SECTION 28 1321

ADMINISTRATIVE ACCESS CONTROL SYSTEM ROUGH-IN

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

LANL MASTER SPECIFICATION

This template must be edited for each project.  In doing so, specifier
must add job-specific requirements.  Brackets are used in the text to
indicate designer choices or locations where text must be supplied by
the designer.  Once the choice is made or text supplied, remove the
brackets.  The specifications must also be edited to delete
specification requirements for processes, items, or designs that are not
included in the project \-- and specifier's notes such as these.  To
seek a variance from requirements in the specifications that are
applicable, contact the Engineering Standards Manual
[Electrical](http://engstandards.lanl.gov/engrman/7elec/htmls/elecnew2.htm)
POC. Please contact POC with suggestions for improvement as well.\
\
When assembling a specification package, include applicable
specifications from all Divisions, especially Division 1, General
Requirements.\
\
Specification developed for ML-4 projects.  For ML-1, 2, and 3
applications, additional requirements and independent reviews should be
added if increased confidence in procurement or execution is desired;
see ESM Chapter 1 Section Z10 Specifications and Quality sections.\
\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

1.  GENERAL

    1.  Section Includes

        A.  Administrative access control system rough-in that
            originates in the telecommunications room and extends to
            each access-controlled door for LANL-furnished badge
            readers, door contacts, and contractor-furnished electric
            strikes.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Edit the following article to match project requirements.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

B.  Access controlled doors include:

    1.  Each exterior door or set of doors except at vestibules install
        the access controls on the interior door or set of doors.

    2.  Electrical room doors.

    3.  Mechanical room doors.

    4.  Telecommunications room doors.

    5.  Server room doors.

```{=html}
<!-- -->
```
2.  LANL Furnished Materials for SUBContractor INstallation

    A.  None

3.  LANL Furnished and Installed Equipment

    A.  LANL will furnish and install badge readers, power supplies, and
        control equipment.

4.  LANL PERFORMED WORK

    A.  LANL will make final wiring connections to administrative access
        control equipment.

5.  SUBMITTALS

    A.  Submit the following in accordance with [Section 01
        3300](http://www.lanl.gov/f6stds/pubf6stds/conspec/htmls/csindex.htm)
        Submittal Procedures:

        1.  Catalog Data: Submit manufacturer\'s data on power,
            signaling, control cables, electric door strikes, and panic
            bars.

        2.  Test Reports: Provide inspection and test report for each
            power, signaling, and control cable.

        3.  As-Built Drawings: Provide as-built drawings showing
            installed administrative access control system raceways,
            boxes, and cables.

6.  Quality Assurance

    A.  Conform to requirements of the National Electrical Code (NEC).

    B.  Furnish products listed and labeled by a Nationally Recognized
        Testing Laboratory (NRTL) as suitable for purposes specified and
        shown.

7.  COORDINATION

    A.  Coordinate installation of administrative access control system
        rough-in with the LANL Telecommunications Group.

    B.  Coordinate electrical requirements for electric strikes with the
        LANL Telecommunications Group. Refer to paragraph 2.4-B in this
        Section.

    C.  Complete telecommunications rooms to allow not less than 5
        working days for the LANL telecommunications group to install
        badge reader equipment rack before scheduled start of badge
        reader system installation. Coordinate schedule with the LANL
        Project Leader.

8.  Receiving, Storing and Protecting

    A.  Receive, store, and protect, and handle products and materials
        according to NECA 1 Standard Practices for Good Workmanship in
        Electrical Construction.

```{=html}
<!-- -->
```
2.  PRODUCTS

    1.  PRODUCT OPTIONS AND SUBSTITUTIONS

        A.  Refer to Section 01 2500, Substitution Procedures.

    ```{=html}
    <!-- -->
    ```
    1.  Raceways and Boxes

        A.  Provide 4-11/16 square, 2-1/8 inch deep boxes for badge
            reader outlets. Provide single-gang raised device covers
            that match the thickness of the wallboard. Provide box
            supports to prevent movement of the box.

        B.  Provide flush-mounted 10" X 10" X 4" hinged cover badge
            reader junction boxes with flush-locking latch and wood
            mounting panel. Hoffman A-TC1010F

        C.  Outside boxes must be weatherproof, R4 or R12, with
            continuous hinges.

        D.  Refer to Section 26 0553, Raceways & Boxes for Electrical
            Systems.

    2.  Cables

        A.  Furnish power, power/switch, and data cables.

        B.  For power cable use 1-twisted pair, 18 AWG stranded, UL type
            CMG, Belden 9740.

        C.  For power/switch cable use 2-twisted pairs, 22 AWG stranded,
            UL type CMG, Belden 9744.

        D.  For data cable use 2-individually shielded twisted pairs, 24
            AWG, UL Type CMP, Belden 82729.

    3.  Electric Door Strikes and panic bars

        A.  Furnish electric door strike for each access-controlled door
            or set of doors. Provide electric panic bars for access
            controlled doors as indicated on the Drawings.

