**Section J, Attachment N**

**Exhibit N-1 -- Table 1**

**System Definitions**

1.  Mechanical

+-----+----+----------+-----------------------------------------------+
| \#  | Sy | System   |                                               |
|     | st |          |                                               |
|     | em |          |                                               |
|     | Ty |          |                                               |
|     | pe |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## Chill |                                               |
| .01 | ec | ed Water |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | [Production]{.underline} -- Water chillers at |
| 1.0 |    | Des      | **\*JSC** consist of large central plant      |
| 1.A |    | cription | systems (up to 2000 tons) and individual      |
|     |    |          | packaged systems serving specific selected    |
|     |    |          | facilities. The central plants, buildings 24  |
|     |    |          | and 28, provide chilled water internally and  |
|     |    |          | through the utility tunnel or direct buried   |
|     |    |          | to the mall buildings for use as HVAC or      |
|     |    |          | process cooling. The emergency power          |
|     |    |          | building, building 48 provides chilled water  |
|     |    |          | internally and through the utility tunnel to  |
|     |    |          | the Mission Control Center (MCC) buildings    |
|     |    |          | (30L, 30M and 30S) to be used in HVAC         |
|     |    |          | cooling. The chiller auxiliary support        |
|     |    |          | equipment in buildings 24, 28, and 48, is the |
|     |    |          | equipment/components required to support the  |
|     |    |          | operation of a plant chilled water system or  |
|     |    |          | a backup to provide chilled water when the    |
|     |    |          | plant chilled water systems not available.    |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} -- The chilled |
|     |    |          | water piping system contains approximately    |
|     |    |          | eight miles of primary supply and return      |
|     |    |          | piping that connects the central/auxiliary    |
|     |    |          | plants to the mall facilities and building    |
|     |    |          | 48. This system includes the direct buried    |
|     |    |          | chilled water supply and return feeds from    |
|     |    |          | both building 24 and 28 that connects in the  |
|     |    |          | tunnel. The Building 48 chilled water         |
|     |    |          | distribution system provides chilled water    |
|     |    |          | supply and return to the MCC and helps feed   |
|     |    |          | the tunnel system when necessary. The         |
|     |    |          | building 48 system can either produce chilled |
|     |    |          | water or redirect building 24 and 28 chilled  |
|     |    |          | water as required.                            |
|     |    |          |                                               |
|     |    |          | Closed loop cooling systems are those systems |
|     |    |          | that use a chilled water heat exchanger to    |
|     |    |          | provide a secondary cooling water loop to     |
|     |    |          | provide cleaner cooling water for             |
|     |    |          | sensitive/critical equipment.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | [Production]{.underline} -- The contractor    |
| 1.0 |    | Output   | shall operate chilled water systems as        |
| 1.B |    |          | necessary to ensure chilled water is          |
|     |    |          | continuously supplied to facilities to        |
|     |    |          | satisfy the load. The central/auxiliary plant |
|     |    |          | chilled water systems must be maintained in   |
|     |    |          | such a manner as to ensure that there are     |
|     |    |          | always two spare chilled water systems        |
|     |    |          | available to be placed in service at all      |
|     |    |          | times. During mission support periods the     |
|     |    |          | building 24 and 28 systems must be available  |
|     |    |          | to immediately support the additional load    |
|     |    |          | from the MCC if necessary. The roof mounted   |
|     |    |          | backup water chiller at the central plant     |
|     |    |          | shall be available at all times to support    |
|     |    |          | critical air handler 24-6 operation in the    |
|     |    |          | event of a plant chilled water outage. The    |
|     |    |          | building 48 chilled water system shall        |
|     |    |          | continuously satisfy the MCC load and shall   |
|     |    |          | provide chilled water at 44°F +/-1°F or as    |
|     |    |          | directed by NASA. The building 48 system      |
|     |    |          | shall maintain at least one chiller in a      |
|     |    |          | standby condition available to be placed into |
|     |    |          | immediate service with one chiller down for   |
|     |    |          | maintenance/repair and with a two chiller     |
|     |    |          | load. All chilled water systems shall be      |
|     |    |          | maintained such that freon leaks are repaired |
|     |    |          | within 30 days of discovery. The contractor   |
|     |    |          | shall operate the chilled water systems that  |
|     |    |          | are the most energy efficient based on lowest |
|     |    |          | \$/ton operational cost per chiller unit      |
|     |    |          | except during outages, equipment training, or |
|     |    |          | weekend equipment rotation operation to       |
|     |    |          | maintain equipment reliability. All systems   |
|     |    |          | shall be free of water leaks.                 |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} -- All chilled |
|     |    |          | water distribution systems shall deliver a    |
|     |    |          | continuous chilled water supply from the      |
|     |    |          | point of production to the facility and shall |
|     |    |          | be maintained free of leaks. All chilled      |
|     |    |          | water systems shall be controlled at each     |
|     |    |          | HVAC system to meet the requirements for cold |
|     |    |          | deck temperatures as specified in the JSC     |
|     |    |          | Spring/Summer and Fall/Winter Seasonal        |
|     |    |          | Adjustment Plan and to meet building          |
|     |    |          | temperature and humidity requirements. Closed |
|     |    |          | loop cooling systems shall meet the equipment |
|     |    |          | requirements for flow, temperature, and       |
|     |    |          | capacity and be free of leaks.                |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | [Production]{.underline} -- The chilled water |
| 1.0 |    | Co       | system components include but are not limited |
| 1.C |    | mponents | to, chilled water pump, filter, evaporator,   |
|     |    |          | condenser and economizer section, electric    |
|     |    |          | motor or steam turbine driver, gear box,      |
|     |    |          | compressor, oil return units, control panels  |
|     |    |          | and the field control systems, heat           |
|     |    |          | exchangers, pumps, surface condensers, hot    |
|     |    |          | well pumps, piping, refrigerant piping,       |
|     |    |          | refrigerant valves, instrumentation including |
|     |    |          | PLC's, flow devices, probes, delta-Pressure   |
|     |    |          | switches, pneumatic controls, etc., makeup    |
|     |    |          | water tanks, side stream filters, compression |
|     |    |          | tanks, freon recovery units, and freon boil   |
|     |    |          | off vessels.                                  |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} -- The tunnel  |
|     |    |          | chilled water system may include but are not  |
|     |    |          | limited to the following: piping, cathodic    |
|     |    |          | protection system, insulation and aluminum    |
|     |    |          | jacketing, air vents, valves and associated   |
|     |    |          | brass tags, instrumentation including flow    |
|     |    |          | devices, probes, delta-Pressure switches,     |
|     |    |          | etc. All chilled water systems include the    |
|     |    |          | chilled water system inside the facilities.   |
|     |    |          | The components of the chilled water system    |
|     |    |          | may include, but not be limited to, pumps,    |
|     |    |          | strainers, instrumentation including flow     |
|     |    |          | devices, probes, delta-Pressure switches,     |
|     |    |          | etc., gauges, controls, orifice plates and    |
|     |    |          | other flow elements, compression tanks,       |
|     |    |          | control valves and associated controls,       |
|     |    |          | valves, fittings, pipe, labels and            |
|     |    |          | insulation.                                   |
|     |    |          |                                               |
|     |    |          | Closed loop cooling systems may contain, but  |
|     |    |          | not be limited to, any combination of heat    |
|     |    |          | exchangers, pumps, piping, fittings, labels,  |
|     |    |          | valves, flow indicators, compression tanks,   |
|     |    |          | strainers, filters, auto air eliminators,     |
|     |    |          | insulation, instrumentation, and controls.    |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## HVAC  |                                               |
| .02 | ec |          |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | That system which supplies conditioned air to |
| 1.0 |    | Des      | a space or facility, to maintain required     |
| 2.A |    | cription | temperature humidity conditions.              |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The space to be conditioned shall be          |
| 1.0 |    | Output   | maintained at temperatures specified in JMI   |
| 2.B |    |          | 8836.1 for personnel comfort and/or equipment |
|     |    |          | requirements. Air exchanges and indoor air    |
|     |    |          | quality shall be provided to meet current     |
|     |    |          | ASHRAE recommendations. Discharge air         |
|     |    |          | temperatures from HVAC units shall be as      |
|     |    |          | directed in Spring/Summer and Fall/Winter     |
|     |    |          | Seasonal Adjustment plans. Provide indoor air |
|     |    |          | quality such that visual inspection of the    |
|     |    |          | supply air ducts, diffusers and cooling coil  |
|     |    |          | section (including coil, pan, piping,         |
|     |    |          | insulation and walls), of the air handler     |
|     |    |          | shall reveal no biological growth, algae,     |
|     |    |          | fungus, mildew, etc. Spot Coolers shall be    |
|     |    |          | installed and operated, including condensate  |
|     |    |          | removal, for short term (less than 6 months)  |
|     |    |          | facility configuration changes.               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | These systems are defined to include chilled  |
| 1.0 |    | Co       | water, direct expansion systems, and PTOA's   |
| 2.C |    | mponents | (Pre-Treated Outside Air), interior and       |
|     |    |          | exterior locations including but not limited  |
|     |    |          | to, mechanical rooms, computer rooms, general |
|     |    |          | office areas, laboratories, vaults, and       |
|     |    |          | overhead installations. This may also include |
|     |    |          | but not be limited to central station units,  |
|     |    |          | portable spot coolers, window units, D/X      |
|     |    |          | split systems, fan coil units, condenser      |
|     |    |          | units, package units, and floor mounted       |
|     |    |          | computer room type units. Components shall be |
|     |    |          | defined as, but not limited to, coil (CW and  |
|     |    |          | refrigerant), fan, constant and variable      |
|     |    |          | frequency drive units, motor drive, belt,     |
|     |    |          | filters, control valves, reboiler, condensate |
|     |    |          | collection pans and piping, hot water coils,  |
|     |    |          | steam coils, refrigerant coils, gas fired     |
|     |    |          | furnace section, overflow protection devices, |
|     |    |          | humidity control heaters (hot water and       |
|     |    |          | electric) and instrumentation, humidifiers,   |
|     |    |          | accelerometers, compressor and associated     |
|     |    |          | instrumentation and controls, gauges and      |
|     |    |          | other instrumentation and controls specific   |
|     |    |          | to the air handler systems including flow     |
|     |    |          | devices, probes, delta-Pressure switches,     |
|     |    |          | etc., air distribution systems such as mixing |
|     |    |          | boxes, variable air terminals, fans, heaters, |
|     |    |          | ducting, dampers ,and insulation.             |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | #        |                                               |
| .03 | ec | # Coolin |                                               |
|     | h. | g Towers |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Cooling towers/condenser/cooling water        |
| 1.0 |    | Des      | systems are heat rejection systems that       |
| 3.A |    | cription | provide cooling water for condensing          |
|     |    |          | refrigerants in HVAC/Chillers or other        |
|     |    |          | cooling applications.                         |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | All condenser/cooling water systems shall     |
| 1.0 |    | Output   | continuously satisfy the plant and/or         |
| 3.B |    |          | facility loads and shall provide condenser    |
|     |    |          | water to the plants at 86 °F to 90 °F on      |
|     |    |          | design days at 80 °F wet bulb temperature     |
|     |    |          | while utilizing an optimum number of cooling  |
|     |    |          | tower cells. The contractor shall provide a   |
|     |    |          | water treatment program to maintain mild      |
|     |    |          | steel corrosion rates less than 2.0 mils per  |
|     |    |          | year and copper corrosion rates less than .2  |
|     |    |          | mils per year and the program shall treat the |
|     |    |          | water and tower areas for algae and           |
|     |    |          | biological growth. When any bacterial growth  |
|     |    |          | is detected that poses potential harm to      |
|     |    |          | personnel or equipment, as determined by the  |
|     |    |          | JSC Occupational Health Office, an aggressive |
|     |    |          | treatment program must be maintained until    |
|     |    |          | the algae/bacteria growth is destroyed. The   |
|     |    |          | system shall be free of leaks. The building   |
|     |    |          | 24 plant condenser water system shall be      |
|     |    |          | maintained to be able to support the two      |
|     |    |          | additional backup chilled water systems as    |
|     |    |          | required in section 1.1.01.B. Condenser water |
|     |    |          | quality shall be maintained within the        |
|     |    |          | chemical limits as specified on JSC Form      |
|     |    |          | 1426, Water Analysis Log for Cooling Towers   |
|     |    |          | in Buildings 28 or 48.                        |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Cooling tower/condenser/cooling water systems |
| 1.0 |    | Co       | are defined as containing, but not limited    |
| 3.C |    | mponents | to, all or any combination of cooling towers, |
|     |    |          | heat exchangers, piping, filters, fittings,   |
|     |    |          | labels, fans, gear boxes, flow elements,      |
|     |    |          | basins, pumps, valves, fire detection and     |
|     |    |          | protection equipment, chemical feed pumps,    |
|     |    |          | chlorine supply system, chemical treatment    |
|     |    |          | systems, side stream filtration, controls,    |
|     |    |          | accelerometers, and instrumentation including |
|     |    |          | flow devices, probes, delta-Pressure          |
|     |    |          | switches, etc.                                |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | #        |                                               |
| .04 | ec | # Compre |                                               |
|     | h. | ssed Air |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | [Production]{.underline} -- Buildings 24 and  |
| 1.0 |    | Des      | 28 shall provide dry, oil-free compressed air |
| 4.A |    | cription | internally and through the tunnel or direct   |
|     |    |          | buried to the site buildings to be used as    |
|     |    |          | instrument or shop air. Building 48 shall     |
|     |    |          | provide dry compressed air internally through |
|     |    |          | the tunnel for building 30M if the central    |
|     |    |          | plant cannot provide sufficient quantity or   |
|     |    |          | pressure. Included are systems that supply    |
|     |    |          | and distribute dry, compressed breathing air  |
|     |    |          | to the building for use as breathing air.     |
|     |    |          | Also included are starting air systems that   |
|     |    |          | supply and deliver starting air to starting   |
|     |    |          | air motors on diesel engines.                 |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} -- The         |
|     |    |          | compressed air distribution system is a       |
|     |    |          | piping network approximately four miles in    |
|     |    |          | length, both tunnel and direct buried, that   |
|     |    |          | connects the central/auxiliary plant outputs  |
|     |    |          | to the JSC facilities and the building 48     |
|     |    |          | output to the Mission Control Center. The     |
|     |    |          | compressed air systems are defined to include |
|     |    |          | the compressed air system inside the facility |
|     |    |          | described as instrument, shop, plant, and     |
|     |    |          | breathing air. All **\*JSC** facilities are   |
|     |    |          | equipped with either an independent           |
|     |    |          | control/shop or breathing air compressor or   |
|     |    |          | have a backup control air compressor when     |
|     |    |          | supplied with plant air.                      |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | [Production]{.underline} -- The building 24   |
| 1.0 |    | Output   | plant air system shall continuously satisfy   |
| 4.B |    |          | the site load and shall provide oil free      |
|     |    |          | compressed air to the site buildings at a     |
|     |    |          | nominal 125-psig +/- 3 psig with a maximum    |
|     |    |          | dew point of -- 40 °F +/- 5 °F or as directed |
|     |    |          | by NASA. The building 28 plant air system     |
|     |    |          | shall operate at 140 PSIG +/-3 PSIG with a    |
|     |    |          | maximum dew point of --40 °F +/- 5 °F or as   |
|     |    |          | directed by NASA. The plant compressed air    |
|     |    |          | system shall have one additional utility air  |
|     |    |          | compressor available to be placed in service  |
|     |    |          | at all times as a standby compressor. The dew |
|     |    |          | point air output from the desiccant dryer     |
|     |    |          | system shall be maintained and the desiccant  |
|     |    |          | shall be replaced, heater elements replaced,  |
|     |    |          | or other repairs made as required to ensure   |
|     |    |          | the dew point requirement. The plant air      |
|     |    |          | system shall be operated at 150-psig +/- 3    |
|     |    |          | psig. The starting air system for the power   |
|     |    |          | engines shall provide compressed air whenever |
|     |    |          | needed at 150-psig +0/-5 psig or as directed  |
|     |    |          | by NASA.                                      |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} - The          |
|     |    |          | compressed air distribution system shall      |
|     |    |          | deliver a continuous supply of compressed air |
|     |    |          | from the point of production to point of use  |
|     |    |          | at the required quantity and pressure. The    |
|     |    |          | instrument air pressure shall be regulated to |
|     |    |          | a nominal 20-PSI +/- 1 PSI. The breathing air |
|     |    |          | system shall deliver dry, compressed          |
|     |    |          | breathing air to the building at 150 PSI +/-  |
|     |    |          | 3 PSI (or as directed by NASA), certified for |
|     |    |          | breathing and conforming to sampling per      |
|     |    |          | American National Standard Commodity          |
|     |    |          | Specification for Air, Compressed Gas         |
|     |    |          | Association, Inc. (ANSI/CGA G-7.1-1989 or     |
|     |    |          | latest version.)                              |
|     |    |          |                                               |
|     |    |          | All **\*JSC** compressed air systems shall    |
|     |    |          | maintain current certification of all         |
|     |    |          | pressure systems and components per JHB       |
|     |    |          | 1710B, and current \*\***Pressure Systems     |
|     |    |          | Inventory Recall** such that no component or  |
|     |    |          | system inspection date can be found to be out |
|     |    |          | of compliance. All **\*JSC** compressed air   |
|     |    |          | systems shall be free of leaks.               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The **\*JSC** compressed air systems may      |
| 1.0 |    | Co       | include but are not limited to, air           |
| 4.C |    | mponents | compressors of all types (both Central plant  |
|     |    |          | and facility), air receiver tanks, air dryers |
|     |    |          | of any type, filters, piping, cooling         |
|     |    |          | systems, pumps, instrumentation, including    |
|     |    |          | flow devices, probes, delta-Pressure          |
|     |    |          | switches, etc., controls, relief valves,      |
|     |    |          | check valves, associated gauges, pressure     |
|     |    |          | regulating stations, oilers, condensate       |
