July 22, 1994

Contract \# TW0592

**SPECIAL SPECIFICATION**

**SECTION 15995**

**[COMMISSIONING]{.underline}**

[Page]{.underline}

**[PART 1 - GENERAL]{.underline}**

1.01
Description\...\...\...\...\...\...\...\...\...\...\...\...\...\...\....
2

1.02Related
Work\...\...\...\...\...\...\...\...\...\...\...\...\...\...\.... 2

1.03Quality
Assurance\...\...\...\...\...\...\...\...\...\...\...\...\..... 3

1.04References\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
3

1.05Submittals\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
4

1.06
Documentation\...\...\...\...\...\...\...\...\...\...\...\...\...\.....
4

1.07 Project/Site
Conditions\...\...\...\...\...\...\...\...\...\...\.... 4

1.08Responsibility of
Others\...\...\...\...\...\...\...\...\...\...\.... 5

1.09 Design
Basis\...\...\...\...\...\...\...\...\...\...\...\...\...\...\... 5

1.10System Intended Operation and Performance\...\...\...\...\..... 7

**[PART 2 - PRODUCTS]{.underline}**

2.01
Materials\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
16

2.02
Report\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
16

2.01 Services and
Equipment\...\...\...\...\...\...\...\...\...\...\..... 19

**[PART 3 - EXECUTION]{.underline}**

3.01
General\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\.....
20

3.02
Procedure\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
20

3.03
Verification\...\...\...\...\...\...\...\...\...\...\...\...\...\...\...
20

3.04 Check
Lists\...\...\...\...\...\...\...\...\...\...\...\...\...\...\.... 22

**SPECIAL SPECIFICATION**

**SECTION 15995**

**[COMMISSIONING]{.underline}**

tc \"PART1-GENERAL\.....\"\\l§**[PART 1 - GENERAL]{.underline}**

tc \"1.01DESCRIPTION\.....\"\\l§\***1.01[DESCRIPTION]{.underline}**

> A. Purpose
>
> 1\. Verify correct installation and pre-operational check.
>
> 2\. Verify operation and functional performance of mechanical systems
> for compliance with Paragraphs 1.09 and 1.10.
>
> 3\. Document mechanical pre-operational checks and functional
> performance checks. See Paragraph 3.04.
>
> 4\. Verify application of operation and maintenance manuals, as-built
> (record) documents, spare parts listing, special tools listing, and
> other items as may be specified in this Section for support of
> mechanical systems and equipment.
>
> 5\. Coordinate and direct training to personnel for operation and
> maintenance of mechanical equipment and systems.
>
> B. General
>
> 1\. Furnish labor and material to accomplish complete commissioning as
> specified in this Section. Complete interim commissioning of HVAC
> systems during initial season operation and followup commissioning of
> required HVAC systems during additional season operation. Note that
> this Section is directed at the Design Professional, Contractor, or
> SNL who may be the Commissioning Authority (CA).

tc \"1.02RELATEDWORK\.....\"\\l§\***1.02[RELATED WORK]{.underline}**

> A. Includes Sections 01300, 10282, and 13943 and all sections of
> Division 15 except for:
>
> 1\. Section 15017
>
> 2\. Section 15023
>
> 3\. Section 15050
>
> 4\. Section 15055
>
> 5\. Section 15135
>
> 6\. Section 15175
>
> 7\. Section 15495
>
> 8\. Section 15501
>
> 9\. Section 15883
>
> 10\. Section 15910
>
> 11\. Section 15932

tc \"1.03QUALITYASSURANCE\.....\"\\l§\***1.03[QUALITY
ASSURANCE]{.underline}**

> A. Use: ASHRAE Guideline 1-1989, \"Guideline for Commissioning of HVAC
> Systems for Defining Commissioning Plan\" for defining the
> \"Commissioning Plan.\"
>
> B. Qualifications: Show proof of a minimum 3 years experience
> performing Commissioning according to ASHRAE Guideline 1-1989 on
> office/laboratory type buildings of at least 10,000 square feet which
> have ducted heating and cooling systems, ducted exhaust systems,
> piping systems, and energy management control systems.

tc \"1.04REFERENCES\.....\"\\l§\***1.04[REFERENCES]{.underline}**

> A. ASHRAE Guideline 1-1989, Guideline for Commissioning of HVAC
> Systems for Defining Commissioning Plan.
>
> B. ASHRAE 62-89.
>
> C. Definitions
>
> 1\. Pre-Operational Tests - Tests which verify that ductwork, power,
> mechanical, fluid, control and instrumentation systems are free from
> leaks, operate correctly, are ready to be placed in service.
>
> 2\. Verification Tests - Tests which verify that controlled systems
> under controlled conditions operate correctly and as intended.
>
> \*

**tc \"\"\\l§**1.05 [SUBMITTALS]{.underline}

> **A. Submit the following for approval prior to starting the
> commissioning process.**
>
> **1. Qualifications proof of experience with the bid.**
>
> **2. Commissioning Plan (See example Commissioning Plan in ASHRAE
> 1-1989, describe extent and delivery schedule.)**
>
> **3. Training Plan (Describe the extent of plan, expected duration of
> training, personnel involved, schedule, etc. See example Commissioning
> Plan.)**
>
> **4. Tool List: Provide tool identification, equipment tools are to be
> used on, reason tools are required, source of tools, price of tools
> and delivery.)**
>
> **5. Test Equipment List: Provide identification of equipment and
> recalibration certification.**
>
> **B. Submit a final report 4 weeks after completion of the mechanical
> system evaluation to SNL for approval. Resubmit commented final report
> after resolving comments and making corrections to SNL\'s
> satisfaction.**

**tc \"1.06DOCUMENTATION\.....\"\\l§\***1.06[DOCUMENTATION]{.underline}

> **A. Obtain the following for the Commissioning process:**
>
> **1. Project plans and specification (contract documents), authorized
> revisions, Mechanical shop drawings and submittals (approved, Test,
> Adjust, and Balance report, equipment start-up and certification
> reports, etc.**
>
> **2. Records of required code authority inspections, documentation
> sign-offs, etc.**
>
> **B. Prepare a bound report at the completion of the pre-operational
> and verification process. Include in the report completed
> pre-operational and verification checklists, all documentation
> identified under Paragraph 1.05A., and an evaluation. Identify in the
> evaluation system operational deviations which adversely affect system
> performance and evaluate the impact (specify design conditions and
> operational conditions as part of the impact evaluation). Prepare
> report according to Part 2.**

tc \"\"\\l§**\*1.07[PROJECT/SITE CONDITIONS]{.underline}**

> A. Expect to adjust the systems during the winter and summer for the
> required operations.

