CONSTRUCTION MASTER SPECIFICATION

SECTION 08710

**[DOOR HARDWARE]{.underline}**

**[NOTICE]{.underline}**

**[THIS SECTION MUST BE EDITED BEFORE USE]{.underline}**

This guide section can be used for preparing door hardware
specifications and hardware schedules for construction projects at
Sandia National Laboratories (SNL). SNL has standardized on Sargent
locksets. Sargent has several different Lockset Lines. SNL most
frequently uses Lines 10 and 11. The Line selection should be matched
with the performance requirements of the door; considering security,
life-safety and maintenance. Acceptable hardware manufacturers and
specific hardware items to be used at SNL are included in this guide.
Other hardware items are described generically referencing American
National Standards Institute (ANSI) standards developed by Builders
Hardware Manufacturers Association (BHMA). The Specifier will need to
edit this section for a specific project and generate a hardware
schedule listing hardware items required for each door opening.
Additional hardware items will need to be added and non-applicable items
should be deleted. The guide section has been written so that most
editing can be accomplished by deleting unnecessary requirements and
options. [Options]{.underline} are indicated by **\[ \]**.
[Notes]{.underline} to assist the Specifier in selecting options and
editing the specification guide are printed in bold and indicated with
**\*\*\*\*\***.

Throughout this product guide specification, references are made to
other specification sections that might be contained in the project
manual. These references are presented as examples and coordination
reminders.

**[For the final document, all brackets, notes, and blue text shall be
deleted from the Section.]{.underline}**

CONSTRUCTION STANDARD SPECIFICATION

SECTION 08710

[DOOR HARDWARE]{.underline}

Page

PART 1 ‑ GENERAL

1.01 Summary
[3](#number-range-level0number-range-level1number-range-level2number-range-level3number-range-level4number-range-level5number-range-level6number-range-level71-summary)

1.02 References
[3](#number-range-level1number-range-level2number-range-level3-references)

1.03 Submittals
[5](#number-range-level1number-range-level2number-range-level3-submittals)

1.04 Quality Assurance
[6](#number-range-level1number-range-level2number-range-level3-quality-assurance)

1.05 Delivery, Storage, And Handling
[7](#number-range-level1number-range-level2-delivery-storage-and-handling)

1.06 Warranty [7](#number-range-level1number-range-level2-warranty)

PART 2 ‑ PRODUCTS

2.01 Acceptable Manufacturers:
[7](#number-range-level0number-range-level1number-range-level2number-range-level3number-range-level4number-range-level5number-range-level6number-range-level71number-range-level1number-range-level2number-range-level3-acceptable-manufacturers)

2.02 General Hardware Schedule [8](#__RefHeading___Toc33328145)

2.03 Butt Hinges [9](#__RefHeading___Toc33328146)

2.04 Electrical Power Transfer
[10](#number-range-level1number-range-level2number-range-level3-electrical-power-transfer)

2.05 Cylindrical Lever Locksets
[10](#number-range-level1number-range-level2number-range-level3-cylindrical-lever-locksets)

2.06 Combination Locksets
[12](#number-range-level1number-range-level2-combination-locksets)

2.07 Exit Devices
[13](#number-range-level1number-range-level2number-range-level3-exit-devices)

2.08 Door Coordinator
[15](#number-range-level1number-range-level2number-range-level3-door-coordinator)

2.09 Closers [15](#number-range-level1number-range-level2-closers)

2.10 Door Trim
[15](#number-range-level1number-range-level2number-range-level3-door-trim)

2.11 Electromagnetic Door Holders
[16](#number-range-level1number-range-level2-electromagnetic-door-holders)

2.12 Manual Flush Bolts
[16](#number-range-level1number-range-level2-manual-flush-bolts)

2.13 Electic Strike
[16](#number-range-level1number-range-level2-electric-strike)

2.14 Low-Energy Power Operated Door Openers
[16](#number-range-level1number-range-level2number-range-level3-low-energy-power-operated-door-openers)

2.15 Auxiliary Hardware
[17](#number-range-level1number-range-level2-auxiliary-hardware)

2.16 Finishes
[18](#number-range-level1number-range-level2number-range-level3-finishes)

PART 3 ‑ EXECUTION

3.01 Inspection
[18](#number-range-level0number-range-level1number-range-level2number-range-level3number-range-level4number-range-level5number-range-level6number-range-level71number-range-level1number-range-level2number-range-level3-inspection)

3.02 Preparation
[18](#number-range-level1number-range-level2-preparation)

3.03 Installation
[18](#number-range-level1number-range-level2-installation)

3.04 Schedule [19](#number-range-level1number-range-level2-schedule)

CONSTRUCTION STANDARD SPECIFICATION

SECTION 08710

[DOOR HARDWARE]{.underline}

# PART 1 ‑ GENERAL

## 1.0Number range level0Number range level1Number range level2Number range level3Number range level4Number range level5Number range level6Number range level71 SUMMARY

A. Section includes hardware for doors.

**\*\*\*\*\* List other specification sections dealing with work
directly related to this section such as the following. \*\*\*\*\***

B. Related sections:

1\. Section 06400, "Interior Architectural Woodwork: Cabinet hardware".

2\. Section 08110, "Steel Doors and Frames".

3\. Section 08210, "Wood Doors".

4\. Section 08361, "Overhead Sectional Steel Doors": Hardware provided
by overhead door manufacturers.

