**SPILL PREVENTION, CONTROL, AND COUNTERMEASURES PLAN**

**NATIONAL WEATHER SERVICE**

**Dodge City Weather Forecast Office**

**104 Airport Road**

**Dodge City, KS 67801**

**Original Date of Plan :** August 1992

**Date of Last Plan Review :** April 2, 2002

**Date of Last Amendment**

**and P.E. Certification :** April 2, 2002

**[Designated Person Responsible for Spill Prevention]{.underline}:**

Larry Noller, Environmental Focal Point

Telephone: (620) 225-6514

**CERTIFICATION**

I hereby certify that I have examined the facility, and being familiar
with the provisions of Title 40 of the Code of Federal Regulations Part
112, I attest that this Spill Prevention, Control, and Countermeasures
(SPCC) Plan has been prepared in accordance with good engineering
practices.

  ----------------------------------------------------- ----------------------
  John McCall                                           

  Printed Name of Registered Engineer                   

                                                        

                                                        

  Signature of Registered Engineer and Date             

                                                        

  Registration No**. [PE-050653-E]{.underline}**        State
                                                        **[PA]{.underline}**
  ----------------------------------------------------- ----------------------

**REVIEW DOCUMENTATION AND MANAGEMENT APPROVAL PAGE**

**REVIEW DOCUMENTATION**

In accordance with Title 40 Code of Federal Regulations (CFR) Part
112.5(b), a review and evaluation of this Spill Prevention, Control, and
Countermeasures (SPCC) Plan shall be conducted at least once every 3
years and shall be conducted by the Meteorologist in Charge, NWS
Regional Environmental/ Safety Coordinator, or NOAA Regional
Environmental Compliance Officer. After the review and evaluation, the
National Weather Service shall amend the SPCC Plan within 6 months to
include more effective prevention and control technology if:

> Such technology will significantly reduce the likelihood of a spill
> event from the facility, and
>
> If such technology has been field-proven at the time of review.

Amendments to the SPCC Plan shall be made when a change in the facility
design, construction, operation, or maintenance materially affects the
potential for the discharge of oil into or upon the navigable waters of
the United States or adjoining shorelines. These amendments shall be
fully implemented as soon as possible, but no later than six months
after such a change occurs, and shall be certified by a Professional
Engineer. Other amendments due to facility changes that do not affect
the potential for discharge (such as changes in personnel or contact
information) can be made at any time, and certification by a
Professional Engineer shall not be required.

+-----------+-------------------------+------------+------------------+
| **Review  | **Signature of          | *          | **PE             |
| Date^1^** | Responsible Manager**   | *Amended** | Certification    |
|           |                         |            | Required         |
|           |                         | **(Yes or  | (Yes/No)?**      |
|           |                         | No)?**     |                  |
+-----------+-------------------------+------------+------------------+
|           |                         |            |                  |
+-----------+-------------------------+------------+------------------+
|           |                         |            |                  |
+-----------+-------------------------+------------+------------------+
|           |                         |            |                  |
+-----------+-------------------------+------------+------------------+

**MANAGEMENT APPROVAL**

The National Weather Service is committed to the prevention of
discharges of oil to navigable waters and the environment. We maintain
the highest standards for spill prevention, control, and countermeasures
through regular review, updating, and implementation of this SPCC Plan
for the Weather Forecast Office.

  -----------------------------------------------------------------------
  **LarryRuthie, Meteorologist in Charge**

  Printed Name and Title of Responsible Manager

  Signature and Date
  -----------------------------------------------------------------------

**CONTENTS**

**[Section]{.underline} [Page]{.underline}**

Certification i

Review Documentation and Management Approval ii

PART I - GENERAL INFORMATION 1

A. GENERAL 1

> 1\. Name 1
>
> 2\. Type 1
>
> 3\. Date of Initial Operation 1
>
> 4\. Location 1
>
> 5\. Name and Address of Operator 1
>
> 6\. Facility Contacts 1

B. SITE DESCRIPTION AND OPERATIONS 1

> 1\. Facility Location, Layout, and Operations 1
>
> 2\. Facility Storage 2
>
> 3\. Drainage Pathway and Distance to Navigable Waters 2
>
> 4\. Spill History 3
>
> 5\. Spill Potential, Volumes, and Rates 3

PART II - DESIGN COMPONENTS AND OPERATIONAL PROCEDURES FOR SPILL
PREVENTION AND CONTROL 4

A. SPILL PREVENTION 4

> 1\. Bulk Storage Tanks and Facility Transfer Operations 4
>
> 2\. Tank Truck Unloading Operations 4
>
> 3\. Inspections And Records 5
>
> 4\. Site Security 6
>
> 5\. Training 6

B. SPILL CONTROL 6

> 1\. Secondary Containment Designs, Construction Material, and Volume 6
>
> 2\. Spill Kits Type and Location 7

PART III - SPILL COUNTERMEASURES AND REPORTING 8

A. SPILL COUNTERMEASURES 8

B. SPILL REPORTING 9

> 1\. General Notification Procedures for All Spills 9
>
> 2\. Federal Notification 9
>
> 3\. State Notification 10
>
> 4\. Cleanup Contractor Notification 10

PART IV - RECOMMENDED IMPROVEMENTS 11

A. PHYSICAL UPGRADES 11

> 1\. Secondary Containment 11

B. PROCEDURAL CHANGES 11

> 1\. Inspections and Preventative Maintenance 11
>
> 2\. Training 11

**[Appendix]{.underline}**

A TANK RECORDS

B TANK ULLAGE/FUELING LOG AND FUEL UNLOADING PROCEDURE CHECKLIST

C INSPECTION CHECKLISTS

D TRAINING OUTLINE AND TITLE 40 OF THE CODE OF FEDERAL REGULATIONS,
PARTS 112.1-112.20-OIL POLLUTION PREVENTION

E SPILL REPORTING FORM

F CROSS REFERENCE OF THE REQUIREMENTS OF TITLE 40 OF THE CODE OF FEDERAL
REGULATIONS, PART 112.7, WITH THIS PLAN

**FIGURES**

**[Figure]{.underline} [Page]{.underline}**

1 SITE LOCATION 12

2 SITE LAYOUT 13

**TABLES**

**[Table]{.underline} [Page]{.underline}**

1 DESCRIPTIVE INVENTORY OF FACILITY STORAGE 14

2 POTENTIAL SPILL SOURCES AND VOLUMES 15

**PART I - GENERAL INFORMATION**

**GENERAL**This section provides general information about the facility.

1.  Name

> National Weather Service (NWS)
>
> Dodge City Weather Forecast Office (WFO)
>
> **Type**This facility is an onshore facility (non-production) that
> operates as a river and weather forecasting center and is staffed 24
> hours per day, 7 days per week, and 365 days per year.
>
> **Date of Initial Operation** October 1989
>
> **Location**104 Airport Road

Dodge City, Ford County, Kansas 67801

> **Name and Address of Operator**National Weather Service

104 Airport Road

Dodge City, Kansas 67801

> **Facility Contacts**[Name]{.underline} [Title]{.underline} [Telephone
> Number]{.underline}

Larry Noller Environmental Focal Point (620) 225-6514

Larry Ruthie Meteorologist in Charge (620) 225-6514

**SITE DESCRIPTION AND OPERATIONS**This section describes the site
location, its operations that store diesel fuel, site drainage patterns,
spill history, and spill potential.