tc \"1.08RESPONSIBILITYOFOTHERS\.....\"\\l§\***1.08[RESPONSIBILITY OF
OTHERS]{.underline}**

> A. General Contractor - Applicable specification sections may outline
> trade responsibilities during the mechanical commissioning process.
>
> 1\. Verify completeness of building envelope, perimeter and interior
> items which effect proper operation and control of Mechanical
> equipment and systems.
>
> 2\. Coordinate participation and cooperation of specialty contractors
> (electrical, TAB, building management, etc.) under your jurisdiction
> as required for the commissioning process.
>
> B. Contractors Specialty
>
> 1\. Provide labor, material, equipment, etc., required within the
> scope of this specialty to facilitate the commissioning process.
> Perform form tests and verification procedures required by the
> commissioning process when requested by the CA and directed by the
> General Contractor.
>
> C. Sandia National Laboratory (SNL)
>
> 1\. Schedule personnel to participate in the commissioning process.
>
> 2\. Advise the CA regarding changes in building occupancy and/or
> usage.

tc \"1.09DESIGNBASIS\.....\"\\l§\***1.09[DESIGN BASIS]{.underline}**

> A. Mechanical
>
> 1\. Location (City, State): Albuquerque, New Mexico
>
> 2\. Elevation: 5300 feet (ft.)
>
> 3\. Design Conditions
>
> Location Winter Summer Relative Notes
>
> Humidity
>
> degrees percent
>
> Fahrenheit relative
>
> dry bulb (deg. Fdb)/ humidity
>
> [(deg. Fdb)]{.underline} [(deg. Fwb)(percent rh)]{.underline}

Outside 12 96/61 - -

Inside (Clean Room) 68 68 30 -

Inside (General) 72 78 Uncontrolled -

> 4\. Building Basis
>
> a\. Area
>
> 1\) Total Conditioned Space gross square feet (gsf)
>
> a\) 43,600 (North Wing)
>
> b\) 8,500 (West Wing)
>
> 2\) Per Floor Conditioned Space gsf
>
> a\) North Wing = 21,600
>
> b\) West Wing = 8,500
>
> b\. Envelope (average)
>
> 1\) Floors Description: On grade is poured concrete; above grade is
> poured concrete on metal deck.
>
> 2\) Roofs Description: 99-percent, opaque, metal deck on joists,
> R-value = 21.1 (ASHRAE Type 1); 1-percent, double-domed skylight,
> R-Value = 2.2, Shading Coefficient = .5.
>
> 3\) Walls Description: 79-percent, opaque, exterior-insulated-finish
> system, R-value = 28.6 (ASHRAE Group G); 21-percent
> gray-tint/insulated, double pane glass, R-Value = 2.57, Shading
> Coefficient = 0.4.
>
> c\. Interior Loads (average)
>
> 1\) People: 148 square foot (ft.2) per person, 315 British thermal
> units (Btu.)/hour (hr.) (sensible), 325 Btu./hr. (latent); occupied
> between 8 a.m and 5 p.m. Monday through Friday except for holidays.
>
> 2\) Lighting: 1.2 Watts (W)/ft.2.
>
> 3\) Equipment: 6.2 W/ft.2.
>
> d\. Ventilating Requirements: 7.4 cubic feet per minute (cfm)/ft.2
>
> e\. Noise Requirements: Identified in the Specifications.
>
> f\. Seismic Requirements: Identified in the Specifications.
>
> g\. Fire Protection Requirements: Coverage density by zone drawings
> and acceptance testing by NFPA 13 and 14.

tc
\"1.10SYSTEMINTENDEDOPERATIONANDPERFORMANCE\.....\"\\l§\***1.10[SYSTEM
INTENDED OPERATION AND PERFORMANCE]{.underline}**