|     |    |          | traps; pressure protective devices; valves;   |
|     |    |          | fittings; and labels, cathodic protection     |
|     |    |          | systems, pressure regulating stations, filter |
|     |    |          | stations.                                     |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | **Steam  |                                               |
| .05 | ec | &        |                                               |
|     | h. | Cond     |                                               |
|     |    | ensate** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | [Production]{.underline} -- The building 24   |
| 1.0 |    | Des      | steam system shall provide steam through the  |
| 5.A |    | cription | utility tunnel and provide for condensate     |
|     |    |          | return to and from the site buildings. This   |
|     |    |          | steam is utilized for at the facilities for   |
|     |    |          | domestic hot water, space heating,            |
|     |    |          | humidification and process uses. Some         |
|     |    |          | **\*JSC** buildings have low-pressure steam   |
|     |    |          | boilers for heating and high-pressure steam   |
|     |    |          | boilers for test applications.                |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} - The utility  |
|     |    |          | tunnel steam supply/condensate return system  |
|     |    |          | is a piping system approximately three and    |
|     |    |          | one half miles in total length that connects  |
|     |    |          | the building 24 output to the JSC mall        |
|     |    |          | facilities. In the facility the steam is      |
|     |    |          | reduced in pressure as required and           |
|     |    |          | distributed to the point of use. The system   |
|     |    |          | includes that portion that collects and       |
|     |    |          | returns condensate produced from the steam    |
|     |    |          | system. The condensate is collected in        |
|     |    |          | condensate return units or through tunnel     |
|     |    |          | steam traps and returned to the plant from    |
|     |    |          | the mall facilities through the tunnel return |
|     |    |          | condensate piping system.                     |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | [Production]{.underline} -- The steam system  |
| 1.0 |    | Output   | shall continuously supply and satisfy the     |
| 5.B |    |          | site load with 400 psig superheated steam to  |
|     |    |          | the plant header system and shall reduce this |
|     |    |          | high-pressure steam to 100 psig plus or minus |
|     |    |          | 10 psig in the summer. The output pressure    |
|     |    |          | shall be adjusted as required in the heating  |
|     |    |          | season to maintain 100 psig at building 35 to |
|     |    |          | meet the building load requirements and may   |
|     |    |          | be adjusted as directed by NASA. The output   |
|     |    |          | steam shall be desuperheated to approximately |
|     |    |          | 300 °F at the plant pressure                  |
|     |    |          | reducing/desuperheating stations. The plant   |
|     |    |          | steam system shall have one additional boiler |
|     |    |          | available to be placed in service at all      |
|     |    |          | times as a warm standby boiler. The           |
|     |    |          | condensate return shall be deaerated at       |
|     |    |          | building 24 and shall be chemically treated   |
|     |    |          | with phosphate to be within 15-25 mg/liter    |
|     |    |          | and sulfite to be within 20-40 mg/liter prior |
|     |    |          | to use in any of the plant boilers. The       |
|     |    |          | supply steam to the site shall be treated     |
|     |    |          | with amines for a condensate water pH of 8-9  |
|     |    |          | to ensure condensate pipe integrity. The      |
|     |    |          | contractor shall ensure condensate return, to |
|     |    |          | be at least 85% of supply, from the site      |
|     |    |          | buildings by verifying condensate return      |
|     |    |          | units and all steam traps are operating       |
|     |    |          | properly. The contractor shall ensure that    |
|     |    |          | the return condensate to the plant is pure by |
|     |    |          | checking condensate return water quality for  |
|     |    |          | hardness with a laboratory color change test  |
|     |    |          | each shift. Potable water that shall be used  |
|     |    |          | as a makeup in the condensate system shall be |
|     |    |          | softened to less that 2 mg/liter, maximum     |
|     |    |          | hardness. Steam production systems in         |
|     |    |          | **\*JSC** buildings not served by the JSC     |
|     |    |          | central plant shall be capable of supplying   |
|     |    |          | continuous steam as required to satisfy the   |
|     |    |          | Fall and Summer Energy Guidelines.            |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} - The tunnel   |
|     |    |          | steam supply/condensate return system shall   |
|     |    |          | continuously supply steam from the plant      |
|     |    |          | production system to the facilities and       |
|     |    |          | return condensate from the facilities to the  |
|     |    |          | plant. All zones of the tunnel                |
|     |    |          | steam/condensate system shall be maintained   |
|     |    |          | in service at all times to ensure a           |
|     |    |          | continuous supply of steam and return of      |
|     |    |          | condensate from mall buildings. Only brief    |
|     |    |          | exceptions of this requirement will be        |
|     |    |          | permitted in an effort to locate potable      |
|     |    |          | water hardness leaks, repair failed           |
|     |    |          | condensate return units, or as required by a  |
|     |    |          | utility procedure. Distribution systems other |
|     |    |          | than the tunnel shall provide the quantity    |
|     |    |          | and quality of steam required for the end     |
|     |    |          | use. All steam/condensate valves shall be in  |
|     |    |          | an operable state with no actuators missing   |
|     |    |          | and all valves, traps, etc. shall be labeled  |
|     |    |          | with brass tags containing the valve station  |
|     |    |          | number and pressure systems inventory         |
|     |    |          | information. The steam system shall deliver   |
|     |    |          | adequate quantity and quality of steam to the |
|     |    |          | building from the tunnel to meet facility     |
|     |    |          | requirements.                                 |
|     |    |          |                                               |
|     |    |          | All **\*JSC** steam systems shall maintain    |
|     |    |          | current certification of all pressure systems |
|     |    |          | and components per JHB 1710B, and current     |
|     |    |          | \*\***Pressure Systems Inventory Recall**     |
|     |    |          | such that no component or system inspection   |
|     |    |          | date can be found to be out of compliance.    |
|     |    |          | All **\*JSC** steam systems shall be free of  |
|     |    |          | leaks.                                        |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Steam/condensate production distribution and  |
| 1.0 |    | Co       | return system and support components of the   |
| 5.C |    | mponents | steam system may include but are not limited  |
|     |    |          | to, storage tanks, deaerator vessels,         |
|     |    |          | condensate pumps, boiler feedwater pumps, hot |
|     |    |          | well pumps, plant boilers, pressure           |
|     |    |          | reducing/desuperating stations, chemical      |
|     |    |          | storage tanks, chemical feed pumps, water     |
|     |    |          | softener, water dealkalizer vessel, steam     |
|     |    |          | traps, condensate return units, natural gas   |
|     |    |          | scrubber, fuel oil supply pumps fuel oil      |
|     |    |          | storage tank, feedwater economizers, boiler   |
|     |    |          | oxygen trim controls, other boiler controls   |
|     |    |          | and instrumentation, plant master pressure    |
|     |    |          | controllers that control the boiler master    |
|     |    |          | loop, steam/condensate/chemical/, and fuel    |
|     |    |          | piping, gas meters for the boilers,           |
|     |    |          | condensate flow meters, make-up water meters, |
|     |    |          | piping, insulation including aluminum         |
|     |    |          | jacketing, supports, expansion joints,        |
|     |    |          | instrumentation, flow devices, probes,        |
|     |    |          | delta-Pressure switches, etc., pressure       |
|     |    |          | reducing/regulating stations, gauges, hot     |
|     |    |          | water converter vessels; boilers; steam coils |
|     |    |          | in outside air units; reboilers; relief       |
|     |    |          | valves and pressure protective devices;       |
|     |    |          | valves; fittings, pumps, condensate traps,    |
|     |    |          | valves; fittings, flash tanks, and labels.    |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | *        |                                               |
| .06 | ec | *Exhaust |                                               |
|     | h. | &        |                                               |
|     |    | Venti    |                                               |
|     |    | lation** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Those facility systems that: (1) exhaust      |
| 1.0 |    | Des      | heat, fumes, odors or other contaminants from |
| 6.A |    | cription | within the facility, (2) provide air flow to  |
|     |    |          | remove paint fumes from the painting booth    |
|     |    |          | facilities (3) exhaust smoke from a facility  |
|     |    |          | to provide personnel protection from          |
|     |    |          | combustion products, (4) supply fresh air     |
|     |    |          | make-up to meet indoor air quality            |
|     |    |          | requirements and (5) maintain required        |
|     |    |          | pressure in the facility.                     |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The systems shall supply/exhaust the required |
| 1.0 |    | Output   | quantity and balance of air as required by    |
| 6.B |    |          | current design parameters as well as comply   |
|     |    |          | with all applicable codes and standards.      |
|     |    |          | Paint booth ventilation systems air mass flow |
|     |    |          | shall be provided per OSHA requirements as    |
|     |    |          | sampled per OSHA 190.107, Spray Finishing     |
|     |    |          | using Flammable and Combustible Materials as  |
|     |    |          | amended. Smoke exhaust systems shall function |
|     |    |          | as designed whenever preset conditions are    |
|     |    |          | met. All required fans and dampers shall      |
|     |    |          | function and be in correct field position     |
|     |    |          | based on location of smoke/fire alarm. All    |
|     |    |          | components of a facility ventilation system   |
|     |    |          | shall function as designed and maintain       |
|     |    |          | indoor air quality in accordance with ASHRAE  |
|     |    |          | standards. All systems shall be properly      |
|     |    |          | labeled to include but not be limited to,     |
|     |    |          | power sources and hazard conditions.          |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Supply/Exhaust ventilation systems may        |
| 1.0 |    | Co       | include, but not be limited to, exhaust fans, |
| 6.C |    | mponents | ducts, dampers, stacks, fume hoods, flow      |
|     |    |          | benches, kitchen hoods, fire dampers, fire    |
|     |    |          | extinguishing equipment, shop hoods,          |
|     |    |          | perchloric acid hoods, wash down systems,     |
|     |    |          | paint booths, controls, instrumentation,      |
|     |    |          | inlet blowers and all associated components,  |
|     |    |          | filters and filter banks and associated       |
|     |    |          | parts, exhaust blowers and all associated     |
|     |    |          | components, associated controls,              |
|     |    |          | instrumentation and gauges, control air       |
|     |    |          | system and related components, heaters, smoke |
|     |    |          | exhaust fans, fresh air fans, insulation,     |
|     |    |          | water scrubbers, dust/sawdust collection      |
|     |    |          | systems, flow measurement devices and labels. |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | *        |                                               |
| .07 | ec | *Refrige |                                               |
|     | h. | ration** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Those systems and components that provide low |
| 1.0 |    | Des      | temperature environments for the preservation |
| 7.A |    | cription | of food, photographic products, medical       |
|     |    |          | specimens, and other items as required.       |
|     |    |          | Included in this are the ice machines,        |
|     |    |          | central water coolers, and refrigerated       |
|     |    |          | drinking fountains and water coolers, at      |
|     |    |          | **\*JSC**.                                    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The temperatures for these systems shall be   |
| 1.0 |    | Output   | controlled to set points defined by the       |
| 7.B |    |          | government. The system shall be free of       |
|     |    |          | leaks. Systems shall function continually to  |
|     |    |          | provide required condition. All **\*JSC**     |
|     |    |          | refrigeration systems shall be free of leaks. |
|     |    |          | All **\*JSC** drinking fountains shall be     |
|     |    |          | free of lead.                                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Refrigeration systems include but not limited |
| 1.0 |    | Co       | to, Walk-in/Reach-in Coolers,                 |
| 7.C |    | mponents | Walk-in/Reach-in Freezers, Refrigerators,     |
|     |    |          | Freezers, Film Vaults, Thermal Chambers, ice  |
|     |    |          | machines, central water coolers, and          |
|     |    |          | refrigerated drinking fountains and bottled   |
|     |    |          | water coolers, refrigerant piping and         |
|     |    |          | components, dryers, mufflers, compressors,    |
|     |    |          | condensers, control systems, fans, and        |
|     |    |          | filters.                                      |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## H     |                                               |
| .08 | ec | ot Water |                                               |
|     | h. |  Heating |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Those systems that produce, supply, and       |
| 1.0 |    | Des      | distribute hot water within the building for  |
| 8.A |    | cription | use in the HVAC systems. These include steam, |
|     |    |          | electric and gas fired boilers.               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The hot water system shall deliver hot water  |
| 1.0 |    | Output   | to the facility from the hot water converter  |
| 8.B |    |          | or hot water boiler and shall be provided at  |
|     |    |          | 80 -180 °F as required by the Spring/Summer   |
|     |    |          | and Fall /Winter Seasonal Adjustment Plans.   |
|     |    |          | The hot water shall be distributed throughout |
|     |    |          | the building as required to meet the above    |
|     |    |          | requirement and shall be free of leaks. It    |
|     |    |          | shall be controlled at each HVAC system       |
|     |    |          | adequately to meet the requirements for hot   |
|     |    |          | deck temperature as specified in the JSC      |
|     |    |          | Fall/Winter Seasonal Adjustment Plan and to   |
|     |    |          | meet building loads. All **\*JSC** hot water  |
|     |    |          | heating systems shall maintain current        |
|     |    |          | certification of all pressure systems and     |
|     |    |          | components per JHB 1710B, and current         |
|     |    |          | \*\***Pressure Systems Inventory Recall**     |
|     |    |          | such that no component or system inspection   |
|     |    |          | date can be found to be out of compliance.    |
|     |    |          | All **\*JSC** hot water heating systems shall |
|     |    |          | be free of leaks.                             |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The components of the hot water system may    |
| 1.0 |    | Co       | include, but not be limited to, boilers, hot  |
| 8.C |    | mponents | water converters, pumps, compression tanks,   |
|     |    |          | strainers, instrumentation including flow     |
|     |    |          | devices, probes, delta-Pressure switches,     |
|     |    |          | etc., gauges, controls, orifice plates and    |
|     |    |          | other flow elements, valves, control valves,  |
|     |    |          | relief valves, fittings, pipe, labels and     |
|     |    |          | insulation.                                   |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## Die   |                                               |
| .09 | ec | sel Fuel |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | That system which stores and supplies diesel  |
| 1.0 |    | Des      | fuel for use in engines and in steam boilers. |
| 9.A |    | cription | The diesel fuel storage at JSC consists of    |
|     |    |          | above ground tanks at building 24, 42, 48,    |
|     |    |          | 207, 300 area, and E245.                      |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Diesel fuel for building 48 shall be high     |
| 1.0 |    | Output   | sulfur, high BTU content per EPA definition   |
| 9.B |    |          | for use in diesel engines to prevent engine   |
|     |    |          | sags when load is added suddenly. Storage     |
|     |    |          | systems shall be fully labeled and contain    |
|     |    |          | appropriate quantities and quality of fuel.   |
|     |    |          | Diesel fuel shall be distributed with the     |
|     |    |          | proper quantity and pressure required by the  |
|     |    |          | point of use. Maintain tank levels as         |
|     |    |          | required and properly monitor the delivery of |
|     |    |          | fuel onsite. Fuel shall be properly tested    |
|     |    |          | before use. All **\*JSC** diesel fuel systems |
|     |    |          | shall be free of fuel leaks.                  |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The diesel fuel system includes but is not    |
| 1.0 |    | Co       | limited to, fuel storage tanks, pumps,        |
| 9.C |    | mponents | piping, fill pumps, recirculating pumps,      |
|     |    |          | supply pumps, valves, environmental controls, |
|     |    |          | containments, level measurement devices, flow |
|     |    |          | indicators, flow elements, pressure           |
|     |    |          | regulators, gauges, fittings, and pipe.       |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## Space |                                               |
| .10 | ec |  Heating |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | That system which provides space heat for     |
| 1.1 |    | Des      | personnel and equipment.                      |
| 0.A |    | cription |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Provide space heating for personnel and       |
| 1.1 |    | Output   | equipment per JMI 8835.1 for occupied space   |
| 0.B |    |          | temperatures. System shall be continuously    |
|     |    |          | available to operate as required per the      |
|     |    |          | Spring/Summer and Fall/Winter Seasonal        |
|     |    |          | Adjustment Plan and meet all codes ,          |
|     |    |          | regulations and standards. All **\*JSC**      |
|     |    |          | space heating systems shall maintain current  |
|     |    |          | certification of all pressure systems and     |
|     |    |          | components per JHB 1710B, and current         |
|     |    |          | \*\***Pressure Systems Inventory Recall**     |
|     |    |          | such that no component or system inspection   |
|     |    |          | date can be found to be out of compliance.    |
|     |    |          | All **\*JSC** space heater fluid systems      |
|     |    |          | shall be free of leaks.                       |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The space heaters system includes but is not  |
| 1.1 |    | Co       | limited to, hot water heaters, catalytic      |
| 0.C |    | mponents | heaters, gas fired heaters, steam heaters,    |
|     |    |          | electric heaters, piping, valves, controls,   |
|     |    |          | conduit, electrical system, thermostats,      |
|     |    |          | fans, motors, belts, insulation and aluminum  |
|     |    |          | jacket, vents, relief valves, and blowers.    |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## Proce |                                               |
| .11 | ec | ss Water |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Process water systems are those **\*JSC**     |
| 1.1 |    | Des      | systems that provide water at closely         |
| 1.A |    | cription | controlled conditions for consumption in      |
|     |    |          | designated processes. These systems may       |
|     |    |          | include, but are not limited to, deionized    |
|     |    |          | water system, process hot water, and process  |
|     |    |          | chilled water. The JSC deionized water system |
|     |    |          | is that system that produces and distributes  |
|     |    |          | deionized, generated water at the reverse     |
|     |    |          | osmosis system in building 9, and distributed |
|     |    |          | through a PVC piping system in the tunnel to  |
|     |    |          | and through several laboratory facilities at  |
|     |    |          | JSC. The deionized water system provides      |
|     |    |          | water that is 90 per cent pure of salts and   |
|     |    |          | the process hot and chilled water systems     |
|     |    |          | provide filtered water that is heated or      |