> **Facility Location, Layout, and Operations**The facility is located
> in Ford County, Kansas, approximately 2.5 miles east of Dodge City and
> adjacent to the Dodge City Regional Airport (Figure 1). Figure 2 shows
> the layout of the facility, including the location of the 750-gallon
> aboveground storage tank (AST), 25-gallon day tank, and two 200-gallon
> Radar Data Acquisition (RDA) tanks.
>
> The 750-gallon AST and 25-gallon day tank are used to store fuel that
> is used to power the WFO emergency generator. The WFO generator and
> the day tank are located in the WFO generator room in the northeast
> corner of the WFO building and are not exposed to precipitation. The
> 750-gallon AST is located outside the WFO generator building to the
> east.
>
> The two 200-gallon RDA tanks are used to fuel the RDA emergency
> generator that supplies power to the RDA systems. The two RDA tanks
> and RDA generator are located inside the RDA generator building
> approximately 50 feet northeast of the WFO and are not exposed to
> precipitation.
>
> The estimated fuel usage is approximately 80 gallons per month. This
> estimate is based on a test of the generators once per week for at
> least 30 minutes. Fuel consumption would increase based on the
> frequency and duration of any power outages.
>
> **Facility Storage**The 750-gallon AST is a welded steel tank situated
> within a sufficiently impervious concrete containment basin and
> designed to hold the entire contents of the tank plus sufficient
> capacity to account for potential precipitation. The 750-gallon AST is
> equipped with a 2-inch-diameter primary vent.
>
> The 750-gallon AST is connected to a pump on top of the day tank via a
> pipe that travels through the outer wall of the WFO building and into
> the WFO generator room. This pump moves fuel from the 750-gallon AST
> into the day tank. The day tank is a 25-gallon single-walled
> rectangular steel tank and is situated over a rupture basin. The day
> tank is connected to the generator by flexible rubber supply and
> return lines.
>
> The two 200-gallon RDA tanks are constructed of steel and located
> within the RDA generator building that is designed and constructed to
> contain potential spills. The RDA tanks supply fuel to the RDA
> generator, that is also located within the RDA generator building.
>
> Table 1 summarizes the pertinent information on the tanks at the
> facility. A copy of all tank registrations and other tank records,
> such as notifications to the Local Emergency Planning Committee or
> tank testing documentation, is included in Appendix A.
>
> **Drainage Pathway and Distance to Navigable Waters**Any fuel spilled
> from outside the secondary containment area of the 750-gallon AST
> would flow northwest along a slope approximately 300 feet and into a
> grassy pasture area. A potential spill from a fuel unloading truck
> could flow to the parking lot and into the surrounding grassy areas.
> Any fuel spilled outside the secondary containment of the two
> 200-gallon RDA tanks likely would flow northwest. All stormwater
> runoff from the site eventually flows to an unnamed intermittent
> stream located west of the site. The intermittent stream flows south.
>
> **Spill History**[Reportable spill events from October 1989 to present
> (date on cover of this plan)]{.underline}:
>
> None.
>
> **Spill Potential, Volumes, and Rates**The most probable causes of
> spills from the 750-gallon AST and RDA tanks are overfilling, a
> ruptured hose during fuel unloading, or from failure of the fuel
> supply lines. For the day tank, the probable causes of spills are from
> a failure of the pump to shut down or failure of the pipe that directs
> fuel from the pump to the day tank. Low probability spill events for
> any of the tanks could include loss of structural integrity because of
> vandalism or a natural disaster. It is possible that a vehicle
> collision could cause a spill from the 750-gallon AST, but the
> probability of such an event is low because the 750-gallon AST is not
> located in the direct line of traffic.
>
> Table 2 summarizes the potential type of failure, potential spill
> volume, estimated rate, and direction of spill flow from the tanks.

**PART II - DESIGN COMPONENTS AND OPERATIONAL PROCEDURES\
FOR SPILL PREVENTION AND CONTROL**

This section discusses spill prevention and control measures that shall
be implemented at the facility.

**SPILL PREVENTION**This section describes design components and
operating procedures that shall be implemented at the facility to
prevent oil spills.

> **Bulk Storage Tanks and Facility Transfer Operations**[750-gallon
> AST]{.underline}: The tank construction is compatible with the diesel
> fuel stored in the tank. Secondary containment is provided for the AST
> that will provide for the entire capacity of the tank plus sufficient
> freeboard to allow for the accumulation of precipitation. A float-type
> level gauge indicates the fuel level (from empty to full). A round
> spill container with 5-gallon capacity surrounds the fill spout to
> capture potential overflow during fuel transfer. The AST is equipped
> with an audible high-level alarm set to engage at 85 percent of
> capacity (638 gallons) and an automatic shutoff valve on the cam-lock
> fitting fill spouts that is set to close at 90 percent of the AST
> capacity (675 gallons). A monitoring system that can detect 1 inch or
> more of fluid in the interstitial space of the storage tank is also
> present.
>
> [Day Tank]{.underline}: The day tank is located inside the WFO
> generator room and provides containment for the contents of the tank.
> The day tank is equipped with a gauge to indicate the amount of fuel
> in the tank (empty to full)and a high-level float switch connected to
> an audible alarm to warn of overfilling. The day tank is situated over
> an open top spill pan (rupture basin) that can hold 100 percent of the
> tank volume. The rupture basin has a float switch designed to detect
> fuel that has spilled or leaked; the float switch is designed to
> activate an audible alarm.
>
> [Piping:]{.underline} An antisiphoning valve is located between the
> 750-gallon AST and the pump to prevent unwanted fuel from being
> siphoned from the 750-gallon AST to the day tank. The piping from the
> 750-gallon AST to the day tank is equipped with a polyvinyl chloride
> pipe sleeve to protect from corrosion.
>
> [Two 200-gallon RDA Tanks]{.underline}: The tanks are located inside
> the RDA generator building that provides sufficient containment for
> the contents of the tank. The tanks are constructed of steel and are
> compatible with the diesel fuel stored. The tanks are equipped with a
> high level audible alarm that sounds when the fuel level is high to
> warn of overfilling.
>
> **Tank Truck Unloading Operations**All delivery drivers shall have
> U.S. Department of Transportation hazardous material transportation
> training as required by Federal law.
>
> The remainder of this section discusses the procedures that shall be
> used during unloading of fuel from the tank truck into the storage
> tank to prevent spills. Using the form in Appendix B, this procedure
> shall be documented every time refueling occurs. Copies of this form
> shall be kept for 3 years.
>
> The following procedure shall be used [prior]{.underline} to fuel
> unloading:

1.  Move spill containment equipment, such as booms or spill barriers,
    into the unloading area.

2.  Ensure that the audible high-level alarm system and the automatic
    shutoff valve are functioning properly.

3.  Determine the available capacity (ullage) of the tank by converting
    the reading on the fuel gauge to gallons (See Appendix B). This
    ullage is communicated to the fuel supply contractor and marked in
    the fueling log.