> A. Mechanical - HVAC
>
> 1\. General Building System Description (Include overall system
> capacities, quantities, and system-to-system functions.)
>
> 2\. Specific Systems
>
> a\. Emergency Chilled Water System:
>
> 1\) Chiller: Single 470 ton-rated water-cooled, centrifugal chiller.
> The chiller uses up to 329 kW to cool water from 38 deg. F to 50
> deg. F with 75 deg. F to 85 deg. F condenser water. The chiller, with
> a cooling tower and associated pumps, provides a backup source of
> chilled water.
>
> 2\) Pump and Components: One 20-hp., base-mounted, end-suction,
> centrifugal pump with one 33.6-gal., diaphragm type, expansion tank
> and an 8-in., air separator are connected to the chiller forming the
> primary circuit of a primary/secondary arrangement. The pump provides
> 940 gpm at 34 ft. of water.
>
> 3\) Controls: The system is controlled by a DDC system.
>
> b\. Tower Water Systems:
>
> 1\) Cooling Tower: Factory assembled, induced-draft, crossflow tower
> with vertical air discharge w/2 - 15-hp., axial-flow fans and four
> 7-kW, sump heaters. The tower cools 1350 gpm of water from 85 deg. F
> to 75 deg. F. The tower with a chiller functions in a back up role for
> the chilled water system.
>
> 2\) Pumping: One 50 hp. base-mounted, end suction, centrifugal pump
> providing 1360 gpm at 98 ft. of water.
>
> 3\) Controls: System is controlled by a DDC system.
>
> c\. Secondary Chilled Water System:
>
> 1\) System Configuration: Primary/secondary arrangement with the
> primary source coming from an existing plant main or from the backup
> chiller. The secondary loop serves chilled water coils for all the air
> handling units and exchanges heat with the process cooling water
> system and process DI water system.
>
> 2\) Pumps: Two 20-hp., base-mounted, end-suction, centrifugal pumps in
> a parallel-pumping arrangement such that each pump provides 50 percent
> of the total flow (940 gpm) at 85 ft. of water. No redundancy or
> excess capacity has been provided; however, one pump operating alone
> can provide approximately 75 percent of the total load.
>
> 3\) Controls: The system is controlled by a DDC system.
>
> d\. Heating Water System
>
> 1\) System Configuration: A heat transfer package uses 15 psig steam
> to generate building heating water which is distributed via a piping
> network to all air terminal units (variable-air-volume boxes),
> duct-mounted heating water coils, hot water unit heaters, radiant
> heaters, and AHU-15 and -16 heating water coils.
>
> 2\) Exchanger: Shell-and-tube type with 15-psig steam on the shell
> side and 160 deg. F entering and 180 deg. F leaving water on the tube
> side.
>
> 3\) Pumps and Components: Two 7.5-hp. base-mounted, end-suction,
> centrifugal pumps with one 44.4-gal., diaphragm type, expansion tank
> and a 3-in. air separator. Pumps are in a parallel-pumping arrangement
> such that each pump provides 50 percent of the total flow (168 gpm) at
> 88 ft. of water. No redundancy or excess capacity has been provided;
> however, one pump operating alone can provide approximately 75 percent
> of the total load.
>
> 4\) Controls: The system is controlled by a DDC system.
>
> e\. Steam and Condensate Piping System:
>
> 1\) System Configuration: An existing 4-in., 120-psig steam line is
> routed into the west side of the building to a two-stage,
> pressure-reducing station which reduces the pressure to 15 psig. The
> low pressure steam serves the basement air handling unit steam coils,
> humidifiers, heat transfer package, domestic water heater, and the
> high temperature cooling water heat exchanger. Condensate is routed to
> a pressure powered pump (w/50 psig steam as a motive source) which
> pumps the condensate at 40 psig to an existing 2-in. condensate header
> on the west side of the building.
>
> f\. Air Conditioning:
>
> 1\) North Wing Offices: The office areas are served by a 27,000 cfm
> built-up variable volume air handler located along the east wall of
> the north wing basement. The unit consist of: steam preheat coil,
> chilled water coil, plenum fan section, 60-65 percent filter section,
> and mixing box. The variable volume terminals are pressure independent
> terminal units. The supply fan is controlled from a static pressure
> sensor located in the medium pressure supply duct directly upstream of
> the most remote variable volume box. The return fan is an in-line
> axial and is controlled to maintain a fixed air flow differential
> between the supply and return mains. This will assure that the minimum
> required outside air is maintained during reduced flow conditions. The
> return fan is suspended in the basement equipment room adjacent to the
> built-up air handler.
>
> 2\) West Wing Offices: The office areas are served by a 12,300 cfm
> built-up variable volume air handler similar to the North Wing Office
> Unit. It is located in the existing mechanical room next to the
> Prototyping Area. This unit will replace the unit presently serving
> this area and utilizes the existing outside air intake hood. A new
> relief hood is provided to relieve excess air during the economizer
> mode of operation. A new distribution system is provided similar to
> the one described for the North Wing Office Area System.
>
> 3\) Laboratories: The laboratories are served by a 37,000 cfm built-up
> variable volume air handler located along the east wall of the North
> Wing Basement. The unit will consist of: steam preheat coil with
> integral face and bypass, chilled water cooling coil, plenum fan
> section, 60-65 percent filter section, and mixing box. Laboratories
> with fume hoods have variable exhaust flow rates due to the operable
> sash on the hoods. Variable volume fume hood controllers are utilized
> to allow the supply and exhaust rates to track the fume hood sash
> positions. Areas served by this air handling system that do not
> contain variable flow exhaust rates are served by variable volume
> terminals like the ones used in the office areas. As the fume hood
> controllers and the variable volume terminals start to close off the
> system supply and exhaust flow streams the respective fans are
> modulated back to maintain constant static pressure set points. The
> return fan tracks the combined volume of the supply and exhaust fans
> to maintain the correct return volume.
>
> 4\) Tritium Envelope Areas: The inner tritium envelope areas are
> served by a 24,000 cfm built-up variable volume air handler located
> along the east wall of the North Wing Basement. The unit is similar to
> the laboratory air-handling unit with the exception that it is 100
> percent outside air.
>
> 5\) Clean Room Recirculation Air Units: The ten recirculation air
> units are sized between 15,000 cfm and 47,000 cfm, are built-up
> constant volume air handlers, and are located directly under their
> respective clean room in the North Wing Basement Mechanical Room. The
> units consist of 90-95 percent filtration system, cooling coil, and
> plenum fan section. Nine of the units serve the three Class 100 clean
> rooms and one of the two Class 1000 laminar flow hoods that are
> provided above the exhaust systems. The tenth unit serves the Class
> 10,000 clean room and the Class 1000 clean rooms. A recessed floor
> plenum is utilized for the return air. Elbow sound attenuators are
> installed on the inlet to the units.
>
> 6\) Clean Room Pressurization Unit: The pressurization unit is a
> 14,000 cfm built-up constant volume air handler located along the east
> wall of the North Wing Basement. The unit dehumidifies and conditions
> 100 percent outside air. A desiccant dehumidification process is used
> and consists of a dehumidifier wheel and reactivation air stream with
> its own fan and steam heater. The remainder of the unit consists of a
> supply fan, preheat and pre-cool coils, final heat and final cool
> coils, 30 percent efficient filters, and 95 percent efficient filters.
>
> 7\) Computer Room: The computer room unit is a floor mounted unit
> designed specifically for computer room applications. The unit
> utilizes chilled water to provide cooling. Infrared humidification and
> hot water heat is utilized along with the chilled water cooling to
> maintain the 72 deg. F plus or minus 2 deg. F and 50 percent rh plus
> or minus 5 percent design space condition.
>
> 8\) Smoke Control/Removal
>
> a\) Clean Rooms: The clean room areas are the only areas in the
> building with smoke removal. A single 3600 cfm floor mounted
> centrifugal fan is provided to serve all of the clean room areas. A
> series of smoke/fire dampers are controlled to isolate the active
> smoke zone from the inactive zones when the building smoke detection
> system indicates smoke in one of the clean room zones. The clean room
> air handlers serving the active smoke zone will be shut down and
> smoke/fire dampers will be closed. Exhausted air from the active smoke
> zone is discharged through a relief air shaft on the exterior of the
> building to above the building roof to assure the smoke laden air does
> not reenter the building outside air intakes. The smoke removal fan is
> located in the northwest corner of the north wing basement mechanical
> room.
>
