CONSTRUCTION STANDARD SPECIFICATION

SECTION 13811

lighting control equipment

[PART 1 - General 2](#__RefHeading___Toc162669851)

[1.01 RELATED DOCUMENTS 2](#__RefHeading___Toc162669852)

[1.02 SUMMARY 2](#__RefHeading___Toc162669853)

[1.03 submittals 2](#__RefHeading___Toc162669854)

[1.04 QUALITY ASSURANCE 3](#__RefHeading___Toc162669855)

[1.05 WARRANTY 3](#__RefHeading___Toc162669856)

[1.06 EXTRA MATERIALS 4](#__RefHeading___Toc162669857)

[PART 2 - products 4](#__RefHeading___Toc162669858)

[2.01 MANUFACTURERS 4](#__RefHeading___Toc162669859)

[2.02 LIGHTING CONTROL SYSEM, GENERAL 4](#__RefHeading___Toc162669860)

[2.03 RELAYS 5](#__RefHeading___Toc162669861)

[2.04 PRE-ASSEMBLED RELAY PANELS 5](#__RefHeading___Toc162669862)

[2.05 CONTROL ELECTRONICS 6](#__RefHeading___Toc162669863)

[2.06 NETWORK MANAGER 6](#__RefHeading___Toc162669864)

[2.07 SATELLITE PANELS 7](#__RefHeading___Toc162669865)

[2.08 LOW VOLTAGE WALL SWITCHES 8](#__RefHeading___Toc162669866)

[2.09 0-10V DIMMER SWITCHES 8](#__RefHeading___Toc162669867)

[2.010 OCCUPANCY SENSORS 9](#__RefHeading___Toc162669868)

[2.011 EXTERIOR PHOTOMETRIC SENSORS 9](#__RefHeading___Toc162669869)

[2.012 INTERIOR PHOTOMETRIC SENSORS 9](#__RefHeading___Toc162669870)

[2.013 DIMMABLE DAYLIGHT SENSORS 10](#__RefHeading___Toc162669871)

[2.014 LOW VOLTAGE WIRING 10](#__RefHeading___Toc162669872)

[PART 3 - Execution 10](#__RefHeading___Toc162669873)

[3.01 INSTALLATION 10](#__RefHeading___Toc162669874)

[3.02 CONTROL WIRING INSTALLATION 11](#__RefHeading___Toc162669875)

[3.03 FIELD QUALITY CONTROL 11](#__RefHeading___Toc162669876)

[3.04 CLEANING AND ADJUSTING 12](#__RefHeading___Toc162669877)

[3.05 DEMONSTRATION 12](#__RefHeading___Toc162669878)

[3.06 COMMISSIONING 12](#__RefHeading___Toc162669879)

[3.07 AS-BUILT DRAWINGS 12](#__RefHeading___Toc162669880)

CONSTRUCTION STANDARD SPECIFICATION

SECTION 13811

[lighting control equipment]{.underline}

[]{#__RefHeading___Toc162669851 .anchor}[General]{.underline}

1.  []{#__RefHeading___Toc162669852 .anchor}RELATED DOCUMENTS

    A.  Drawings and general provisions of the Contract, including
        General and Supplementary Conditions and Division 1
        Specification Sections apply to this Section.

2.  []{#__RefHeading___Toc162669853 .anchor}SUMMARY

    A.  This Section includes the following types of lighting controls:

        1.  Low voltage manual type momentary override switches

        2.  Programmable lighting control systems

        3.  Photo sensors

        4.  Power relays and contractors

        5.  Low voltage wiring

    B.  Low voltage is defined as 24 VAC + - 10% HZ for purposes of this
        section.

    C.  This Section DOES NOT address Lighting Control Systems for Large
        Conference Room and Auditorium type Spaces.

3.  []{#__RefHeading___Toc162669854 .anchor}submittals

    A.  General: Submit the following according to provisions of
        Standard Section 01330.

    B.  Supply manuals on system components to permit ease of
        installation, system operation and maintenance including, but
        not limited to the following:

        1.  Lighting control system step-by-step operating instructions.

        2.  Relay panel schedules indicating circuits connected, inputs
            assigned, area controlled, panel location and panel
            equipment details.