4.  Block the tank truck wheels.

5.  Place drip pans under all pump hose fittings (if applicable) prior
    to unloading.

6.  Ensure the fill nozzle is place in the appropriate tank
    appurtenance.

> Both the NWS representative and the delivery driver shall remain with
> the vehicle at all times during unloading. Gauges on the tank and the
> truck shall be continuously monitored to ensure the ullage is not
> exceeded. If an alarm engages, the unloading of fuel shall be stopped
> as soon as possible.
>
> After fuel unloading is completed:

7.  Record the amount of fuel transferred to the tank in the log
    (Appendix B).

8.  Drain the fill hose and then ensure that all drain valves are closed
    (if applicable) prior to removal of the hose from the tank.

9.  Pour any fuel in the drip pans, tank truck containment pool, or
    spill container on the fill pipe into the tank (if it has the
    capacity) or disposed of appropriately.

10. Inspect the tank truck before removing the blocks to ensure the
    lines have been disconnected from the tank.

11. Remove the blocks from the truck wheels

12. Place a copy of the fuel unloading checklist in the SPCC plan.

> **Inspections And Records**[Inspection and Maintenance of
> Tanks]{.underline}: The 750-gallon AST, day tank, and two 200-gallon
> RDA tanks shall be inspected weekly for any fuel outside the tank,
> especially at seams (including the underside). The concrete is
> inspected for cracks. The outside of exposed piping also is inspected
> weekly, especially at the joints such as gasket fittings. Monthly and
> annual inspections shall follow the checklists shown in Appendix C.
>
> [Record Keeping]{.underline}: The Environmental Focal Point or
> designated alternate is responsible for completing the ullage logs and
> documentation of fuel unloading procedures. These records, as well as
> records of all inspections, shall be maintained for at least 3 years
> from the time of inspection.
>
> **Site Security**The facility is operational 24 hours a day and well
> lit. Security cameras also are strategically placed around the outside
> of the facility. Adequate lighting is provided for all storage tanks
> to detect spills that may occur at night and to deter vandalism.
>
> The WFO generator and day tank are located in the WFO generator room
> that can be locked to restrict access. Signage around the day tank and
> 750-gallon AST warns of the presence of a combustible liquid, that the
> combustible liquid is diesel fuel number 2, and that smoking is not
> permitted near the tank. A fire extinguisher is located in the
> adjacent generator enclosure. The 750-gallon AST is situated such that
> is not in the direct line of vehicular traffic.
>
> The two 200-gallon RDA tanks are located within the RDA generator
> building and within a fenced area. The RDA generator building can be
> locked to restrict access. Signage around the of the tanks warns of
> the presence of a combustible liquid, that the combustible liquid is
> diesel fuel number 2, and that smoking is not permitted near the tank.
> A fire extinguisher is located in the RDA generator building.
>
> **Training**The Environmental Focal Point (person responsible for
> spill prevention) and an alternate shall be trained in the intent of
> applicable oil spill regulations and how to implement the inspection
> and maintenance procedures outlined in paragraph 3, above. Spill
> control and countermeasures also shall be included in the training.
>
> Training shall be repeated once per year. All new personnel
> responsible for implementing this SPCC plan shall be properly trained
> before beginning the new position. A record of who was trained, when,
> and by whom, shall be filed with this SPCC plan and kept for a period
> of 3 years.

**SPILL CONTROL**This section describes control measures that shall be
implemented to prevent any spilled oil from entering navigable waters or
adjoining shorelines.

> **Secondary Containment Designs, Construction Material, and
> Volume**The 750-gallon AST is situated within a concrete secondary
> containment basin. The basin is equipped with a manual drainage valve
> that is normally kept closed. Should precipitation accumulate in the
> basin and require draining, the valve is manually opened only after it
> is verified that no sheen or other evidence of fuel is present to
> ensure that the water will not cause a harmful discharge per 40 CFR
> 110 prior to discharge. A round spill container with 5-gallon capacity
> surrounds the fill spout to capture potential overflow during fuel
> transfer. The AST is equipped with an audible high-level alarm set to
> engage at 85 percent of capacity (638 gallons) and an automatic
> shutoff valve on the cam-lock fitting fill spout that is set to close
> at 90 percent of the AST capacity (675 gallons). A monitoring system
> that can detect one inch or more of fluid in the interstitial space of
> the storage tank is also present.
>
> The WFO generator day tank is contained within the WFO generator room
> that provides containment and is not exposed to precipitation. The day
> tank is situated over a rupture basin that is equipped with a float
> switch designed to detect fuel that has spilled or leaked. This float
> switch automatically shuts off the pump if engaged.
>
> Secondary containment for the two 200-gallon RDA tanks is provided for
> in the RDA generator building design and construction. The RDA
> generator building is designed with "tub flooring" that is
> approximately 6-to 8-inches deep, with a raised door frame to keep
> fuel from spilling out of the doorway.
>
> **Spill Kits Type and Location**The facility shall have kits designed
> to absorb diesel fuel and which can prevent discharged oil from
> reaching nearby water bodies or storm sewers. The kits include oil
> absorbent socks and mats in a polyethylene container that serves also
> as a disposal container. One spill kit is stored in each of the WFO
> generator room and RDA generator building.

**PART III - SPILL COUNTERMEASURES AND REPORTING**

The primary emphasis of this SPCC plan is on prevention. The spill
countermeasures presented do [not]{.underline} constitute a contingency
plan detailed in Title 40 CFR Part 109, nor is one required. Such a plan
is only required under Title 40 CFR 112.7(d) if it is impracticable to
provide containment, diversionary structures, or equipment to prevent
the discharge of oil to navigable waters. In addition, this facility is
not required to have a facility response plan under Title 40 CFR Part
112.20 because it does [not]{.underline}:

13. Transfer oil over water from vessels and have a total oil storage
    capacity of greater than or equal to 42,000 gallons, or

14. Have a total storage capacity over 1 million gallons.

**SPILL COUNTERMEASURES**This section presents countermeasures to
contain, clean up, and mitigate the effects of an oil spill that impacts
navigable waters or adjacent shorelines.