|     |    |          | cooled for specific purposes.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | These systems shall provide the selected      |
| 1.1 |    | Output   | operating parameters for pressure, quantity   |
| 1.B |    |          | and quality of water at designated locations  |
|     |    |          | and shall be free of leaks.                   |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Process water systems may contain, but not be |
| 1.1 |    | Co       | limited to, a reverse osmosis unit, polishing |
| 1.C |    | mponents | bottles, heat exchangers, boilers, pumps,     |
|     |    |          | piping, compression tanks, fittings, labels,  |
|     |    |          | valves, chillers, flow elements, strainers,   |
|     |    |          | filters, instrumentation, controls, gauges,   |
|     |    |          | labels, holding tanks, and insulation.        |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## C     |                                               |
| .12 | ec | afeteria |                                               |
|     | h. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | That kitchen or cafeteria equipment used in   |
| 1.1 |    | Des      | food preparation.                             |
| 2.A |    | cription |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | This equipment shall be maintained in proper  |
| 1.1 |    | Output   | working order and be capable of performing    |
| 2.B |    |          | the function for which it was intended.       |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | This equipment is defined as including, but   |
| 1.1 |    | Co       | not limited to, all or any combination of the |
| 2.C |    | mponents | following: (1) Steam tables, (2) Ovens, (3)   |
|     |    |          | Griddles and cook tops, (4) Ranges, (5) Ice   |
|     |    |          | Makers, (6) Steamers, (7) Kettles, (8)        |
|     |    |          | Dishwashers, (9) Conveyors, (10) Toasters,    |
|     |    |          | and other built-in equipment normally         |
|     |    |          | associated with food preparation.             |
+-----+----+----------+-----------------------------------------------+
| 1.1 | M  | ## Hy    |                                               |
| .13 | ec | perbaric |                                               |
|     | h. |  Chamber |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The hyperbaric chamber system is utilized for |
| 1.1 |    | Des      | human testing at elevated pressures, as well  |
| 3.A |    | cription | as for emergency repressurization of divers   |
|     |    |          | and/or suited test subjects from the NBL,     |
|     |    |          | should the need arise. Subsequently, its      |
|     |    |          | proper operation and functional reliability   |
|     |    |          | are of paramount importance as a life safety  |
|     |    |          | issue.                                        |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Each individual component within this system  |
| 1.1 |    | Output   | shall provide its designed function and       |
| 3.B |    |          | manufacturer's specified output. Availability |
|     |    |          | of system output shall be 100% during those   |
|     |    |          | periods defined by the user as critical to    |
|     |    |          | its operational requirements. Any component   |
|     |    |          | outage shall be coordinated with the user,    |
|     |    |          | and shall be of brief enough duration as to   |
|     |    |          | not impact scheduled testing.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The equipment items comprising this           |
| 1.1 |    | Co       | particular system shall consist of, but shall |
| 3.C |    | mponents | not be limited to, the physical hyperbaric    |
|     |    |          | chamber and it attachments, breathing air     |
|     |    |          | compressor, reserve breathing air storage,    |
|     |    |          | the communication system/intercom, as well as |
|     |    |          | the chamber's ancillary valves and piping.    |
+-----+----+----------+-----------------------------------------------+

**1.2 Electrical**

+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Site  |                                                |
| .01 | le |   | Ele     |                                                |
|     | ct |   | ctrical |                                                |
|     |    |   | 138 kV  |                                                |
|     |    |   | Transmi |                                                |
|     |    |   | ssion** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Two Houston Lighting & Power Company 138 kV    |
| 2.0 |    |   | Desc    | transmission lines serve a closed ring bus     |
| 1.A |    |   | ription | feeding the four site power step/down          |
|     |    |   |         | transformers. The tubular aluminum ring bus    |
|     |    |   |         | has six 2000 ampere SF6 gas circuit breakers.  |
|     |    |   |         | Each Circuit breaker and transformer can be    |
|     |    |   |         | isolated by an array of sixteen air break      |
|     |    |   |         | switches. There are three 138 kv/15 kV step    |
|     |    |   |         | down transformers (with auto load tap          |
|     |    |   |         | changers), which provide the primary power to  |
|     |    |   |         | the site. There is one 138 kv/15kv step-down   |
|     |    |   |         | transformer with auto load tap changer, which  |
|     |    |   |         | services large test loads. The control panel   |
|     |    |   |         | and protective relay panel are located in an   |
|     |    |   |         | adjacent building. The system starts at the    |
|     |    |   |         | HL&P transmission line connections to the      |
|     |    |   |         | wavetraps and ends at the substation           |
|     |    |   |         | transformers secondary bushings. It            |
|     |    |   |         | encompasses all control, measurement and       |
|     |    |   |         | protection circuits associated with the        |
|     |    |   |         | system. Enclosed in a fenced in area including |
|     |    |   |         | five space condition buildings with three      |
|     |    |   |         | gates. Control and monitoring cables between   |
|     |    |   |         | buildings are direct buried and in duct walk   |
|     |    |   |         | cable trays.                                   |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | The site electrical 138 kV transmission system |
| 2.0 |    |   | Output  | is an integral part of the HL&P 138 kV         |
| 1.B |    |   |         | transmission system. This NASA owned and       |
|     |    |   |         | operated substation provides a means of tying  |
|     |    |   |         | the site step down transformers to the HL&P    |
|     |    |   |         | grid. The ring bus is configured to provide a  |
|     |    |   |         | method of isolating sections with either       |
|     |    |   |         | manual switching or through coordinated        |
|     |    |   |         | protective relaying circuits. The outputs of   |
|     |    |   |         | the system are four separate 12.47kV, 3 phase, |
|     |    |   |         | 60 Hz, sources to the inputs of the site       |
|     |    |   |         | electrical 15 kV distribution system. Each     |
|     |    |   |         | output is limited to the nameplate data of the |
|     |    |   |         | associated step-down transformer. The output   |
|     |    |   |         | of the four primary transformers is regulated. |
|     |    |   |         | Substation yard provides step potential        |
|     |    |   |         | protection.                                    |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Components including ring bus, circuit         |
| 2.0 |    |   | Com     | breakers, air break switches, transformers,    |
| 1.C |    |   | ponents | transformer grounding resistors, auto load tap |
|     |    |   |         | changers, protective relaying circuits,        |
|     |    |   |         | control wiring, switches, control panels,      |
|     |    |   |         | metering and instrumentation that is remotely  |
|     |    |   |         | recorded by the EMCS or manually recorded to   |
|     |    |   |         | provide energy management or ECM data,         |
|     |    |   |         | connecting and structural bus supports Pt's,   |
|     |    |   |         | CT's, CT & PT supports, batteries, battery     |
|     |    |   |         | chargers, UPS's, manual transfer switches,     |
|     |    |   |         | automatic transfer switches, grounding mat,    |
|     |    |   |         | lightning masts, fence and gates. Substation   |
|     |    |   |         | yard comprised of washed river rock, concrete  |
|     |    |   |         | duct walk cable trays with French drains.      |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Site  |                                                |
| .02 | le |   | Ele     |                                                |
|     | ct |   | ctrical |                                                |
|     |    |   | 15 kV   |                                                |
|     |    |   | Distrib |                                                |
|     |    |   | ution** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | [15KV Distribution]{.underline}: The five 138  |
| 2.0 |    |   | Desc    | kv/15kv transformers provide input to the 15   |
| 2.A |    |   | ription | kV distribution system. Each transformer feeds |
|     |    |   |         | a 15 kV switchgear line up. The five line-ups  |
|     |    |   |         | are 500 MVA indoor metalclad switchgear        |
|     |    |   |         | located in individual climate controlled       |
|     |    |   |         | buildings. The five switchgear assemblies      |
|     |    |   |         | contain four main breakers, four tie breakers, |
|     |    |   |         | and forty one feeder breakers. The tie         |
|     |    |   |         | breakers allow for the isolation of the four   |
|     |    |   |         | primary power transformers. The switchgear     |
|     |    |   |         | assemblies have automatic rollover between the |
|     |    |   |         | station AC service. Additionally the DC        |
|     |    |   |         | services are configured so that they have      |
|     |    |   |         | multiple feeds. Two of the switchgear          |
|     |    |   |         | assemblies and the tie breakers are provided   |
|     |    |   |         | with remote control panel switching and        |
|     |    |   |         | status. All are provided with SCADA control    |
|     |    |   |         | and monitoring. There are four 4,800 kvar      |
|     |    |   |         | capacitor banks for power factor correction,   |
|     |    |   |         | one attached to each of the primary power      |
|     |    |   |         | switchgear line up. The feeders are divided    |
|     |    |   |         | between overhead on wooden poles, cable in     |
|     |    |   |         | duct banks and armored cable in the utility    |
|     |    |   |         | tunnel. Some of the feeders have distribution  |
|     |    |   |         | switches that provide alternate feeder         |
|     |    |   |         | selection for downstream distribution. The     |
|     |    |   |         | distribution system starts at the 138kV/15kV   |
|     |    |   |         | step down transformer and extends to the input |
|     |    |   |         | of the 15 kV facility switches.                |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Switching Facilities]{.underline}: Air,  |
|     |    |   |         | gas or oil 15 kV switch assemblies. System     |
|     |    |   |         | begins at the input of the 15kV facility       |
|     |    |   |         | switch and extends to the input of the medium  |
|     |    |   |         | voltage transformer.                           |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Medium Voltage                           |
|     |    |   |         | Transformers]{.underline}: 15 kV transformers  |
|     |    |   |         | begin with the primary bushings of the         |
|     |    |   |         | transformer and extend to the secondary        |
|     |    |   |         | bushings.                                      |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | [15kv Distribution]{.underline}: Provides      |
| 2.0 |    |   | Output  | 12.47kV, 3 phase, 60 Hz voltage to the         |
| 2.B |    |   |         | facility 15kV switches. Most of the facilities |
|     |    |   |         | are served by two feeders and have provisions  |
|     |    |   |         | for isolating faulted components. System       |
|     |    |   |         | switching is accomplished through phased       |
|     |    |   |         | closed transition of loads between feeders.    |
|     |    |   |         | The output of the system is 12.47kV 3 phase,   |
|     |    |   |         | 60 Hz.                                         |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Switching Facilities]{.underline}:       |
|     |    |   |         | Provide open and closed transition 15kV        |
|     |    |   |         | switching for single -phase and 3-phase        |
|     |    |   |         | sectionalizing; isolation of equipment such as |
|     |    |   |         | buses or other live apparatus; and load        |
|     |    |   |         | management.                                    |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Medium Voltage                           |
|     |    |   |         | Transformers]{.underline}: Provide step down   |
|     |    |   |         | from site electrical 15 kV distribution to the |
|     |    |   |         | secondary distribution level voltages          |
|     |    |   |         | \[Voltage phase to phase ranging from 6900,    |
|     |    |   |         | 690, 480, 208\].                               |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | [15kv Distribution]{.underline}: Components    |
| 2.0 |    |   | Com     | include switchgear, circuit breakers, bus,     |
| 2.C |    |   | ponents | meters, control wiring, batteries, battery     |
|     |    |   |         | chargers, transfer switches, control panels,   |
|     |    |   |         | capacitors/switches, cable, cable splices,     |
|     |    |   |         | demountable cable terminations, duct banks,    |
|     |    |   |         | cabletrays, manholes, sump pumps, poles, cross |
|     |    |   |         | arms, insulators fuses, distribution switches, |
|     |    |   |         | service/control power/instrument transformers, |
|     |    |   |         | grounding system relays, SCADA, transducers,   |
|     |    |   |         | fences, reactors, fused disconnects, lightning |
|     |    |   |         | arrestors, static cables, ground rods, power   |
|     |    |   |         | monitors, splice shields, strip heaters        |
|     |    |   |         | automatic transfer switches and manual         |
|     |    |   |         | transfer switches. Metering and                |
|     |    |   |         | instrumentation that is remotely recorded by   |
|     |    |   |         | the EMCS or manually recorded to provide       |
|     |    |   |         | energy management or ECM data.                 |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Switching Facilities]{.underline}: Air,  |
|     |    |   |         | gas or oil 15 kV switches. Fuse enclosures,    |
|     |    |   |         | fuses, fuse holders, heater strips, secondary  |
|     |    |   |         | breakers, thermostat controls, and control     |
|     |    |   |         | circuits. Fault indicators with associated     |
|     |    |   |         | equipment.                                     |
|     |    |   |         |                                                |
|     |    |   |         | [15kv Medium Voltage                           |
|     |    |   |         | Transformers]{.underline}: 15 kV               |
|     |    |   |         | transformers - dry type, mineral oil filled,   |
|     |    |   |         | silicon oil filled and other less flammable    |
|     |    |   |         | fluid filled. Associated hardware - gauges,    |
|     |    |   |         | fans, fan motors, heater strips, meters,       |
|     |    |   |         | current transformers, potential transformers,  |
|     |    |   |         | nitrogen tanks and regulators, secondary       |
|     |    |   |         | breakers, control circuits, thermostat         |
|     |    |   |         | controls, drain/fill valves, relief valves and |
|     |    |   |         | ground resistors.                              |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | ##      |                                                |
| .03 | le |   | B48 D&B |                                                |
|     | ct |   | X Power |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Electric power generation/distribution system  |
| 2.0 |    |   | Desc    | that provides normal and standby power for B48 |
| 3.A |    |   | ription | ancillary electrical loads and provides        |
|     |    |   |         | standby power for B30S. The system starts at   |
|     |    |   |         | the D2 metal clad switchgear and extends to    |
|     |    |   |         | the B48 loads and the line side of the         |
|     |    |   |         | generator breakers in B30S switchgear. It also |
|     |    |   |         | includes the engine/generators and associated  |
|     |    |   |         | controls, all protective systems, and          |
|     |    |   |         | measurement systems.                           |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | 6.9 kv/60 hz/3 pH, two bus, nominal 2800 kW    |
| 2.0 |    |   | Output  | per bus, sourced from either utility           |
| 3.B |    |   |         | transformers or diesel driven generators with  |
|     |    |   |         | uninterrupted transfer between transformers    |
|     |    |   |         | and generators. Output limited to source       |
|     |    |   |         | nameplate data.                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Power circuits including medium and low        |
| 2.0 |    |   | Com     | voltage current carrying and switching         |
| 3.C |    |   | ponents | components, by which electrical power is       |
|     |    |   |         | generated, delivered and used. Includes        |
|     |    |   |         | generators, transformers, disconnect switches, |
|     |    |   |         | circuit breakers, power fuses, cables, bus     |
|     |    |   |         | ducts, switchgear, MCC's, and loadbanks.       |
|     |    |   |         |                                                |
|     |    |   |         | Metering circuits including instrument         |
|     |    |   |         | transformers, ammeters, voltmeters, frequency  |
|     |    |   |         | meters, wattmeters, varmeters, elapsed time    |
|     |    |   |         | meters, which measure or compute operating     |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Protective relaying circuits including         |
|     |    |   |         | instrument transformers, and protective        |
|     |    |   |         | devices that operate for abnormal operating    |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Control circuits including DC power supplies,  |
|     |    |   |         | control power transformers, instrument         |
|     |    |   |         | transformers, fuses, switches, relays,         |
|     |    |   |         | governors, regulators, rheostats,              |
|     |    |   |         | potentiometers, transducers, synchronizers,    |
|     |    |   |         | control panels, batteries, chargers panels and |
|     |    |   |         | SCADA.                                         |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | ## B48  |                                                |
| .04 | le |   | B Power |                                                |
|     | ct |   |         |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Electric power generation/distribution system  |
| 2.0 |    |   | Desc    | that provides normal and standby source for B  |
| 4.A |    |   | ription | 48 A Power, B30M Tech loads, and B30M select   |
|     |    |   |         | facility loads. The system starts at the metal |
|     |    |   |         | enclosed switchgear and extends to the loads   |
|     |    |   |         | for B30M it finds at the line side of the      |
|     |    |   |         | secondary distribution device in the facility. |
|     |    |   |         | The system also includes engine/generators and |
|     |    |   |         | associated controls, protective systems and    |
|     |    |   |         | measurement systems.                           |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | 480v/60 hz/3 pH, one triple generator bus, two |
| 2.0 |    |   | Output  | nominal 1300 kW source busses, two load        |
| 4.B |    |   |         | busses. Source bus fed from either utility     |
|     |    |   |         | transformers or diesel driven generators with  |
|     |    |   |         | uninterrupted transfer between transformers    |
|     |    |   |         | and generators. Output limited to source       |
|     |    |   |         | nameplate data.                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Power circuits include all low voltage current |
| 2.0 |    |   | Com     | carrying and switching components by which     |
| 4.C |    |   | ponents | electrical power is generated, delivered, and  |
|     |    |   |         | used. Includes generators, disconnect          |
|     |    |   |         | switches, circuit breakers, power fuses,       |
|     |    |   |         | contactors, cable, bus ducts, switchgear,      |
|     |    |   |         | MCC's, heaters and loadbanks.                  |
|     |    |   |         |                                                |
|     |    |   |         | Metering circuits include instrumentation      |
|     |    |   |         | transformers, ammeters, voltmeters, frequency  |
|     |    |   |         | meters, wattmeters, varmeters, elapsed time    |
|     |    |   |         | meters, which measure or compute operating     |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Protective Relaying circuits include           |
|     |    |   |         | instrument transformers, and protective        |
|     |    |   |         | devices which operate for abnormal operating   |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Control circuits include DC power supplies,    |
|     |    |   |         | control power transformers, instrument         |
|     |    |   |         | transformers, fuses, switches, relays,         |
|     |    |   |         | governors, regulators, rheostats,              |
|     |    |   |         | potentiometers, transducers, synchronizers,    |
|     |    |   |         | control panels, batteries, chargers, and       |
|     |    |   |         | SCADA.                                         |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | ##      |                                                |