    C.  Lists of ballast and lamp combinations compatible with control
        systems, by manufacturer and catalog number. Acceptable ballast
        manufactures will be Universal or Advance. All fluorescent
        ballasts shall be electronic type.

    D.  Maintenance data for products for inclusion in Operating and
        Maintenance Manual specified in Division 1.

    E.  Record of field tests for tests specified in Part 3 of this
        Section.

    F.  Programming documentation for software.

4.  []{#__RefHeading___Toc162669855 .anchor}QUALITY ASSURANCE

    A.  Manufacturer Qualifications: Firms experienced in manufacturing
        and servicing equipment of the types and capacities indicated
        that have a record of successful in-service performance.
        Qualifications include ability to provide training, parts, and
        emergency repairs at the Project site within 24-hour response
        time.

    B.  Comply with NFPA 70, "National Electrical Code," for components
        and installation.

    C.  Listing and Labeling: Provide products specified in this Section
        that are listed and labeled.

        1.  The Terms "Listed" and "Labeled": As defined in the
            "National Electrical Code" Article 100.

        2.  Listing and Labeling Agency Qualifications: A "Nationally
            Recognized Testing Laboratory" (NRTL) as defined in OSHA
            Regulation 1910.7.

5.  []{#__RefHeading___Toc162669856 .anchor}WARRANTY

    A.  Special Project Warranty: A written warranty mutually executed
        by manufacturer and the principal Installer, agreeing to replace
        programmable lighting control system components that fail in
        materials or workmanship within the special Project warranty
        period specified below. This warranty shall be in addition to,
        and not a limitation of, other rights and remedies the Owner may
        have against the Contractor under the Contract Documents.

    B.  Special Project Warranty Period: 2 years beginning on the date
        of Substantial Completion.

6.  []{#__RefHeading___Toc162669857 .anchor}EXTRA MATERIALS

    A.  Furnish extra products as described below. Package with
        protective covering for storage and identify with labels
        describing contents. Deliver extra materials to the Owner.

        1.  Relays: Single-pole mechanically held, 1 for every 10
            installed.

        2.  Occupancy Sensors and Power Supply/Relay Packs: 1 for every
            10 installed

        3.  Low-voltage light switch: 1 for every 10 installed

            []{#__RefHeading___Toc162669858
            .anchor}[products]{.underline}

7.  []{#__RefHeading___Toc162669859 .anchor}MANUFACTURERS

    A.  All components are to be supplied by same manufacturer.
        Manufacturer is to be a supplier of this type of equipment for
        over 10 years:

        1.  Low voltage control system shall be manufactured by:

            a.  Douglas Lighting Controls, Inc.

            b.  Hubbell Buildings Automation

            c.  Intelligent Lighting Controls

            d.  Lighting Control & Design

8.  []{#__RefHeading___Toc162669860 .anchor}LIGHTING CONTROL SYSEM,
    GENERAL

    A.  Provide a complete low voltage lighting control system for the
        building shown on the plans and specified herein.

    B.  Lighting control system shall utilize networking technology
        based upon "LonWorks" and be LonMark certified to Level 3.1.
        System shall be able to operate as a stand-alone entity with the
        option of using a web server device so that programming and
        viewing of status can be accomplished by any PC connected to the
        same LAN or via the internet.

    C.  All relay panel interiors shall be pre-assembled complete with
        the necessary relays, transformers and devices. Relay panels
        that are wall mounted shall have interiors separate from
        enclosure so as to permit easy mounting, conduit installation
        and wire pull to enclosures. Enclosures mounted in the ceiling
        space are not required to have separate interiors.

9.  []{#__RefHeading___Toc162669861 .anchor}RELAYS

    A.  Lighting control relays shall be mechanically latching and shall
        come complete with a manual ON/OFF switch. The mechanical switch
        shall continuously display the true state of the relay's
        internal contacts. Relays requiring control power for manual
        operation and/or status feedback are not acceptable.