A spill containment and cleanup activity will never take precedence over
the safety of personnel. No countermeasure activities will be undertaken
until conditions are safe for workers. The "SWIMS" procedures should be
implemented as countermeasures:

**S** - Stop the leak and eliminate ignition sources.

> a\. Attempt to seal or some how stop leak if it can be done safely.
>
> b\. Attempt to divert flow away from catch basins with a spill barrier
> or the contents of the spill kit.
>
> c\. Eliminate all ignition sources in the immediate area.

**W** - Warn others.

> a\. Yell out "SPILL." Inform the person in-charge at your facility.
>
> b\. Account for all personnel and ensure their safety.
>
> c\. Notify contacts and emergency response contractor as described in
> the following section for assistance in control and cleanup.
>
> **I** - Isolate the area.

a\. Rope off the area.

**M** - Minimize your exposure. Stay upwind.

**S** - Stand by to assist the emergency response contractor, if
necessary.

**SPILL REPORTING**This section discusses the reporting procedures for
spills of diesel fuel at the facility. The individuals and organizations
that are notified vary based on the quantity of the spill, whether it
reaches navigable waters or adjoining shorelines, and the frequency of
spills.

A spill report form that requests the information to be reported to all
agencies in written form (to the extent known) is included in Appendix
E. Copies of the completed form should be submitted, preferably by
e-mail, to the NWS Environmental Compliance Officer and the NOAA
Regional Environmental Compliance Officer.

> **General Notification Procedures for All Spills**The responsible
> person or designee is directly charged with reporting
> [all]{.underline} oil spills that result from facility operations as
> follows:

1.  First, call 9-1-1 if there is an immediate emergency

2.  Next, notify the appropriate individuals within the NWS such that
    the individuals can keep internal records regarding the spill event.
    If necessary, the individuals can provide technical assistance
    regarding the procurement of cleanup contractors, the potential need
    for follow-up assessments, regulatory reporting, waste disposal, or
    other issues.

> 1\. **Mike Jacob, (301) 713-1838 Ext. 165**,
> [[JMichael.Jacob@noaa.gov]{.underline}](mailto:jmichael.jacob@noaa.gove,)**,**
> NWS Environmental Compliance Officer
>
> 2\. **Olga Kebis, (301) 713-1838 Ext. 173**,
> [Olga.Kebis@noaa.gov]{.underline}, NWS Safety Officer
>
> 3\. **Kirt Grahl**, **(816) 426-3226, Ext. 470**,
> [Kirt.Grahl@noaa.gov]{.underline}**,** NWS Central Regional
> Environmental/Safety Coordinator
>
> 4\. **Sherilyn Villegas**, **(816) 426-3925, Ext. 263**,
> [Sherilyn.S.Villegas@noaa.gov]{.underline}, NOAA Central Regional
> Environmental Compliance Officer
>
> **2. Federal Notification**
>
> The Federal Clean Water Act as described in Title 40 CFR Part 110.6,
> requires notifying the U.S. Environmental Protection Agency's (EPA)
> National Response Center (or the U.S. Coast Guard \[USCG\]) as soon as
> anyone has knowledge of any discharges of oil in quantities that "may
> be harmful." Title 40 CFR Part 110.3 defines "may be harmful" as a
> discharge that:

1.  Violates applicable water quality standards, or

2.  Causes a film or sheen upon or discoloration of the surface of the
    water or adjoining shorelines or causes a sludge or emulsion to be
    deposited beneath the surface of the water or upon adjoining
    shorelines.

> If either of these criterion are met contact:

3.  The National Response Center (EPA and USCG): **(800) 424-8802**

> Under the SPCC regulations, spill information listed in Title 40 CFR
> Part 112.4(a) must be reported to the regional EPA office within 60
> days if [either]{.underline} of the following occurs:

4.  A discharge of more than 1,000 gallons of oil into or upon navigable
    waters or adjoining shorelines in a single event, or

5.  Two spill events that cause visible sheens upon navigable waters or
    adjoining shorelines within any 12-month period.

> Diesel fuel is not listed as a hazardous substance under the
> Comprehensive Environmental Response, Compensation, and Liability Act
> (CERCLA); therefore, no other notification to the EPA is required for
> discharges of diesel fuel other than those listed above.
>
> **3. State Notification**
>
> To satisfy the state reporting requirements, the location and quantity
> of the spill must be determined. Under the Kansas Administrative
> Regulations, Part 28-44-24, a reportable quantity (RQ) is defined as
> follows:

6.  Any spill over 25 gallons, or

7.  Any spill which creates a sheen upon navigable waters of the State.

> If one or both of these criteria are met, contact the Kansas Emergency
> Spill Hotline within 24 hours of obtaining knowledge of the release:

8.  **(785) 296-1679** (During business hours)

9.  **(785) 296-0614** (After business hours)

> **4. Cleanup Contractor Notification**
>
> An emergency response contractor also should be notified to assist
> with the clean up of a spill, if necessary. Contact information for at
> least three emergency response vendors shall be maintained in this
> plan. NWS has identified the following contractors that are available
> for emergency response:

10. Haz-Mat Response, Inc. **(800) 229-5252**

11. Integrated Solutions **(620) 264-7050**

12. Safety Kleen **(620) 225-5016**

13. 3E Company **(800) 468-1760**

**PART IV - RECOMMENDED IMPROVEMENTS**

In accordance with Title 40 CFR Section 112.7, this section presents
physical upgrades or procedural changes that are not yet fully
operational but are called for in the plan.

> **PHYSICAL UPGRADES** **Secondary Containment**The facility should
> install a locking valve onto the drainage valve of the 750-gallon AST
> containment basin. This upgrade should be implemented within 6 months
> of the date of this plan.
>
> **PROCEDURAL CHANGES Inspections and Preventative Maintenance**The
> inspection checklists found in Appendix C should be followed. This
> requirement is found in Title 40 CFR Part 112.7(e)(8). The area within
> and around all tanks shall be inspected for signs of leakage
> regularly. Visual inspections of the outside each of the tank's walls
> shall be inspected for potential problems with tank integrity such as
> leaks or evidence of cracking or breaching. Also, the interstitial
> monitoring device in the 750-gallon AST is designed to monitor the
> integrity of its primary tank. If a problem is suspected with any
> tank, tightness testing should be initiated soon after discovery.
>
> **Training**The Environmental Focal Point (person responsible for
> spill prevention at the facility) and an alternate should be trained
> in the intent of the applicable oil spill regulations and how to
> implement the inspection and maintenance procedures outlined in the
> previous section. Spill control and countermeasures also should be
> included in the training. The alternate should be designated in case
> the primary person is off the site at the time of a spill. A
> recommended outline for the training is found in Appendix D.
>
> Training should be repeated once per year. All new personnel
> responsible for implementing the SPCC plan should be properly trained
> before beginning the new position. A record of who was trained, when,
> and by whom, should be filed with this SPCC plan and kept for a period
> of three years. This requirement is found in Title 40 CFR
> 112.7(e)(10).
>
> Spill prevention briefings for operating personnel should be conducted
> at frequent intervals to ensure adequate understanding of the SPCC
> plan and to describe spill events or failures, malfunctioning
> components, and recently developed precautionary measures.