## 1.02Number range level1Number range level2Number range level3 REFERENCES

**\*\*\*\*\* List by number and full title reference standards referred
to in remainder of specification section. Delete non-applicable
references. \*\*\*\*\***

A. American National Standards Institute (ANSI):

ANSI A115 Set Steel Steel Door and Frame Preparation for Hardware

ANSI A115 Set Wood Wood Door Hardware Standard

ANSI A156.1 Butts and Hinges.

ANSI A156.3 Exit Devices.

ANSI A156.4 Door Controls - Closers.

ANSI A156.6 Architectural Door Trim.

ANSI A156.7 Template Hinge Dimensions.

ANSI A156.15 Closer Holder Release Devices.

ANSI A156.16 Auxiliary Hardware.

ANSI A156.21 Thresholds.

ANSI A156.22 Door Gasketing Systems.

ANSI A156.26 Continuous Hinges

ANSI A612 Specification for Pressure Vessel Plates, Carbon Steel, High
Strength, for Moderate and Lower Temperature Service.

ANSI A250.6 Hardware on Steel (Reinforcement-Application)

ANSI J405

B. American National Standards Institute/Builders Hardware
Manufacturer's Association (ANSI/BHMA):

ANSI A156.2 Bored and Preassembled Lock and Latches. Same as BHMA 601.

ANSI A156.19 Power Assist and Low-Energy Power-Operated Doors.

C.Number range level3 American Society of Testing and Materials (ASTM):

ASTM E90 Laboratory Measurement of the Sound Transmission Loss of Door
Panels and Door Systems.

ASTM E413 Classification for Rating Sound Insulation.

D.  Architectural Hardware Consultant (AHC)

E. Builder hardware Manufacturers Association (BHMA)

F.  Door and Hardware Institute (DHI):

Sequence and Format for the Hardware Schedule.

G.  Factory Mutual (FM)

H.  International Code Council (ICC):

IBC 2006 Positive Pressure Fire Tests of Door Assemblies.

IBC 2006 Standard for Fire Doors and Other Opening Protectives

I Number range level3International Code Council/American National
Standards Institute (ICC/ANSI):

J ADA and ABA Accessibility Guidelines for Buildings and Facilities,
Part II: ABA Application and Scoping.

Number range level3K.Number range level3 Underwriters Laboratories (UL):

UL 10C Standard for Positive Pressure Fire Tests of Door Assemblies.

## 1.03Number range level1Number range level2Number range level3 SUBMITTALS

A. Submit in accordance with Section 01330, "Submittal Procedures":

1\. Product data for each hardware item including function descriptions,
materials, finishes, dimensions, power requirements for electrified
items, and installation and interface requirements.

2\. Shop drawings illustrating special installation requirements and
diagrams for wiring electrified items and interface with fire alarm,
security, and access control system\].

3\. Hardware schedule: Format in accordance with DHI Sequence and Format
for the Hardware Schedule. Organize hardware sets in same sequence as
Hardware Schedule in Part 3.

4\. Keying schedule detailing final keying and indexing key sets to
designated doors.

5\. Certificates documenting:

a\. Hardware items comply with ANSI 156, Grade 1 in accordance with
Paragraph \[1.4.B\].

**\*\*\*\*\* Include the following paragraph if fire-rated doors are
required. \*\*\*\*\***

b\. Items being provided for fire-rated assemblies have been
successfully tested in accordance with Paragraph \[1.4.E\].

**\*\*\*\*\* Include the following paragraph if sound rated door
assemblies are required. \*\*\*\*\***

c\. Sound transmission class: Showing compliance with Paragraph 1.4.F.

6.Number range level4 Manufacturer\'s instructions for preparing doors
and frames to receive hardware and for hardware installation,
adjustment, and maintenance.

7\. Copy of warranties required by Paragraph \[1.6\] for review by
Contracting Officer.

B.Number range level3 Submit in accordance with Special Construction
Specification Section 01780, "Closeout Submittals":

1\. Operation and maintenance manuals.

2\. Special wrenches, maintenance tools, and accessories as applicable
to hardware items and as supplied by hardware manufacturer.

C. Preliminary Hardware Submittal Conference

1\. Meet with the Architect, SNL Project Manager, SNL Systems Architect
and the SNL Locksmith to review the Hardware Schedule Submittal.

> a\. Review each room function and door operation required for that
> room and occupancy.
>
> b\. Confirm manufacturer and model number of hardware proposed to meet
> current SNL Standards.
>
> c\. Identify any conflicts, changes or modifications to the original
> layout that may modify the hardware schedule.
>
> d\. Discuss any security issues for the building and the impact that
> may have on the hardware proposed and how it relates to access
> control, exiting requirements or alarm considerations.

2\. All participants at the conference shall be familiar with the
Project and authorized to conclude matters relating to the Work.

3\. Record significant conference discussions, agreements,
disagreements, including required corrective measures and actions.

## 1.04Number range level1Number range level2Number range level3 QUALITY ASSURANCE

A. Supplier qualifications: Hardware shall be scheduled and detailed by
Architectural Hardware Consultant (AHC) certified by Door and Hardware
Institute (DHI) or 10 years of experience in the commercial finish
hardware business. Hardware consultant shall be available to consult
with Contracting Officer regarding hardware submittal, items to be
provided, and keying schedule.