    B.  Single pole relays shall be rated and UL listed for 120 or 277
        VAC lighting loads at 20 amps.

    C.  Double pole relays shall be rated and UL listed for 208, 240 or
        480 VAC lighting loads at 20 amps.

    D.  Each lighting control relay shall be contained in an individual
        molded casing and shall be capable of containing a short circuit
        fault current of 14,000 amperes. Relays with exposed electronic
        devices are not acceptable

    E.  Each lighting control relay shall be capable of controlling
        incandescent, fluorescent, electronic ballast and MHID lighting
        loads.

    F.  Lighting control relays shall include captive, color-coded screw
        terminals for both the line voltage and the low voltage
        connections.

10. []{#__RefHeading___Toc162669862 .anchor}PRE-ASSEMBLED RELAY PANELS

    A.  Where indicated on the drawings, provide a factory pre-assembled
        relay panel. The panel's enclosure shall be for surface or flush
        installation, with a screw-on cover or hinged door assembly as
        required.

    B.  The panel shall consist of a pre-assembled interior insert;
        UL/CSA approved with capacities for 12, 24, 36, 48 and 72 relays
        as required. Panel enclosure must be UL/CSA Approved.

    C.  Panel interior shall have the following pre-assembled and
        pre-wired:

        1.  Suitable divider separating class1 and class 2 compartments

        2.  Control transformer, UL/CSA approved for class 2 circuits

        3.  Low voltage relays as required by switched circuits shown on
            plans or schedules

        4.  Control devices as required

11. []{#__RefHeading___Toc162669863 .anchor}CONTROL ELECTRONICS

    A.  When groups of relays are to be switched by master switches or
        time controls and it still must be possible to switch individual
        relays by local switches, provide programmable relay scanner
        WRS-2224.

    B.  Each scanner shall be solid state and have 24 relay outputs. An
        output shall be capable of switching the connected relay ON and
        OFF and sensing if the connected relay is ON or OFF.

    C.  Each programmable relay scanner shall have 5 switch inputs to
        accommodate group switches. Each switch input can be set with
        the keypad built into the scanner to switch some or all of the
        24 relay outputs of the scanner. Each switch input must indicate
        an ON state if any of the relays in the group is ON. If all
        relays are OFF, then indicate an OFF state to the group switch.

    D.  The scanner shall be able to provide an optical flick warn
        option for each of the 5 groups. After the flick warn, the
        occupant has 5 minutes to prevent the local lights from
        switching OFF by activating the local switch.

    E.  The scanner shall provide an optional time-out option. When
        activated, this option will allow any relay in the system when
        switched on, to be timed for a 2 hour interval before being
        switched off. Flick warn may also be added to this option.

    F.  The programming of the scanner shall be user friendly with
        instructions printed on the scanner label.

    G.  The relay scanner shall accept a plug-in module, WNX-2624
        Network Node. The network node shall use LonWorks technology and
        shall be LonMark certified (V3.1). This node shall be capable of
        connecting to an FTT-10A data line to communicate with other
        scanners in different relay panels or with other vendors using
        LonWorks technology.

12. []{#__RefHeading___Toc162669864 .anchor}NETWORK MANAGER

    A.  Provide as required on the drawings a WNP-2150 Network Manager
        complete with web server capability. The system shall have the
        following features:

        1.  Program and control up to 60 Network Nodes

        2.  Allow Photo sensors to be connected on the data line and to
            assign multiple set points to different groups of relays