Figure 1 Site Location

Figure 2 Site Layout

**TABLE 1**

**DESCRIPTIVE INVENTORY OF FACILITY STORAGE**

  ---------------------- --------------- ---------------- ---------- -----------
  **Tank**               **Nominal       **Product        **Type**   **Double\
                         Capacity        Stored**                    Walled?**
                         (Gallons)**                                 

  750-Gallon AST         750             Diesel fuel      AST        No^1^
                                         number 1                    

  RDA Tank               200             Diesel fuel      AST        No^2^
                                         number 1                    

  RDA Tank               200             Diesel fuel      AST        No^2^
                                         number 1                    

  25-Gallon Day Tank     25              Diesel fuel      AST        Yes^3^
                                         number 1                    

  **Total Capacity**     **1,175**                                   
  ---------------------- --------------- ---------------- ---------- -----------

Notes:

AST Aboveground storage tank

1 Tank is situated within a sufficiently impervious concrete containment
basin.

2 The RDA tank is located within a building that is designed and
constructed to provide sufficient secondary containment.

3 The day tank is situated over a rupture basin that is capable of
containing 110 percent the tank volume and is located within a building.

**TABLE 2**

**POTENTIAL SPILL SOURCES AND VOLUMES**

+------+---------------+------+---------+--------+-------------------+
| **   | **Event**     | **P  | **Es    | **Dir  | **Remarks**       |
| Sour |               | oten | timated | ection |                   |
| ce** |               | tial | Rate**  | of**   |                   |
|      |               | S    |         |        |                   |
|      |               | pill | **(     | *      |                   |
|      |               | Volu | gallons | *Spill |                   |
|      |               | me** | per     | Flow** |                   |
|      |               |      | mi      |        |                   |
|      |               | *    | nute)** |        |                   |
|      |               | *(ga |         |        |                   |
|      |               | llon |         |        |                   |
|      |               | s)** |         |        |                   |
+------+---------------+------+---------+--------+-------------------+
| 75   | Overfilling   | \>0  | 80^b^   | Nor    | Operational       |
| 0-Ga | or a ruptured | to   |         | thwest | procedures are in |
| llon | hose during   | 4    |         | or     | place to prevent  |
| AST  | fueling       | 0^a^ |         | South  | overfilling.      |
+------+---------------+------+---------+--------+-------------------+
|      | Failure of    | \>0  | V       | Nor    | Can be minimized  |
|      | fuel supply   | to   | ariable | thwest | through routine   |
|      | line to pump  | 750  |         | or     | inspections.      |
|      |               |      |         | South  |                   |
+------+---------------+------+---------+--------+-------------------+
|      | Structural    | \>0  | V       | Nor    | Low probability   |
|      | failure or    | to   | ariable | thwest | event that both   |
|      | vandalism     | 750  |         | or     | primary and       |
|      |               |      |         | South  | secondary tank    |
|      |               |      |         |        | shells would      |
|      |               |      |         |        | fail.             |
+------+---------------+------+---------+--------+-------------------+
|      | Vehicle       | \>0  | V       | Nor    | Tank is not in    |
|      | collision     | to   | ariable | thwest | the direct line   |
|      |               | 750  |         | or     | of traffic.       |
|      |               |      |         | South  |                   |
+------+---------------+------+---------+--------+-------------------+
|      | Overturn or   | \>0  | V       | Nor    | Low probability   |
|      | puncture      | to   | ariable | thwest | event.            |
|      | during        | 750  |         | or     |                   |
|      | natural       |      |         | South  |                   |
|      | disaster      |      |         |        |                   |
+------+---------------+------+---------+--------+-------------------+
| 2    | Failure of    | \>0  | V       | Nor    | Can be minimized  |
| 5-Ga | the pump to   | to   | ariable | thwest | through routine   |
| llon | shut down     | 750  |         |        | inspections.      |
| Day  | after filling |      |         |        |                   |
|      | day tank or   |      |         |        |                   |
| Tank | failure of    |      |         |        |                   |
|      | the line from |      |         |        |                   |
|      | pump to day   |      |         |        |                   |
|      | tank.         |      |         |        |                   |
+------+---------------+------+---------+--------+-------------------+
|      | Failure of    | \>0  | 10^c^   | Nor    | Can be minimized  |
|      | fuel return   |      |         | thwest | through routine   |
|      | line          |      |         |        | inspections.      |
+------+---------------+------+---------+--------+-------------------+
|      | Structural    | \>0  | V       | Nor    | Low probability   |
|      | failure or    | to   | ariable | thwest | event can be      |
|      | vandalism     | 25   |         |        | minimized through |
|      |               |      |         |        | regular           |
|      |               |      |         |        | inspections and   |
|      |               |      |         |        | maintenance.      |
+------+---------------+------+---------+--------+-------------------+
|      | Overturn or   | \>0  | V       | Nor    | Low probability   |
|      | puncture      | to   | ariable | thwest | event.            |
|      | during        | 25   |         |        |                   |
|      | natural       |      |         |        |                   |
|      | disaster      |      |         |        |                   |
+------+---------------+------+---------+--------+-------------------+

Notes:

> a Based on a maximum pumping rate of 80 gallons per minute from the
> fill truck and a maximum of 30 seconds to turn off the pump.
>
> b Approximate maximum pumping rate of fill truck.
>
> c Estimated return line flow rate.