B. Hardware shall meet minimum requirements of ANSI A156, Grade 1.

C. The Sargent Line 11 installation instructions and direction from SNL
Locksmith on specific installation requirements will be provided in a 1
hour training session to those individuals indentified by the contractor
who will be responsible for the installation of the door hardware.
Attendance is mandatory for this training unless the contractor is
providing certified hardware installers for this project.

D.  Handicapped access: Door hardware on doors accessible to the
    handicapped shall comply with ADA and ABA Accessibility Guidelines
    for Buildings and Facilities, Part II: ABA Application and Scoping.
    Hardware shall be adjusted and demonstrated to function properly.
    Damaged or defective hardware shall be replaced at no cost to Sandia
    National Laboratories (SNL).

E.  Hardware shall be adjusted and demonstrated to function properly.
    Damaged or defective hardware shall be replaced at no cost to Sandia
    National Laboratories (SNL).

**\*\*\*\*\* Include and edit the following paragraph if fire-rated
doors are required. \*\*\*\*\***

F.  Fire-rated doors: Provide hardware complying with NFPA 80, identical
    to items tested and listed by Underwriters Laboratories (UL), or
    other National Recognized testing agency acceptable to SNL Site Fire
    Marshall. Include positive pressure testing. Units shall bear
    testing agency labels.

**\*\*\*\*\* Include the following paragraph if sound rated door
assemblies including door panel, frame, and hardware are required.
\*\*\*\*\***

G. Sound transmission class: Provide certificate that door assemblies
including door panel, frame, and hardware have been tested in accordance
with ASTM E90 and ASTM E413 to achieve sound transmission class of STC
\[33\] \[45\] \[50\] \[\_\_\_\_\_\_\].

## 1.05Number range level1Number range level2 DELIVERY, STORAGE, AND HANDLING

A. Ship door hardware to site in unopened boxes, clearly labeled with
manufacturer\'s name and item description.

B. Store and protect hardware until needed for installation.

## 1.06Number range level1Number range level2 WARRANTY

A. Provide under provisions of Section 01700, "Contract Closeout":

1\. Closers: Ten (10) year warranty against mechanical failure.

2\. Exit devices: Five (5) year warranty against mechanical failure.

3\. Cylindrical Locks and Latchsets: Seven (7) year warranty against
mechanical failure.

4\. All other Hardware: One (1) year warranty.

# PART 2 ‑ PRODUCTS

## 2.0Number range level0Number range level1Number range level2Number range level3Number range level4Number range level5Number range level6Number range level71Number range level1Number range level2Number range level3 ACCEPTABLE MANUFACTURERS:

**\*\*\*\*\* Only approved products may be substituted, except where
noted.\*\*\*\*\***

A. Exit Devices, Electrified Exit Devices and Electrical Power
Transfers:

1\. Von Duprin; Indianapolis, In.; (www.vonduprin.com).

B.Number range level3 Mechanical Push-Button Combination Locks:

1\. Simplex, by Kaba-Ilco, Winston-Salem, NC (www.kaba-ilco.com)

C.Number range level3 Butt Hinges:

1\. Stanley; New Britain, CT;
([www.stanleyworks.com](http://www.stanleyworks.com/)).

2\. McKinney, McKinney Products Company, Scranton , PA

Number range level3 Silencers, Door Bumpers, Mop Plates, Kick Plates,
Stops/Holders, Flush Bolts, Push/Pull Latches:

1\. Trimco; Los Angeles, CA; (www.trimcobbw.com).

D.Number range level3 Electrical Push-Button combination lockset:

1\. Hirsch Electronics Corporation; Santa Ana, CA
(www.hirshelectronics.com).

E.Number range level3 Spin Dial Combination Locks:

1\. Kaba Mas; Lexington, KY; (www.kaba-mas.com).

F.Number range level3 High Security Locks, Electric Exit Device Trim and
Electric Locking Hardware:

1\. Securitech; (www.securitech.com).

G.Number range level3 Key Removable Mullions: (Precision Exit Devices
recommended for use with Securitech Electrified Trim products).

1\. Precision Hardware, Inc.; Romulus, MI;(www.precisionhardware.com).

H.Number range level3 Exit Devices with Electrical Latch Retraction,
Locksets, Padlocks, Door Closers, Mullions and Latchsets: (No
substitutions allowed, except for Door Closers.)

> 1\. Sargent Manufacturing Company (ASSA Abloy, Inc.); New Haven, CT;
> ([www.sargentlock.com](http://www.sargentlock.com/)).
>
> 2\. Lockmasters Incorporated, Nicholasville, KY - LMK 7003 w/ KABA MAS
> X-09 for VTRs with fewer than 50 occupants.

I.Number range level3 Electro-magnetic Door Holders:

1\. Honeywell; ([www.honeywell.com](http://www.honeywell.com/)).

2\. LCN. (www.lcnclosers.com)

J.Number range level3 Thresholds, Door Gasketing Systems and Astragals:

1\. National Guard Products, Inc; Memphis, Tennessee; (www.npginc.com).

K.Number range level3 Low-energy, Power Operated Interior Door Openers:
(No substitutions allowed)

1\. Horton Automatics; Corpus Christi, Texas; (www.hortondoors.com).

2\. Lewis C. Norton (LCN),
([www.lcnclosers.com](http://www.lcnclosers.com/)).

