SECTION 23 2500

HVAC WATER TREATMENT

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

LANL MASTER SPECIFICATION

This specification specifies Garratt-Callahan, Lakos, and Thermo
Polysonics products for chemical treatment of closed HVAC, open cooling
tower, and steam boiler systems. Consult with the FOD Facility Engineer
for the type of treatment system/chemicals required. ***Italicized***
text identifies recommended guidance (not mandatory). All other text in
regular type indicates mandatory requirements.

**All chemicals must be identified in LANL's NPDES permit application
and LANL's waste profile form (WPF) as potential contaminants of
concern. Consult with the LANL Water Quality Group.**

This template must be edited for each project.  In doing so, specifier
must add job-specific requirements.  Brackets are used in the text to
indicate designer choices or locations where text must be supplied by
the designer.  Once the choice is made or text supplied, remove the
brackets.  The specifications must also be edited to delete
specification requirements for processes, items, or designs that are not
included in the project \-- and specifier's notes such as these.  To
seek a variance from requirements in the specifications that are
applicable, contact the Engineering Standards Manual Mechanical
[POC](http://engstandards.lanl.gov/engrman/6mech/htmls/mechnew2.htm).
Please contact POC with suggestions for improvement as well.\
\
When assembling a specification package, include applicable
specifications from all Divisions, especially Division 1, General
requirements.\
\
Specification developed for ML-4 projects.  For ML-1, 2, and 3
applications, additional requirements and independent reviews should be
added if increased confidence in procurement or execution is desired;
see ESM Chapter 1 Section Z10 Specifications and Quality sections.\
\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

1.  GENERAL

    1.  SECTION INCLUDES

```{=html}
<!-- -->
```
A.  Cleaning of HVAC piping systems.

B.  Chemical water treatment of \[closed HVAC\], \[open cooling tower\],
    and \[steam boiler\] system(s).

    1.  SUBCONTRACTOR REQUIREMENTS

> A. Notify LANL Subcontract Technical Representative (STR) at least 24
> hours (1 working day) in advance to witness cleaning (flushing) and
> water treatment activity.
>
> B. Do not fill or flush piping systems until source of water supply is
> approved by LANL STR.
>
> C. Do not clean or chemically treat piping systems until systems have
> been successfully pressure tested.
>
> D. For discharge requirements of water used for flushing and water
> treatment, comply with Section 01 3545, Water Discharge Requirements.
>
> E. Notify LANL STR immediately in the event of any accidental
> discharge.
>
> F. Do not place piping systems in service until LANL STR approves
> cleaning and chemical treatment results.

2.  LANL STR REQUIREMENTS

> A. For discharge requirements of water used for flushing and water
> treatment, comply with Section 01 3545, Water Discharge Requirements.

B.  Verify proper cleaning, flushing, chemical concentration and
    circulation.

C.  Immediately after receiving list of chemicals to be used from
    subcontractor, including chemical composition, submit copy to the
    LANL Water Quality Group for approval.

    1.  SUBMITTALS

```{=html}
<!-- -->
```
A.  Submit the following in accordance with Section 01 3300, Submittal
    Procedures:

```{=html}
<!-- -->
```
1.  Catalog data of flushing and chemical water treatment chemicals and
    equipment including electrical characteristics and connection
    requirements.

2.  Operation and Maintenance data on equipment, procedures, and
    treatment program. Include instructions on test procedures including
    target concentrations.

3.  Submit material list of all chemicals to be used, including chemical
    composition, to LANL STR 30 days prior to using chemicals. Do not
    begin chemical treatment until chemicals have been approved by the
    LANL Water Quality Group.

    1.  QUALIFICATIONS OF CHEMICAL SUPPLIER

```{=html}
<!-- -->
```
A.  Company specializing in performing the Work of this section with
    minimum 10 years experience and approved by chemical manufacturer.

B.  Personnel using biocide products shall have a New Mexico Department
    of Agriculture (NMDA) pesticide applicator license.

    1.  QUALITY ASSURANCE

> A. Biocide products shall be registered with the EPA, with the
> registration number clearly shown on drum labels.

2.  PRODUCTS

    1.  PRODUCT OPTIONS AND SUBSTITUTIONS

        A.  Alternate products may be accepted; follow Section 01 2500,
            Substitution Procedures.

        B.  A single water treatment supplier shall provide treatment
            chemicals and chemical feed/chemical control equipment.

    ```{=html}
    <!-- -->
    ```
    1.  MATERIAL SAFETY DATA SHEETS

> A. Maintain on site Material Safety Data Sheets (MSDS) for chemical
> products.

2.  SYSTEM CLEANING

    A.  Manufacturer: Garratt-Callahan, Formula 248L.

    ```{=html}
    <!-- -->
    ```
    A.  Treatment Chemical: Alkaline liquid blend of phosphates,
        silicates, iron oxide chelants, dispersants, and surface active
        agents.

3.  CLOSED LOOP WATER TREATMENT (heating water and chilled water)

```{=html}
<!-- -->
```
1.  Manufacturer: Garratt-Callahan.