**TABLE 2**

**POTENTIAL SPILL SOURCES AND VOLUMES**

+------+---------------+------+---------+--------+-------------------+
| **   | **Event**     | **P  | **Es    | **Dir  | **Remarks**       |
| Sour |               | oten | timated | ection |                   |
| ce** |               | tial | Rate**  | of**   |                   |
|      |               | S    |         |        |                   |
|      |               | pill | **(     | *      |                   |
|      |               | Volu | gallons | *Spill |                   |
|      |               | me** | per     | Flow** |                   |
|      |               |      | mi      |        |                   |
|      |               | *    | nute)** |        |                   |
|      |               | *(ga |         |        |                   |
|      |               | llon |         |        |                   |
|      |               | s)** |         |        |                   |
+------+---------------+------+---------+--------+-------------------+
| Each | Overfilling   | \>0  | 80^b^   | Nor    | Operational       |
| of   | or a ruptured | to   |         | thwest | procedures are in |
| two  | hose during   | 4    |         |        | place to prevent  |
| 25   | fueling       | 0^a^ |         |        | overfilling.      |
| 0-Ga |               |      |         |        |                   |
| llon |               |      |         |        |                   |
| RDA  |               |      |         |        |                   |
| T    |               |      |         |        |                   |
| anks |               |      |         |        |                   |
+------+---------------+------+---------+--------+-------------------+
|      | Failure of    | \>0  | V       | Nor    | Can be minimized  |
|      | fuel supply   | to   | ariable | thwest | through routine   |
|      | line to pump  | 200  |         |        | inspections.      |
+------+---------------+------+---------+--------+-------------------+
|      | Structural    | \>0  | V       | Nor    | Low probability   |
|      | failure or    | to   | ariable | thwest | event that both   |
|      | vandalism     | 200  |         |        | primary and       |
|      |               |      |         |        | secondary tank    |
|      |               |      |         |        | shells would      |
|      |               |      |         |        | fail. The RDA     |
|      |               |      |         |        | generator         |
|      |               |      |         |        | building is       |
|      |               |      |         |        | within a fenced   |
|      |               |      |         |        | area, can be kept |
|      |               |      |         |        | locked, and       |
|      |               |      |         |        | designed and      |
|      |               |      |         |        | constructed to    |
|      |               |      |         |        | contain spills.   |
+------+---------------+------+---------+--------+-------------------+
|      | Overturn or   | \>0  | V       | Nor    | Low probability   |
|      | puncture      | to   | ariable | thwest | event.            |
|      | during        | 200  |         |        | Double-walled     |
|      | natural       |      |         |        | tank gives extra  |
|      | disaster      |      |         |        | protection from   |
|      |               |      |         |        | rupture, but a    |
|      |               |      |         |        | large tornado     |
|      |               |      |         |        | could cause a     |
|      |               |      |         |        | spill.            |
+------+---------------+------+---------+--------+-------------------+

Notes:

> a Based on a maximum pumping rate of 80 gallons per minute from the
> fill truck and a maximum of 30 seconds to turn off the pump.
>
> b Approximate maximum pumping rate of fill truck.
>
> c Estimated return line flow rate.

**APPENDIX A**

**TANK RECORDS**

**APPENDIX B**

**TANK ULLAGE/FUELING LOG AND**

**FUEL UNLOADING PROCEDURE CHECKLIST**

**(2 Pages)**

**APPENDIX B-1**

**TANK ULLAGE AND FUELING LOG**

Tank Capacity gallons

+---+----+--------+--------+---------+---------+--------------------+
| * | ** | *      | **I    | **Av    | **Q     | **Comments**       |
| * | In | *Gauge | nitial | ailable | uantity |                    |
| D | it | Rea    | Volume | C       | Added** |                    |
| a | ia | ding** | of     | apacity |         |                    |
| t | ls |        | Fuel   | or      | **(Gal  |                    |
| e | ** |        | in     | Ulla    | lons)** |                    |
| * |    |        | Tan    | ge^b^** |         |                    |
| * |    |        | k^a^** |         |         |                    |
|   |    |        |        | **(Gal  |         |                    |
|   |    |        | *      | lons)** |         |                    |
|   |    |        | *(Gall |         |         |                    |
|   |    |        | ons)** |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+
|   |    |        |        |         |         |                    |
+---+----+--------+--------+---------+---------+--------------------+

Notes:

a From gauge reading

b Available capacity = tank capacity - initial volume of fuel in tank

**APPENDIX B-2**

**FUEL UNLOADING PROCEDURE CHECKLIST**

**Date:** **Tank:**

**NWS Representative:** **Supplier:**

  --------------------- ---------- ------------------------------------------------ ---------------
                        **ITEM**   **DESCRIPTION**                                  **COMMENT**

  **The following six                                                               
  items must be                                                                     
  completed                                                                         
  [prior]{.underline}                                                               
  to fuel unloading:**                                                              

                        1          Move spill containment equipment, such as booms  
                                   or spill barriers, into the unloading area.      

                        2          Ensure the audible high-level alarm system and   
                                   automatic shutoff valve are functioning          
                                   properly.                                        

                        3          Determine the available capacity (ullage) of the 
                                   tank by converting the reading on the fuel gauge 
                                   to gallons (see Appendix B, page B-1 in SPCC     
                                   plan). This ullage should then be marked in the  
                                   fueling log and communicated to the tank truck   
                                   unloading contractor.                            

                        4          Block the wheels of the tank truck.              

                        5          Place drip pans under all pump hose fittings (if 
                                   applicable) after the hose is hooked up to the   
                                   tank and prior to unloading.                     

                        6          Ensure the fill nozzle is placed in the          
                                   appropriate tank appurtenance.                   

  **During unloading**                                                              

                        7          Ensure that the NWS representative and the tank  
                                   truck operator remain with the vehicle at all    
                                   times during unloading.                          

                        8          Monitor the gauges on the tank and the truck     
                                   continuously to ensure the ullage is not         
                                   exceeded. If the audible high-level alarm        
                                   sounds, the unloading of fuel is stopped as soon 
                                   as possible.                                     

  **After fuel                                                                      
  unloading is                                                                      
  completed**                                                                       

                        9          Record the amount of fuel unloaded in the log    
                                   (Appendix B, page B-1).                          

                        10         Prior to removing the fill hose from the tank,   
                                   ensure that it is drained and that all drain     
                                   valves are closed (if applicable).               

                        11         Any fuel accumulated in the drip pans or spill   
                                   container on the fill pipe should be poured into 
                                   the tank (if it has the capacity) or disposed of 
                                   appropriately (describe how it was disposed of,  
                                   if applicable).                                  

                        12         Inspect the tank truck prior to removing the     
                                   blocks to ensure the lines have been             
                                   disconnected from the tank.                      