> 3\. Sargent Manufacturing Company (ASSA Abloy, Inc.); New Haven, CT;
> (www.sargentlock.com).
>
> 4\. Wikk Industries, Inc. Glendale, WI (switch only, not the operator)

[]{#__RefHeading___Toc33328145 .anchor}2.02Number range level1Number
range level2Number range level3 GENERAL HARDWARE SCHEDULE

A. General: Hardware shall be identified by ANSI as Grade One hardware
where applicable. Where applicable, function shall be as noted on
Contract Documents, or as chosen at time of Submittals.

B. Opening Force: Maximum force for pushing or pulling open door shall
be 8.5 pounds (3.9kg) for exterior and 5 pounds (2.3kg) for interior
doors.

C. Hand of door: Refer to Drawings for swing of each door leaf. Furnish
hardware items suitable for indicated door movement.

D. Base metals: Produce hardware units of basic metal and forming method
indicated using the manufacturer\'s standard alloy, composition, temper,
and hardness.

E. Hardware to conform to templates prepared for screw installation.

F. Furnish installation screws with each hardware item. Provide Phillips
flat-head screws except as otherwise indicated. Finish of screws to
match hardware finish.

G. Hex bolts: Install door closers, door holders, and exit devices on
wood doors with through bolts and hex nuts.

H.  Where possible, provide concealed fasteners for hardware items,
    which are exposed when the door is closed. Do not use through bolts
    for installation where bolt head or nut is exposed on opposite face
    except where it is not feasible to reinforce the work.

I.  Finishes: Finish for all hardware shall be US26D, Plated, Satin
    Chrome, unless otherwise specified in Construction Documents.

J.  Fire Rated Door Hardware: Fire Rated Door Hardware shall be listed
    and labeled by Underwriters Laboratories (UL) and Factory Mutual
    (FM) as "Fire Exit Hardware." Exit devices on fire rated doors shall
    not have dog down capacity.

[]{#__RefHeading___Toc33328146 .anchor}2.03Number range level1Number
range level2 BUTT HINGES

**\*\*\*\*\* Electrical Hinges are not allowed.\*\*\*\*\***

A. Full mortise hinges:

1\. Comply with ANSI A156.1 and ANSI A156.7.

2\. Type: Full mortise, anti-friction, ball bearing, flat tip, five
knuckles, ANSI Grade 1.

3.Number range level4 Hinge weight:

a\. Exterior, airlock entry doors, toilet room entry door, and other
doors with closers: Heavy weight. Use Stanley FBB168.

b\. All other doors: Standard weight. Use Stanley FBB179.

4.  Number range level4Pins:

a\. Non-removable: Provide set screw to prevent pin removal when door is
closed for:

1\) Out-swinging exterior doors.

2\) Vault room doors and other outs-winging interior doors with locks.

b.Number range level5 Provide all other doors with non-rising, loose
pins.

5.  Number range level4Pin tip: Flat button.

6.  Minimum number of hinges per door:

a\. Door height to inches: 2.

b\. Door height from 60 to 90 inches: 3.

c\. Door height from 90 to 120 inches: 4.

d\. Door height above 120 inches: 4 plus 1 additional hinge per 30
inches.

7.  Number range level4Minimum hinge height for 1-3/4 inch thick door:

a\. Door width to 42 inches: 4-1/2 inches.

b\. Door width over inches: 5 inches.

**\*\*\*\*\* Include the following paragraph if concealed monitoring
switch is required. \*\*\*\*\***

8.  Concealed switch: To monitor door position and interface with alarm
    or other security device.

**\*\*\*\*\* Include the following paragraph if geared continuous hinges
are required. \*\*\*\*\***

B.Number range level3 Continuous hinges:

1\. Comply with ANSI A156.26.

2\. Type: Pinless assembly of three interlocking aluminum extrusions
applied to full height of door and frame without mortising. Door leaf
and jamb leaf shall be geared together for entire length of hinge and
joined by channel extrusion. Vertical loads carried by multiple thrust
bearings. Working metal surfaces coated with dry lubricant.

3\. Minimum weight capacity for 84" inch high door:

a.  Standard duty: 280 pounds.

b.  Heavy duty: 540 pounds.

## 2.04Number range level1Number range level2Number range level3 ELECTRICAL POWER TRANSFER

A. Provide one (1) each Electrical Power Transfer on doors where
electrified exit devices or other electrified locking hardware is
specified elsewhere in Construction Documents. Use only Von Duprin
EPT-2.

## 2.05Number range level1Number range level2Number range level3 CYLINDRICAL LEVER LOCKSETS

> A. Keyed function locksets and Non-Keyed Function Latchsets: Keyed
> function locksets shall remain secure after withstanding 2400 inch
> pounds of torque applied to the locked lever. All locksets shall
> maintain horizontal lever position after two million cycles per ANSI
> A156.2. All locksets shall be mountable without the use of through
> bolts and shall fit in a standard 2-1/8" inch (55MM) bore. Locksets
> shall fit a minimum door stile width of 4-1/4" inch (108mm). Lockset
> levers shall not contain any plastic fillers and shall be made of
> solid material. Locksets shall have 2-3/4" inch (70mm) backset,
> standard. Latchbolt heads shall be one-piece stainless steel, 7/8"
> inch (22mm) diameter x ½" inch (13mm) throw, ¾" inch (19mm) throw for
> pairs of doors. All keyed locksets shall be provided with six-pin lock
> cylinders manufactured by Sargent Manufacturing Company, New Haven,
> CT. Lock cylinders shall be provided in the Sargent "LA" keyway and
> shall be "1" bitted. SNL-NM locksmiths will provide proper restricted
> lock cylinder plugs and keying into the SNL-NM master key system.