        B.  Provide 24-volt door strikes and panic bars that operate on
            0.5 amperes or less, are easily serviceable, and are
            electrically compatible with the LANL-furnished access
            control system, functionally compatible with each
            access-controlled door, and with finish compatible with the
            other door hardware. (Von Duprin crash bars EL33, EL35,EL98
            and EL99 are NOT allowed. Von Duprin E996L and E360L-BE
            trims are Acceptable.)

        C.  Coordinate with Section 08 7100, Door Hardware.

3.  EXECUTION

    1.  EXISTING WORK

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Delete this article when existing construction is not affected.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

A.  Remove abandoned administrative access control system cables.

B.  Remove abandoned raceways and boxes when administrative access
    control system cables servicing boxes are abandoned or removed.
    Install blank cover for abandoned boxes not removed.

C.  Maintain access to existing administrative access control system
    connections remaining active and requiring access. Modify
    installation or provide access panels.

```{=html}
<!-- -->
```
1.  EXAMINATION

    A.  Verify interior of the building has been protected from weather.

    B.  Verify that installation of telecommunications rooms is
        complete.

    C.  Examine raceways and building finishes for compliance with
        installation tolerances and other conditions affecting
        performance of the administrative access control system. Do not
        proceed with installation until unsatisfactory conditions have
        been corrected.

2.  Raceway and Box Installation

    A.  Install a complete raceway and box system for administrative
        access control system.

    B.  Install a flush mounted 4-11/16 square, 2-1/8 inch deep badge
        reader outlet box on the strike side of each access-controlled
        door. Flush mount the outlet box with center 44 inches above the
        finished floor and approximately 12 inches from the doorframe.
        Provide single-gang raised device covers that match the
        thickness of the wallboard. Provide box supports to prevent
        movement of the box. At each exterior location provide a minimum
        12 inch x 12 inch surface around the outlet box suitable for
        mounting the LANL badge reader weather shield.

    C.  Install a flush-mounted 10" X 10" X 4" hinged cover badge reader
        junction box on the wall interior to the card reader with center
        56 inches above the finished floor and approximately 12 inches
        from the door frame.

    D.  Install a 3/4 inch conduit from each badge reader outlet box to
        the nearby badge reader junction box.

    E.  Install a 1/2-inch conduit from the badge reader junction box to
        the access-controlled doorframe for cables to the electronic
        lock and door contacts.

    F.  Install a 1-inch conduit from each badge reader junction box to
        the badge reader wireway in the entrance telecommunications
        room.

    G.  Install a 6" X 6" wireway in the telecommunications room and
        located above the cable tray. Terminate conduits from badge
        readers into the wireway. Install a 2 inch conduit from the
        wireway to the LANL badge reader equipment rack; coordinate with
        the LANL Telecommunication Group.

3.  Cable Installation

    A.  Clean foreign matter from interior of boxes and conduits before
        installing cables.

    B.  Install one power/switch cable from the access controlled
        doorframe strike location to the badge reader outlet box. Leave
        15 inches slack at both ends and 15 inches coiled slack in the
        badge reader junction box.

    C.  Install one power/switch cable from the access controlled
        doorframe contacts location to the badge reader outlet box.
        Leave 15 inches slack at both ends and 15 inches coiled slack in
        the badge reader junction box.

    D.  Install one data cable from the badge reader outlet box to the
        badge reader equipment rack. Leave 15 inches slack at the badge
        reader outlet box and enough slack to reach bottom of badge
        reader equipment rack.

    E.  Install one power cable from the badge reader outlet box to the
        badge reader equipment rack. Leave 15 inches slack at the badge
        reader outlet box and 8 feet slack at the badge reader equipment
        rack.

    F.  Uniquely identify each cable at both ends using a numbering
        scheme that complies with instructions from the LANL
        Telecommunications Group; use a tag or an indelible marker

4.  Door Strike and Panic Bar Installation

    A.  Install electric door strikes and panic bars in accordance with
        manufacturer's instructions. Have installation instructions
        available at the construction site.

    B.  Adjust electric strikes for proper fit and proper electrical and
        mechanical operation.

5.  GROUNDING

    A.  Ground badge reader raceways and boxes in accordance with
        Section 26 0526, Grounding and Bonding for Electrical Systems,
        Secondary Grounding using the raceway system as the equipment
        grounding conductor.

6.  FIELD QUALITY CONTROL

    A.  Test power, power/switch, and control cables for continuity,
        shorts, and unintentional grounds.

    B.  Verify proper labeling of cables.

    C.  Submit test and inspection report.

END OF SECTION

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Do not delete the following reference information.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

FOR LANL USE ONLY

This project specification is based on LANL Master Specification 28 1321
Rev. 2, dated July 22, 2008.