> b\) Stairwells: The stairwells are automatically pressurized anytime
> the building fire alarm system detects smoke or fire water flow
> anywhere in the building. The pressurization fans are 12,900 cfm
> hooded propeller fans located on the roof directly above the stairwell
> served. The fans are sized to accommodate two open doors in the
> stairwell at any time. A barometric pressure relief is provided to
> relieve excess pressure when the stairwell doors are not open. The
> stairwell fans power supply is backed by the emergency generator.
>
> g\. Exhaust Systems
>
> 1\) Laboratory: The laboratory exhaust system is served by redundant
> 17,000 cfm centrifugal fans located in the second floor mechanical
> room. The ductwork is constructed from all-welded galvanized steel.
> Variable flow fume hood controllers are used as described earlier
> under laboratory HVAC systems. Space is being provided in the
> equipment room for the addition of a future fume scrubber on the
> exhaust leg serving the second floor plating operation.
>
> 2\) Tritium Exhaust: The tritium exhaust system is served by redundant
> 29,300 cfm centrifugal fans and filter systems located in the second
> floor mechanical room. The ductwork is constructed from all-welded
> stainless steel. Ductwork penetrating 2-hour fire rated partitions in
> the tritium areas is wrapped with a fire-proof blanket. No fire
> dampers are installed in the exhaust system.
>
> 3\) Toilet, Mechanical Spaces, and Chiller Room Exhaust: These spaces
> are all served similarly by roof mounted centrifugal exhausters.
>
> B. Mechanical - Non-HVAC
>
> 1\. Mechanical Systems Description - Refer to Equipment Schedule and
> specifications for detailed capacity and performance requirements.
> Salient features of piping systems and major equipment are as follows:
>
> 2\. Specific Systems
>
> a\. Process Cooling Water System:
>
> 1\) System Configuration: A closed loop reverse-return piping system
> serving various process users within the building.
>
> 2\) Heat Exchanger: One plate-and-frame heat exchanger uses process
> cooling water entering at 70 deg. F and leaving at 55 deg. F. Heat is
> rejected to the secondary chilled water system (38 deg. F/52 deg. F).
>
> 3\) Pumps and Components: Two 10-hp., base-mounted, end-suction,
> centrifugal pumps with one 21.7-gal. diaphragm type, expansion tank, a
> 4-in. air separator and one in-line 35 micron filter downstream of the
> pumps. Each pump provides 200 gpm at 105 ft. of water. One pump serves
> as 100 percent backup. Each pumps power supply is backed by the
> emergency generator.
>
> 4\) Controls: The system is controlled by a DDC system.
>
> b\. High Temperature Cooling Water System:
>
> 1\) System Configuration: The continually operating system provides
> 104 deg. F cooling water to four exhaust systems and two evaporators.
> A primary/secondary piping arrangement is used with the secondary loop
> being the High Temperature Process Cooling water loop. The process,
> cooling water system serves as the primary loop. Heat rejected by the
> equipment to the secondary loop is bled to the primary loop via a
> cross-over-bridge.
>
> 2\) Heat Exchanger: A shell-and-tube heat exchanger uses 15-psig steam
> to maintain the loop temperature at a minimum of 104 deg. F during
> periods when the evaporators and exhaust systems are not rejecting
> heat to the loop.
>
> 3\) Pumps: One 3-hp., in-line pump recirculates water in the High
> Temperature Cooling water loop.
>
> 4\) Controls: The system will be controlled by a DDC system.
>
> c\. Deionized Water System:
>
> 1\) System Configuration: Skid-mounted, pre-piped and pre-wired
> packaged system with integral controls and a single-point power
> connection providing 18-meg-ohm quality, deionized water. Package
> components are listed below. Distribution piping network is CPVC.
>
> 2\) Components: Items include activated carbon bed, 2 pre-filters,
> water softener, reverse-osmosis unit w/ degasifying membranes,
> 245-gal. storage tank, two recirculating pumps, four mixed-bed
> deionization unit, two post filters, two ultraviolet disinfection
> units, flow indicator, and resistivity monitor.
>
> d\. Process Deionized Water System:
>
> 1\) System Configuration: Closed-loop, 2 meg-ohm quality, deionized
> cooling water loop provides cooling to two evaporators and a plasma
> cleaner. The system receives make-up water from the 18 meg-ohm,
> deionized water system.
>
> 2\) Heat Exchanger: One shell-and-tube heat exchanger with stainless
> steel components. The process deionized water system (72/57 deg. F)
> rejects heat to the secondary chilled water loop (38/52 deg. F).
>
> 3\) Pumps and Components: One, 5 hp., continuously-operating,
> end-suction, centrifugal pump with all CPVC construction circulates
> deionized water in the closed loop. A 3 ft. long section of 10-in. PVC
> pipe serves as an expansion tank.
>
> 4\) Controls: The system will be controlled by a DDC system.
>
> e\. Pumping Systems:
>
> 1\) Water Service:
>
> a\) Potable Water: A 3-in., water supply line ties into an existing
> 12-in. main on the west side of the building. The water supply is
> metered and passes through a pressure regulator. Potable water
> supplies building restrooms, safety showers, eye washes, exterior
> hose-bibs, and a steam-fired water heater.
>
> b\) Non-Potable Water: A branch off of the potable water supply passes
> through a back-flow-preventer and serves as non-potable water.
> Non-potable water serves process sinks, tower water make-up, and as a
> make-up source to the closed loop hydronic systems.
>
> c\) Domestic Hot Water: Domestic, hot water is generated with a
> 50-gal. steam-to-water heater which has a 750-gph recovery rate. This
> water serves the restrooms. Process sinks in the building have
> instantaneous water heaters.
>
> 2\) Drainage:
>
> a\) Sanitary Drainage: The first and second floor restroom drainage
> exits the north side of the building in a 4-in., gravity line. Two
> other gravity lines pick up some floor drains on the 1st floor and
> exit the north side of the building. Basement restroom, floor drains,
> receptors, and all other building floor drains associated with safety
> shower and eye washes (except those in the tritium areas) gravity
> drain to a package, duplex, sump pump station. The package includes
> two, 1.5-hp., sump pumps each pumping 70 gpm at 24 ft. of water. The
> pumped discharge exits the west side of the building.
>
> b\) Storm Drainage: Roof drains and overflow roof drains are provided
> to accommodate a rainfall rate of 2 in. per hour. Two, 8-in., rain
> water leaders exit the east side of the building. Drainage from the
> area way on the east side of the building is routed to a sump pump in
> the basement which ties into one of the 8-in., rain water leaders.
>
> c\) Firewater drainage: Concrete trenches with drains are located in
> the doorways of all rooms within the tritium areas. These drains are
> routed to the firewater retention basin in the basement. The basin has
> a manually operated sump pump discharging to the sanitary sewer or
> collection containers.
>
> d\) Tritium drains: All floor drains and sink drainage originating
> from tritium areas are routed to a 300-gal., collection-tank located
> on top of the firewater retention basin in the basement. The tank is
> equipped with an overflow that is routed to the firewater retention
> basin.
>
> f\. Gas Piping Systems:
>
> 1\) Compressed Air:
>
> a\) System Configuration: Compressed air is distributed for general
> service use throughout the building with each outlet containing a
> pressure regulator.
>
> b\) Air Compressor: Two, 20-hp., single-stage, rotary-screw,
> air-cooled, packaged, air compressors is completely piped, wired, and
> base-plate-mounted w/ solid state controls. Each providing 77 cfm at
> 125 psig.
>
> c\) Refrigerated, Air Dryer: One, refrigerated, air dryer is used to
> reduce the dew point of 180 cfm of 110 deg. F air at 125 psig to a
> pressure dew point of 33 to 39 deg. F.
>
> d\) Air Filter: One 0.01-micron, filter is used to remove liquid
> water, solid particulates, and oil mists from 180 cfm of 125 psig air.
>
> e\) Air Receiver: One, 240-gal. ASME rated receiver.
>
> 2\) Nitrogen and Argon:
>
> a\) System Configuration: Nitrogen and argon service ties into
> existing 3/4-in., valved taps in the prototyping area and are routed
> throughout the building to various users. Each outlet terminates with
> a pressure regulator.
>
> 3\) Natural Gas:
>
> a\) System Configuration: A 2-in., natural gas line ties into an
> existing main on the south side of the building. Natural gas goes
> through a meter and a pressure-reducing station before entering the
> building to serve six fume hoods.
>
> g\. Fuel Oil Piping System:
>
> 1\) System Configuration: The system supports the emergency generator
> which has a day tank and fuel oil transfer pump. This system consists
> of a storage tank, and interconnecting fuel oil supply and return
> piping between the generator and the day tank, and the piping between
> the day tank/pump and the storage tank.
>
> 2\) Tank: One, 560-gal., double-wall, horizontal, aboveground tank
> with leak detection.