\*\*\*\*\* SNL has standardized on Sargent locksets. Sargent has several
different Lockset Lines. SNL most frequency uses Lines 10 and 11. Line
11 is required, except as noted. The Line selection should be matched
with the performance requirements of the door, considering security,
life-safety and maintenance. Select various lock functions required for
project and indicate function in appropriate hardware sets scheduled in
Part 3. Add additional functions as required and delete non-applicable
functions. \*\*\*\*\*

Standard Staff Office: Single or Double Office where locking devices are
not required by the operational or programmatic needs of the building
occupants:

Schedule office passage function --11U15 latch bolt operated by lever
from either side.

\*\*\*\*\* Schedule the following function for Privacy Bathroom
Function-Single Occupant Bathrooms and Passage Functions. The Latchset
most frequency used in this application is Sargent 11Line Series with
following functions, but shall be matched with the performance
requirements of the door: \*\*\*\*\*

1\. Passage Function Latchset; 28-11U15-LL. Latch bolt operated by lever
from either side at all times. For all doors, including utility rooms,
where keyed locksets, exit devices or other auxiliary locking devices
are not specified. Outside lever is locked by push button inside and
unlocked by emergency release on outside, by rotating inside lever, or
by closing door. Inside lever always active.

2.  Privacy Bathroom Function, for Single Occupant Bathrooms;
    28-11UG65-LL. Outside lever is locked by push button inside and
    unlocked by emergency release on outside, by rotating inside lever,
    or by closing door. Inside lever always active.

**\*\*\*\*\* Schedule the following function for Multi-Occupant Toilet
Rooms, provide auxiliary latchsets. The Latchset most frequency used in
this application is Sargent 11 Line Series with following functions, but
shall be matched with the performance requirements of the door:
\*\*\*\*\***

3\. Multi-Occupant Toilet Room door latch sets & push/pull; For
fire-rated doors use lever set + closer, 28-11U15-LL, Passage function
latch set. Latch bolt operated by lever from either side. For non-
fire-rated doors use\_\_\_\_\_ . Push/pull plates 4'x16"

4\. Classroom Function lockset; 28-11G37-LL. Either lever operates
latchbolt except when outside lever is locked from inside. Pushing
button in inside lever locks outside lever. Lever automatically releases
when inside lever is turned or key is rotated in locked outside lever.
Push button must be manually released. Latchbolt is operated by key in
outside lever or by rotating inside lever. Inside lever always active.

**\*\*\*\*\* Schedule the following function for Exterior Entrances
requiring locked security at times and remaining open at other times.
The Latchset most frequency used in this application is Sargent 11 Line
Series with following functions, but shall be matched with the
performance requirements of the door. \*\*\*\*\***

4.  Entrance Function lockset; 28-11G05-LL.

**\*\*\*\*\* Schedule the following function for equipment, store room,
and mechanical chase doors, and in electronic access control
applications with jamb mounted electric strikes. The Latchset most
frequency used in this application is Sargent 10 Line Series with
following functions, but shall be matched with the performance
requirements of the door. \*\*\*\*\***

5.  Store Room Function lockset; 28-10G04-LL. Latchbolt operated by
    lever inside and by key in outside lever. Outside lever always
    locked and inside lever always active.

**\*\*\*\*\* Schedule the following function for use in Electronic
Access Control application using through door circuit in conjunction
with electrical power transfer, use only electronic door strike. The
Latchset most frequency used in this application is Sargent 10 Line
Series with following functions, but shall be matched with the
performance requirements of the door. \*\*\*\*\***

6.  Number range level3Electromechanically (fail secure) Function
    lockset; 28-10G71-LL.

7.  Electromechanically (fail safe) Function lockset; 28-10G70-LL

**\*\*\*\*\* Schedule the following function for use on Roof Access
Doors. The Latchset most frequency used in this application is Sargent
11 Line Series with following functions, but shall be matched with the
performance requirements of the door. \*\*\*\*\***

8.  Number range level3Asylum Function lockset; 28-11G17-LL.

## 2.06Number range level1Number range level2 COMBINATION LOCKSETS

A. Spin Dial Combination Lock: Security lock resistant to X-ray imaging
with spy-proof Centi-spline dial. Provide Kaba Mas Model X-09 pedestrian
door deadbolt with strike type 1,2,3, or 9 and key override module.
Procure from Defense Supply Center Philadelphia (DSCP), 700 Robbins
Avenue, Philadelphia, PA 19111. Ph. 215-737-2218. National Stock Number
(NSN) 5340-01-469-5906. If other than #1 strike is needed, call DOD Lock
Program Hotline at 800-290-7607. SNL Locksmith to install for projects
with six (6) or less installations

B. Mechanical Push-Button Combination Lock: Provide Simplex Unican
Lefthand LL1021B-26D-41, Righthand LR 1021B-26D-41 with key bypass.

C.Number range level3 Electrical Push-Button Combination Lock: Provide
electrical push-button combination locks activated by using keypad to
enter personal identification code number. Provide Infographics Keypads
& controllers per Contract Documents.