2.  Chemical Pot Feeder: Model FTF-5, 71/2 gallon capacity, steel
    construction, rated at 300 psi and 200 degree F, with option of
    adding a filter bag.

3.  Treatment Chemical: Formula 1015L, corrosion and scale inhibitor
    based on phosphorate and orthophosphate. Furnish 1 year's supply.

    1.  OPEN COOLING TOWER WATER TREATMENT

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Refer to Mechanical Drawings ST-D30GEN-1 (Guidance), Open Cooling Tower
Water Treatment Flow Diagram.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

A.  Manufacturer: Garratt-Callahan.

```{=html}
<!-- -->
```
A.  Control Panel: Model 25-161-FS-CR30-330-SPLMB. Prewired and
    preplumbed on a stainless steel wall mounting plate with a Plexiglas
    safety shield, size 42L x 32H x 12D (inches), furnished with a 15
    amp, 120VAC duplex receptacle for incoming power. Components
    include:

    1.  Two chemical pumps, Model Lb-64-KTC.

    2.  Conductivity controller, Model 161FS, conductivity range 0-5000
        S.

    3.  ORP controller, Model 330, ORO range 0-1000mV.

B.  Brominator: Model SC-10-S-05, Factory assembled with flow meter,
    drain valves, inlet and outlet valves, and base.

C.  Chemical Tanks (treatment chemicals 1265 and 2011): Model G-40-F, 40
    gallon polyethylene tank, double contained with cover.

D.  Chemical Tank with pump (treatment chemical 159):

    1.  Tank, Model G-40-4, 40 gallon polyethylene tank, double
        contained with cover.

    2.  Chemical pump, Model Lb-64-KTC.

E.  Solenoid Valves (brominator and dechlorination lines): Model
    8210G95, 2-way normally closed, zero pressure, 3/4 inch pipe size,
    and 120VAC.

F.  Corrosion Coupon Rack: Model 9050, 3/4 inch schedule 80 PVC.

G.  Treatment Chemicals: (Furnish 1 Year's Supply)

```{=html}
<!-- -->
```
1.  Formula 159 oxygen scavenger. Crystallized liquid formation of
    potassium/sodium/bisulfate.

2.  Formula 314T biocide. Solid tablets that dissolve in water to
    release chlorine and bromine.

3.  Formula 2011 cooling water treatment. Corrosion inhibitor to protect
    steel and copper metal from oxygen corrosion.

4.  Formula 1265 Polymeric Dispersant: Aqueous blend of proprietary
    polymer for silica control.

    1.  SEPARATOR (Open Cooling Tower)

        A.  Manufacturer: Lakos, No. TC-\[ \]-CRS or AXL-\[ \].

        B.  Steel construction, rated at 150 psig, flanged connections.
            Flow range \[ \] gpm.

    2.  FLOW METER (Open Cooling Tower)

        A.  Manufacturer: Thermo Polysonics, Model SX40

        ```{=html}
        <!-- -->
        ```
        A.  Doppler ultrasonic flow meter, dedicated, noninvasive,
            digital display of rate (gpm) and total flow (gallons), 4-20
            mA output signal, 120VAC, single phase, 20-foot standard
            cable length, accuracy within plus or minus 2 percent of
            full scale, NEMA 4X thermoplastic housing, for use on \[ \]
            SCH 40 pipe, standard flow range 1-10 fps.

    3.  STEAM BOILER WATER TREATMENT

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Consult with the FM Facility Engineer and chemical supplier for type of
chemical feed and control equipment required for the steam boiler water
treatment system.

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

A.  Manufacturer: Garratt-Callahan, Formula 1152.

B.  Treatment Chemical: Formula 1152 boiler water treatment, liquid
    all-polymeric scale corrosion inhibitor. Furnish 1 year's supply.

```{=html}
<!-- -->
```
3.  EXECUTION

    3.1 INSTALLATION

    A.  Subcontractor shall furnish and install water treatment system
        supplied by the water treatment supplier.

    ```{=html}
    <!-- -->
    ```
    2.  PRE OPERATION CLEANING (Open Cooling Tower and Closed Loop
        System)

```{=html}
<!-- -->
```
A.  Prior to startup, clean system with Formula 248L, following the
    written procedures furnished by the chemical supplier.

    1.  Ensure water filters, instrumentation, gages, flow transmitters,
        and similar items are removed or protected. Provide a temporary
        bypass or plugs as required.

    ```{=html}
    <!-- -->
    ```
    2.  CHEMICAL SUPPLIER WATER TREATMENT SERVICE PROGRAM

        A.  Provide consulting services for a period of 1 year from the
            time of startup which shall include:

            1.  Installation and startup recommendations.

            2.  Field water analysis and recommendations.

            3.  Quarterly lab analysis on treated systems for metals,
                microorganisms, and standard analysis.

            4.  Training of plant personnel in proper feed and control.

            5.  Minimum monthly service calls.

            6.  Log sheets and record forms.

END OF SECTION

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

Do not delete the following reference information:

\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*\*

FOR LANL USE ONLY

This project specification is based on LANL Master Specification 23 2500
Rev. 1, dated June 11, 2008.