July 22, 1994

Contract #TW0592

SPECIAL SPECIFICATION

SECTION 08710-S

[FINISH HARDWARE]{.underline}

[Page]{.underline}

[PART 1 - GENERAL]{.underline}

1.01 Description Of Work 2

1.02 References 2

1.03 Submittals 3

1.04 Quality Assurance 3

1.05 Delivery, Storage, and Handling 3

PART 2 - PRODUCTS

2.01 Manufacturers 4

2.02 General Hardware Schedule 4

PART 3 - EXECUTION

3.01 Examination. 9

3.02 Installation. 9

3.03 Adjustments. 10

SPECIAL SPECIFICATION

SECTION 08710-S

[FINISH HARDWARE]{.underline}

# PART 1 - GENERAL

## 1.01 [DESCRIPTION OF WORK]{.underline}

[Section Includes]{.underline}: This section includes furnishing and
installing finish hardware as scheduled and/or as called for on contract
documents. It does not include hardware for aluminum entrance doors.

## 1.02 [REFERENCES]{.underline}

A. [American National Standards Institute/Builder\'s Hardware
Manufacturer\'s Association (ANSI/BHMA)]{.underline}

A156.1 Specification for Butts and Hinges

A156.2 Specification for Locks and Latches

A156.3 Specification for Exit Devices

A156.4 Specification for Closers

A156.5 Specification for Auxiliary Locks

A156.6 Specification for Architectural Door Trims

A156.10 Specification for Automatic Doors

A156.15 Specification for Closer/Holder Release Devices

A156.16 Specification for Auxiliary Hardware

A156.18 Specification for Materials and Finishes

A156.19 Specification for Assisted Doors and Low Energy Power Operated
Doors

B. [Underwriter\'s Laboratory, Inc., (UL)]{.underline}

UL-305 Standard for Safety

C. [Factory Mutual (FM)]{.underline}

Fire Tests of Materials

D. [Americans With Disabilities Act Accessibility Guidelines
(ADAAG)]{.underline}

E. [Uniform Building Code (UBC)]{.underline}

F. [National Fire Code (NFC)]{.underline}

G. [Life Safety Code (NFPA 101)]{.underline}

## 1.03 [SUBMITTALS]{.underline}

[General]{.underline}: Submit the following items in accordance with the
Conditions of Contract and Division 1, Section \"Descriptive
Submittals.\"

A. [Product Data]{.underline}: Submit manufacturer\'s catalog data for
each item of finish hardware including evidence of UL listing for fire
rated hardware.

B. [Quality Certification]{.underline}: Submit manufacturer\'s written
certification that hardware to be used on project is Grade One quality.

C. [Asbestos Free and Lead Paint Free Certification]{.underline}: Submit
manufacturer\'s written certification that all finish hardware materials
are free of asbestos and lead paint.

## 1.04 [QUALITY ASSURANCE]{.underline}

A. [Qualifications]{.underline}: Finish hardware manufacturer shall have
a minimum of ten (10) years experience in the manufacturing of hardware.

B. [Product Quality]{.underline}: Provide products which have been
tested and are in compliance with references listed in Section 1.02 of
this specification for the required assemblies.

C. [Dial Combination Locks]{.underline} shall be installed by safe and
lock companies with a minimum of five (5) years experience in the
installation and service of combination locks.

D. [Warranties]{.underline}: Provide ten (10) year warranty on closers
and one (1) year warranty on all other hardware.

## 1.05 [DELIVERY, STORAGE, AND HANDLING]{.underline}

A. [Packing and Shipping]{.underline}: Finish hardware shall be packed
and shipped to the job site in unopened boxes, clearly labeled with the
manufacturer\'s name and item description.

B. [Storage and Protection]{.underline}: Store finish hardware in a
manner to prevent damage until needed for installation.

# PART 2 - PRODUCTS

## 2.01 [MANUFACTURERS]{.underline}

A. [General]{.underline}: Manufacturers with capability to meet this
specification include, but are not limited to, the following:

1\. [Stanley]{.underline}: Butt hinges

2\. [Sargent]{.underline}: Exit devices, locksets, padlocks, door
closers, mullions.

3\. [Sargent & Greenleaf]{.underline}: Dial combination lock.