1\. Provide mechanical override in event of power failure.

2\. System to provide computerized audit trail of usage and access.

3\. Keypads, Controllers, etc.: Single keypad installed at door opening:
Model as manufactured by Infographics.

## 2.07Number range level1Number range level2Number range level3 EXIT DEVICES

A.  Exit Devices: Provide exit device only where specified on Contract
    Documents. Exit device latch bolts shall be released by depressing
    actuating push pad.

```{=html}
<!-- -->
```
1.  For single doors and double doors with removable or fixed center
    mullion, exit device shall be Sargent 80 Series, Precision 1100 or
    Von Duprin 90 series reversible rim device. The device shall have,
    appropriate strike and lever handle trim for application and
    function.

    a.  For Hollow Metal or Extruded Aluminum Storefront Non-Fire Rated
        Doors with a minimum stile width of 4 ¾" inch provide Sargent
        Model 8888 x ETL with Model 641 strike. Doors with vision-lite
        frames or moldings protruding at device mounting location
        provide Precision Models; 1100-1800, based on situation, Sargent
        80 Series, or Von Duprin 90 Series with appropriate strike. At
        double doors add Precision, Sargent or Von Duprin steel
        removable mullions. Where contract specifies key removable
        mullion provide Precision Model A-KR822 head cap.

    b.  For Fire Rated Doors, provide Sargent Model 12-8888 x ETL with
        Model 649 strike. Doors with vision lite frames or moldings
        protruding at device mounting location provide Precision Models
        1100-1800, based on situation, Sargent 80 Series or Von Duprin
        90 Series with appropriate strike. At double doors add
        Precision, Sargent or Von Duprin fire rated steel removable
        mullions.

    c.  For Extruded Aluminum Narrow Stile Storefront Doors with a
        minimum stile width of 1 ¾" inch provide Sargent 8500 x ETL,
        Precision 1400 on standard hollow metal door or wood door use
        narrow mullion Von Duprin 33 Series rim device.

2.  For pair of active doors without center mullion, exit devices on
    each leaf shall be Sargent 8700 Series, Precision 1200 series or Von
    Duprin 90/33 Series surface vertical rod exit devices. The device
    shall have appropriate strikes and lever handle trim for application
    and function.

    a.  For Hollow Metal or Extruded Aluminum Storefront Non-Fire Rated
        Doors with a minimum stile width of 4 ¾" inch, provide Sargent
        Model 8713 x 713-8 ETL with Model 629 top strike and 624 bottom
        strike. Doors with vision lite frames or molding protruding at
        device mounting location provide Precision Model 1208 x 39LA
        with Model 1200-06 top strike and 020-97 bottom strike.

    b.  For Fire Rated Doors, provide Sargent Model 12-8713 x ETL with
        Model 629 top strike and 624 bottom strike. Doors with vision
        lite frames or moldings protruding at device mounting location
        provide Precision Model FL-1208 x 39LA with Model 1200-06 top
        strike and 020-97 bottom strike.

    c.  For Extruded Aluminum Narrow Storefront Doors with a minimum
        stile width of 1 ¾" inch provide Sargent 8413 x ETL concealed
        rod device or Precision 1608 x 29LA concealed rod device. For
        double doors use Sargent 650A mullion or Precision 815 mullion.

3.  For Single Doors and Double Doors with removable or fixed center
    mullion, and which are indicated to be unlocked via electric
    actuation device (e.g., badge reader, key pad), provide Von Duprin
    EL99 Series exit device with electric latch retraction, Precision EL
    1100 Series exit device with electric latch retraction or Sargent 80
    Series w/electric latch retraction. The device must be provided with
    the manufacturers specified power supply, appropriate strike and
    lever handle trim. All electrical actuated devices actuated via
    electronic access control systems shall have outside lever trim,
    which remains in a constant locked position at all times. Key
    override retracts latch bolt but does not unlock lever.

    a.  For Hollow Metal or Extruded Aluminum Storefront Non-Fire Rated
        Doors with a minimum stile width of 4 ¾" inch, provide Von
        Duprin Model EL99NL x 992L-NL. Doors with vision lite frames or
        moldings protruding at device mounting location provide
        Precision Model ELR1103 x 39LA with Model 1200-06 strike. At
        double doors add Precision Model 822 steel removable mullions.
        Where contract specifies key removable mullion provide Precision
        Model A-KR822 head cap. Use device manufacturer's specified
        power supplies and Von Duprin Electric Power Transfer Model EPT
        or equal.

    b.  At Fire Rated Doors, provide Von Duprin Model 99-F-EL99NL x
        992L-NL or Precision Model FL-ELR1103 x 39LA. At double doors
        provide Precision Model FL-822 fire rated steel removable
        mullions. Where contract specifies key removable mullion provide
        Precision Model A-FL-KR822 head cap. Use device manufacturer's
        specified power supplies and Von Duprin Electric Power Transfer
        Model EPT or equal.

    c.  For Extruded Aluminum Narrow Storefront Doors with a minimum
        stile width of 1 ¾" inch provide Von Duprin EL33NL x 370L or
        Precision ELR1403 x 29LA rim device. For double doors use
        Sargent 650A mullion or Precision 815 mullion. Use device
        manufacturer's specified power supplies and Von Duprin Electric
        Power Transfer Model EPT-10.

