![](media/image1.png){width="1.6666666666666667in"
height="0.5833333333333334in"}

**MuTr Response to Alarms in 1008 PROCEDURE**

**[PHENIX Procedure No. PP-2.5.2.12-10]{.underline}**

**[Revision:A Date: 12-19-00]{.underline}**

**[Hand Processed Changes]{.underline}**

**[HPC No.]{.underline} [Date]{.underline} [Page Nos.]{.underline}
[Initials]{.underline}**

\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_

**[Approvals]{.underline}**

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PHENIX S E & I Date Cognizant Scientist/Engineer Date

/Activity Manager

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PHENIX Safety Date C-AD SAFETY Date

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

**[1.0 Purpose and Scope]{.underline}**

This procedure describes the steps that watch people should follow when
the South Muon Tracking system is in operation.

2.  **[Watch Procedures]{.underline}**

The CCAS watch or PHENIX people on shift should check the alarm panel
located in the PHENIX Control Room. The alarms that are associated only
with the Muon Tracker are as follows:

> Window Box A:

-   1-4 MuTr South High Level Smoke

-   2-4 MuTr South Low/Mid Level smoke

-   3-4 MuTr South Smoke Detector Trouble

-   4-1 South Muon Main Power Breaker Trip

-   4-2 South Muon Main Power Breaker Fail

-   4-4 MuTr South Smoke Detector Isolated

-   5-8 MuTr South Water Leak Detected

> Window Box B:

-   1-1 Electronics Racks Smoke Detected

-   1-2 Electronics Racks/TOF Smoke Detected

-   2-1 Electronics Racks Heat Detected

-   3-1 Electronics Racks Water Detected

-   3-4 Detector water Hi Temp/Makeup

-   4-2 VESDA Power Supply Trouble

-   5-4 Magnet Water Flow Low

> If any of the above alarms are noted the watch person should:

1.  Note the alarms in the shift log book located next to the alarm
    panel.

2.  Hit the Acknowledge button

3.  If the alarm clears (signified by a warbling tone and a flashing
    window), hit the RESET button.

4.  If the alarm did not clear, call the appropriate person(s) on the
    on-call list until you reach someone.

The following alarms should be ignored as they will not be in operation
during this running period or are of no consequence:

> Window Box A:

-   1-6 East or West Carriage high level gas

-   1-7 GMH high level gas

-   2-6 Carriage low level gas

-   2-7 GMH low level gas

-   3-6 Carriage Gas Detector Malfunction

-   3-7 GMH Gas Detector Malfunction

-   4-6 IR Return Air High Level Gas

-   5-6 IR (PASS)floor high level gas

-   6-6 IR return air gas detector malfunction

-   6-7 IR HVAC/Vent fans off

-   6-8 PHENIX Bypass Active

> Window Box B:

-   6-2 TOF Blowers Trouble

-   6-4 Power Supply water flow low

3.  **[Responsibilities]{.underline}**

> The on-call people responsible for the MuTr system are:
>
> John Haggerty 689-2991
>
> Paul Giannotti 821-3486 or 315-568-8480
>
> Frank Toldo 732-5950
>
> Ming Liu 924-7417