| .05 | le |   | B48 A&A |                                                |
|     | ct |   | X Power |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | System that provides continuous power for the  |
| 2.0 |    |   | Desc    | B30M critical loads. The system starts at the  |
| 5.A |    |   | ription | input to the "A" power UPS's and extends to    |
|     |    |   |         | the secondary distribution devices.            |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | 480/60 hz/3 pH, two bus, nominal 500 kW per    |
| 2.0 |    |   | Output  | bus, output from either UPS or directly from B |
| 5.B |    |   |         | power if UPS fails                             |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Power circuits including low voltage current   |
| 2.0 |    |   | Com     | carrying and switching components by which     |
| 5.C |    |   | ponents | electrical power is generated , delivered and  |
|     |    |   |         | used. Includes ,dual redundant UPS's ,         |
|     |    |   |         | batteries, disconnect switches, bypass         |
|     |    |   |         | switches, circuit breakers, power fuses,       |
|     |    |   |         | cables , bus ducts, switchgear,                |
|     |    |   |         |                                                |
|     |    |   |         | Metering circuits including instrument         |
|     |    |   |         | transformers, ammeters, voltmeters, frequency  |
|     |    |   |         | meters, wattmeters, varmeters, lapsed time     |
|     |    |   |         | meters, which measure or compute operating     |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Protective relaying circuits including         |
|     |    |   |         | instrument transformers, and protective        |
|     |    |   |         | devices, which operate for abnormal operating  |
|     |    |   |         | parameters.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Control circuits including DC power supplies,  |
|     |    |   |         | control power transformers, instrument         |
|     |    |   |         | transformers, fuses, switches, relays,         |
|     |    |   |         | transducers, control panels, batteries,        |
|     |    |   |         | chargers panels and SCADA.                     |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **E     |                                                |
| .06 | le |   | xterior |                                                |
|     | ct |   | Lig     |                                                |
|     |    |   | hting** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which comprises the exterior       |
| 2.0 |    |   | Desc    | lighting for roadways, parking area's, flood   |
| 6.A |    |   | ription | lighting in parking and ramp areas. (See       |
|     |    |   |         | General Site Plan Exterior Lighting Drawings   |
|     |    |   |         | and Master Utility Plans in TRL.) System       |
|     |    |   |         | starts at secondary circuit breaker serving    |
|     |    |   |         | street lighting circuit up to and including    |
|     |    |   |         | lighting standards.                            |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide perimeter lighting to reduce risk of   |
| 2.0 |    |   | Output  | injury, theft, or property damage and          |
| 6.B |    |   |         | safeguard and facilitate vehicular and         |
|     |    |   |         | pedestrian traffic. The minimum in-service     |
|     |    |   |         | luminance values shall be as listed in         |
|     |    |   |         | ANSI/IESRP-8 for Roadway Lighting, Tables 2,   |
|     |    |   |         | 3, and 4.                                      |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | This system is defined to include, but is not  |
| 2.0 |    |   | Com     | limited to: lamps, reflectors, ballasts, lens, |
| 6.C |    |   | ponents | light poles, conductors, conduit, associated   |
|     |    |   |         | hardware (hardware associated with lamps,      |
|     |    |   |         | reflectors, ballasts, lens, light poles,       |
|     |    |   |         | conductors, and conduit for exterior           |
|     |    |   |         | lighting), and low voltage power circuits and  |
|     |    |   |         | switching components, control circuits and     |
|     |    |   |         | control devices (photo-cells, time-clocks,     |
|     |    |   |         | hand-off-automatic switches.).                 |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Site  |                                                |
| .07 | le |   | Traffic |                                                |
|     | ct |   | Co      |                                                |
|     |    |   | ntrol** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which comprises the site traffic   |
| 2.0 |    |   | Desc    | control and Site pedestrian crosswalk warning  |
| 7.A |    |   | ription | devices as detailed.                           |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Monitors traffic flow control based on the     |
| 2.0 |    |   | Output  | parameters programmed in the traffic           |
| 7.B |    |   |         | controller hardware. Notifies vehicular        |
|     |    |   |         | traffic of possible pedestrians in crosswalks. |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | This system is defined to include, but is not  |
| 2.0 |    |   | Com     | limited to: lamps, reflectors, lens,           |
| 7.C |    |   | ponents | batteries, signs, conduit, conductors, and     |
|     |    |   |         | associated fittings and hardware to traffic    |
|     |    |   |         | signal heads, controllers, sensor loop         |
|     |    |   |         | detectors, and pedestrian crosswalk warning    |
|     |    |   |         | devices.                                       |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  | * |         |                                                |
| .08 | le | * |         |                                                |
|     | ct | E |         |                                                |
|     |    | n |         |                                                |
|     |    | e |         |                                                |
|     |    | r |         |                                                |
|     |    | g |         |                                                |
|     |    | y |         |                                                |
|     |    | M |         |                                                |
|     |    | a |         |                                                |
|     |    | n |         |                                                |
|     |    | a |         |                                                |
|     |    | g |         |                                                |
|     |    | e |         |                                                |
|     |    | m |         |                                                |
|     |    | e |         |                                                |
|     |    | n |         |                                                |
|     |    | t |         |                                                |
|     |    | a |         |                                                |
|     |    | n |         |                                                |
|     |    | d |         |                                                |
|     |    | C |         |                                                |
|     |    | o |         |                                                |
|     |    | n |         |                                                |
|     |    | t |         |                                                |
|     |    | r |         |                                                |
|     |    | o |         |                                                |
|     |    | l |         |                                                |
|     |    | * |         |                                                |
|     |    | * |         |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    | A |         | The Energy Management Control System (EMCS)    |
| 2.0 |    | . |         | monitors and controls the electrical power ,   |
| 8.A |    | D |         | steam, chilled water, utility air, and         |
|     |    | e |         | building HVAC systems at JSC. The EMCS is, in  |
|     |    | s |         | addition, an energy management and control     |
|     |    | c |         | system designed to monitor and control various |
|     |    | r |         | parameters of utility systems and equipment in |
|     |    | i |         | buildings and facilities. By monitoring the    |
|     |    | p |         | equipment controlled by EMCS field devices,    |
|     |    | t |         | the EMCS acts as an effective management tool  |
|     |    | i |         | for monitoring and controlling energy          |
|     |    | o |         | consumption, utility operations, operational   |
|     |    | n |         | and maintenance activities. The EMCS           |
|     |    |   |         | integrates the databases and operation of      |
|     |    |   |         | numerous control systems into EBI. The EMCS is |
|     |    |   |         | also required to monitor and control in        |
|     |    |   |         | building 24 the offsite SCTF facilities        |
|     |    |   |         | utilities and HVAC via a separate PC interface |
|     |    |   |         | called System 20/20 marketed by Automatic      |
|     |    |   |         | Logic Corporation and currently supported by   |
|     |    |   |         | UES Corporation a sub to existing site COSS    |
|     |    |   |         | contractor.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Honeywell's Enterprise Buildings Integrator,   |
|     |    |   |         | EBi is the site Energy Management Control      |
|     |    |   |         | System (EMCS) that monitors and controls all   |
|     |    |   |         | equipment at NASA, Johnson Space Center. This  |
|     |    |   |         | system runs on a Windows NT Platform using     |
|     |    |   |         | Dell Power edge 2300 Domain Servers. These     |
|     |    |   |         | servers communicate with Honeywell XL5000      |
|     |    |   |         | Series Controllers and other third party       |
|     |    |   |         | Programmable Logic Controllers (PLC's) and     |
|     |    |   |         | devices.                                       |
|     |    |   |         |                                                |
|     |    |   |         | The following is a list of systems connected   |
|     |    |   |         | to EBI:                                        |
|     |    |   |         |                                                |
|     |    |   |         | 1\. The Honeywell Building Control System is a |
|     |    |   |         | microprocessor based unit (Excel 5000          |
|     |    |   |         | controllers) that provides the interface to    |
|     |    |   |         | monitor and control Building HVAC and site     |
|     |    |   |         | utilities and provides data to the Man-Machine |
|     |    |   |         | Host Honeywell System known as Enterprise      |
|     |    |   |         | Buildings Integrator (EBI) for energy          |
|     |    |   |         | management, maintenance and operations         |
|     |    |   |         | support. The controllers are daisy chained     |
|     |    |   |         | from building to building using Honeywell      |
|     |    |   |         | C-Bus and integrated to EBI with Domain        |
|     |    |   |         | Controller Workstation. The Excel controllers  |
|     |    |   |         | uses DDC programmable software to maintain and |
|     |    |   |         | regulate buildings /utilities environment by   |
|     |    |   |         | using algorithms to determine what the         |
|     |    |   |         | conditions are and what points must do to      |
|     |    |   |         | achieve the desired conditions. Computer aided |
|     |    |   |         | Regulation Engineering (CARE) software is used |
|     |    |   |         | to program the controller for points,          |
|     |    |   |         | databases, processes, algorithms etc.          |
|     |    |   |         |                                                |
|     |    |   |         | 2\. The Metasys Building Control System is an  |
|     |    |   |         | building energy management and control system. |
|     |    |   |         | The Metasys is a distributed system            |
|     |    |   |         | accomplishing Standalone control, Supervisory  |
|     |    |   |         | Control and Information Management. These      |
|     |    |   |         | systems hardware architecture links integrated |
|     |    |   |         | electronic modules and controllers over three  |
|     |    |   |         | types of networks and provides access to users |
|     |    |   |         | through a variety of interface devices. The    |
|     |    |   |         | Metasys systems currently provides the         |
|     |    |   |         | interface to monitor control, and supervise    |
|     |    |   |         | HVAC and building functions and provides data  |
|     |    |   |         | to the host computers (EBI). The Metasys       |
|     |    |   |         | system uses propriety software to maintain     |
|     |    |   |         | processes.                                     |
|     |    |   |         |                                                |
|     |    |   |         | 3\. Programmable Logic Controllers (PLC's)     |
|     |    |   |         | systems are microprocessor based units that    |
|     |    |   |         | provide the interface to monitor and control   |
|     |    |   |         | standalone HVAC units and dedicated site       |
|     |    |   |         | utilities in the facilities and provides data  |
|     |    |   |         | to the Host EMCS computers (EBI). These third  |
|     |    |   |         | party PLC controllers PLC's are implemented on |
|     |    |   |         | a variety of platforms, which include          |
|     |    |   |         | Allen-Bradley PLC, Modicon PLC, Woodward PLC.  |
|     |    |   |         |                                                |
|     |    |   |         | 4\. Automated 20/20 Building Control System -  |
|     |    |   |         | The automatic logic system - 20/20, is a       |
|     |    |   |         | building energy management and control system. |
|     |    |   |         | The system provides for distributed            |
|     |    |   |         | architecture accomplishing stand-alone         |
|     |    |   |         | control, supervisory control, and information  |
|     |    |   |         | management. The 20/20 system provides the      |
|     |    |   |         | capability to monitor, control, and maintain   |
|     |    |   |         | buildings total HVAC, plant and lighting       |
|     |    |   |         | environment at the Sonny Carter Training       |
|     |    |   |         | Facility. The system begins at the 20/20       |
|     |    |   |         | system located in Building 24 and extends to   |
|     |    |   |         | all controllers and instrumentation located in |
|     |    |   |         | Sonny Carter.                                  |
|     |    |   |         |                                                |
|     |    |   |         | 5\. Miscellaneous Power Monitoring Systems --  |
|     |    |   |         | These include Mint IMPACC Westinghouse System, |
|     |    |   |         | Power Demand and Acquisition System (PDDAC),   |
|     |    |   |         | and Exide Uninterruptible System (UPS). The    |
|     |    |   |         | IMPACC and PDDAC Systems are used to read      |
|     |    |   |         | electrical subsystem data.                     |
|     |    |   |         |                                                |
|     |    |   |         | 6\. CTS Interface System- Monitors Central     |
|     |    |   |         | Telephone HVAC and power for Ellington and     |
|     |    |   |         | Building 420.                                  |
|     |    |   |         |                                                |
|     |    |   |         | Honeywell System begins at XPC cards in Dell   |
|     |    |   |         | Domain Workstation to Excel 5000 controllers   |
|     |    |   |         | and extends to field Subsystems/ devices and   |
|     |    |   |         | extends to all field instrumentation or        |
|     |    |   |         | devices.                                       |
|     |    |   |         |                                                |
|     |    |   |         | The 20/20 System begins at the 20/20 system    |
|     |    |   |         | located in Building 24 and extends to all      |
|     |    |   |         | controllers and instrumentation located in     |
|     |    |   |         | Sonny Carter.                                  |
|     |    |   |         |                                                |
|     |    |   |         | For all other systems or devices system begins |
|     |    |   |         | at the Rs232 Terminal Servers to field         |
|     |    |   |         | Subsystems/ devices and extends to all field   |
|     |    |   |         | sensor/control instrumentation or devices.     |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    | B |         | The EMCS shall function as an overall          |
| 2.0 |    | . |         | network/system coordinator, perform energy     |
| 8.B |    | O |         | management functions, control and monitor      |
|     |    | u |         | devices, perform calculations/functions        |
|     |    | t |         | associated with operator interactions, operate |
|     |    | p |         | within the limits specified for EMCS points,   |
|     |    | u |         | alarm reporting and logging of events,         |
|     |    | t |         | continuous reliable and accurate operational   |
|     |    |   |         | state shall be maintained to survey all data,  |
|     |    |   |         | devices, and subsystems monitored and          |
|     |    |   |         | controlled via EMCS operator workstations.     |
|     |    |   |         |                                                |
|     |    |   |         | ALL Building Controllers, PLC's, Subsystems    |
|     |    |   |         | and Devices listed in 1.2.8 A shall            |
|     |    |   |         | continuously perform their intended functions  |
|     |    |   |         | of monitoring and controlling facilities and   |
|     |    |   |         | provide reliable operation and data within the |
|     |    |   |         | accuracy of the Controllers and subsystems,    |
|     |    |   |         | data field equipment and associated            |
|     |    |   |         | instrumentation and controls. These systems    |
|     |    |   |         | shall perform to ensure all software/hardware  |
|     |    |   |         | design functionality is maintained within      |
|     |    |   |         | designed performance                           |
|     |    |   |         | specifications/requirements but not limited    |
|     |    |   |         | to: scanning field data acquisition and        |
|     |    |   |         | control points periodically, perform           |
|     |    |   |         | algorithms to achieve desired conditions;      |
|     |    |   |         | convert the data and tests it for an out-of    |
|     |    |   |         | -limits condition (analog sensors) or improper |
|     |    |   |         | state (discrete sensors), report any out-of    |
|     |    |   |         | limits conditions to the EMCS EBI Control      |
|     |    |   |         | System, process messages transmitted by the    |
|     |    |   |         | host systems, perform commanded data           |
|     |    |   |         | acquisition and control functions to field     |
|     |    |   |         | devices, monitor the communications lines      |
|     |    |   |         | failures and perform power failover sequences. |
|     |    |   |         | For instrumentation and associated sensor,     |
|     |    |   |         | each output is limited to nameplate data.      |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | The EMCS system is comprised of all equipment  |
| 2.0 |    |   | Com     | connected to the EBI or Automated 20/20        |
| 8.C |    |   | ponents | Systems. For all Building Controllers, PLC's , |
|     |    |   |         | Subsystems or Devices listed in 1.2.8A, the    |
|     |    |   |         | components are defined to include but not      |
|     |    |   |         | limited to chassis, LED Status lights, power   |
|     |    |   |         | supplies , terminal blocks, microprocessor,    |
|     |    |   |         | memory, disk drives, analog /digital interface |
|     |    |   |         | boards, communication boards, sx XPC           |
|     |    |   |         | communication cards installed in three Dell    |
|     |    |   |         | Domain Workstations, repeaters, terminal       |
|     |    |   |         | servers/modems, batteries, connectors , wiring |
|     |    |   |         | , software/firmware residing on field systems  |
|     |    |   |         | to perform control and monitoring of field     |
|     |    |   |         | points and configurations, operator interface  |
|     |    |   |         | devices and software for maintenance           |
|     |    |   |         | management, RS 232 interfaces, Honeywell       |
|     |    |   |         | C-BUS, application specific controllers (AHU,  |
|     |    |   |         | VAV,UNT), Metasys LAN's (N1,N2,L2) , Network   |
|     |    |   |         | control units, Metasys network terminal, and   |
|     |    |   |         | Metasys Maintenance Stations and software. The |
|     |    |   |         | controls and instrumentation components are,   |
|     |    |   |         | but not limited to, the following: electrical, |
|     |    |   |         | electronic, electro-pneumatic, and mechanical  |
|     |    |   |         | equipment: thermocouples, RTD's, pressure,     |
|     |    |   |         | flow and temperature (transmitters/switches/   |
|     |    |   |         | indicators/controllers), position indicators,  |
|     |    |   |         | RCPA's, level controllers, transducers, signal |
|     |    |   |         | conditioners, watts and phase angle            |
|     |    |   |         | transmitters, voltage transmitters, control    |
|     |    |   |         | and acquisition relays, flow meters, pH meters |
|     |    |   |         | and analyzers, conductivity meters,            |
|     |    |   |         | thermostats and humidistats, alarm systems,    |
|     |    |   |         | control valves, freeze stats and controls,     |
|     |    |   |         | humidifiers , mixing boxes, control wiring,    |
|     |    |   |         | terminal strips, transformers, transducers,    |
|     |    |   |         | pneumatic solenoids, modems, data transmission |
|     |    |   |         | lines , power supplies, field status panels,   |
|     |    |   |         | water detection sensor s, and associated       |
|     |    |   |         | equipment.                                     |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Se    |                                                |