4.  Vault Type Rooms (VTR): Provide LMK7003 with key bypass module and
    the KABA MAS X-09 Spin Dial with electric strike.

    a.  Refer to requirements for spin dial combination lock specified
        in Section 2.6- Spin Dial Combination Lock.

    b.  Provide KABA MAS CDX-09 with High Security Pedestrian Exit
        Device for occupant load of 50 or more.

## 2.08Number range level1Number range level2Number range level3 DOOR COORDINATOR

A. Comply with ANSI A156.3, Grade 1.

B. Provide coordinator at all pairs of active doors without center
mullion. Use Sargent Model 3487 with Model 3497 carry open bar.

C. UL listed for fire-rated openings.

## 2.09Number range level1Number range level2 CLOSERS

A. Closers: Closers shall be surface mount type with parallel arms, back
check, key control valves, and 50% percent power adjustments and shall
facilitate automatic closure of door. Provide Sargent Model EN351 series
closers on exterior doors, interior fire rated doors, doors with
electro-magnetic door holders, interior doors with exit devices,
push-pull devices, auxiliary latchsets and additional doors indicated on
Contract Documents.

B.Number range level3Number range level4 Compliance:

1\. ANSI A156.4, Grade 1 and BHMA Directory of Certified Door Closers

2\. ADA and ABA Accessibility Guidelines for Buildings and Facilities
for reduced opening force requirements.

3\. UL listed for doors without hold-open.

4\. IBC 2006 Positive pressure fire test.

C.Number range level3 Operation: One valve controlling closing speed and
second valve controlling latching speed. Fully adjustable back-check and
selector valve.

D. Where indicated in Hardware Schedule or functionally required,
provide adjustable hold open arm.

E. Where door cannot swing open 180 degrees or as indicated in Hardware
Schedule, provide auxiliary stop.

F. Provide brackets, drop plates, through bolts and grommet nuts, and
other required accessories for mounting.

G. Cover: Plastic with painted finish.

## 2.10Number range level1Number range level2Number range level3 DOOR TRIM

A. Comply with ANSI A156.6.

B. Kick Plates: Heavy-Duty, 16-gauge (2mm) smooth surface metal. Provide
Trimco K-.050 -- 12" inches x 34" inches (306 mm x 867 mm) US26D LDW on
push side of doors scheduled for exit devices, on both side of doors
with push/pull devices or auxiliary latchsets; ANSI J102.

C. Push/Pull Plates: Heavy-Duty, 4" inches x 16" inches (102 mm x 408
mm), straight loop pull; ANSI J405.

## 2.11Number range level1Number range level2 ELECTROMAGNETIC DOOR HOLDERS

A. Comply with ANSI A156.15, Grade 1.

B. Electro-Magnetic Door Holder: Provide electro-magnetic door holder
device only when specified in Contract Documents. The device shall be
Underwriter's Laboratory (UL) listed and Factory Mutual (FM) approved
and shall be fail safe, conforming to NFPA 72, NFPA 80, and NFPA 101.
Release device shall be so designed that it may be automatically
released by power interruption and manually released by some simple and
readily obvious operation.

Provide Honeywell, NOTIFIER FM Series or equal for 120 VAC. Provide
appropriate floor mount pedestal where needed for floor mount
installation.

1.  In new construction, where indicated to be installed on walls, door
    holder shall be flush mounted.

2\. In renovation work, where indicated to be installed on walls, door
holder may be surface mounted.

When wall or floor mounting device is not appropriate, Provide LCN
4040SE Series. The 4040SE or SE(L) is a heavy duty, non-handed,
non-sized closer/holder designed to provide single point hold-open for
fire and smoke barrier doors.

## 2.12Number range level1Number range level2 MANUAL FLUSH BOLTS

A. Comply with ANSI 156.16.

B. Top and bottom Manual Flush Bolts, shall be Trimco 3917.

## 2.13Number range level1Number range level2 ELECTRIC STRIKE

A. Comply with ANSI 156.16.

B. When noted elsewhere in Contract Documents, provide heavy-duty
electric strikes fully compatible with door, frame, and hardware
specified for intended application. Strike shall have latchbolt
monitoring capability.

## 2.14Number range level1Number range level2Number range level3 LOW-ENERGY POWER OPERATED DOOR OPENERS

A. Low Energy Power Operated Door Openers: On specified doors only,
provide power operated door opener(s). The power opener shall be low
energy, self-contained electric operating mechanism. It shall be powered
open with DC motor working through reduction gears.

1.  The motor shall be off when door is in closing mode.

2.  The door shall be capable of being manually opened or closed with
    power on or off without damage to mechanism.

3.  The opener shall include the following variable adjustments in
    compliance with ANSI/BHMA A156.19.

```{=html}
<!-- -->
```
a.  Opening Speed - three to five seconds

b.  Closing Speed - three to five seconds

c.  Time Delay Before Closing - five to fifteen seconds

4\. Opening and closing force, measured 2" inches (51 mm) out from lock
stile of door, shall not exceed 15 pounds (6.8 kg) of force to stop door
when operating in either direction.

5\. The opener shall include means of turning off opening force when
door is stopped for one second. After stopping door, it should then
close and opener shall reset itself to accept another signal.

6\. The opener shall be mounted in extruded aluminum cover.