tc \"PART2-PRODUCTS\.....\"\\l§**[PART 2 - PRODUCTS]{.underline}**

**2.01 [MATERIALS]{.underline}**

> A. Report Paper is to be:
>
> 1\. 8 1/2 inches by 11 inches.
>
> 2\. Hole punched, white, 20 pound minimum.
>
> B. Drawings are to be:
>
> 1\. Folded to match report paper size.
>
> 2\. Hole punched and reinforced to match 3-ring binder.
>
> C. Tabs are to be:
>
> 1\. Heavy duty paper separator for each section.
>
> 2\. Hole punched, index tabbed.
>
> D. Binders are to be:
>
> 1\. Heavy duty three ring type with vinyl cover.
>
> 2\. Commercially printed cover or cover inset for each binder
> identifying the contents.

**\*2.02[REPORT]{.underline}**

> A. Includes the following:
>
> 1\. Approved commissioning plan.
>
> 2\. Schematic drawings of the air and water systems to be used for
> recording test data at specific points within each system.
>
> 3\. Completed pre-operational and verification check lists (see
> attachments.)
>
> a\. Air-conditioning unit, computer room
>
> b\. Air filter housing (bag-in/bag-out)
>
> c\. Air handling unit, cooling coil
>
> d\. Air handling unit, fan and motor
>
> e\. Air handling unit, filter
>
> f\. Air handing unit, heating coil
>
> g\. Air shower, fan and motor
>
> h\. Air terminal unit - shut-off type
>
> i\. Air terminal unit - shut-off type, heating coil
>
> j\. Chiller, centrifugal water
>
> k\. Coil, cooling
>
> l\. Coil, heating
>
> m\. Controls
>
> n\. Controls, space pressurization
>
> o\. Cooling tower
>
> p\. Dampers
>
> q\. Dehumidifier
>
> r\. Ductwork, air-conditioning
>
> s\. Ductwork, exhaust
>
> t\. Ductwork, welded galvanized
>
> u\. Ductwork, welded stainless steel
>
> v\. Fan and motor
>
> w\. Fume hood
>
> x\. Heat exchanger
>
> y\. Humidifiers, steam
>
> z\. Laminar flow benches/fume hood
>
> 27.Piping, chilled water
>
> 28.Piping, compressed gases
>
> 29.Piping, deionized water
>
> 30.Piping, fuel oil
>
> 31.Piping, hot water
>
> 32.Piping, natural gas
>
> 33.Piping, steam and condensate
>
> 34.Piping, tower water
>
> 35.Plumbing
>
> 36.Pump and motor
>
> 37.Pump and motor, sewage/sump
>
> 38.Terminal unit-fin tube radiator
>
> 39.Unit heater, electric
>
> 40.Unit heater, hot water
>
> 41.Valves
>
> 42.Water heater, electric
>
> 43.Water heater, steam
>
> 4\. Certificate of compliance with applicable codes, standards, and
> specifications.
>
> 5\. Records of code authority inspections, documentation sign-offs,
> etc.
>
> 6\. Project plans.
>
> 7\. Specifications.
>
> 8\. Authorized revisions.
>
> 9\. Mechanical shop drawings.
>
> 10\. Submittals (i.e. approved test, adjusted balance report,
> equipment certifications.)
>
> B. Order of Presentation is indicated below:
>
> 1\. Report purpose
>
> 2\. Building and systems description
>
> 3\. Air and water systems schematics
>
> 4\. Overall evaluation
>
> 5\. Pre-operational and verification check out
>
> a\. Copies of pre-operational and verification test data
>
> b\. List and description of deviations
>
> c\. List and description of resolutions
>
> d\. Completed pre-operational and verification check lists
>
> 6\. Tool list
>
> 7\. Test equipment list
>
> 8\. Test equipment recalibration certification
>
> 9\. Certificate of codes, standards, and specifications compliance
>
> 10\. Records of code authority inspections, documentation sign-offs,
> etc.
>
> 11\. Project Plans
>
> 12\. Specifications
>
> 13\. Authorized revisions
>
> 14\. Mechanical shop drawings
>
> 15\. Submittals (i.e. approved test, adjusted balance report,
> equipment certifications)

**\*2.03[SERVICES AND EQUIPMENT]{.underline}**

> A. Obtain services and instrumentation of the agency performing tests
> in this Section.

tc \"PART3-EXECUTION\.....\"\\l§**[PART 3 - EXECUTION]{.underline}**

tc \"3.01GENERAL\.....\"\\l§\***3.01[GENERAL]{.underline}**

> A. Actively participate in construction phase of the project to assure
> compliance with commissioning requirements.