| .09 | le |   | condary |                                                |
|     | ct |   | Distr   |                                                |
|     |    |   | ibution |                                                |
|     |    |   | Equi    |                                                |
|     |    |   | pment** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Secondary Distribution System: That system     |
| 2.0 |    |   | Desc    | which comprises the secondary distribution     |
| 9.A |    |   | ription | equipment, other than service entrance         |
|     |    |   |         | equipment, defined to include motor control    |
|     |    |   |         | centers, load centers, meter panels or         |
|     |    |   |         | centers, and molded-case circuit breaker       |
|     |    |   |         | distribution panels (PP, MDP, DP, LP and RP    |
|     |    |   |         | classified panels). System extends from the    |
|     |    |   |         | line side of the secondary distribution        |
|     |    |   |         | equipment to the end load. Step transformers   |
|     |    |   |         | within facilities, manholes and electrical     |
|     |    |   |         | enclosures.                                    |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Bussing Systems: That system which   |
|     |    |   |         | provides all medium and low voltage bussing    |
|     |    |   |         | systems between the building transformer       |
|     |    |   |         | secondary bushings or subfed from another      |
|     |    |   |         | source or building via a secondary service and |
|     |    |   |         | the building main disconnecting means          |
|     |    |   |         | including but not limited to: air or sandwich  |
|     |    |   |         | busduct, busway, cablebus, overhead secondary  |
|     |    |   |         | drops, and conduit/wire systems. Secondary     |
|     |    |   |         | service to electrical manholes.                |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Main Disconnecting Means: That       |
|     |    |   |         | system, comprised of the 480 Volt or 120/208   |
|     |    |   |         | Volt main disconnecting means, protection and  |
|     |    |   |         | switching, which includes but is not limited   |
|     |    |   |         | to: Switchboards, Switchgears of the indoor,   |
|     |    |   |         | outdoor, drip-proof, protected aisle and       |
|     |    |   |         | common aisle variety of metal-clad switchgear; |
|     |    |   |         | motor control centers, and load-centers, meter |
|     |    |   |         | panels or centers, and molded-case circuit     |
|     |    |   |         | breaker distribution panels (PP, MDP, DP       |
|     |    |   |         | classified panels) and their components for    |
|     |    |   |         | voltage transformation, metering, circuit      |
|     |    |   |         | switching, and system protection in the        |
|     |    |   |         | Secondary Electrical Distribution Systems.     |
|     |    |   |         | System begins at line side of main             |
|     |    |   |         | disconnecting means and extends to the line    |
|     |    |   |         | side of the secondary distribution equipment.  |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Secondary Distribution System: Operate to 80%  |
| 2.0 |    |   | Output  | name plate ratings on continuous loads without |
| 9.B |    |   |         | exceeding the maximum hot-spot temperature     |
|     |    |   |         | rise of 55 degrees Centigrade on 60 cycle      |
|     |    |   |         | equipment, providing for the given indoor and  |
|     |    |   |         | outdoor environmental conditions. The ratio of |
|     |    |   |         | load current to the ampere rating of the       |
|     |    |   |         | overcurrent protective device determines it    |
|     |    |   |         | operating temperature and shall be used for    |
|     |    |   |         | panelboards and other distribution equipment.  |
|     |    |   |         | Manual and automatic transfer for              |
|     |    |   |         | configuration changes as conditions warrant.   |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Bussing Systems: Operate to name     |
|     |    |   |         | plate data to carry energy reliably without    |
|     |    |   |         | exceeding the maximum hot-spot temperature     |
|     |    |   |         | rise of 55 degrees Centigrade for 60 cycle     |
|     |    |   |         | systems, providing for the given indoor and    |
|     |    |   |         | outdoor environmental conditions. Buses must   |
|     |    |   |         | maintain the ability to dissipate heat losses. |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Main Disconnecting Means: Operate,   |
|     |    |   |         | control and protect low voltage distribution   |
|     |    |   |         | equipment, and provide service entrance,       |
|     |    |   |         | power, and lighting distribution. Where        |
|     |    |   |         | protection is afforded, the overcurrent        |
|     |    |   |         | protective device closest to the fault must    |
|     |    |   |         | isolate faults.                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Secondary Distribution System: This system is  |
| 2.0 |    |   | Com     | defined to include, but is not limited to:     |
| 9.C |    |   | ponents | main protective devices, enclosures, busbar    |
|     |    |   |         | and terminal connections, disconnects, fuses,  |
|     |    |   |         | contactors, motor overload relays, pilot and   |
|     |    |   |         | miscellaneous control devices, and interlocks, |
|     |    |   |         | conductors, electric interconnections and      |
|     |    |   |         | accessories. Manual and automatic transfer     |
|     |    |   |         | switches with associated monitoring and        |
|     |    |   |         | control equipment.                             |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Bussing Systems: These systems are   |
|     |    |   |         | defined to include, but are not limited to:    |
|     |    |   |         | busbar, straight lengths, elbows, tees, tap    |
|     |    |   |         | boxes, power take offs, plugs, housings or     |
|     |    |   |         | raceways, insulation, heater strips, hangers   |
|     |    |   |         | and other mounting hardware and fittings.      |
|     |    |   |         |                                                |
|     |    |   |         | Secondary Main Disconnecting Means: This       |
|     |    |   |         | system is defined to include, but is not       |
|     |    |   |         | limited to: assembled indoor or outdoor        |
|     |    |   |         | equipment, switching, interrupting, control,   |
|     |    |   |         | metering including kWh metering and            |
|     |    |   |         | instrumentation that is remotely recorded by   |
|     |    |   |         | the EMCS or manually recorded to provide       |
|     |    |   |         | energy management or ECM data protective, and  |
|     |    |   |         | regulating devices, together with their        |
|     |    |   |         | supporting structure(s), enclosure(s),         |
|     |    |   |         | conductors, electric interconnections and      |
|     |    |   |         | accessories; grounding, bus, bus supports, and |
|     |    |   |         | heaters. Examples of these systems are         |
|     |    |   |         | switches (automatic and manual), motor control |
|     |    |   |         | centers, load-centers, meter panels or         |
|     |    |   |         | centers, and molded-case circuit breaker       |
|     |    |   |         | distribution panels (PP, MDP, DP classified    |
|     |    |   |         | panels) in the Secondary Electrical            |
|     |    |   |         | Distribution System.                           |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **L     |                                                |
| .10 | le |   | ighting |                                                |
|     | ct |   | (       |                                                |
|     |    |   | General |                                                |
|     |    |   | Area)** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | A.      | That system which comprises the facility or    |
| .2. |    |   | Desc    | structure interior general area lighting and   |
| 10A |    |   | ription | exterior perimeter lighting from the           |
|     |    |   |         | panelboard to the end-user. Also included are  |
|     |    |   |         | the lighting contactors with reset pushbuttons |
|     |    |   |         | installed in various Mechanical and Electrical |
|     |    |   |         | closets and hallways for control of office     |
|     |    |   |         | lighting.                                      |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | B.      | Operate at recommended building illumination   |
| .2. |    |   | Output  | levels in accordance with JMI 8836.1, and IES  |
| 10B |    |   |         | Lighting Handbook (HB-99, ISBN Number          |
|     |    |   |         | 0-87995-150-8), 9th Edition (1999). Maximum    |
|     |    |   |         | Tolerance duration of power is indefinite;     |
|     |    |   |         | depends on analysis and evaluation.            |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | C.      | This system is defined to include, but is not  |
| .2. |    |   | Com     | limited to: fixtures, lamps, reflectors,       |
| 10C |    |   | ponents | ballasts, lens, diffusers, guards, lighting    |
|     |    |   |         | contactors, push buttons, fuses, switches,     |
|     |    |   |         | mounting hangers and hardware, conductors,     |
|     |    |   |         | conduit, and controls. It also includes        |
|     |    |   |         | circadian lighting systems, ballpark lighting, |
|     |    |   |         | and roadway signs, including crosswalk signs.  |
|     |    |   |         | This includes systems in general office,       |
|     |    |   |         | hi-bays, laboratories, cafeteria's, etc\...    |
|     |    |   |         | Lamp types vary and include but are not        |
|     |    |   |         | limited to Halogen, incandescent, fluorescent, |
|     |    |   |         | HI Intensity Discharge lighting fixtures       |
|     |    |   |         | (mercury, metal-halide, high-pressure sodium,  |
|     |    |   |         | and low-pressure sodium).                      |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Em    |                                                |
| .11 | le |   | ergency |                                                |
|     | ct |   | Lig     |                                                |
|     |    |   | hting** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | A.      | That system which comprises the life safety    |
| .2. |    |   | Desc    | lighting including, but not limited to         |
| 11A |    |   | ription | emergency lighting units (i.e.                 |
|     |    |   |         | wall-mounted)**,** emergency lighting systems, |
|     |    |   |         | exit lighting, stairwell and egress lighting.  |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | B.      | Emergency lighting for evacuation purposes     |
| .2. |    |   | Output  | must energize automatically upon loss of       |
| 11B |    |   |         | normal lighting. Emergency lighting must be    |
|     |    |   |         | maintained for at least 1-1/2 hour for         |
|     |    |   |         | battery-powered units. Maximum toleration      |
|     |    |   |         | duration of power failure is up to 10 seconds, |
|     |    |   |         | preferably not more than 3 seconds, in         |
|     |    |   |         | accordance with ANSI/IEEE Std 446-1995 (ISBN   |
|     |    |   |         | Number 1-5593-7598-1). Light levels must be    |
|     |    |   |         | maintained to provide enough illumination per  |
|     |    |   |         | NFPA 101 Life Safety Code 2000 Edition to      |
|     |    |   |         | allow easy and safe egress from the area       |
|     |    |   |         | involved. Comply with ANSI/NFPA 70-1999,       |
|     |    |   |         | Article 700 for the operation and maintenance  |
|     |    |   |         | requirements and ANSI/NFPA 101-2000 for        |
|     |    |   |         | emergency lighting specific to life safety     |
|     |    |   |         | lighting.                                      |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | C.      | This system is defined to include, but is not  |
| .2. |    |   | Com     | limited to: lamps, reflectors, ballasts, lens, |
| 11C |    |   | ponents | batteries, cords, conduit, fuses, conductors,  |
|     |    |   |         | circuit cards, receptacles, and light poles,   |
|     |    |   |         | controls and LED's.                            |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Obst  |                                                |
| .12 | le |   | ruction |                                                |
|     | ct |   | and     |                                                |
|     |    |   | Warning |                                                |
|     |    |   | Lig     |                                                |
|     |    |   | hting** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which comprises the obstruction    |
| 2.1 |    |   | Desc    | lighting systems (aircraft warning lights on   |
| 2.A |    |   | ription | water towers, office buildings roofs,          |
|     |    |   |         | laboratory buildings roofs, shop buildings     |
|     |    |   |         | roofs, antenna towers, and aircraft hangar     |
|     |    |   |         | roofs). System extends from source circuit     |
|     |    |   |         | breaker through lighting fixture.              |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Operate at recommended building illumination   |
| 2.1 |    |   | Output  | levels in accordance with JMI 8836.1, and IES  |
| 2.B |    |   |         | Lighting Handbook, 9th Edition (1999) ISBN     |
|     |    |   |         | Number 0-87995-150-8.                          |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | This system is defined to include, but is not  |
| 2.1 |    |   | Com     | limited to: lamps, reflectors, ballasts, lens, |
| 2.C |    |   | ponents | and light poles, fixtures, fixture hardware,   |
|     |    |   |         | conduit, fuses, conductors, cords, and         |
|     |    |   |         | controls.                                      |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Li    |                                                |
| .13 | le |   | ghtning |                                                |
|     | ct |   | Prote   |                                                |
|     |    |   | ction** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which comprises the lightning      |
| 2.1 |    |   | Desc    | protection and detection systems for all       |
| 3.A |    |   | ription | facilities and structures including            |
|     |    |   |         | substations, technical equipment buildings,    |
|     |    |   |         | towers, antennas, masts, fuel storage tanks,   |
|     |    |   |         | metal buildings, metal sheds, and stacks.      |
|     |    |   |         | System extends from the connection point to    |
|     |    |   |         | the earth electrode subsystem to the highest   |
|     |    |   |         | masted point of the aerial lightning           |
|     |    |   |         | protection subsystem.                          |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Maintain the systems per NFPA 780 1997         |
| 2.1 |    |   | Output  | Edition. Lightning protection subsystem is to  |
| 3.B |    |   |         | direct high currents or limit the voltage      |
|     |    |   |         | gradients developed by high currents to safe   |
|     |    |   |         | levels and protect structures, facilities,     |
|     |    |   |         | personnel, and equipment from lightning        |
|     |    |   |         | damage.                                        |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | The components which comprise this requirement |
| 2.1 |    |   | Com     | include but are not limited to: air terminals, |
| 3.C |    |   | ponents | roof conductors, own conductors, ground rods,  |
|     |    |   |         | exothermically welded connections, mechanical  |
|     |    |   |         | fastener connections, surge arrestors and      |
|     |    |   |         | suppressors, all separately mounted shielding  |
|     |    |   |         | systems, and overhead ground wires.            |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Grou  |                                                |
| .14 | le |   | nding** |                                                |
|     | ct |   |         |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which comprises the facility       |
| 2.1 |    |   | Desc    | ground system.                                 |
| 4.A |    |   | ription |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Assure continuous means to limit voltages due  |
| 2.1 |    |   | Output  | to lightning, line surges, or unintentional    |
| 4.B |    |   |         | contact with higher voltage lines, and to      |
|     |    |   |         | stabilize the voltage to ground during normal  |
|     |    |   |         | operation. Reference ANSI/IEEE 142-1991, and   |
|     |    |   |         | for ground-fault protection reference          |
|     |    |   |         | ANSI/IEEE std 242-1986.                        |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | The components that comprise this requirement  |
| 2.1 |    |   | Com     | include but are not limited to: ground rods,   |
| 4.C |    |   | ponents | grounding conductors**,** counterpoise, bonds, |
|     |    |   |         | connections, and test wells. Integrity of      |
|     |    |   |         | grounding systems maintained for continuous    |
|     |    |   |         | operation.                                     |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **      |                                                |
| .15 | le |   | Central |                                                |
|     | ct |   | Tele-   |                                                |
|     |    |   | communi |                                                |
|     |    |   | cations |                                                |
|     |    |   | System  |                                                |
|     |    |   | (CTS)** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which provides electrical power    |
| 2.1 |    |   | Desc    | for the Central Telecommunications System      |
| 5.A |    |   | ription | (CTS) and the Program Support Communications   |
|     |    |   |         | Network (PSCN).                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide continuous power to the Center         |
| 2.1 |    |   | Output  | Telecommunications System (CTS) and the        |
| 5.B |    |   |         | Program Support Communications Network (PSCN). |
|     |    |   |         | In the event of commercial power failure or    |
|     |    |   |         | system malfunction provide emergency backup    |
|     |    |   |         | power that, upon failure or outage of the      |
|     |    |   |         | normal source, automatically provides power to |
|     |    |   |         | critical devices and equipment whose failure   |
|     |    |   |         | to operate satisfactorily would jeopardize     |
|     |    |   |         | health and safety of personnel or cause        |
|     |    |   |         | equipment damage. The emergency lighting       |
|     |    |   |         | system will be activated at the time of        |
|     |    |   |         | failure. Electrical schematics (one-line       |
|     |    |   |         | diagrams) and equipment layout for facility    |
|     |    |   |         | included in the TRL.                           |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | The components which comprise this requirement |
| 2.1 |    |   | Com     | include but are not limited to: motor control  |
| 5.C |    |   | ponents | centers, automatic transfer switches, manual   |
|     |    |   |         | transfer switches, disconnect switches,        |
|     |    |   |         | circuit breakers, panelboards, transformer,    |
|     |    |   |         | battery banks, battery chargers, generator,    |
|     |    |   |         | voltage regulators and exciters, motors,       |
|     |    |   |         | uninterruptible power supplies, and inverters. |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Em    |                                                |
| .16 | le |   | ergency |                                                |
|     | ct |   | Power   |                                                |
|     |    |   | B       |                                                |
|     |    |   | ackup** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | That system which serves as an emergency       |
| 2.1 |    |   | Desc    | source for supplying power to critical loads   |
| 6.A |    |   | ription | in the event of loss of a service interruption |
|     |    |   |         | or loss of power.                              |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide emergency backup power that, upon      |
| 2.1 |    |   | Output  | failure or outage of the normal source,        |
| 6.B |    |   |         | automatically provides power to critical       |
|     |    |   |         | devices and equipment whose failure to operate |
|     |    |   |         | satisfactorily would jeopardize health and     |
|     |    |   |         | safety of personnel or cause equipment damage. |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | The components which comprise this requirement |
| 2.1 |    |   | Com     | include but are not limited to: storage        |
| 6.C |    |   | ponents | batteries, generator sets, UPS's (energy       |
|     |    |   |         | storage batteries, rectifiers, inverters, and  |
|     |    |   |         | associated controls), transfer switching       |
|     |    |   |         | devices, relay synchronizing, protective and   |
|     |    |   |         | auxiliary devices, alarms and controls,        |
|     |    |   |         | conductors, wiring components, and grounds.    |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Em    |                                                |
| .17 | le |   | ergency |                                                |
|     | ct |   | Wa      |                                                |
|     |    |   | rning** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Emergency Warning Systems are stand-alone pole |
| 2.1 |    |   | Desc    | mounted systems strategically located at JSC   |
| 7.A |    |   | ription | that are programmed to generate loud warning   |
|     |    |   |         | sounds to alert JSC personnel that a           |
|     |    |   |         | particular hazard is about to occur or has     |