4\. [Simplex]{.underline}: Mechanical push button combination locks.

5\. [Hirsch]{.underline}: Electrical push button combination locks.

6\. [Trimco]{.underline}: Silencers, door bumpers, mop plates, kick
plates, stops/holders, flush bolts, push/pull latches.

7\. [Honeywell]{.underline}: Electro-magnetic door holders.

8\. [National Guard Products (NGP)]{.underline}: Thresholds, door sweeps
and door bottoms, weatherstripping, smoke seals, astragals.

9\. [Horton Automatics, Power Access Corporation or Gyro
Tec]{.underline}h: Low energy power operated interior door openers.

10\. [Folger Adams]{.underline}: Electric Hinges

B. [Substitutes]{.underline}: Only approved equal products may be
substituted.

## 2.02 [GENERAL HARDWARE SCHEDULE]{.underline}

A. [General]{.underline}: All hardware shall be identified by ANSI as
Grade One hardware where applicable. Where applicable, function shall be
as noted on contract documents or as chosen at time of submittals.

B. [Opening Force]{.underline}: Doors complete with hardware shall have
a minimum opening/closing force of 8.5 pounds (3.9 kg) for exterior
doors and 5.0 pounds (2.3 kg) for interior doors.

C. [Manufactured Units]{.underline}: Unless otherwise indicated in a
finish hardware schedule or elsewhere in the contract documents, provide
the following hardware:

1\. [Butt Hinges]{.underline}: Butt hinges shall be 4-1/2 inches (114
mm) x 4-1/2 inches (114 mm), steel, full mortise, five knuckle, ball
bearing, flat tip hinges with a polished and plated finish.

a\. Provide heavy weight hinges on all exterior doors, airlock entry
doors, doors with closers, and toilet room entry doors. Use Stanley FBB
168.

b\. Provide standard weight hinges on all other doors. Use Stanley FBB
179.

c\. Provide manufacturer\'s heavy duty non-removable pins at all
exterior doors, designated vault type room doors and other doors as
designated on contract documents.

2\. [Electric Hinges]{.underline}: Provide one each electric hinge on
doors where electric devices or electric locks are specified elsewhere
in the contract documents. Use Folger Adams Model No. 4-1/2 EH Electric
Hinge (non-load bearing).

3\. [Locks and Latches]{.underline}: Locks and latches shall all be
lever type, positive latching, and shall be bored locks and latches with
a 2-3/4 inch (70 mm) backset, 1/2 inch (13 mm) latch bolt throw, 4-1/2
inch (114 mm) lever with a 3-1/2 inch (89 mm) outside and inside rose
where applicable to conceal through bolts.

a\. Locksets shall be Sargent 10 Line Series with number 808 strike and
appropriate function.

\(1\) 28-10G04-LL for equipment and utility room/chase doors.

\(2\) 28-10G05-LL for all other doors where exit devices latch sets and
mechanical push button combination locks are not specified.

b\. Latchsets shall be Sargent 10 Line Series with number 808 strike and
appropriate function.

Provide 28-10U15-LL for all doors where indicated on contract documents.

c\. At all toilet room doors, provide auxiliary latchsets.

Provide Sargent 24-114P x 808 strike.

4\. [Exit Devices]{.underline}: Provide exit device only where specified
on the contract documents. Exit device latch bolts shall be released by
depressing an actuating push pad.

a\. For single doors and double doors with removable or fixed center
mullion, exit device shall be Sargent Series 8888. The device shall have
a reversible rim, appropriate strike, and lever handle trim.

\(1\) At non-fire rated doors, provide Model 8888 x 713-8 ETL with Model
641 strike and at double doors add Sargent model 980 aluminum removable
mullion or fixed steel mullion.

\(2\) For fire rated doors, provide Model 12-888 x 713-8ETL with Model
649 strike and at double doors add Model 12-980 fire rated steel
removable mullion or fixed steel mullion.

b\. For a pair of active doors without a center mullion, exit devices on
each leaf shall be Sargent Series 8700 vertical rod type exit device.
The devices shall have the appropriate model 629 top and model 624
bottom strikes and shall have lever handle trim.

\(1\) For non-fire rated door, provide model 8713 x 713 ETL.

