with no more than 3 in.
deflection from top to bottom. Bottom of pole shall extend at least 5
ft. into the ground and shall be encased in 2 ft. dia. (min.) concrete.
Mount fixture at 30 ft. above grade.**

** I. Poles: Shall be as follows:**

**  1. Wind Load: Pole, light and support combination shall be capable
of withstanding at least 90 mph continuous wind load.**

** 2. Hardware: Pole shall include all brackets, nuts, bolts and other
hardware necessary for a complete installation.**

** 3. Mounting Arms: Shall be as specified with fixture and shall be
compatible with pole and fixture supplied.**

** 4. Concrete Bases: Metal poles shall be mounted on concrete bases as
shown on the drawings.**

** 5. Mounting Bolts: Shall be sized as recommended by the pole
manufacturer and shall be galvanized steel with corrosion-resistant nuts
and washers.**

** 6. Wood Poles: Shall be pressure treated according to Section 06312 -
Preservative Treated Poles and Posts. Poles shall be set in concrete as
shown on the drawings.**

**[PART 3: EXECUTION]{.underline}**

**3.1 INSTALLATION**

** A. General: Install lighting fixtures and accessories as indicated,
complying with the manufacturer\'s written instructions, applicable
requirements of codes and standards, and according to recognized
industry practices.**

** B. Alignment: Where lighting fixtures are shown on the drawings to be
in line in any direction, locate them so that they will be aligned with
building features and with each other.**

** C. Poles: Mount poles plumb and level. Mounting bolt pattern shall be
as recommended by manufacturer. Locate mounting arms in directions shown
on drawings.**

** D. Lamping: Install specified lamps in lighting fixtures.**

**3.2 CLEANING**

** A. Requirements: When dust, dirt, grime or adhesives (other than name
or data labels) exists on lamps, lenses, reflectors or exposed parts,
remove with soft cloth and mild suds and rinse clean.**

**[PART 4: MEASUREMENT AND PAYMENT]{.underline}**

**\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\***

**WHEN A \"LUMP SUM\" CONTRACT IS USED, DELETE THE TITLE PART 4:
MEASUREMENT AND PAYMENT, AND BOTH ARTICLES FROM THIS SECTION.
MEASUREMENT AND PAYMENT WILL BE ADDRESSED IN PART 4 OF SECTION 01010 -
SUMMARY OF WORK.**

**\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\***

**4.1 METHOD OF MEASUREMENT**

** A. Units: The work described in this section will not be measured for
payment.**

**4.2 BASIS OF PAYMENT**

** A. Payment: No direct payment for the work described under this
section will be made. Consideration for this item shall be included in
the bid price for other items of the Contract.**

**END OF SECTION**