|     |    |   |         | occurred. The system is also used as a public  |
|     |    |   |         | address system.                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide for a reliable and continuous          |
| 2.1 |    |   | Output  | operation of various audible sounds generated  |
| 7.B |    |   |         | by Emergency Warning System in the event a     |
|     |    |   |         | hazardous condition occurs or is about to      |
|     |    |   |         | occur at JSC.                                  |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Components include not limited to: Poles,      |
| 2.1 |    |   | Com     | strobe lights, speakers, solar panels, control |
| 7.C |    |   | ponents | cabinet (electronics), antennas, batteries,    |
|     |    |   |         | ground rods, lightning rods, lightning         |
|     |    |   |         | protection down conductors, lightning          |
|     |    |   |         | protection connectors and fasteners, portable  |
|     |    |   |         | computer, portable computer                    |
|     |    |   |         | transmitter/receive antenna, portable hand     |
|     |    |   |         | held control panel, and field and              |
|     |    |   |         | communication wiring and PC Computer           |
|     |    |   |         | interface.                                     |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Site  |                                                |
| .18 | le |   | Int     |                                                |
|     | ct |   | ercom** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Site Intercom Systems are used by Operation    |
| 2.1 |    |   | Desc    | Control Center and the Emergency Operations    |
| 8.A |    |   | ription | Center (EOC) to communicate to field tunnel    |
|     |    |   |         | and mechanical rooms' locations.               |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide continuous and reliable communication  |
| 2.1 |    |   | Output  | between Operations Control Center and all      |
| 8.B |    |   |         | tunnel and mechanical stations, and the        |
|     |    |   |         | station in the Emergency Operations Center     |
|     |    |   |         | (EOC).                                         |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | These systems are defined to include but not   |
| 2.1 |    |   | Com     | limited to: amplifiers, impedance              |
| 8.C |    |   | ponents | transformers, speakers, switches relays,       |
|     |    |   |         | conductors, cords, conduits, lamps, and wire.  |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Radio |                                                |
| .19 | le |   | Tape    |                                                |
|     | ct |   | Monit   |                                                |
|     |    |   | oring** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | A.      | Radio Tape Monitoring System is used to record |
| 2.1 |    |   | Desc    | all radio transmissions used in field for O&M  |
| 9.A |    |   | ription | activities.                                    |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | B.      | Provide continuous recording of radio          |
| 2.1 |    |   | Output  | communication/transmission on tape.            |
| 9.B |    |   |         |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.  |    |   | C.      | Radio Tape Interface Scanner and Recorder      |
| 2.1 |    |   | Com     | hardware.                                      |
| 9.C |    |   | ponents |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1.2 | E  |   | **Fire  |                                                |
| .20 | le |   | Pro     |                                                |
|     | ct |   | tection |                                                |
|     |    |   | and     |                                                |
|     |    |   | Sec     |                                                |
|     |    |   | urity** |                                                |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | A.      | The cable system for fire protection and       |
| .2. |    |   | Desc    | security both above ground on poles, and       |
| 20A |    |   | ription | underground in duct bank.                      |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | B.      | Provide reliable operation of JSC fire         |
| .2. |    |   | Output  | protection and security system. Provide bucket |
| 20B |    |   |         | truck and personnel support to install,        |
|     |    |   |         | remove, repair or rearrange alarm/security     |
|     |    |   |         | cables on overhead distribution system as      |
|     |    |   |         | needed.                                        |
+-----+----+---+---------+------------------------------------------------+
| 1   |    |   | C.      | This system is defined to include, but is not  |
| .2. |    |   | Com     | limited to cable, cable clamps, messengers,    |
| 20C |    |   | ponents | tie-off insulators, tie-wraps, pole hardware,  |
|     |    |   |         | and cable identifiers.                         |
+-----+----+---+---------+------------------------------------------------+

1.4.0 Civil

+-----+----+----------+-----------------------------------------------+
| \#  | Sy | System   |                                               |
|     | st |          |                                               |
|     | em |          |                                               |
|     | Ty |          |                                               |
|     | pe |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ## Potab |                                               |
| .01 | iv | le Water |                                               |
|     | il |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | [Production]{.underline} -- This is the       |
| 4.0 |    | Des      | system that provides production,              |
| 1.A |    | cription | pressurization, treatment, and distribution   |
|     |    |          | of the JSC site potable water system. This    |
|     |    |          | system begins at the property line and        |
|     |    |          | continues through to the point of use. The    |
|     |    |          | JSC site normally operates on surface water   |
|     |    |          | provided by contract through Clear Lake City  |
|     |    |          | Water Authority (CLCWA). Two water wells      |
|     |    |          | provide backup supply to the site in the      |
|     |    |          | event that surface water is unavailable due   |
|     |    |          | to poor quality or low quantity. This utility |
|     |    |          | system includes ground and elevated storage   |
|     |    |          | of JSC site potable water. Exhaust fans are   |
|     |    |          | on top of the 1,000,000-gallon ground storage |
|     |    |          | tank to remove methane gas when well water is |
|     |    |          | used. The elevated storage tank and each of   |
|     |    |          | the ground storage tanks have their own       |
|     |    |          | impressed current cathodic protection systems |
|     |    |          | in place and a separate cathodic protection   |
|     |    |          | system protects the bases of both ground      |
|     |    |          | storage tanks.                                |
|     |    |          |                                               |
|     |    |          | [Distribution/Use]{.underline} - This utility |
|     |    |          | system provides for the distribution of       |
|     |    |          | potable and fire water to all facilities at   |
|     |    |          | JSC. This system supplies water not           |
|     |    |          | considered potable water to systems that are  |
|     |    |          | not considered facilities such as turf        |
|     |    |          | irrigation or fire protection devices. The    |
|     |    |          | system provides potable water to restrooms,   |
|     |    |          | sinks, showers, drinking fountains, etc. and  |
|     |    |          | includes supply piping to domestic hot water  |
|     |    |          | systems, fire water systems, and make up      |
|     |    |          | supplies to mechanical equipment.             |
|     |    |          |                                               |
|     |    |          | The system provides for the distribution of   |
|     |    |          | potable water at EF and SCTF. This system     |
|     |    |          | begins at the point of the backflow           |
|     |    |          | preventers at the property line and continues |
|     |    |          | through to the point of use. This system also |
|     |    |          | includes appurtenances that the water system  |
|     |    |          | supplies that are not considered facilities   |
|     |    |          | such as turf irrigation and fire protection.  |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The water quality in all portions of the      |
| 4.0 |    | Output   | water systems at **\*JSC** must meet TNRCC    |
| 1.B |    |          | requirements. The JSC system shall be free of |
|     |    |          | leaks and shall provide each facility with a  |
|     |    |          | continuous supply of potable water / fire     |
|     |    |          | water at 68 psi pressure from a reference     |
|     |    |          | point of the elevated storage tank. The       |
|     |    |          | booster pump system shall be used to maintain |
|     |    |          | this pressure except during operation of the  |
|     |    |          | emergency supply line when the site is        |
|     |    |          | provided with pressure from CLCWA. All        |
|     |    |          | potable water systems shall provide the       |
|     |    |          | quantity needed to operate facility fixtures  |
|     |    |          | and associated appurtenances per the          |
|     |    |          | International Building Code 2000 Standard.    |
|     |    |          | All valves shall be operational. The storage  |
|     |    |          | system shall be inspected annually and        |
|     |    |          | disinfected to provide potable water per AWWA |
|     |    |          | and TNRCC standards. The cathodic protection  |
|     |    |          | systems shall prevent deterioration of the    |
|     |    |          | metal structures and shall be tested to       |
|     |    |          | verify the functionality of the system. The   |
|     |    |          | potable water storage tank paint coatings     |
|     |    |          | shall protect the structures from corrosion.  |
|     |    |          | The exhaust fans on the top of the            |
|     |    |          | 1,000,000-gallon ground storage tank shall    |
|     |    |          | remove 100% of methane gas from the tank. The |
|     |    |          | system shall be free of leaks and shall       |
|     |    |          | provide the sufficient quantity and pressure  |
|     |    |          | of potable water to all equipment to meet the |
|     |    |          | International Building Code 2000 Standard.    |
|     |    |          | Repairs shall maintain water quality as set   |
|     |    |          | in Annex 4 and after repairs equipment shall  |
|     |    |          | be disinfected per TNRCC Chapter 290 and AWWA |
|     |    |          | regulations. A tester accredited by the TNRCC |
|     |    |          | or its designated agents must perform         |
|     |    |          | backflow preventer testing and repairs.       |
|     |    |          | Testing of the backflow preventers located at |
|     |    |          | the EF property lines shall also be           |
|     |    |          | coordinated with the City of Houston. Repairs |
|     |    |          | shall be accomplished within AWWA and TNRCC   |
|     |    |          | standards. Backflow preventer testing shall   |
|     |    |          | be done and recorded in accordance with TNRCC |
|     |    |          | regulations by certified testers. Backflow    |
|     |    |          | test reports must be maintained per the TNRCC |
|     |    |          | Chapter 290 regulations. Maintain current     |
|     |    |          | certification of all pressure systems and     |
|     |    |          | components per JHB 1710B, and current         |
|     |    |          | \*\***Pressure Systems Inventory Recall**     |
|     |    |          | such that no component or system inspection   |
|     |    |          | date can be found to be out of compliance. At |
|     |    |          | JSC, water well #4 shall provide 1500 gallons |
|     |    |          | per minute and water well #2 shall provide    |
|     |    |          | 1000 gallons per minute flow rate, as         |
|     |    |          | measured at the meters located at the well    |
|     |    |          | heads. The booster pump system shall be       |
|     |    |          | maintained in such a manner to ensure         |
|     |    |          | compliance with operational requirements in   |
|     |    |          | Annex 4. The pumps shall be capable of        |
|     |    |          | pumping 2500 gallons per minute flow on       |
|     |    |          | electric drive and 2000 gallons per minute    |
|     |    |          | flow on natural gas drive. The chemical       |
|     |    |          | treatment system located in buildings 322,    |
|     |    |          | 319 and bulk storage tank shall be free of    |
|     |    |          | leaks and shall provide the quality of water  |
|     |    |          | which meets Annex 4 and TNRCC Chapter 290     |
|     |    |          | standards for chemical dosages and quality    |
|     |    |          | control of bacteria. System alarms shall      |
|     |    |          | operate to properly signal low level or leaks |
|     |    |          | of chemicals. The building ventilation system |
|     |    |          | shall remove all chemical fumes from the      |
|     |    |          | building on a continuous basis. The system    |
|     |    |          | consists of the injection of sodium           |
|     |    |          | hypochlorite, ammonia, and a corrosion        |
|     |    |          | inhibitor and monitoring devices for those    |
|     |    |          | chemicals.                                    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The potable water system is defined to        |
| 4.0 |    | Co       | include, but is not limited to, the following |
| 1.C |    | mponents | facility components, appurtenances and        |
|     |    |          | equipment which it supplies: generation       |
|     |    |          | systems include wells with associated pumps,  |
|     |    |          | motors, natural gas engines with associated   |
|     |    |          | battery charger, casing and it includes       |
|     |    |          | piping, cathodic protection, valves, vents    |
|     |    |          | and vent screens, air lines, gages and drip   |
|     |    |          | oilers. Also, the piping, fittings, meters    |
|     |    |          | and instrumentation flush valves between the  |
|     |    |          | wells and the ground storage tanks. Tank      |
|     |    |          | components include structural framing, gages, |
|     |    |          | drainpipes, site level gages, cathodic        |
|     |    |          | protection including it's power source,       |
|     |    |          | anodes, support cables, screens, vents and    |
|     |    |          | paint systems. The tank controls include      |
|     |    |          | pressure sensing lines, a Clayton control     |
|     |    |          | valve, and tank high and low level alarms.    |
|     |    |          | Piping inside the elevated storage tank is    |
|     |    |          | also included. Cathodic protection components |
|     |    |          | include anodes, rectifiers, flotation buoys,  |
|     |    |          | collector cables and other associated         |
|     |    |          | components. The booster pump system includes  |
|     |    |          | electric and natural gas booster pumps,       |
|     |    |          | piping, Clayton control valves, gate valves,  |
|     |    |          | fittings, strainers, gages, insulation,       |
|     |    |          | freeze protection devices, hose bibbs,        |
|     |    |          | sampling taps, flush valves, labels and       |
|     |    |          | meters including the digital readout panel    |
|     |    |          | and meter totalizer inside building 322 and   |
|     |    |          | the paper circle chart recorder for logging   |
|     |    |          | the booster pump operations and surface water |
|     |    |          | flow times. The control system includes a PLC |
|     |    |          | at building 322 for booster pump controls,    |
|     |    |          | alarms, tank level controls, and gages. The   |
|     |    |          | chemical treatment system components include, |
|     |    |          | but are not limited to: chemical feed pumps,  |
|     |    |          | chemical analyzers, a PLC for controls, leak  |
|     |    |          | detection devices, chemical storage tanks and |
|     |    |          | drum containments, building ventilation       |
|     |    |          | system, associated piping, valves, fittings,  |
|     |    |          | freeze protection devices, labels,            |
|     |    |          | insulation, scales, alarm devices for leaks,  |
|     |    |          | a bulk storage tank and drums.                |
|     |    |          |                                               |
|     |    |          | The water analysis panel components includes  |
|     |    |          | pen recorders to monitor chlorine levels, low |
|     |    |          | level alarms on the drums (ammonia and        |
|     |    |          | corrosion inhibitor) and bulk tank (sodium    |
|     |    |          | hypochlorite), leak detectors for the ammonia |
|     |    |          | and sodium hypochlorite, and flow meters with |
|     |    |          | associated pen recorders. Facility components |
|     |    |          | include pneumatic tanks, surge tanks,         |
|     |    |          | pressure boosting pumps, level controls and   |
|     |    |          | alarms, piping and piping insulation (up to   |
|     |    |          | and including backflow preventers), labels,   |
|     |    |          | fittings and valves. Facility appurtenances   |
|     |    |          | including backflow preventers, strainers,     |
|     |    |          | relief valves, surge arresters, pressure      |
|     |    |          | reducing valves, water hammer arresters, air  |
|     |    |          | eliminators, water filters, timers and        |
|     |    |          | control valves, and pressure gages. Facility  |
|     |    |          | equipment includes water chillers, drinking   |
|     |    |          | fountains, safety showers, eyewashes,         |
|     |    |          | Jacuzzi's, showers, restroom sinks,           |
|     |    |          | janitorial sinks, and other sinks, hose bibbs |
|     |    |          | and associated hardware for listed equipment. |
|     |    |          | Portable eyewashes are also included in this  |
|     |    |          | definition. The piping system includes all    |
|     |    |          | piping, valves, fittings, valve boxes, valve  |
|     |    |          | markers, insulation and labeled marker posts. |
|     |    |          | Associated appurtenances include backflow     |
|     |    |          | preventers, eyewashes, safety showers, hose   |
|     |    |          | reels, wash racks, truck fill lines, gages,   |
|     |    |          | and meters.                                   |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | **       |                                               |
| .02 | iv | Sanitary |                                               |
|     | il | Sewer**  |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The system that provides for the removal of   |
| 4.0 |    | Des      | wastewater from the point of origination      |
| 2.A |    | cription | through the interconnected system of gravity  |
|     |    |          | lines and manholes to the lift stations where |
|     |    |          | it is routed through an interconnected system |
|     |    |          | of force mains, gravity lines and manholes to |
|     |    |          | the JSC property line. The Space Center       |
|     |    |          | Houston Visitor Center also sends JSC         |
|     |    |          | wastewater through their own pumping station, |
|     |    |          | which is maintained by their personnel. Lift  |
|     |    |          | stations are equipped with dual pumps for     |
|     |    |          | redundancy and the JSC piping system also has |
|     |    |          | some versatility for outages by changing      |
|     |    |          | valve configurations.                         |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The entire JSC Sanitary Sewer system shall be |
| 4.0 |    | Output   | free of leaks (infiltration and exfiltration) |
| 2.B |    |          | and shall provide for the continuous removal  |
|     |    |          | of wastewater at designed flow rates from all |
|     |    |          | components of the building, which tie into    |
|     |    |          | this system. The **\*JSC** gravity flow       |
|     |    |          | portion of the system must provide for the    |
|     |    |          | continuous flow of wastewater through the     |
|     |    |          | pipes in accordance with the existing field   |
|     |    |          | conditions such as slope and size of pipe     |
|     |    |          | without impact to the facilities. The         |
|     |    |          | unplanned repairs of blockages are covered    |
|     |    |          | under this system definition. Any failure of  |
|     |    |          | surrounding soil around appurtenances or      |
|     |    |          | along the piping route shall be repaired. The |
|     |    |          | **\*JSC** forced main portion of the system   |
|     |    |          | must provide for continuous service required  |
|     |    |          | to accomplish the removal of wastewater       |
|     |    |          | without impact to the system and facilities.  |
|     |    |          | A minimum of one pump shall be available at   |
|     |    |          | each lift station. Pumps shall meet           |
|     |    |          | capacities specified in O&M manuals. At       |
|     |    |          | building 223, two electric pumps shall be     |
|     |    |          | available to pump at O&M manual stated        |
|     |    |          | capacity for a combined flow of 350 gpm. The  |
|     |    |          | natural gas engine shall provide 600 gpm at   |
|     |    |          | suction lift from the bottom of the wet well. |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The facility waste water system is defined to |
| 4.0 |    | Co       | include, but is not limited to, the following |
| 2.C |    | mponents | facility components, appurtenances, and       |
|     |    |          | equipment which is connected to it.           |
|     |    |          |                                               |