\(2\) For fire rated doors, provide model 12-8713 x 713 ETL.

c\. For single doors and double doors with a removable or fixed center
mullion and which are indicated to be unlocked via an electric actuation
device (e.g., badge reader, key switch), provide Sargent Series 8800
exit device with an electro-mechanical lever control.

\(1\) At non-fire rated doors, provide Model 8876-776ETL with
appropriate strike, electric butt hinge, power supply, and at double
doors add Sargent Model 980 mullion if fixed steel mullion is not
indicated to be installed.

\(2\) At fire rated doors, provide Model 12-8876-776ETL with appropriate
strike, electric butt hinge, power supply, and at double doors add Model
12-980 fire rated steel removable mullion if fixed steel mullion is not
indicated to be installed.

5\. [Closers]{.underline}: Closers shall be surface mount type with
parallel arms, back check, key control valves, and 50% power adjustments
and shall facilitate automatic closure of door.

> Provide Sargent Model EB350 series closers on all exterior doors,
> interior fire rated doors, doors with electro-magnetic door holders,
> interior doors with exit devices, push-pull devices, auxiliary
> latchsets and additional doors indicated on the contract documents.

6\. [Dial Combination Locks]{.underline}: Provide three position dial
combination locks only when noted in the contract documents. Provide
Sargent & Greenleaf 8470 x T8415MP x D41 x DR162 with appropriate
strike. Base plate shall be hardened steel.

7\. [Mechanical Push-Button Combination Locks]{.underline}: Provide
mechanical push-button combination locks only when noted in the contract
documents. Provide Simplex Unican L1000-2B with key bypass. Provide
uncombinated Falcon core 12607A with two blank keys.

8\. [Electrical Push-Button Combination Locks]{.underline}: Provide
electrical push-button combination locks only when noted elsewhere in
the contract documents. Unless otherwise indicated, provide Hirsch key
pads, controllers, etc. per contract documents.

9\. [Architectural Door Trim]{.underline}: Kick plates shall be of heavy
duty 16 gauge (2 mm) smooth surface metal.

> Provide Trimco 1024- 12\" x 2\" (305 mm x 51 mm) LDW on push side of
> all doors scheduled for exit devices, on both sides of doors with
> push/pull devices or auxiliary latchsets.

10\. [Electro-Magnetic Door Holder]{.underline}: Provide
electro-magnetic door holder device only when specified in the contract
documents. The device shall be UL listed and FM approved and shall be
fail safe, conforming to National Fire Code Nos. 80 and 101. The release
device shall be so designed that it may be automatically released by
power interruption and manually released by some simple and readily
obvious operation.

> Provide Honeywell series S4003 for 120 VAC. Provide appropriate floor
> mount pedestal where needed for floor mount installation.

\(1\) In new construction, where indicated to be installed on walls,
door holder shall be flush mounted.

\(2\) In renovation work, where indicated to be installed on walls, door
holder may be surface mounted.

11\. [Door Coordinators]{.underline}: Provide coordinator at all pairs
of active doors without a center mullion. Use Sargent Model 3487 with
Model 3497 carry open bar .

12\. [Auxiliary Hardware]{.underline}: **Auxiliary hardware shall be
provided only where specified herein and/or elsewhere on the contract
documents.**

a\. Combination stop and holder device shall be a Trimco model 1224-5
manually operated device.

b\. Concave wall mount door bumpers shall be provided at all doors
opening onto adjacent walls.

> Provide Trimco model W1276-CCS Series with appropriate fasteners.

c\. Floor mount door bumpers shall be provided on all doors where wall
type door bumpers are not provided.

> Provide Trimco model W1210ES Series.

d\. Provide Trimco model 1229A neoprene door silencers on all non-fire
rated doors. Provide three per each door.

e\. Provide a flexible silicone rubber smoke seal on all fire rated
doors. Use NGP 2525 x D.S.

f\. Manual flush bolts shall be Trimco 3917 top and bottom.

g\. Provide weatherstripping, door sweep(s), and threshold at all
exterior doors.

\(1\) Provide NGP 160 weatherstripping at all non-fire rated exterior
doors.

\(2\) Provide NGP 200 NA door sweep at all exterior doors.

\(3\) Provide NGP 424 threshold at all exterior doors.

h\. Provide security astragal on exterior pairs of doors without center
mullions and exit devices.