        3.  Provide Astronomic time clock capability

        4.  Display relay panels individually and allow relays to be
            assigned to groups by simple point and click

        5.  Schedules allow for 1024 events and 16 unique holiday
            schedules

        6.  Groups can be configured to have user settable flick warn,
            time out and cleaning variables

        7.  Flick warn and time out durations are user settable on an
            individual relay basis

        8.  Allow switches to control groups spanning all panels in the
            system

        9.  Web interface must use standard HTML pages that allow any PC
            with a Web Browser access to the system

        10. Security access available with 4 levels

        11. Diagnostic tools for queries of status of network devices,
            relays and log reports

        12. Full backup and restore capabilities

13. []{#__RefHeading___Toc162669865 .anchor}SATELLITE PANELS

    A.  Where indicated on the drawings, provide a WSP-2718 Satellite
        Panel complete with 8 latching relays capable of switching 20
        amp lighting loads and rated for 120/277/247VAC. Each panel is
        to be connected on to the data line network and configured using
        the WNP/2150 Network Manager and shall contain the following
        hardware features:

        1.  10 switch inputs

        2.  2 -- 24VDC inputs for occupancy sensors requiring DC voltage

        3.  1 DC power supply rated for 250ma for supplying power to
            occupancy sensors

        4.  2 digital inputs for accepting signals from WPS-5533 or
            WPS-5527 photo sensors capable of sensing 0 -- 6,000
            footcandles.

    B.  Switch inputs are to be capable of switching individual relays,
        local groups of relays within the panel or global groups of
        relays system wide. Each switch input can be configured for
        connection to standard Douglas switches, momentary 24VAC
        switches or maintained contract 24VAC switches. Each input can
        also be configured to be ON or OFF only. The inputs may also be
        configured to have interlocking logic so that if the photo
        sensor has switched a relay off it is possible to set an input
        so a local wall switch cannot override the photo sensor relay on
        unless there is insufficient light.

    C.  In rooms with photo sensor control, it shall be possible to set
        relays to switch at different light levels so that as the amount
        of daylight changes, different amounts of artificial light can
        be switched on or off. It shall be possible to set a sequence of
        switching 3 lamp fixtures with a relay each for the single lamp
        and outer lamps as follows: As daylight increases, the single
        lamp relay is switched off first. The next step requires the
        outer lamp relay OFF and the single lamp relay ON
        simultaneously. As daylight passes the maximum threshold, the
        single lamp relay is switched off. This sequence is reversed as
        daylight declines.

    D.  The Satellite Panels shall accept either 24VDC or 24VAC
        occupancy sensors. The inputs may be configured for OFF only or
        ON/OFF switching scenarios. It shall be possible to link the
        photo sensor control with occupancy sensing so that when light
        levels are high enough, the occupancy sensor will not switch the
        photo sensor controlled relays ON.

14. []{#__RefHeading___Toc162669866 .anchor}LOW VOLTAGE WALL SWITCHES

    A.  Low voltage control switches and switch hardware shall mount to
        standard wall boxes.

    B.  Switch modules shall be available with 1, 2, 3 and 4 switches
        per gang and shall fit into standard 'Decora' style switch
        plates.

    C.  Individual switches shall include an integral tri-state LED to
        indicate both ON and OFF states (red=ON, green=OFF).

    D.  Each switch shall be clearly identified with a paper switch
        label. The label shall be held in place with a clear plastic cap
        and shall be field replaceable should the operation of the
        switch change. Permanently etched switches are not acceptable.

    E.  Switches shall have color coded captive screw terminals. Use #18
        AWG solid conductors.

    F.  Where required provide keyed switches to control lights.
        Switches shall include an integral tri-state LED to indicate
        both ON and OFF states (red=ON, green=OFF).

15. []{#__RefHeading___Toc162669867 .anchor}0-10V DIMMER SWITCHES

    A.  Dimmer switches shall be compatible with dimming ballasts using
        the 0-10V control protocol.

    B.  An LED indicator bar shall display the proportional level of the
        connected ballasts.

    C.  UP & DOWN buttons shall permit the operator to raise and lower
        the light level as required.

    D.  Where indicated on the lighting plans, the dimmer switches shall
        be combined with daylight sensors (WPS-5700) to limit the
        maximum electric light level. Manual dimmers cannot exceed the
        light level determined by the daylight sensor.

