<!-- Title: 00:01:26  Sun May 23 2004 -->
<!-- Crewchief: KC nights -->
<!-- Op1: Dean days -->
<!-- Op2: &nbsp; -->
<!-- Op3: &nbsp; -->
<!-- Op4: &nbsp; -->
<!-- Op5: &nbsp; -->
<!-- Op6: &nbsp; -->
<!-- Notes: -->
Cot recir pump flow is 105 scfh.


<!-- Date: Sun May 23 00:56:23 2004 -->
COT recir pump flow is 104 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 01:55:43 2004 -->
COT recir pump flow is 99 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 03:06:00 2004 -->
COT recir pump flow is 99 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 03:53:31 2004 -->
Pumped wattcan from 4.2 to 1.5 microns.
<!-- Author: KC -->


<!-- Date: Sun May 23 04:05:39 2004 -->
COT recir pump flow is 85 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 04:10:45 2004 -->
I gave the cdf gas key to Joaquin Maldonado ID # 13567N from FESS electrical. He is doing pm's. He will just be scanning bar codes on the heaters and fan. His shop ext is 4744 or 3364 and pager is 72-0101. He will return the key when finished.
<!-- Author: KC -->
<!-- Comment: Sun May 23 04;32;39 comment by...KC -->
CDF gas key was returned.


<!-- Date: Sun May 23 04:55:19 2004 -->
COT recir pump flow is 86 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 06:27:49 2004 -->
cot recir pump flow is 75 scfh
<!-- Author: Dean -->


<!-- Date: Sun May 23 06:51:28 2004 -->
cdf checklist is completed everything is normal at this time
<!-- Author: Dean -->


<!-- Date: Sun May 23 07:16:14 2004 -->
started a argon/ethane mix on tank # 3, switched argon-co2 trailer 500-68 psi to trailer 474 - 1471 psi
<!-- Author: Dean -->


<!-- Date: Sun May 23 08:00:03 2004 -->
adjusted the check valve on the cot recir pump
<!-- Author: Dean -->


<!-- Date: Sun May 23 09:02:37 2004 -->
<table border=0><td><tr><td bgcolor=#e0e030>switched the o2 gas analyzer back to check all the chambers for one reading .</td></tr></td></table>
<!-- Author: Dean -->


<!-- Date: Sun May 23 09:26:05 2004 -->
the cot recir pump flow is 70 scfh
<!-- Author: Dean -->


<!-- Date: Sun May 23 11:01:01 2004 -->
<table border=0><td><tr><td bgcolor=#e0e030>the co2 regulator for the east co2 trailer is bad, the safety relief keep going off, the regulator is good up to 3000psi and the co2 trailer pressure is at 1700psi,I used the west set up on the east co2 trailer 474</td></tr></td></table>
<!-- Author: Dean -->


<!-- Date: Sun May 23 11:13:32 2004 -->
the cot recir pump flow is 60
<!-- Author: Dean -->


<!-- Date: Sun May 23 13:16:24 2004 -->
Dean called me about a Watt Can pumping problem. Rather than dick with it over the phone I came in. The plan was to use TM70 but it would not pump the WAVV down. I thought I might have to do some poking around in 4-mation but I was able to use TM90 with PV90 that has a bad limit switch. This method seems to work fine so we will continue this until the whole system can be evaluated and repairs made.
<!-- Author: Bill Noe -->


<!-- Date: Sun May 23 18:12:47 2004 -->
Completed cdf system checklist and everything is ok.
<!-- Author: KC -->


<!-- Date: Sun May 23 18:15:23 2004 -->
COT recir pump flow is 64 SCFH after a tiny adjustment.
<!-- Author: KC -->


<!-- Date: Sun May 23 19:14:51 2004 -->
COT recir pump flow is 60 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 19:54:14 2004 -->
Just played with COT recir pump and flow is 73 SCFH and maybe climbing.
<!-- Author: KC -->


<!-- Date: Sun May 23 20:31:17 2004 -->
Adj. COT recir pump and flow is 90 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 22:09:52 2004 -->
COT recir pump flow is 62 SCFH.
<!-- Author: KC -->


<!-- Date: Sun May 23 23:11:23 2004 -->
COT recir pump flow is 70 SCFH.
<!-- Author: KC -->