|     |    |          | Facility components include grinder pumps,    |
|     |    |          | all drain, sewer and vent piping connected to |
|     |    |          | the sanitary sewer system from sinks,         |
|     |    |          | drinking fountains, floor drains, and misc.   |
|     |    |          | equipment.                                    |
|     |    |          |                                               |
|     |    |          | Facility appurtenances include alarms, grease |
|     |    |          | traps at cafeterias, and oil-water            |
|     |    |          | separators.                                   |
|     |    |          |                                               |
|     |    |          | Facility equipment includes restroom water    |
|     |    |          | closets, urinals, and associated flush valves |
|     |    |          | and hardware. The sanitary sewer pumping      |
|     |    |          | system is defined to include, but is not      |
|     |    |          | limited to wet wells, dry wells, pumps and    |
|     |    |          | associated grease lines and appurtenances,    |
|     |    |          | pump motors, sump pumps, controls, PLC's,     |
|     |    |          | alarms piping with in the lift station,       |
|     |    |          | valves, check valves, vents, air relief       |
|     |    |          | valves, comminutors, blowers, air             |
|     |    |          | compressors, and natural gas engine. The      |
|     |    |          | components include meters, wastewater         |
|     |    |          | manholes, process water manholes, force       |
|     |    |          | mains, cleanouts and gravity lines.           |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | **Storm  |                                               |
| .03 | iv | Sewer**  |                                               |
|     | il |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | This system is defined as the storm water     |
| 4.0 |    | Des      | collection system that collects onsite        |
| 3.A |    | cription | surface drainage and facility roof drainage   |
|     |    |          | and conveys it to the appropriate drainage    |
|     |    |          | ditch system that further conveys the storm   |
|     |    |          | water offsite. Also included as contributing  |
|     |    |          | to the overall system are the building 29     |
|     |    |          | dewatering wells, and sump pumps located at   |
|     |    |          | building 14, the weigh station north of       |
|     |    |          | building 420, elevator pits, tunnel, and      |
|     |    |          | electrical manholes.                          |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The entire Storm Sewer system shall be free   |
| 4.0 |    | Output   | of leaks (infiltration and exfiltration) and  |
| 3.B |    |          | shall provide for the continuous conveyance   |
|     |    |          | of storm water onsite from all points of      |
|     |    |          | entry into the system to the **\*JSC**        |
|     |    |          | property line. Clear passages shall be        |
|     |    |          | maintained throughout the storm water         |
|     |    |          | collection system to allow for continuous     |
|     |    |          | conveyance of the maximum amount of storm     |
|     |    |          | water to the property line in the most        |
|     |    |          | expedient manner limited only by the system's |
|     |    |          | designed capacity. Any failure of surrounding |
|     |    |          | soil around appurtenances or along the piping |
|     |    |          | route shall be repaired. Ditch linings,       |
|     |    |          | headwalls and other storm sewer appurtenances |
|     |    |          | shall not have any undercutting or            |
|     |    |          | displacement of slabs. Dewatering pumps and   |
|     |    |          | sump pumps shall be available when needed.    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The components of this system include         |
| 4.0 |    | Co       | drainage inlets and grates, manholes and      |
| 3.C |    | mponents | covers, concrete and metal collection piping, |
|     |    |          | swales, ditches, concrete aprons and          |
|     |    |          | associated energy dissipating structures,     |
|     |    |          | headwalls, corrugated metal culverts          |
|     |    |          | including inserts and concrete box culverts.  |
|     |    |          | Special attention shall be given to depressed |
|     |    |          | loading dock area storm water removal systems |
|     |    |          | (especially at building 14 which has the      |
|     |    |          | potential to flood a portion of the building  |
|     |    |          | if not adequately operating during a heavy    |
|     |    |          | rain event) to assure timely removal of storm |
|     |    |          | water in the case of heavy rains. The         |
|     |    |          | facility storm water removal system is        |
|     |    |          | defined to include, but is not limited to,    |
|     |    |          | the following facility components: Roof       |
|     |    |          | drains, drain lead flashing, pipes,           |
|     |    |          | insulation, labels, fittings, loggia ledge    |
|     |    |          | drains and associated piping, fittings and    |
|     |    |          | insulation, and all other miscellaneous       |
|     |    |          | drains and associated components which are    |
|     |    |          | connected to this system. It also includes    |
|     |    |          | associated pumps and piping which are         |
|     |    |          | designed to remove storm water from           |
|     |    |          | facilities. In this case, "associated pumps"  |
|     |    |          | refers to sump pumps that are located in the  |
|     |    |          | driveway depressions at the loading docks of  |
|     |    |          | some of the 400 area (logistics/warehousing)  |
|     |    |          | buildings. Also included in this system is    |
|     |    |          | the gutter and building downspout system.     |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ## Nat   |                                               |
| .04 | iv | ural Gas |                                               |
|     | il |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | This facility system provides for the         |
| 4.0 |    | Des      | distribution of natural gas from the point of |
| 4.A |    | cription | entry to the sites at the metering station to |
|     |    |          | equipment such as space heaters, hot water    |
|     |    |          | heaters, boilers, gas engines, cafeteria      |
|     |    |          | equipment, test equipment and laboratory      |
|     |    |          | equipment. The point of entry for JSC is      |
|     |    |          | right after the gas metering station          |
|     |    |          | (building 340) and the point of entry for EF  |
|     |    |          | and SCTF is the user's side of the meter.     |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The system shall be free of leaks and provide |
| 4.0 |    | Output   | for natural gas to and through the regulator  |
| 4.B |    |          | to the facilities at the designed rate and    |
|     |    |          | pressure based on the designated regulator    |
|     |    |          | settings and individual building usage.       |
|     |    |          | Maintain current certification and repairs of |
|     |    |          | all pressure systems and components per JHB   |
|     |    |          | 1710B, and current \*\***Pressure Systems     |
|     |    |          | Inventory Recall** such that no component or  |
|     |    |          | system inspection date can be found to be out |
|     |    |          | of compliance.                                |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The natural gas system is defined to include, |
| 4.0 |    | Co       | but is not limited to: piping, pipe wrapping, |
| 4.C |    | mponents | associated fittings, building regulator       |
|     |    |          | stations, gages, valves, identification       |
|     |    |          | markers and labels, blow offs, regulators,    |
|     |    |          | valve stations, relief valves, cathodic       |
|     |    |          | protection system, isolation unions and       |
|     |    |          | anodes, meters, instrumentation and gas       |
|     |    |          | scrubbers (building 24).                      |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | #        |                                               |
| .05 | iv |  Fire Pr |                                               |
|     | il | otection |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The facility firewater protection system is   |
| 4.0 |    | Des      | the system that provides water for fire       |
| 5.A |    | cription | protection in the **\*JSC** facilities. The   |
|     |    |          | water supply system for fire protection at    |
|     |    |          | JSC and SCTF is part of the potable water     |
|     |    |          | distribution system. The **\*JSC** fire       |
|     |    |          | protection contractor does a major part of    |
|     |    |          | the fire protection system tests, operations  |
|     |    |          | and planned maintenance. Also, fire           |
|     |    |          | protection is the utility system that         |
|     |    |          | provides for storage, pumping and             |
|     |    |          | distribution of firewater at Ellington Field, |
|     |    |          | which is a deluge system for most of the      |
|     |    |          | site, and a concentrated foam system at EF    |
|     |    |          | Hangar 990. There is also a deluge system on  |
|     |    |          | the building 48 cooling tower.                |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The entire system shall be free of leaks and  |
| 4.0 |    | Output   | shall provide for the continuous supply of    |
| 5.B |    |          | firewater protection per NFPA including       |
|     |    |          | annual exercising of fire hydrants,           |
|     |    |          | lubricating per manufacturer's                |
|     |    |          | recommendations and annual greasing of fire   |
|     |    |          | hydrant caps. The JSC system shall provide    |
|     |    |          | for the continuous supply of firewater        |
|     |    |          | protection to the facilities as designed      |
|     |    |          | based on a supply pressure of 68 PSI. The EF  |
|     |    |          | deluge system shall maintain continuous       |
|     |    |          | service for the storage, pumping and          |
|     |    |          | distribution of firewater for most of the     |
|     |    |          | site along with a concentrated foam system at |
|     |    |          | EF Hangar 990. Support brackets for fire      |
|     |    |          | extinguishers at all locations shall be       |
|     |    |          | maintained in a structurally sound condition. |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The components of the utility fire water      |
| 4.0 |    | Co       | distribution system include post indicator    |
| 5.C |    | mponents | valves, fire hydrants, deluge system piping   |
|     |    |          | and associated valves, piping, wet pipe       |
|     |    |          | sprinkler systems, and pipes on dry sprinkler |
|     |    |          | systems, valves outside cabinets and booster  |
|     |    |          | pumps on standpipe systems, insulation,       |
|     |    |          | freeze protection devices, labels, and        |
|     |    |          | meters. The components of the EF deluge       |
|     |    |          | firewater storage system include, but are not |
|     |    |          | limited to the following: two 150,000 gallon  |
|     |    |          | ground storage tanks with associated vents,   |
|     |    |          | paint coatings, alarms, screens, piping,      |
|     |    |          | controls and control valves, motors and       |
|     |    |          | diesel engines, pumps and pump controllers,   |
|     |    |          | foam generation system, piping, gate valves   |
|     |    |          | and post indicator valves, fittings, backflow |
|     |    |          | preventers, insulation and labels,            |
|     |    |          | underground valve pits, and associated freeze |
|     |    |          | protection devices.                           |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ## P     |                                               |
| .06 | iv | otable H |                                               |
|     | il | ot Water |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The **\*JSC** facility system that provides   |
| 4.0 |    | Des      | for the generation and distribution of        |
| 6.A |    | cription | domestic hot water to restrooms, sinks,       |
|     |    |          | cafeteria equipment, shower facilities,       |
|     |    |          | eyewashes, EF washrack and tempered water to  |
|     |    |          | safety showers.                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The system shall be free of leaks and shall   |
| 4.0 |    | Output   | provide domestic hot water temperature per    |
| 6.B |    |          | Federal Regulations Ref. NHB 8831.2 latest    |
|     |    |          | version. The system shall provide pressure    |
|     |    |          | and quantity to the fixtures to meet          |
|     |    |          | International Building Code 2000 Standard.    |
|     |    |          | Maintain current certification of all         |
|     |    |          | pressure systems and components per JHB       |
|     |    |          | 1710B, and current \*\***Pressure Systems     |
|     |    |          | Inventory Recall** such that no component or  |
|     |    |          | system inspection date can be found to be out |
|     |    |          | of compliance.                                |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The domestic hot water system is defined to   |
| 4.0 |    | Co       | include, but is not limited to, steam,        |
| 6.C |    | mponents | natural gas, instantaneous and electric hot   |
|     |    |          | water generators, electric or gas hot water   |
|     |    |          | heaters, insulation, instrumentation,         |
|     |    |          | thermostats, controls, filters, relief valves |
|     |    |          | and pressure protective devices, trace heat   |
|     |    |          | strips (B30S), in line recirculating pumps,   |
|     |    |          | hot water distribution piping, labels, valves |
|     |    |          | and fittings associated with such piping.     |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ##       |                                               |
| .07 | iv |  Turf Ir |                                               |
|     | il | rigation |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | This system provides for the irrigation of    |
| 4.0 |    | Des      | turf areas at **\*JSC**.                      |
| 7.A |    | cription |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The system shall be free of leaks and shall   |
| 4.0 |    | Output   | provide for the irrigation of **\*JSC**       |
| 7.B |    |          | grounds per the system design. Backflow       |
|     |    |          | preventers shall be tested and documented per |
|     |    |          | TNRCC Chapter 290 regulations. The mall fish  |
|     |    |          | ponds shall be provided with sufficient       |
|     |    |          | quantity of make-up water to keep the fish    |
|     |    |          | alive through water change out, overcome      |
|     |    |          | evaporation quantities and to maintain the    |
|     |    |          | water level to allow free water flow through  |
|     |    |          | pond interconnecting canal at all times.      |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The utility turf irrigation system is defined |
| 4.0 |    | Co       | to include, but is not limited to backflow    |
| 7.C |    | mponents | preventers and valve boxes, solenoid valves,  |
|     |    |          | gate valves, quick couplers, quick connects,  |
|     |    |          | pop-up heads, and automatic timers.           |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | **       |                                               |
| .08 | iv | Facility |                                               |
|     | il | In       |                                               |
|     |    | terior** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The facility interior system provides an      |
| 4.0 |    | Des      | architectural environment that allows         |
| 8.A |    | cription | **\*JSC** occupants to fully function in the  |
|     |    |          | performance of their duties. Facility         |
|     |    |          | interior systems are the numerous components  |
|     |    |          | comprising the building interior that         |
|     |    |          | includes but is not limited to the following  |
|     |    |          | items: floors, walls, ceilings, doors,        |
|     |    |          | stairs, handrails, interior glass windows and |
|     |    |          | doors, projection screens, auditorium chairs, |
|     |    |          | and the curtain and associated mounting and   |
|     |    |          | operating system located in the Teague        |
|     |    |          | Auditorium, building 2.                       |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | A continuous condition of safe, clean and     |
| 4.0 |    | Output   | reliable interior systems shall be maintained |
| 8.B |    |          | to provide safe working conditions for        |
|     |    |          | facility occupants. This includes but is not  |
|     |    |          | limited to the following items: operational   |
|     |    |          | door locks, securely hung projection screens, |
|     |    |          | no broken, damaged, loose, cracked, or        |
|     |    |          | missing floor tiles including uneven or loose |
|     |    |          | computer flooring, electrical tombstones and  |
|     |    |          | underfloor utility cover plates securely      |
|     |    |          | fastened, no loose or deteriorated non-skid   |
|     |    |          | matting on ramps, no holes or damage to walls |
|     |    |          | due to maintenance efforts, proper operation  |
|     |    |          | of all doors including door stops, door       |
|     |    |          | locks, door closers and associated hardware,  |
|     |    |          | panic door hardware, and no holes in walls    |
|     |    |          | due to missing or malfunctioning door stops,  |
|     |    |          | no cracked or damaged glass, properly aligned |
|     |    |          | trench cover plates and carpet tiles to       |
|     |    |          | preclude a tripping hazard, ceiling tiles     |
|     |    |          | must not be water damaged, cracked, broken,   |
|     |    |          | bowed, misaligned or missing and associated t |
|     |    |          | bar support grid shall be securely installed  |
|     |    |          | and properly aligned. Stair steps shall be in |
|     |    |          | a safe configuration with no worn non-skid    |
|     |    |          | coatings, no loose nosings and all handrails  |
|     |    |          | securely fastened.                            |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The components include, but are not limited   |
| 4.0 |    | Co       | to, fire doors, personnel doors, computer     |
| 8.C |    | mponents | flooring and associated support grid, floor   |
|     |    |          | surfaces including surface coatings, carpet   |
|     |    |          | tiles and floor tiles, ceiling tiles and      |
|     |    |          | support grid, walls, handrails, steps,        |
|     |    |          | projection screens, and permanently mounted   |
|     |    |          | auditorium and viewing room chairs. The stage |
|     |    |          | curtain components consist of the stage       |
|     |    |          | curtain, mounting hardware and operating      |
|     |    |          | mechanisms used to move the curtain.          |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ## F     |                                               |
| .09 | iv | acility  |                                               |
|     | il | Exterior |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The facility exterior system provides an      |
| 4.0 |    | Des      | architectural protection from the elements    |
| 9.A |    | cription | and prevents the internal environment from    |
|     |    |          | being adversely affected. This system         |
|     |    |          | provides for weatherproofing of the facility  |
|     |    |          | from rain and inclement weather.              |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The system shall provide for the safe         |
| 4.0 |    | Output   | condition and continuous waterproofing of the |
| 9.B |    |          | facility exterior structure without leaks.    |
|     |    |          | Corrective measures shall be taken to         |
|     |    |          | alleviate further leakage. If defects in the  |
|     |    |          | roofing, loggia ledge, or PEAF panel caulking |
|     |    |          | are found, temporary repairs shall be         |
|     |    |          | accomplished under this section and the       |
|     |    |          | requirements for permanent repairs shall be   |
|     |    |          | submitted to the CO for accomplishment        |
|     |    |          | through Annex 3 or Annex 6. Typical Facility  |
|     |    |          | Exterior tasks that are covered under this    |
|     |    |          | definition include but are not limited to:    |
|     |    |          | replacement of broken glass in windows and    |
|     |    |          | doors, repair of rain water leaks through     |
|     |    |          | window seals and frames, PEAF panel caulking  |
|     |    |          | to alleviate leaks, repair of exterior        |
|     |    |          | personnel door hardware or weatherstripping,  |
|     |    |          | door painting to alleviate corrosion, or door |
|     |    |          | replacement due to excessive corrosion, no    |
|     |    |          | build-up of debris on roofs that causes       |
|     |    |          | ponding, temporary repair of roof leaks and   |
|     |    |          | associated vent installation, if necessary,   |
|     |    |          | repair of roof drain leaks, repair of antenna |
|     |    |          | or other tie-downs due to corrosion or        |
|     |    |          | stretching, replacement of portions of metal  |
|     |    |          | building siding as a result of wind damage,   |
|     |    |          | leaks, or excessive corrosion and replacement |
|     |    |          | of fasteners on siding and roofs that have    |
|     |    |          | come loose, are missing or are deteriorated.  |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The components include any portion of the     |