tc \"3.02PROCEDURE\.....\"\\l§\***3.02[PROCEDURE]{.underline}**

> A. Attend pre-construction meeting and establish requirements for
> commissioning authority process throughout construction phase.
>
> B. Prepare and submit to SNL, 6 weeks after contract award,
> Commissioning Plan which shall outline:
>
> 1\. Responsibility of each trade affected by the Commissioning, as
> required by appropriate Section.
>
> 2\. Requirement for documentation as listed in this Section.
>
> 3\. Requirements for documentation of tests and inspections required
> by code authorities.
>
> 4\. Requirements for the Commissioning program during specified
> operational seasons, part and full loads as further delineated in
> Paragraph 3.03.
>
> 5\. Format for the training program for operation and maintenance
> personnel.
>
> C. Periodically attend construction and coordination meetings.

tc \"3.03VERIFICATION\.....\"\\l§\***3.03[VERIFICATION]{.underline}**

> A. Start the pre-operational checking and verification after
> mechanical equipment and systems, along with related equipment,
> systems, structures and areas are complete.
>
> B. Verify TAB reading, such as:
>
> 1\. Supply, return, and exhaust air
>
> 2\. Fan performance
>
> 3\. Hydronic performances
>
> 4\. Branch duct readings
>
> 5\. Refrigeration side performance
>
> 6\. Chiller performance
>
> 7\. Cooling tower performance
>
> C. Verify calibration of thermostats and related controls, such as:
>
> 1\. Air terminal units
>
> 2\. Damper settings
>
> 3\. Valve positions
>
> D. Verify readings of remote data and control systems, such as:
>
> 1\. Temperature
>
> 2\. Air Flow
>
> 3\. Damper positions
>
> 4\. Water pressure
>
> 5\. Water temperatures
>
> E. Verify operation of system modes, such as economy cycle, smoke
> removal and in specific:
>
> 1\. Damper and fan operation
>
> 2\. Smoke detector response
>
> 3\. Zone response
>
> F. Verify that total mechanical system is performing to provide
> conditions as outlined in Paragraphs 1.09 and 1.10.
>
> 1\. Temperature
>
> 2\. Humidity
>
> 3\. Air changes
>
> 4\. Air movement
>
> 5\. Air quality
>
> 6\. Zone Control
>
> 7\. Energy management
>
> 8\. Pressurization
>
> 9\. Smoke control
>
> 10\. Control response
>
> G. Complete all checklists. Some checklists are general and apply to
> several similar pieces of equipment. (i.e. Dehumidifier Checklist is
> to be used for Custom Dehumidification System and Modular
> Dehumidifiers).
>
> H. Prepare a report at the completion of the Commissioning Process per
> Paragraph 1.06A.

tc \"3.04CHECKLISTS\.....\"\\l§\***3.04[CHECK LISTS]{.underline}**

> A. See attachments.
>
> **END OF SECTION**
>
> **EXCEPT FOR ATTACHED**
>
> **CHECK LISTS**
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air-Conditioning Unit, Computer Room

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filters Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Installation is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Accessories are Provided
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolator Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Cooling Btu\'s @ Voltage
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

EER (Btuh/Watt)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Heating Btu\'s @ Voltage
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

COP @ 47°F Outside/EER
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE TEST

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air-Conditioning Unit, Computer Room

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Adj. Controls Functions
Oper.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Normal Controls Oper.
Modes\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Lead/Lag Compressor
Oper.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolator Adj.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Cooling Btu\'s @ Voltage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Heating Btu\'s @ Voltage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Filter Housing (Bag-In/Bag-Out)

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Door Latches Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Door Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Frames Sealed to Housing
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Free from Damage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Clamping Mechanism Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Clean and Rust Free
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Correct Quantity of Bags
Provided\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Correct New Filters Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

D\'ffrntl Gage Kit
Inst\'lld/Oper.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filter Bank Tested & Approved
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pre-filter Clean Pr\'ssr Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Final Filter Clean Pr\'ssr Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

T\'tl F\'ltr & F\'ltr H\'sg Pr\'ssr Drop

(in. w.g.) \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Filter Housing (Bag-In/Bag-Out)

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clamping Mechanism
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify D\'ffrntl Gauge Kit
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pre-Filter Clean Pr\'ssr Drop

(in. w.g.) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Final F\'ltr Clean Pr\'ssr Drop

(in. w.g.) \_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify T\'tl F\'ltr & F\'ltr H\'sg Pr\'ssr Drop

(in. w.g.) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Cooling Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Air Pressure Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL TEST CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Cooling Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Air Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

> 3.RESULTS
>
> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Tension
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Alignment with Ductwork
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Drive Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Keyway and Setscrew Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Proper No. of Belts Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Motorrpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan cfm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan rpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan/Motor Noise Level
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Filter

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filters Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

D\'ffrnt/Gage Kit Inst\'ld/Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Filter

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify D\'ffrnt/Gage
Kit/Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Heating Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Air Pressure Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Handling Unit, Heating Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Air Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Shower, Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Tension
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Drive Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Keyway and Setscrew Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Proper No. of Belts Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Shower, Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Motor rpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan cfm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan rpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan/Motor Noise Level
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Terminal Unit - Shut-Off Type

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Alignment with Ductwork
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Connection Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Connections Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Installed/Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Damper is in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Damper Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

OPERATING DATA (designed/installed)

Minimum Inlet Pressure (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Unit Pressure Drop (in. w.g.)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Terminal Unit - Shut-Off Type

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Damper Operation
Correct\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Minimum Inlet Press. (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Unit Press. Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Terminal Unit - Shut-Off Type,
Heating Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Air Pressure Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Air Terminal Unit - Shut-Off Type,
Heating Coil

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Air Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Chiller, Centrifugal Water

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

No Shipping Damage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Sh\'ppng Hold Down Plates are
Removed\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Features Match Specifications
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation is Level
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Adequate Oper. & Service Area
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Connections are
Tight\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Adequate Unit Grounding
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Correct Fuses and Fuse Size
Inst\'lld\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Elec. Service Matches Unit
Nameplate\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fld. W\'rng Matches Unit Elec.
Diag.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flow Switches Correctly
Installed\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Rupture Disc Piped to Bldg.
Exterior\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belly Heater is Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Ea. Refrig. Cir. is Fully
Charged\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Crankcase Oil Level is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Liq. Refrig. Drier is Installed

in Ea. Refrig. Cir.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Liq. Line Solen\'d Valve is Inst\'lld

in Ea. Refrig. Cir.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Exp\'nsn Valve Bulb is Correctly

Inst\'lld and Insulated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

All Serv. and Liq. Line Valves

are Open \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Req. 24 Hr. C\'mprssr Cr\'nkcs H\'tr

Oper. Prior to Startup
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Condenser W\'tr Sys. is Sized and