    E.  Each switch shall be capable of controlling up to 50 dimming
        ballasts.

16. []{#__RefHeading___Toc162669868 .anchor}OCCUPANCY SENSORS

    A.  Where required, provide a PIR occupancy sensor Model WRM-5104.
        The occupancy sensor shall control up to 4 Douglas relays
        directly. It shall also be possible to connect Douglas wall
        switches in parallel to each relay for occupant override if
        required

    B.  Occupancy sensor to include the following features:

        1.  Adjustable time out (30 sec to 30 min) and sensitivity

        2.  Tilt & swivel lens direction adjustment

        3.  Coverage of 1600 sq. ft., Indoor ceiling mount, ceiling
            heights 8' to 16' max

        4.  Function select -- on/off switching or off-only switching

17. []{#__RefHeading___Toc162669869 .anchor}EXTERIOR PHOTOMETRIC SENSORS

    A.  Provide where required an exterior photometric sensor capable of
        sensing from 1-60,000 lux. The sensor shall be connected to the
        lighting control network via a 4-wire (2 power + 2 data)
        dataline.

    B.  The ambient light level shall be continuously monitored and be
        displayed by the Network Manager.

    C.  One exterior sensor shall be capable of controlling one, some or
        all relays in the entire lighting control network shall permit
        different relays to switch at different light levels. Lights
        shall be controlled by 'sensor only' or by a combination of
        time& light level.

18. []{#__RefHeading___Toc162669870 .anchor}INTERIOR PHOTOMETRIC SENSORS

    A.  Provide where required an interior photometric sensor capable of
        sensing from 1-60,000 lux. The sensor shall be connected to the
        lighting control network via a 4-wire (2 power + 2 data)
        dataline.

    B.  The ambient light level shall be continuously monitored and be
        displayed by the Network Manager

    C.  Each interior sensor shall be capable of controlling one, some
        or all relays in the entire lighting control network and shall
        permit different relays to switch at different light levels.
        Lights shall be controlled by 'sensor only' or by a combination
        of time & light level.

19. []{#__RefHeading___Toc162669871 .anchor}DIMMABLE DAYLIGHT SENSORS

    A.  Provide where required and indoor daylight sensor WPC-5700 for
        applications that harvest daylight by regulating the electronic
        dimmable fluorescent ballasts. The sensor shall regulate the
        ballast so that when natural light is bright the lamp is dim and
        when natural light is dim the lamp is bright. The sensor shall
        be ceiling mounted and measures light reflected upward from the
        surface below. The sensor shall have a range setting and a
        set-point slider located under the front faceplate.

    B.  The sensor shall be compatible with Phillips/Advance Mark VII,
        Motorola Helios or any other ballast that uses the same 0-10V
        dimming control method. The sensor shall connect with 2 wires
        connected in parallel to a maximum of 50 ballasts. No other
        connections to the sensor are required for the dimming function.

20. []{#__RefHeading___Toc162669872 .anchor}LOW VOLTAGE WIRING

    A.  All wiring shall meet UL and NEC standards.

    B.  All low voltage wiring shall be 18-guage (#18AWG) unless
        otherwise specified. Color coded as per manufacturers
        recommendations. All low voltage wiring shall be run in EMT
        conduit. No exposed wiring will be allowed.

    C.  Dataline wiring between relay panels shall be 18 gage 2
        conductor shielded. Color coded as red/black/shield. All low
        voltage wiring shall be run in EMT conduit. No exposed wiring
        will be allowed.

        []{#__RefHeading___Toc162669873 .anchor}[Execution]{.underline}

21. []{#__RefHeading___Toc162669874 .anchor}INSTALLATION

    A.  General: Install equipment according to manufacturer's written
        instructions.

    B.  Mount control equipment according to manufacturer's instructions
        and Section 16001, "Electrical Work".

    C.  Mounting heights indicated are to bottom of unit for suspended
        items and to center for wall-mounted ones.

22. []{#__RefHeading___Toc162669875 .anchor}CONTROL WIRING INSTALLATION

    A.  Install wiring between control devices as specified in Division
        16 Section "Electrical Work" for hard wire connections.

