<!-- Title: 00:34:27  Fri Mar 21 2003 -->
<!-- Crewchief: Steve - owl -->
<!-- Op1: Dean - evening -->
<!-- Op2: &nbsp; -->
<!-- Op3: &nbsp; -->
<!-- Op4: &nbsp; -->
<!-- Op5: &nbsp; -->
<!-- Op6: &nbsp; -->
<!-- Notes: -->
Solenoid is online to store #2328 (record luminosity). Monitoring process systems. 


<!-- Date: Fri Mar 21 04:04:36 2003 -->
Readings taken and tours made. No problems. 
<!-- Author: Steve -->


<!-- Date: Fri Mar 21 06:28:52 2003 -->
At CDF Control Room's request-------turned hvac fans to low and turned RF fans off for an access to the enclosure.------ silenced hvac fan alarms also.
<!-- Author: Jim L -->
<!-- Comment: Fri Mar 21 09;44;31 comment by...KC -->
About 9:00 am I turned the hvac back to full at D. Hahn's request. The first time  the rf fans did not turn on. The 2nd time bf-1 did not turn on. I reset the breaker on bf-1 and it still does not turn on. Craig and I are looking into it.
<!-- Comment: Fri Mar 21 10;38;44 comment by...KC -->
Craig called fes.
<!-- Comment: Fri Mar 21 11;49;37 comment by...KC -->
Craig said that FESS thinks that the  problem with BF-1 is in the fan motor. FESS will have to wait for some shutdown time to work on it because it is in a radiation area.
<!-- Date: Fri Mar 21 08:46:10 2003 -->
FES guys are working on chill water pump 3. Bill wants to run it when they finish and keep an eye on it.
<!-- Author: KC -->
<!-- Comment: Fri Mar 21 10;18;24 comment by...KC -->
<table border=0><td><tr><td bgcolor=#e0e030>Craig said that the fes guys said do not turn on chill water 3 pump until Monday to give the gasket sealer time to dry.</td></tr></td></table>
<!-- Comment: Fri Mar 21 10;52;03 comment by...KC -->
<table border=0><td><tr><td bgcolor=#e0e030>B. Noe called and said if an emergency occurs then it is ok to valve chilled water pump 3 in and run it, if it has been repaired.</td></tr></td></table>
<!-- Comment: Fri Mar 21 15;08;51 comment by...KC -->
The FESS guys Dan and John have finished the chiller pump 3. I asked Steve to ask them to leave it unlocked so that if there is an emergency we can run it.  
<!-- Date: Fri Mar 21 09:11:21 2003 -->
Filled clc west from 21.08 to 22.54 psia for Dmitri. Butane bottle heater had been left on from previous fill. I closed all valves and turned heater off.
<!-- Author: KC -->






<!-- Date: Fri Mar 21 11:22:09 2003 -->
There was a gas alarm that I couldn't reach in time. Don't know what it was.
<!-- Author: KC -->



<!-- Date: Fri Mar 21 12:46:55 2003 -->
The collision hall DP alarm went off briefly.  So did the Argon trailer loss alarm.  Historical for both show them to have just barely tripped the alarm and then returned to normal.  I'll keep an eye on them.
<!-- Author: WB -->



<!-- Date: Fri Mar 21 16:23:02 2003 -->
Dean on duty , reading taken everything is normal
<!-- Author: Dean -->


<!-- Date: Fri Mar 21 16:33:36 2003 -->
flammable gas alarms imu north-east was reading trouble, reset alarm ok, bled all three chillers transducer lines
<!-- Author: Dean -->


<!-- Date: Fri Mar 21 21:43:25 2003 -->
the lcw water system added some water to the system and the deionizer bottle reading is low
<!-- Author: Dean -->
<!-- Comment: Fri Mar 21 21;59;58 comment by...Dean -->
reading is back to normal


<!-- Date: Fri Mar 21 22:57:34 2003 -->
<table border=0><td><tr><td bgcolor=#e0e030><pre>gas alarm, tank # 1 outlet valve did not open ,I open the valve </pre></td></tr></td></table>
<!-- Author: Dean -->