Installed per the Drawings
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Condenser W\'tr Sys. is Connected and

Functional \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Chilled W\'tr Sys. is Sized and

Installed per the Drawings
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Chilled W\'tr Sys. is Connected and

Functional \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Level of Oil in Sight Glass is at

Least 1/3 and No More Than 1/2

with the C\'mprssrs Running
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pre-Operational Check List
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Chilled/Condenser Water Pumps

Pre-Operational Check Lists are

Completed and Submitted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cooling Tower Pre-Operational

Check is Complete and
Submitted\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Pre-Operational Check List

is Complete and Submitted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Test and Balance Report is
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

and Submitted

Chemical Treatment Pre-Operational

Check List is Complete &
Submitted\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

OPERATING DATA (designed/installed)

Condenser W\'tr Temp. In (°F)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Condenser W\'tr Temp. Out (°F)
\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

C\'ndnsr W\'tr Pr\'ssr Drop (ft.
w\'tr)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Chilled W\'tr Temp. In (°F)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Chilled W\'tr Temp. Out (°F)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Ch\'lld W\'tr Pr\'ssr Drop (ft.
w\'tr)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE TEST

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Chiller, Centrifugal Water

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Time-of-Day Program
Oper.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Soft-Start Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Chiller Shut Down Open
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Chiller Re-Start Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Full-Load Condenser W\'tr Temp.

In (oF) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Full-Load Condenser W\'tr Temp.

Out (oF) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify W\'tr Pr\'ssr Drop (ft.
w\'tr)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Full-Load Chilled W\'tr Temp.

In (oF) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Full-Load Chilled W\'tr Temp.

Out (oF) \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Ch\'lld W\'tr Pr\'ssr Drop (ft.
w\'tr)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify RLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Coil, Cooling

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs.
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs. in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Air Pressure Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Coil, Cooling

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Air Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Coil, Heating

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometer Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Pressure Drop (in. w.g.)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Coil, Heating

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Controls

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Instrument Air Meets
Specifications\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Instrument Air Connections
Tight\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Pr\'ssr Gages Inst\'lld/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrls Properly
Inst\'lld/Operating\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vent Valves Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Equip. No. Tag
Inst\'lld\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Spring/Throttle Ranges
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Set Point at Design Conditions
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. Bee Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Controls

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Adequate Supply Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Air Pr\'ssr Gauges
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Spring/Throttle Ranges
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Components
Operations\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control System
Operations\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Controls, Space Pressurization

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Instrument Air Meets
Specifications\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Instrument Air Connections
Tight\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Pr\'ssr Gages
Inst\'lld/Operating\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrls Properly
Inst\'lld/Operating\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vent Valves Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Controls Equip. No. Tag
Inst\'lld\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Spring/Throttle Ranges
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Set Point at Design Conditions
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK LIST

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Controls, Space Pressurization

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Adequate Supply Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Air Pr\'ssr Gauges
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Spring/Throttle Ranges
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Components
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control System
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Cooling Tower

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Level \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Corrosion Protection Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fan (Axial) Pitch Angle
Correct\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Tension
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Drive Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Keyway and Setscrew Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Proper No. of Belts Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Clearance Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fill Clean/Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Louver Clean/Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Chemical Treatment Pre-Operational

Check List is Complete and
Submitted\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tower Water Pumps Pre-Operational

Check List is Complete and
Submitted\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Sump Control System Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Make-up Water Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Sump Heater Operable

Vibration Switch Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Water Distribution System Water

Level Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE TEST

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Cooling Tower

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Motor RPM
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan cfm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan rpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan/Motor Noise Level
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Correct Sump Control System

Operation \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Correct Make-Up Water System

Operation \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Correct Sump Heater
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Dampers

INSPECTED BY :

CONDITION EVALUATED: OPERABLE NORM. POS. CURR. POS.

EQUIPMENT NO.

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Dampers

INSPECTED BY :

CONDITION EVALUATED: VERIFY CURRENT OPERATION

EQUIPMENT NO.

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Dehumidifier

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Desiccant Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Installation is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Piping Connections Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Alignment Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Connection Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Accessories are Provided
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolator Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE TEST

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Dehumidifier

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Desiccant Wheel
Rotation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Adj. Functions Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Normal Oper. Modes
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolator Adj.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Air-Conditioning

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Test Ports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Doors/Cleanouts Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Term. Devices Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Dampers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire/Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Joints Sealed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flex. Conn. Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cleaned \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Correctly Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Air-Conditioning

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN

Verify Leak Test
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Exhaust

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Test Ports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Doors/Cleanouts Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Dampers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire/Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Joints Sealed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flex. Conn. Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cleaned \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Correctly Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Exhaust

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Leak Test \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Welded Galvanized

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Test Ports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Doors/Cleanouts Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Dampers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire/Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Joints Sealed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flex. Conn. Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cleaned \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Correctly Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.

FUNCTIONAL PERFORMANCE CHECK

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Welded Galvanized

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Leak Test \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Welded Stainless Steel

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Test Ports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Access Doors/Cleanouts Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Dampers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fire/Smoke Dampers Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Joints Sealed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flex. Conn. Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cleaned \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Correctly Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Ductwork, Welded Stainless Steel

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Leak Test \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Tension
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fan Alignment with Ductwork
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Drive Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Keyway and Setscrew Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Belt Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Proper No. of Belts Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE TEST

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Fan and Motor

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Safeties Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Motor RPM
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan cfm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan rpm
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan/Motor Noise Level
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Fume Hood

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Piping Connxs. Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs Correctly Piped
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Connx. Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Services in the Correct
Location\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Accessories Provided
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Provided
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Maximum Air Flow Rate (cfm)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Minimum Air Flow Rate (cfm)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL TEST CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Fume Hood

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Correct Remove Baffle
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Correct Sash Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Man. Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Light Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST
>
> SYSTEM/EQUIPMENT/COMPONENT CHECKED: Heat Exchanger

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Minimal Air Leakage
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Pressure Drop (in. w.g.)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Heat Exchanger

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Clean Pressure Drop (in.
w.g.)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Humidifiers, Steam

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Supply Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Humidifiers, Steam

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Verify Supply Pressure (psig)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Laminar Flow Benches/Fume Hood

INSPECTED BY :

EQUIPMENT NO:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Piping Connxs. Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs Correctly Piped
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Duct Connx. Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Grounding Connx.
Tight\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power is Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filter Frames Sealed Correctly to
Housing\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Correct Filters Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

