<!-- Title: 05:34:38  Mon Jun  2 2008 -->
<!-- Crewchief: Steve - day -->
<!-- Op1: Jim L - night -->
<!-- Op2: &nbsp; -->
<!-- Op3: &nbsp; -->
<!-- Op4: &nbsp; -->
<!-- Op5: &nbsp; -->
<!-- Op6: &nbsp; -->
<!-- Notes: -->
Process systems are running well.


<!-- Date: Mon Jun 2 05:59:59 2008 -->
CDF systems checklist completed. IMU northeast gas head needed a reset.
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 06:54:26 2008 -->
Conductivity for SVX is .2µS/cm and ISL is .3µS/cm. pH for SVX is 6.60 and ISL is 5.86.
<!-- Author: KC -->


<!-- Date: Mon Jun 2 10:08:34 2008 -->
Scico called to say they are ending the store.
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 11:31:17 2008 -->
Gamma alarm CEM SE arch. Informed the Scico.
<!-- Author: Steve -->
<!-- Comment: Mon Jun  2 11;50;35 comment by...Steve -->
Steve Hahn changed the limits so it is green again.
<!-- Date: Mon Jun 2 11:42:45 2008 -->
TE66 came into alarm. Chiller 3 has been started up.
<!-- Author: Steve -->
<!-- Comment: Mon Jun  2 12;30;56 comment by...Bill Noe -->
Chiller 5 won't stay running. It is valved out. Chiller 4 and 3 are running OK.
<!-- Date: Mon Jun 2 11:48:22 2008 -->
I tested the override logic for rack SVNET (aka SVNE1). I now understand what we need.
<!-- Author: Bill Noe -->




<!-- Date: Mon Jun 2 12:31:36 2008 -->
SVX chiller setpoint has been changed to -10.
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 12:50:07 2008 -->
Gas alarm: SWX flow too low. I raised the flow on SWX and NWX.
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 13:11:43 2008 -->
TE66 came into alarm again, so I fired up chiller #2.
<!-- Author: Steve -->
<!-- Comment: Mon Jun  2 13;13;19 comment by...Steve -->
I noticed that compressor 1 on chiller #4 was off.

<!-- Comment: Mon Jun  2 13;23;22 comment by...Steve -->
It was off on high oil temp. I cleared the diagnostics and it's back running again.


<!-- Date: Mon Jun 2 13:31:15 2008 -->
Started an A/E mix to tank 1.
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 14:38:57 2008 -->
I followed CDF trailer hook-up procedure and connected ethane trailer #167 in mix shed station #2.
<!-- Author: KC -->


<!-- Date: Mon Jun 2 14:42:19 2008 -->
I connected helium trailer #466 to the east helium trailer slot and purged the line, then turned the trailer valve off.
<!-- Author: KC -->


<!-- Date: Mon Jun 2 14:46:55 2008 -->
<table border=0><td><tr><td bgcolor=#e0e030>Argon carbon dioxide trailer #500 is empty and needs to be removed from mix shed station #7. Argon carbon dioxide trailer #87 located in mixshed station #5 needs to be moved to mix shed station #7. </td></tr></td></table>
<!-- Author: KC -->


<!-- Date: Mon Jun 2 14:49:27 2008 -->
I vacuumed chiller #5 coils inside and outside. I also vacuumed the screens.
<!-- Author: KC -->


<!-- Date: Mon Jun 2 15:13:04 2008 -->
Water alarm: this time TE81 went over 67 degrees. It came back down to 65 right now. CV5 is in loop and operating. 
<!-- Author: Steve -->


<!-- Date: Mon Jun 2 18:45:28 2008 -->
Mix is completed.
<!-- Author: Jim L -->


<!-- Date: Mon Jun 2 20:47:27 2008 -->
Late note: Walk-a-round and readings done.
<!-- Author: Jim L -->


<!-- Date: Mon Jun 2 21:35:45 2008 -->
The Scico called to ask about a high temp alarm on the Plug Temp Controls. --> WE have no alarms!--> He's contacting a plug expert.
<!-- Author: Jim L -->


<!-- Date: Mon Jun 2 23:50:54 2008 -->
PSM ALARM --> West END Plug PS off.-->Called  the Scico and he asked to Trip the 400Hz and reset it--Done, But no good.--> He asked to do it again --> Still no good.--=>So then we decided to trip the 60Hz and it tripped the Solenoid.--> Caught it at 4000Amps and powering back up.---> West End Plugs still out ---> He is calling a plug expert.
<!-- Author: Jim L -->
<!-- Comment: Mon Jun  2 23;57;57 comment by...Jim L -->
They must be rebooting VOLTMAN !
<!-- Comment: Tue Jun  3 00;03;59 comment by...Jim L -->
SOLENOID is back at full power.
<!-- Date: Mon Jun 2 23:55:36 2008 -->
Noticed that S6's heart beat was dead.-->It must have rebooted it self --> i LOGGED IT IN AND it's working again.
<!-- Author: Jim L -->



<!-- Date: Tue Jun 3 00:02:09 2008 -->
Noticed that CONWT has a single fan failure --> Upper-mid fan is OFF.
<!-- Author: Jim L -->



<!-- Date: Tue Jun 3 02:02:43 2008 -->
PSM ALARM --> same as before-- West end plug----> Steve H is debugging it.
<!-- Author: Jim L -->


<!-- Date: Tue Jun 3 02:04:20 2008 -->
Admin. Scan started on all Nodes.
<!-- Author: Jim L -->


<!-- Date: Tue Jun 3 04:38:42 2008 -->
ISL and L00 ALARMS --> Ceans are off--> Scico said it was them.
<!-- Author: Jim L -->