    B.  Bundle, train, and support wiring in enclosures.

23. []{#__RefHeading___Toc162669876 .anchor}FIELD QUALITY CONTROL

    A.  Manufacturer's Field Services: Arrange and pay for the services
        of factory-authorized service representatives to test, adjust
        and program the lighting control systems. Programming shall
        include assigning all switch inputs to the required relays in
        each panel to ensure proper lighting operation. At the
        conclusion of programming, the contractor shall provide Sandia
        with an as-built drawing of all cabinets which will include a
        list of termination locations for all low-voltage switches.

    B.  Reports: Prepare written reports of tests and observations.
        Report defective materials and unsatisfactory test results.
        Record repairs and adjustments.

    C.  Test Labeling: Upon satisfactory completion of tests and
        inspections, apply a label to tested components indicating test
        results, date, and testing organization and person.

    D.  Schedule visual and mechanical inspections and electrical tests
        within 7-days' notice

    E.  Visual and Mechanical Inspections: Include the following
        inspections:

        1.  Inspect for defects and physical damage, NRTL labeling, and
            nameplate compliance with current project drawings

        2.  Check tightness of electrical connections with torque wrench
            calibrated within the previous 6 months. Use manufacturer's
            recommended torque values

        3.  Verify proper protective device settings and fuse types and
            ratings

        4.  Verify settings of photoelectric devices with photometer
            calibrated to NIST standards within the past 6 months

        5.  Exercise mechanical parts and operable devices according to
            manufacturer's instructions to verify proper operation.

    F.  Electrical Tests: Exercise particular caution when testing
        devices containing solid-state components. Perform the following
        tests according to manufacturer's instructions:

        1.  Insulation resistance tests of conducting parts of control
            components and connecting supply, feeder, and control
            circuits. Insulation resistance less than 100 megohms is not
            acceptable.

        2.  Continuity test of circuits.

24. []{#__RefHeading___Toc162669877 .anchor}CLEANING AND ADJUSTING

    A.  Remove paint spatters and other spots, dirt, and debris. Touch
        up scratches and mars of finish to match original finish. Clean
        equipment and devices internally and externally using methods
        and materials recommended by manufacturers.

    B.  Occupancy Adjustments: Upon request within 1 year of date of
        substantial completion, adjust light levels, make program
        changes, and adjust sensors and controls.

25. []{#__RefHeading___Toc162669878 .anchor}DEMONSTRATION

    A.  Training: Arrange and pay for the services of a
        factory-authorized service representative to demonstrate
        programmable lighting control system and train Owner's
        maintenance personnel. Allow a minimum of 2 working days for
        this training.

    B.  Train Owner's personnel to operate, service and maintain
        equipment and system components. Allow at least 4 hours to
        conduct training. Schedule training with at least 7 working
        days' notice.

26. []{#__RefHeading___Toc162669879 .anchor}COMMISSIONING

    A.  Operational Tests: Energize systems, program control, and check
        each controlled are for light levels and lamp and component
        noise. Use light meters appropriate for the test and calibrated
        to NIST standards. Adjust components and revise installation as
        required to correct deficiencies. Operate the system to prove
        compliance with requirements.

    B.  Correct malfunctions and retest until proper operation is
        achieved.

27. []{#__RefHeading___Toc162669880 .anchor}AS-BUILT DRAWINGS

    A.  The drawings issued for construction are representative of the
        work to be performed and of existing equipment. AS part of this
        contract, the Contractor shall provide Sandia National
        Laboratories with a set of "red-marked" prints, including all
        equipment relating to the fire protection system, both existing
        and contractor installed. The lighting drawings consist of
        plans, wiring, diagrams, and controller panel schedule. The
        marked-up prints shall show all junction boxes, conduit sizes,
        devices, and any other information relevant to the as-built
        condition. Conduit and junction box locations shall be shown on
        the as-builts if they were shown on the original plans.

END OF SECTION