7\. Provide two (2) 6" inch (152 mm) round stainless steel push plate
control switches marked \"Handicapped\" on each side of opening, unless
otherwise indicated in Contract Documents.

\- OR -

> 8\. (Preferred Alternative Switch) Provide single bar switch.
>
> **\*\*\*\* I-36 INGRESS'R, 6"inches wide, 36" inches tall: model \#
> I36-5 clear anodized aluminum with blue logo. \*\*\*\***

## 2.15Number range level1Number range level2 AUXILIARY HARDWARE

A. Auxiliary Hardware: Auxiliary hardware shall be provided only where
specified herein and/or elsewhere on Contract Documents.

1.  Combination stop and holder device shall be Trimco Model 1224-5,
    manually operated device.

2.  Concave wall mount door bumpers shall be provided at doors opening
    onto adjacent walls. Provide Trimco Model W1270-W x CP x Pl Series
    with appropriate fasteners.

3.  Floor mount door bumpers shall be provided on doors where wall type
    door bumpers are not provided. Provide Trimco Model W1210ES Series.

4.  Provide Trimco Model 1229A neoprene door silencers on non-fire rated
    doors. Provide three per each door.

5.  Provide flexible silicone rubber smoke seal on fire rated doors in
    compliance with ANSI A156.22. Use NGP 2525 x Door Size.

6.  Provide weather-stripping, door sweep(s), and threshold at exterior
    doors in compliance with ANSI A156.21 and A156.22.

```{=html}
<!-- -->
```
a.  Provide NGP 160 weather-stripping at all non-fire rated exterior
    doors.

b.  Provide NGP 200 NA door sweep at exterior doors.

c.  Provide NGP 424E threshold at exterior doors.

```{=html}
<!-- -->
```
7.  Astragal:

```{=html}
<!-- -->
```
a.  Provide NGP 125 NGA astragal for all other fire rated and non-fire
    rated double doors without center mullion where security astragal is
    not specified.

b.  Provide security astragal on exterior pairs of doors without center
    mullions and exit devices. Provide NGP 139 SP

    8.  Automatic door bottoms for both fire rated and non-fire rated
        doors shall be NGP 420NA. Comply with ANSI A156.22.

## 2.16Number range level1Number range level2Number range level3 FINISHES

A. Finishes for all door hardware shall comply with ANSI A612, US26D,
Plated, Satin Chrome except otherwise scheduled.

# PART 3 ‑ EXECUTION

## 3.0Number range level0Number range level1Number range level2Number range level3Number range level4Number range level5Number range level6Number range level71Number range level1Number range level2Number range level3 INSPECTION

A. Prior to installation, verify that doors and frames are ready to
receive hardware. Verify that hardware is free of surface defects,
warpage, and other defects which might impede performance of hardware.

## 3.02Number range level1Number range level2 PREPARATION

A. Prepare doors and frames to receive new hardware items.

1.  For Steel Doors and Frames comply with ANSI/DHI A115-Set Steel
    series.

2.  For Wood Doors comply with ANSI/DHI A115-Set Wood series.

3.  Surface-Applied Door Hardware: Drill and tap doors and frames
    according to ANSI A250.6.

B. Use manufacturer provided templates. Cuts shall be straight and
smooth without jagged edges. File and grind edges to provide smooth
appearance.

C. Reinforce cutouts as required to provide rigidity and support.

## 3.03Number range level1Number range level2 INSTALLATION

A. Install hardware in accordance with manufacturer\'s instructions.

B. Locate hardware from finished floor in accordance with DHI
publications unless shown otherwise on Drawings.

1.  Butt Hinges: Install minimum of 1-1/2 pair per door on doors no
    taller than 7'-2" (2.18 m), otherwise install two (2) pair butt
    hinges per door.

2.  Lock and Latches: Install locks and latches at 36" inches (914 mm)
    above bottom of door.

3.  Dial and Push Button Combination Locks: Install per manufacturer\'s
    installation instructions at 42"inches (1.07 m) above finish floor.

> 4\. Push Plate Control Switches: Install 6" inch (152 mm) round push
> plate control switches at 9" inches (229 mm) and 39" inches (991 mm)
> above finish floor to center line of round plates. Two (2) plates are
> required on each side of opening.
>
> 5\. Wikk I-36 INGRESS'R™ Control Switch: Install 6" above finished
> floor to bottom of switch. Provide side to side clearances that comply
> with the ADA and ABA Accessibility Guidelines for Buildings and
> Facilities, Part II: ABA Application and Scoping.6. Thresholds: Set
> thresholds for exterior doors in full bed of sealant complying with
> requirements specified in Section 07900, "Joint Sealants."

C. Protect hardware finish until painting and other work is completed.

D. Adjust operating hardware, thoroughly clean, and polish in accordance
with manufacturer\'s instructions.

## 3.04Number range level1Number range level2 SCHEDULE

A. Requirements for design, grade, function, finish, size, and other
distinctive qualities of are indicated in Schedule. Products are
identified by \[ANSI 156 reference numbers\] \[and\] \[using
manufacturer\'s hardware model numbers\].

B. Manufacturer\'s product designation: Manufacturers are listed for
hardware items to establish minimum requirements. Provide product
designated in Paragraph 2.1 for specific hardware category.

C. Items shall be proper type for attaching securely to specific project
substrate.

\- END OF SECTION -