                        13         Remove the blocks from tank truck wheels.        

                        14         Place a copy of this fuel-unloading checklist in 
                                   the SPCC plan.                                   
  --------------------- ---------- ------------------------------------------------ ---------------

**APPENDIX C**

**INSPECTION CHECKLISTS**

**(2 Pages)**

  ----------------------- ----------------- --------- -------- -----------------------
  **MONTHLY INSPECTION                                         
  CHECKLIST**                                                  

  Date of Inspection:     Tank Name or No.:                    

  Date of Last            Inspected by:                        
  Inspection:             Signature:                           

  **A. TANKS**                              **YES**   **NO**   **NOTES**

  1\. Are tanks marked                                         
  properly?                                                    

  2\. Is area atop and                                         
  around tank and within                                       
  berm free of                                                 
  combustible materials,                                       
  debris, and stains?                                          

  3\. Is there any oil on                                      
  the ground, concrete,                                        
  or asphalt around the                                        
  tank?                                                        

  4\. Are there any                                            
  visible cracks or                                            
  indications of                                               
  corrosion on the tank,                                       
  at fittings, joints, or                                      
  seals (such as paint                                         
  peeling or rust spots)?                                      

  5\. Are there any                                            
  raised spots, dents, or                                      
  cracks on the tank?                                          

  6\. Does it appear that                                      
  the foundation has                                           
  shifted or settled?                                          

  7\. Is the fuel gauge                                        
  working properly?                                            

  8\. Are all vents clear                                      
  so they may properly                                         
  operate?                                                     

  9\. If rainwater is                                          
  present within                                               
  containment, does                                            
  capacity remain for                                          
  spill control (if                                            
  applicable)?                                                 

  **B. PIPING**                                                

  1\. Is there any oil on                                      
  the outside of or under                                      
  any aboveground piping,                                      
  hoses, fittings, or                                          
  valves?                                                      

  2\. Are aboveground                                          
  piping, hoses,                                               
  fittings, or valves in                                       
  good working condition?                                      

  **C.                                                         
  SECURITY/SAFETY/SPILL                                        
  COUNTERMEASURES**                                            

  1\. Are lights working                                       
  properly to detect a                                         
  spill at night?                                              

  2\. Are all locks in                                         
  the "lock" position?                                         

  3\. Are all warning                                          
  signs properly posted                                        
  and readable?                                                

  4\. Are vehicle guard                                        
  posts in place and                                           
  properly secured (if                                         
  applicable)?                                                 

  5\. Are spill kits                                           
  easily accessible,                                           
  protected from the                                           
  weather, complete, and                                       
  replenished if                                               
  necessary?                                                   

  **Corrective Actions                                         
  Required:**                                                  
  ----------------------- ----------------- --------- -------- -----------------------

  --------------------- ----------------- --------- -------- -----------------------
  **ANNUAL INSPECTION                                        
  CHECKLIST**                                                

  Date of Inspection:   Tank Name or No.:                    

  Date of Last          Inspected by:                        
  Inspection:           Signature:                           

  **A. MONTHLY                            **YES**   **NO**   **NOTES**
  CHECKLIST**                                                

  1\. Have monthly                                           
  inspection checklists                                      
  been completed?                                            

  **B. TANKS**                                               

  1\. Are all alarms                                         
  and automatic shutoff                                      
  devices working                                            
  properly?                                                  

  2\. Is interstitial                                        
  monitor functioning                                        
  properly (if                                               
  applicable)?                                               

  **C. OTHER**                                               

  1\.                                                        

  **Corrective Actions                                       
  Required:**                                                
  --------------------- ----------------- --------- -------- -----------------------

**APPENDIX D**

**TRAINING OUTLINE AND**

**TITLE 40 OF THE CODE OF FEDERAL REGULATIONS**

**PARTS 112.1 THROUGH 112.20 - OIL POLLUTION PREVENTION**

**(29 Pages)**

**APPENDIX D**

**OUTLINE FOR SPILL PREVENTION, CONTROL, AND COUNTERMEASURES TRAINING**

Training will be provided for facility personnel at the following times:

> System startup or whenever new equipment is installed
>
> Within the first week of employment for new personnel
>
> Annually

The training will include complete instruction in the elements of the
facility's Spill Prevention, Control, and Countermeasures plan and will
include the following:

> A. Pollution Control Laws, Rules, and Regulations Including a Summary
> of Title 40 of the Code of Federal Regulations Part 112, "Oil
> Pollution Prevention" (see Attachment)
>
> B. Fuel Storage
>
> 1\. Purpose and application of the following system elements:
>
> a\. Tanks
>
> b\. Piping
>
> c\. Pumps
>
> d\. Accessory equipment
>
> e\. Electronic monitors
>
> 2\. Operation, maintenance, and inspection of system elements
>
> C. Spill Prevention
>
> 1\. Potential spill sources
>
> 2\. Spill flow direction and impact on navigable waters
>
> 3\. Procedures to prevent spills, especially during fuel unloading
>
> D. Spill Control
>
> 1\. Secondary containment
>
> 2\. Safety valves
>
> 3\. Pump and equipment shutoff switches
>
> 4\. Use of catch basin inlet covers or other diversionary devices
>
> E. Spill Countermeasures
>
> 1\. Location and use of emergency phone numbers
>
> 2\. Location and use of fire extinguishers
>
> 3\. Location and use of spill cleanup kit
>
> 4\. Stopping the leak

