<!-- Title: 00:01:31  Thu Feb 15 2007 -->
<!-- Crewchief: Jim H. night -->
<!-- Op1: KC day -->
<!-- Op2: &nbsp; -->
<!-- Op3: &nbsp; -->
<!-- Op4: &nbsp; -->
<!-- Op5: &nbsp; -->
<!-- Op6: &nbsp; -->
<!-- Notes: -->
Store #5228 is colliding. Monitoring process systems.


<!-- Date: Thu Feb 15 02:12:08 2007 -->
I added 8 bottles of alcohol to the barrel. There's 14 bottles left in the cabinet.
<!-- Author: Jim H. -->




<!-- Date: Thu Feb 15 05:50:46 2007 -->
There was a problem when gas tank 3 went empty and tried to switch to tank 1. I manually opened the outlet valve for tank 1 and cleared the alarm.
<!-- Author: Bill Noe -->


<!-- Date: Thu Feb 15 05:52:08 2007 -->
I have started a mix to tank #3.
<!-- Author: KC -->
<!-- Comment: Thu Feb 15 10;38;42 comment by...KC -->
Mix to tank #3 is complete.
<!-- Date: Thu Feb 15 06:13:48 2007 -->
I walked thru the CDF systems checklist and all items are doing fine.
<!-- Author: KC -->


<!-- Date: Thu Feb 15 06:39:45 2007 -->
Called Wilson Cross of "BEAMS", and requested to get our North Dry Engine over-hauled(no rush).--> He said OK will schedule it.
<!-- Author: Jim L -->
<!-- Comment: Fri Feb 16 06;52;57 comment by...Jim L -->
Engine guys here after lunch working on the north dry engine.
<!-- Date: Thu Feb 15 07:25:08 2007 -->
ISL flow loops FT-CCE1SUP fluxuates between low warning alarm, which is set at 1.7, and ok. I informed the 2nd floor control room and Mary said that she would have Urich come talk to me about it when he comes in.
<!-- Author: KC -->


<!-- Date: Thu Feb 15 07:57:00 2007 -->
Silicon and rack alarms were caused by the silicon guys working on the ISL flows. 
<!-- Author: cahill -->


<!-- Date: Thu Feb 15 08:15:37 2007 -->
SILICON ALARMS---RACK ALARMS---PSM ALARMS--->silicon guys are working on it and tripped all the silicon racks/power supplies.
<!-- Author: Jim L -->
<!-- Comment: Thu Feb 15 08;26;15 comment by...Jim L -->
After the required 10 minutes reset all the silicon racks and that caused a Generator 3 alarm on current--->reset and OK for now.


<!-- Date: Thu Feb 15 08:56:55 2007 -->
I silenced the SVX chiller TE-CHLR 1 for the silicone guys.
<!-- Author: KC -->


<!-- Date: Thu Feb 15 09:22:11 2007 -->
RACK ALARMS-----PSM ALARMS---GEN ALARMS----> silcon guys working on ISL fow tripped all the SVX racks which caused gen and psm alarms.---> sinenced for now
<!-- Author: Jim L -->


<!-- Date: Thu Feb 15 10:20:32 2007 -->
Silicon guys seam to have it running now(lowered ISL supply pressure) so, I am resetting all the SVX Racks.
<!-- Author: Jim L -->
<!-- Comment: Thu Feb 15 10;21;54 comment by...Jim L -->
Also unsilenced all alarms!



<!-- Date: Thu Feb 15 10:39:28 2007 -->
SVX ALARM-->PS-TRIP--- B0W7 layer ) and others. They are on it.
<!-- Author: Jim L -->


<!-- Date: Thu Feb 15 11:15:37 2007 -->
Cleared CLC-W flammable gas trouble alarm with a reset. 
<!-- Author: KC -->


<!-- Date: Thu Feb 15 13:29:44 2007 -->
SVX ALARM ---> Caen ps trip ---> their still working it.
<!-- Author: Jim L -->


<!-- Date: Thu Feb 15 13:31:55 2007 -->
Dervin and company replaced a power supply in rack #1RR12E-3 and fan packs in 1RR21F and 1RR27H.
<!-- Author: KC -->


<!-- Date: Thu Feb 15 17:26:57 2007 -->
The CDF systems checklist and mechanical rooms are normal at this time.
<!-- Author: Jim H. -->


<!-- Date: Thu Feb 15 18:03:11 2007 -->
SVX alarm, CAEN PS tripped off. I talked to Willis and the silicon experts are here working on this.
<!-- Author: Jim H. -->