<!-- Title: 00:00:03  Thu Jun 17 2004 -->
<!-- Crewchief: Bruce / KC / Bruce -->
<!-- Op1: &nbsp; -->
<!-- Op2: &nbsp; -->
<!-- Op3: &nbsp; -->
<!-- Op4: &nbsp; -->
<!-- Op5: &nbsp; -->
<!-- Op6: &nbsp; -->
<!-- Notes: -->
All systems are running fine the cot system O2 level is at 184, mechanical rooms are running fine no unusual leaks or noises, Switched the nitrogen evaporator.


<!-- Date: Thu Jun 17 05:09:40 2004 -->
All systems are running fine ther are no problems at this time,The cot O2 level is at 206.
<!-- Author: Bruce -->


<!-- Date: Thu Jun 17 05:59:50 2004 -->
<table border=0><td><tr><td bgcolor=#e0e030>FESS is ready to go so I have turned off AC2, AC3, BF1 and EF2. I'm leaving the RF fans running. I asked the Mechanics to waste no time with this project due to the humidity concerns.</td></tr></td></table>
<!-- Author: Bill Noe -->
<!-- Comment: Thu Jun 17 06;12;07 comment by...Bill Noe -->
The guys working on PF1 have discovered a condensate drain problem with AC2. The filters are soaking wet and there was water running out the door when they opened it. I will pull the plug and then contact FESS.

<!-- Comment: Thu Jun 17 06;26;16 comment by...Bill Noe -->
I removed the pipe plug on the condesate drain piping for AC2 and water came gushing out for 2 min and was still running strong when the mosquitoes drove me away.


<!-- Comment: Thu Jun 17 09;06;56 comment by...Bill Noe -->
<table border=0><td><tr><td bgcolor=#e0e030>PF1 is repaired!</td></tr></td></table>
<!-- Comment: Thu Jun 17 15;58;10 comment by...Bill Noe -->
This drain has been cleared (finally) and the FESS mechanic will put the piping back together and call it good.
<!-- Date: Thu Jun 17 07:28:03 2004 -->
I finished checking the CDF systems checklist and everything is ok.
<!-- Author: KC -->



<!-- Date: Thu Jun 17 09:10:21 2004 -->
HVAC Summary:<p>PF1 has been rebuilt and is now running. We tested it in high speed and low speed and the system is running now in "Low HVAC". The condensate drain for AC2 still has the plug removed and the mechanics are going to rod out the drain. EF2 is back on and running and there is pleanty of flow but the instrument is still reading 1 (one) SCFH. This is bogus and KC is troubleshooting this now. So for the most part we are back to normal on the HVAC system.
<!-- Author: Bill Noe -->
<!-- Comment: Thu Jun 17 11;42;40 comment by...Bill Noe -->
KC and Wnyae hvae fnuod nniohtg wnrog wtih the intsrmuenattion for EF2 so the tohghut now is taht smohtnigeg has bolkced up the pbroe. Istveniagtin is udnreawy.
<!-- Comment: Thu Jun 17 12;00;13 comment by...Bill Noe -->
KC and I removed the probe and inspected the duct and can find nothing blocking air flow to the probe. The instrument has failed somehow. I believe it is electrical.
<!-- Comment: Thu Jun 17 15;56;19 comment by...Bill Noe -->
Wayne and KC have given us a run status for EF2. I will tie it into the alarm scheme tomorrow. In the meantime the old alarm is setup in 4-mation to read 450 all the time. It's all good...
<!-- Date: Thu Jun 17 09:12:26 2004 -->
Upon Craig Olson's request I turned of the "RF Fans" in the Chall.
<!-- Author: Bill Noe -->




<!-- Date: Thu Jun 17 13:59:06 2004 -->
Hallelujah!!! Not one but TWO technical representatives from Trane are here to do the preflight checkout on the new chiller #4. If all goes well then they will return to start it up tomorrow.
<!-- Author: Bill Noe -->
<!-- Comment: Thu Jun 17 15;54;38 comment by...Bill Noe -->
We passed inspection with flying colors and the Trane guys said they would be back tomorrow to startup the unit.




<!-- Date: Thu Jun 17 17:03:05 2004 -->
Bill returned coll. hall HVAC to full at Rob R. request about 4:00pm.
<!-- Author: KC -->


<!-- Date: Thu Jun 17 17:18:17 2004 -->
Bruce on duty.
<!-- Author: Bruce -->


<!-- Date: Thu Jun 17 17:27:48 2004 -->
Gas and cryo readings taken all systems are running fine at this time,mechanical rooms are running fine also no unusual leaks or noises.
<!-- Author: Bruce -->


<!-- Date: Thu Jun 17 18:28:03 2004 -->
I installed the two flex hoses on the argon/Co2 trailers and made up a spare regulator set-up the spare regulator is taged and is over in the mixing shed, Also the mixing rack air intake screen was pluged up with dandelion fur and dirt I cleaned all the debris off the screen it is clear as of today at this time.
<!-- Author: Bruce -->