D\'ffrnt Pr\'ssr Gauge Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Control Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Air Flow Gauge Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Services in Correct Location
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Installation is Correct and
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Unit Accessories are Provided
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Maintenance Access Adequate
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolator Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Snubbers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Total Filter Clean Pressure Drop (in.
w.g.)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Laminar Flow Benches/Fume Hood

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fan Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify D\'frntl Gauge Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Air Flow Control Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Air Flow Gauge Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Man. Valve Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Light Oper.
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Chilled Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pump Discharge Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component
>
> to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Chilled Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gages Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Return Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Compressed Gases

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Installed/Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Operating Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Compressor Discharge Pressure
(psig)\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Compressed Gases

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify PRVs Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Compressor Discharge Pr\'ssr
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Deionized Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Skid Mounted Equipment
Completely\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Connected

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Cleaned and Sterilized
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, (With Deionized
Water)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Connected to Vendor-Installed

Equipment \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vendor Equipment Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pump Discharge Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Deionized Water

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_

Verify Vendor Equipment
Operation\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Unit Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Unit Return Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Fuel Oil

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Clean Sediment Bowl/Primary
Filter\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fill Storage Tank with Correct
Fuel\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Unit Discharge Pressure (psig)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Fuel Oil

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Unit Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Hot Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pump Discharge Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Hot Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Return Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Test\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Natural Gas

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Meter Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Installed/Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Operating Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Natural Gas

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Meter Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify PRVs Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Steam and Condensate

INSPECTED BY :

INSPECTION ITEM: STEAM CONDENSATE

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pipe Sloped Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Installed/Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

PRVs Operating Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Traps Installed/Accessible
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Traps Operating Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Supply Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Steam and Condensate

INSPECTED BY :

INSPECTION ITEM: STEAM CONDENSATE

Verify PRVs Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Traps Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs

Operating Correctly \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Supply Pr\'ssr (psig) \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Tower Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pump Discharge Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Piping, Tower Water

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operating
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Return Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Plumbing

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed, Refilled, Vented
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Insulation Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Pump Discharge Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Plumbing

INSPECTED BY :

INSPECTION ITEM: SUPPLY RETURN \_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Return Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Pump and Motor

INSPECTED BY :

EQUIPMENT NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pump/Motor Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Coupling Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Snubbers Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pipe Vibration Isolation
Inst\'lld\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Flow (gpm)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Discharge (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Return, (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Pump and Motor

INSPECTED BY :

EQUIPMENT NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Motor RPM
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauge Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge (psig)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Return (psig)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Pump and Motor, Sewage/Sump

INSPECTED BY :

EQUIPMENT NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-

Motor Type Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pump/Motor Alignment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Coupling Tightness
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Vibration Isolators Adjustment
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Snubbers Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pipe Vibration Isolation
Inst\'lld\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Shaft Guard Installation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Motor Cover Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment Lubricated
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electrical Connections Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Alternator Operates Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Sump/Basin Cover Installed
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Basin Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Connections Tight
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Float Installed/Operable
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Horsepower \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

RPM \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Volts \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Phase \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Flow (gpm)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Pump Discharge (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Pump and Motor, Sewage/Sump

INSPECTED BY :

EQUIPMENT NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-

Verify Pump Rotation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Vibration Isolators
Adj.\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Alternator Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Float Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify MotorRPM
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify FLA
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pump Discharge (psig)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Terminal Unit-Fin Tube Radiator

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Control Valve Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Balancing Valve
Installed/Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gauges Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fins Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Tubes Undamaged
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Fluid Flow Unrestricted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Clean Pressure Drop (in. w.g.)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Temperature (oF)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Inlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

Outlet Fluid Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

General Contractor:

Mechanical Contractor:

Controls Contractor:

Electrical Contractor:

Commissioning Authority:

SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Terminal Unit-Fin Tube Radiator

INSPECTED BY :

EQUIPMENT
NO.:\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_-\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Control Valve Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Fluid Flow (gpm)
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gauges Operation
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Temperature
(oF)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Inlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Verify Outlet Fluid Pressure
(psig)\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Unit Heater, Electric

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Electric Power Correct
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

FLA \_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Unit Heater, Electric

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Unit Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify FLA \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Unit Heater, Hot Water

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Supports Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Seismic Restraints Inst\'lld
Correctly\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Filled and Hydrostatically
Tested\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

C\'ntrl V\'lvs Normal Position
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Thermometers Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Pr\'ssr Gages Installed/Visually
Acc\'ssbl\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

NAMEPLATE DATA (designed/installed)

Supply Pressure (psig)
\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_\_\_\_\_/\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Unit Heater, Hot Water

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify C\'ntrl V\'lvs Operation \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_

Verify Thermometers Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Pr\'ssr Gages Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Supply Pressure (psig) \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Valves

INSPECTED BY :

CONDITION EVALUATED: OPERABLE NORM. POS. CURR. POS.

EQUIPMENT NO.

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Valves

INSPECTED BY :

CONDITION EVALUATED: VERIFY CORRECT OPERATION

EQUIPMENT NO.

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Water Heater, Electric

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Electric Power Correct \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Relief Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Installation Correct & Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Water Heater, Electric

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Relief Valve Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Thermometer Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.
>
> PRE-OPERATIONAL CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Water Heater, Steam

INSPECTED BY :

INSPECTION ITEM:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Flushed \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Cleaned
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Strainers Installed Correctly
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Relief Valve
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs
Installed/Accessible\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Man. V\'lvs in the Correct
Position\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Equipment No. Tag Installed
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Installation Correct &
Complete\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Submittal Data Complete
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

FUNCTIONAL PERFORMANCE CHECK

1\. PERSONNEL PRESENT FOR THE PERFORMANCE TEST

> General Contractor:
>
> Mechanical Contractor:
>
> Controls Contractor:
>
> Electrical Contractor:
>
> Commissioning Authority:
>
> SNL Representative:

2\. FUNCTIONAL PERFORMANCE

> A. Demonstrate (by the Contractor) operation of the
> system/equipment/component to be checked.
>
> B. See Functional Performance Check List below.
>
> FUNCTIONAL PERFORMANCE CHECK LIST

SYSTEM/EQUIPMENT/COMPONENT CHECKED: Water Heater, Steam

INSPECTED BY :

INSPECTION ITEM: \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Relief Valve Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

Verify Thermostat Operation \_\_\_\_\_\_\_\_\_\_ \_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_

3\. RESULTS

> A. Report (by the CA) the results obtained in the Functional
> Performance Test.
>
> B. Report (by the CA) remedial action for system/equipment/component
> which is not verified as meeting its specified performance.
> Re-schedule Functional Performance Test for unverified
> system/equipment/component.

4\. REPORTS

> A. Submit reports on the \"Functional Performance Check\" to the
> Architect/Engineer.