**ATTACHMENT**

**TITLE 40 OF THE CODE OF FEDERAL REGULATIONS**

**PARTS 112.1 THROUGH 112.20 - OIL POLLUTION PREVENTION**

**APPENDIX E**

**SPILL REPORTING FORM**

**(1 Page)**

**APPENDIX E**

**SPILL REPORTING FORM**

+-----------------------------------+-----------------+-----------------+
| 1.  **GENERAL**                   |                 |                 |
+-----------------------------------+-----------------+-----------------+
| Name of Facility: **National      | Address: **104  |                 |
| Weather Service**                 | Airport Road**  |                 |
|                                   |                 |                 |
| **Dodge City Weather Forecast     | **Dodge City,   |                 |
| Office**                          | KS 67801**      |                 |
+-----------------------------------+-----------------+-----------------+
| Completed By:                     | Organization:   |                 |
|                                   | **National      |                 |
|                                   | Weather         |                 |
|                                   | Service**       |                 |
+-----------------------------------+-----------------+-----------------+
| Position:                         | Phone:          |                 |
+-----------------------------------+-----------------+-----------------+
| 2.  **SPILL INFORMATION**         |                 |                 |
+-----------------------------------+-----------------+-----------------+
| Date:                             | Time:           |                 |
+-----------------------------------+-----------------+-----------------+
| Location at Facility:             | Quantity:       |                 |
+-----------------------------------+-----------------+-----------------+
| Substance Spilled:                | Other:          |                 |
+-----------------------------------+-----------------+-----------------+
| 3.  **OUTSIDE NOTIFICATIONS**     |                 |                 |
+-----------------------------------+-----------------+-----------------+
| **Agencies**                      | **Recorder at   | **Date and      |
|                                   | Outside         | Time**          |
|                                   | Agency**        |                 |
+-----------------------------------+-----------------+-----------------+
| Call **9-1-1** if there is an     |                 |                 |
| immediate emergency               |                 |                 |
+-----------------------------------+-----------------+-----------------+
| NWS/NOAA:                         |                 |                 |
|                                   |                 |                 |
| **Mike Jacob: (301) 713-1838,     |                 |                 |
| Ext. 165**                        |                 |                 |
|                                   |                 |                 |
| **Olga Kebis: (301) 713-1838,     |                 |                 |
| Ext. 173**                        |                 |                 |
|                                   |                 |                 |
| **Kirt Grahl: (816) 426-3226,     |                 |                 |
| Ext. 470**                        |                 |                 |
|                                   |                 |                 |
| **Sherilyn Villegas: (816)        |                 |                 |
| 426-3925, Ext. 263**              |                 |                 |
+-----------------------------------+-----------------+-----------------+
| EPA NATIONAL RESPONSE CENTER or   |                 |                 |
|                                   |                 |                 |
| U.S. COAST GUARD: **(800)         |                 |                 |
| 424-8802**                        |                 |                 |
+-----------------------------------+-----------------+-----------------+
| Kansas Emergency Spill Hotline:   |                 |                 |
|                                   |                 |                 |
| **During Business Hours: (785)    |                 |                 |
| 296-1679**                        |                 |                 |
|                                   |                 |                 |
| **After Business Hours: (785)     |                 |                 |
| 296-0614**                        |                 |                 |
+-----------------------------------+-----------------+-----------------+
| 4.  **INFORMATION ON SOURCE AND   |                 |                 |
|     CAUSE**                       |                 |                 |
+-----------------------------------+-----------------+-----------------+
|                                   |                 |                 |
+-----------------------------------+-----------------+-----------------+
| **5. DESCRIPTION OF ENVIRONMENTAL |                 |                 |
| DAMAGE**                          |                 |                 |
+-----------------------------------+-----------------+-----------------+
|                                   |                 |                 |
+-----------------------------------+-----------------+-----------------+
| **6. CLEANUP ACTION(S) TAKEN**    |                 |                 |
+-----------------------------------+-----------------+-----------------+
|                                   |                 |                 |
+-----------------------------------+-----------------+-----------------+
| **7. CORRECTIVE ACTION(S) TO      |                 |                 |
| PREVENT FUTURE SPILLS**           |                 |                 |
+-----------------------------------+-----------------+-----------------+
|                                   |                 |                 |
+-----------------------------------+-----------------+-----------------+

Note: All information must be filled in. If something is unknown, write
"unknown."

> Copies must be submitted to the NWS/NOAA personnel listed above.

**APPENDIX F**

**CROSS REFERENCE OF THE REQUIREMENTS OF**

**TITLE 40 OF THE CODE OF FEDERAL REGULATIONS,**

**PART 112.7, WITH THIS PLAN**

**(1 Page)**

**APPENDIX F**

**CROSS REFERENCE OF THE REQUIREMENTS OF 40 CFR 112.7 WITH THIS PLAN**

  ------------------- --------------------------------------- ------------------
  **CFR Citation**    **Item**                                **Plan Location**

  112.7(a)            Spill History                           Part I.B.4

  112.7(b)            Potential Spill Prediction, Volumes,    Part I.B.5 and
                      and Rates                               Table 2

  112.7(c)            Containment and Diversionary Structures Part I.B.2 and
                                                              Part II.B.2

  112.7(d)            Secondary Containment Impracticability  Not Applicable

  112.7(e)(1)         Drainage Control                        Part I.B.3

  112.7(e)(2)         Bulk Storage Tanks and Secondary        See Subparts
                      Containment                             

  112.7(e)(2)(I)      Tank Compatibility with Its Contents    Part II.A.1

  112.7(e)(2)(ii)     Diked Area Construction and Containment Not Applicable
                      for Storage Tanks                       

  112.7(e)(2)(iii)    Diked Area Inspection and Drainage of   Not Applicable
                      Rainwater                               

  112.7(e)(2)(iv)     Corrosion Protection of Buried Metallic Not Applicable
                      Storage Tanks                           

  112.7(e)(2)(v)      Corrosion Protection of Partially       Not Applicable
                      Buried Metallic Tanks                   

  112.7(e)(2)(vi)     Aboveground Tank Periodic Integrity     Part IV.B.1
                      Testing                                 

  112.7(e)(2)(vii)    Control of Leakage through Internal     Not Applicable
                      Heating Coils                           

  112.7(e)(2)(viii)   Tank Installation Fail-safe Engineered  Part II.A.1, B.1

  112.7(e)(2)(ix)     Observation of Disposal Facilities for  Not Applicable
                      Effluent Discharge                      

  112.7(e)(2)(x)      Visible Oil Leak Corrections from Tank  Part II.A.3 &
                      Seams and Gaskets                       Appendix C

  112.7(e)(2)(xi)     Appropriate Position of Mobile or       Not Applicable
                      Portable Tanks                          

  112.7(e)(3)         Facility Transfer Operations            See Subparts

  112.7(e)(3)(i)      Buried Piping Installation Protection   Part II.A.1 &
                      and Examination                         Appendix C

  112.7(e)(3)(ii)     Not-in-service and Standby Terminal     Not Applicable
                      Connections                             

  112.7(e)(3)(iii)    Pipe Support Designs                    Not Applicable

  112.7(e)(3)(iv)     Aboveground Valve and Pipeline          Not Applicable
                      Examination                             

  112.7(e)(3)(v)      Aboveground Piping Protection from      Not Applicable
                      Vehicular Traffic                       

  112.7(e)(4)         Facility Truck Unloading Operations     Part II.A.2

  112.7(e)(5-7)       Oil Production Facilities (Onshore) and Not Applicable
                      Oil Drilling, Production, or Work over  
                      Facilities (On Shore and Offshore)      

  112.7(e)(8)         Inspections and Record Keeping          Part II.A.3

  112.7(e)(9)         Security                                See Subparts

  112.7(e)(9)(i)      Fencing                                 Part II.A.4

  112.7(e)(9)(ii)     Flow Valves Locked                      Not Applicable

  112.7(e)(9)(iii)    Starter Controls Locked                 Not Applicable

  112.7(e)(9)(iv)     Pipeline Loading and Unloading          Not Applicable
                      Connections Securely Capped             

  112.7(e)(9)(v)      Lighting Adequate to Detect Spills      Part II.A.4

  112.7(e)(10)        Training                                See Subparts

  112.7(e)(10)(i)     Personnel Instructions                  Part II.A.5 &
                                                              Appendix D

  112.7(e)(10)(ii)    Designated Person Responsible for Spill Page i
                      Prevention                              

  112.7(e)(10)(iii)   Spill Prevention Briefings              Part IV.B.2
  ------------------- --------------------------------------- ------------------

Note: CFR Code of Federal Regulations