> Provide NGP 139 SP.

i\. Provide NGP 125 NGA astragal for all other fire rated and non-fire
rated double doors without center mullion where a security astragal is
not specified.

j\. Automatic door bottoms for both fire rated and non-fire rated doors
shall be NGP 420A.

13\. [Low Energy Power Operated Door Openers]{.underline}: On specified
doors only, provide power operated door opener(s). The power opener
shall be a low energy, self-contained electric operating mechanism. It
shall be powered open with a DC motor working through reduction gears.

a\. The motor shall be off when the door is in the closing mode.

b\. The door shall be capable of being manually opened or closed with
power on or off without damage to the mechanism.

c\. The opener shall include the following variable adjustments in
compliance with ANSI A156.19.

\(1\) Opening Speed - three to five seconds

\(2\) Closing Speed - three to five seconds

\(3\) Time Delay Before Closing - five to twenty-five seconds

d\. Opening and closing force, measured 2\" (51 mm) out from the lock
stile of the door, shall not exceed 15 pounds (6.8 kg) of force to stop
the door when operating in either direction.

e\. The opener shall include a means of turning off the opening force
when the door is stopped for one second. After stopping door, it should
then close and the opener shall reset itself to accept another signal.

f\. The opener shall be mounted in an extruded aluminum cover.

g\. Provide two (2) 6\" (152 mm) round stainless steel push plate
control switches marked \"Handicapped\" on each side of opening unless
otherwise indicated in contract documents.

h\. Furnish 120 VAC, 60 cycle, single phase, 15 amp service to the
operator.

14\. [Electric Strikes]{.underline}: When noted elsewhere in the
contract documents, provide heavy duty electric strikes fully compatible
with the door, frame, and hardware specified for the intended
application. Strike shall have latchbolt monitoring capability.

D. [Fire Rated Door Hardware]{.underline}: Fire rated door hardware
shall be listed and labeled by Underwriter\'s Laboratories (UL) and
Factory Mutual (FM) as \"Fire Exit Hardware.\" Exit devices on fire
rated doors shall not have dog down capability.

E. [Finishes]{.underline}: Finish for all hardware shall be US26D ,
plated, clear coated dull chrome or US32D plated satin stainless steel
unless otherwise specified in the contract documents.

F. [Cylinders and Keys]{.underline}: Unless otherwise specified, all
locks shall be furnished with cylinders and two keys and shall be
capable of accepting Sargent six-pin tumbler cylinders without
modification. Keyway style will be selected at time of submittals.
Unless otherwise directed, provide zero pinned cylinders.

G. [Fabrication]{.underline}: Manufacturer\'s hardware shall conform to
published templates prepared for screw installation.

H. [Fasteners]{.underline}: Furnish screws for installations with each
hardware item. Provide concealed fasteners for hardware units which are
exposed when the door is closed.

# PART 3 - EXECUTION

## 3.01 [EXAMINATION]{.underline}

[Examine materials]{.underline} on which hardware is to be installed to
check for surface defects including warpage which might impede
performance of hardware.

## 3.02 [INSTALLATION]{.underline}

[Install all hardware]{.underline} per manufacturer\'s installation
instructions, being careful not to damage the finish on the hardware.

A. [Butt Hinges]{.underline}: Install a minimum of 1-1/2 pair per door
on doors no taller than 7 feet 2 inches (2.18 m), otherwise install two
(2) pair butt hinges per door.

B. [Lock and Latches]{.underline}: Install locks and latches at 36
inches (914 mm) above bottom of door.

C. [Dial and Push Button Combination Locks]{.underline}: Install dial
and push button combination locks per manufacturer\'s installation
instructions at 48 inches (1.2 m) above bottom of door.

D. [Push Plate Control Switches]{.underline}: Install 6\" (152 mm) round
push plate control switches at 12\" (305 mm) above finish floor and 39\"
(991 mm) above finish floor to center line of 6\" (152 mm) round plates.
Two (2) plates are required on each side of opening.

## 3.03 [ADJUSTMENTS]{.underline}

[All hardware shall be adjusted]{.underline} and demonstrated to
function properly. Damaged or defective hardware shall be replaced at no
cost to Sandia National Laboratories (SNL).

END OF SECTION

EXCEPT FOR ATTACHMENT