| 4.0 |    | Co       | building exterior system which are either     |
| 9.C |    | mponents | unsafe or compromise the waterproofing        |
|     |    |          | integrity or security of the system. It       |
|     |    |          | includes, but is not limited to, all exterior |
|     |    |          | glass systems, window seals and frames,       |
|     |    |          | exterior doors and seals, sheet metal siding  |
|     |    |          | walls and fasteners, PEAF panel walls and     |
|     |    |          | joints, other miscellaneous wall              |
|     |    |          | construction, loggia ledges, facility roofs,  |
|     |    |          | roof fasteners, parapets, associated roof     |
|     |    |          | hoods and appurtenances, and any wall         |
|     |    |          | penetrations.                                 |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ##       |                                               |
| .10 | iv | Doors &  |                                               |
|     | il | Barriers |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Rolling metal-coiled doors, interior or       |
| 4.1 |    | Des      | exterior, horizontal or vertical sliding      |
| 0.A |    | cription | doors that provide ingress and egress of      |
|     |    |          | personnel or large equipment at facilities.   |
|     |    |          | This includes the interior high-speed roll-up |
|     |    |          | curtain in building 421, coiling hurricane    |
|     |    |          | shutters, accordian metal security gates and  |
|     |    |          | strip curtains.                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Provide maximum reliability and safety in all |
| 4.1 |    | Output   | door operations. They must be available for   |
| 0.B |    |          | continuous service in case an emergency       |
|     |    |          | situation arises in a building which would    |
|     |    |          | require their immediate use. Safe and         |
|     |    |          | reliable operation of automatic personnel     |
|     |    |          | doors shall be available for building         |
|     |    |          | occupants to enter and exit buildings. System |
|     |    |          | shall operate doors from presence detectors   |
|     |    |          | where available and shall not close           |
|     |    |          | prematurely. Exterior doors that are damaged  |
|     |    |          | by the elements or wind will be repaired and  |
|     |    |          | recoated and hardware will be repaired or     |
|     |    |          | replaced. Corrosion protection shall be       |
|     |    |          | maintained on exterior doors.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Rolling metal coiled and large, interior and  |
| 4.1 |    | Co       | exterior, horizontal or vertical sliding door |
| 0.C |    | mponents | systems includes all of the door hardware,    |
|     |    |          | controls, mechanical components and operating |
|     |    |          | mechanisms. This includes components of the   |
|     |    |          | interior high-speed roll-up curtain in        |
|     |    |          | building 421 and coiling hurricane shutters.  |
|     |    |          | Component parts include but are not limited   |
|     |    |          | to: motors, gearbox, clutch assembly, labels, |
|     |    |          | safety boot take-up reel, control box,        |
|     |    |          | forward and reversing relays, start-stop      |
|     |    |          | stations, limit switches or worm-gear,        |
|     |    |          | sliding door frames/rails, counterweights,    |
|     |    |          | caging, roller suspension tracks, travel      |
|     |    |          | blocks etc., and electronics microprocessor   |
|     |    |          | controllers, detectors (motion, safety beams, |
|     |    |          | sensitivity sensors, motors, switches, relays |
|     |    |          | etc).                                         |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | #        |                                               |
| .11 | iv | # Fences |                                               |
|     | il |  & Gates |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Fencing refers to the perimeter security      |
| 4.1 |    | Des      | fence system and other internal fence systems |
| 1.A |    | cription | utilized to secure areas at **\*JSC**         |
|     |    |          | including associated gates. Also included at  |
|     |    |          | JSC are recreational area (ball fields,       |
|     |    |          | batting cage and tennis courts) fences, PEAF  |
|     |    |          | enclosures and bollards with chains adjacent  |
|     |    |          | to the building 30/48 complex and building 24 |
|     |    |          | and PEAF enclosures surrounding utility and   |
|     |    |          | transformers and HV switches.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Fence systems shall be maintained to provide  |
| 4.1 |    | Output   | continuous security of the associated areas   |
| 1.B |    |          | including an uninterrupted section of barbed  |
|     |    |          | wire along the top of the fence, where        |
|     |    |          | applicable. Gates (especially the west        |
|     |    |          | entrance electric controlled gate and the     |
|     |    |          | tram road electric operated gate) shall be    |
|     |    |          | maintained in a condition that allows         |
|     |    |          | continuous operation and access to areas as   |
|     |    |          | needed. Bollards shall be in place and the    |
|     |    |          | chains continuous and corrosion free.         |
|     |    |          | Immediate repair mitigation shall be made on  |
|     |    |          | fences impacted by vehicles to provide site   |
|     |    |          | security with permanent repairs following.    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The fence system includes security bollards   |
| 4.1 |    | Co       | and associated chains, chain link fencing,    |
| 1.C |    | mponents | mounting and support hardware, barbed wire    |
|     |    |          | and all components associated with the        |
|     |    |          | operation of gates including locking          |
|     |    |          | mechanisms to provide a system of continuous  |
|     |    |          | area security.                                |
+-----+----+----------+-----------------------------------------------+
| 1.4 | C  | ##       |                                               |
| .12 | iv |  Public  |                                               |
|     | il | Displays |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Public displays include: the static Rocket    |
| 4.1 |    | Des      | Display viewed by visitors to JSC, the        |
| 2.A |    | cription | permanently mounted flagpoles at **\*JSC**,   |
|     |    |          | the memorial tree grove (located east of      |
|     |    |          | building 110) signage, the historical         |
|     |    |          | memorial displays located outside of building |
|     |    |          | 2, outside of building 30M, at Rocket Park    |
|     |    |          | and attached to the east side of building 5N  |
|     |    |          | outside the high bay, and the large JSC       |
|     |    |          | entrance signs located on NASA Road One, at   |
|     |    |          | the Second Street entrance and the tram road  |
|     |    |          | entrance at Rocket Park.                      |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Safe and secure display of the static rocket  |
| 4.1 |    | Output   | hardware and it's mounting components and     |
| 2.B |    |          | safe pedestrian travel areas utilized by JSC  |
|     |    |          | visitors. Continuous safe and reliable        |
|     |    |          | service shall be available for the daily use  |
|     |    |          | of the flagpole systems. Preservation and     |
|     |    |          | secure mounting of memorial displays and      |
|     |    |          | entrance signs shall be maintained.           |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The Rocket Park Display consists of the       |
| 4.1 |    | Co       | static Rocket Display, mounting hardware and  |
| 2.C |    | mponents | signage, and associated hardware along with   |
|     |    |          | pedestrian travel areas including roped       |
|     |    |          | stanchions. The flagpole system consists of   |
|     |    |          | the flagpoles, flag mounting rope and all of  |
|     |    |          | the hardware and mechanical components        |
|     |    |          | necessary to provide continuous safe,         |
|     |    |          | reliable and easy operation of the flagpole   |
|     |    |          | assembly. Components of the memorial displays |
|     |    |          | and entrance signs includes the plaques,      |
|     |    |          | letters, logos, and mounting and display      |
|     |    |          | hardware.                                     |
+-----+----+----------+-----------------------------------------------+

**1.5.0 Environmental**

+-----+----+----------+-----------------------------------------------+
| 1.5 | En | **Waste  |                                               |
| .01 | vi | Tank     |                                               |
|     | ro | Coll     |                                               |
|     | n. | ection** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The waste collection system including tanks,  |
| 5.0 |    | Des      | piping, leak detection and overfill           |
| 1.A |    | cription | protection systems and all associated         |
|     |    |          | equipment for the collection of wastes from   |
|     |    |          | the photographic lab, the metal               |
|     |    |          | finishing/cleaning labs for storage prior to  |
|     |    |          | disposal/treatment off-site or treatment      |
|     |    |          | onsite.                                       |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The tank systems and surrounding structures   |
| 5.0 |    | Output   | shall be maintained to ensure:                |
| 1.B |    |          |                                               |
|     |    |          | Accurate daily Resource Conservation and      |
|     |    |          | Recovery Act (RCRA) and other environmental   |
|     |    |          | and OSHA regulatory required inspections can  |
|     |    |          | be completed and logged. Silver recovery      |
|     |    |          | collection systems can be operated as needed. |
|     |    |          | Wastes can be collected, removed and          |
|     |    |          | transferred as required by regulatory         |
|     |    |          | requirements, e.g. every 90 days. The         |
|     |    |          | operation and all equipment functions in      |
|     |    |          | compliance with all RCRA and other state and  |
|     |    |          | federal environmental regulatory              |
|     |    |          | requirements, JSC requirements, permit        |
|     |    |          | conditions and OHSA requirements. Samples can |
|     |    |          | be collected as needed from tank sample ports |
|     |    |          | or other sample locations to collect annual   |
|     |    |          | waste characterization sampling or during     |
|     |    |          | process changes or as required by regulatory  |
|     |    |          | or JSC requirements. The high level alarms    |
|     |    |          | shall detect levels at the high level set     |
|     |    |          | points and sound an alarm and initiate the    |
|     |    |          | visual alarm at the facility and the EMCS at  |
|     |    |          | all times in accordance with RCRA regulations |
|     |    |          | and other state and federal environmental     |
|     |    |          | regulatory requirements, permit conditions    |
|     |    |          | and OSHA requirements. Leak detection systems |
|     |    |          | shall immediately detect all leaks and shall  |
|     |    |          | initiate panel alarms, visual alarms and EMCS |
|     |    |          | at all times as required by RCRA regulations  |
|     |    |          | and permit conditions.                        |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The waste collection system includes, but is  |
| 5.0 |    | Co       | not limited to; tanks and all tank            |
| 1.C |    | mponents | appurtenances, piping, double-walled piping,  |
|     |    |          | quick disconnects, pumps, valves, aerators,   |
|     |    |          | gratings, pH meters, electrodes, leak         |
|     |    |          | detection cables, tank level sensors, sump    |
|     |    |          | high level sensors, flow                      |
|     |    |          | indicators/totalizers, level controls, main   |
|     |    |          | panels for alarms, visual level indicators,   |
|     |    |          | heaters, piping insulation, overfill          |
|     |    |          | containers, compressors, carbon absorption    |
|     |    |          | canisters, tank identification labels,        |
|     |    |          | outside visual alarm indicator light, leak    |
|     |    |          | detection systems, and panel zones, tank      |
|     |    |          | system identification labels, safety showers  |
|     |    |          | and eyewash stations.                         |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | #        |                                               |
| .02 | vi | # Vaults |                                               |
|     | ro |          |                                               |
|     | n. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Vaults are the in ground concrete structures  |
| 5.0 |    | Des      | which house waste collection tanks.           |
| 2.A |    | cription |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The structures must be maintained to meet     |
| 5.0 |    | Output   | RCRA and other state and federal              |
| 2.B |    |          | environmental regulatory requirements, JSC    |
|     |    |          | requirements, permit conditions and OHSA      |
|     |    |          | requirements, and in such a manner that daily |
|     |    |          | RCRA and other regulatory inspections can be  |
|     |    |          | safely conducted, waste can be collected,     |
|     |    |          | transferred or removed from the tanks, allows |
|     |    |          | for accumulated liquids to be detected and    |
|     |    |          | removed. Structures must be maintained to     |
|     |    |          | prevent rainwater or other water infiltration |
|     |    |          | into the vaults and are impervious and will   |
|     |    |          | prevent any liquids from leaching into the    |
|     |    |          | concrete or surrounding soil.                 |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Structure components include, but are not     |
| 5.0 |    | Co       | limited to, concrete walls, and floors,       |
| 2.C |    | mponents | chemical resistant coatings on walls and      |
|     |    |          | flooring, drain caps, gratings/coverings,     |
|     |    |          | roof, doors, locks, stairways, vents,         |
|     |    |          | ventilation fans, air vents, lighting, safety |
|     |    |          | bollards, tire stops, electrical components,  |
|     |    |          | warning signs, identification labels, safety  |
|     |    |          | showers and eyewash stations.                 |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | **C      |                                               |
| .03 | vi | ontainer |                                               |
|     | ro | Storage  |                                               |
|     | n. | Areas**  |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Areas used for the accumulation or storage of |
| 5.0 |    | Des      | containers holding wastes.                    |
| 3.A |    | cription |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The container storage areas must be           |
| 5.0 |    | Output   | maintained to allow for the safe receipt      |
| 3.B |    |          | inspection, accumulation, packaging and       |
|     |    |          | sampling, and transfer of waste containers    |
|     |    |          | and to comply with all environmental          |
|     |    |          | regulations, JSC requirements and permit      |
|     |    |          | conditions.                                   |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Components may include, but are not limited   |
| 5.0 |    | Co       | to: Bracing, roof, louvers, lighting,         |
| 3.C |    | mponents | forklift pathways, tie downs, fences, locks,  |
|     |    |          | gates, signs, audible telephone bells, safety |
|     |    |          | showers and eyewash stations.                 |
+-----+----+----------+-----------------------------------------------+
|     |    |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | **Con    |                                               |
| .04 | vi | tainment |                                               |
|     | ro | Berms**  |                                               |
|     | n. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Containment Berms are used to provide         |
| 5.0 |    | Des      | secondary or tertiary containment for areas   |
| 4.A |    | cription | storing or accumulating wastes in tanks or    |
|     |    |          | containers.                                   |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Containment structures shall be maintained in |
| 5.0 |    | Output   | a manner such that the structure will collect |
| 4.B |    |          | and hold any released liquids and any         |
|     |    |          | incidental rainwater and allow the            |
|     |    |          | accumulation of liquids to be detected and    |
|     |    |          | removed. The containment must be impervious   |
|     |    |          | and prevent any liquids from leaching into    |
|     |    |          | the concrete or surrounding soil. All         |
|     |    |          | gratings must be maintained to be rust free.  |
|     |    |          | Containment structures shall be maintained in |
|     |    |          | accordance with all RCRA and other state and  |
|     |    |          | federal environmental regulatory              |
|     |    |          | requirements, permit conditions, JSC          |
|     |    |          | requirements and OHSA requirements.           |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Containment structures include, but are not   |
| 5.0 |    | Co       | limited to, concrete (or other construction   |
| 4.C |    | mponents | materials) floors and sides, coatings or      |
|     |    |          | liners, drain caps, and gratings, safety      |
|     |    |          | showers and eyewash stations.                 |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | **Wa     |                                               |
| .05 | vi | stewater |                                               |
|     | ro | Impoun   |                                               |
|     | n. | dments** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Wastewater impoundments are in-ground         |
| 5.0 |    | Des      | imperviously lined concrete structures and    |
| 5.A |    | cription | all appurtenances used to collect process or  |
|     |    |          | storm water prior to discharge to the         |
|     |    |          | sanitary sewer and with the ability to        |
|     |    |          | provide aeration.                             |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Impoundments shall be maintained shall be     |
| 5.0 |    | Output   | maintained in accordance with all RCRA and    |
| 5.B |    |          | other state and federal environmental         |
|     |    |          | regulatory requirements, permit conditions,   |
|     |    |          | JSC requirements and OHSA requirements, and   |
|     |    |          | to retain all wastewaters that are pumped or  |
|     |    |          | gravity fed into them without leaking or      |
|     |    |          | overflowing. Aeration capability shall be     |
|     |    |          | continuously available in sufficient amounts  |
|     |    |          | to reduce organics to meet discharge limits.  |
|     |    |          | The pumps shall be maintained to pump         |
|     |    |          | wastewater to the sanitary sewer in order to  |
|     |    |          | prevent overflowing or exceeding operating    |
|     |    |          | levels as needed.                             |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The wastewater impoundments include, but are  |
| 5.0 |    | Co       | not limited to, the concrete structure,       |
| 5.C |    | mponents | liners, pumps, aerators, diffusers, blowers,  |
|     |    |          | piping, dewatering pumps and handrails,       |
|     |    |          | safety showers and eyewash stations.          |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | **Gro    |                                               |
| .06 | vi | undwater |                                               |
|     | ro | Tre      |                                               |
|     | n. | atment** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The system that provides the collection,      |
| 5.0 |    | Des      | treatment and disposition of contaminated     |
| 6.A |    | cription | groundwater.                                  |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The groundwater treatment system shall be     |
| 5.0 |    | Output   | maintained to allow for a continuous          |
| 6.B |    |          | operations that will provide draw down in the |
|     |    |          | contaminated zone, treat the collected        |
|     |    |          | groundwater to 1 ppb Freon 113, and to comply |
|     |    |          | with the applicable TNRCC Standard Exemption  |
|     |    |          | #68(e) 4 and shall be maintained in           |
|     |    |          | accordance with all RCRA and other state and  |
|     |    |          | federal environmental regulatory              |
|     |    |          | requirements, permit conditions, JSC          |
|     |    |          | requirements and OHSA requirements.           |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The groundwater treatment system includes,    |
| 5.0 |    | Co       | but is not limited to: the extraction wells;  |
| 6.C |    | mponents | submersible pumps, flow meters, sample ports, |
|     |    |          | electrical panels, piping and insulation;     |
|     |    |          | piping and insulation, the air stripping      |
|     |    |          | towers, air stripper packing, carbon          |
|     |    |          | adsorption units, pumps, strainers, valves,   |
|     |    |          | fan blowers, liquid probes, level indicators, |
|     |    |          | high level alarms/shut offs systems,          |
|     |    |          | three-way valves, tanks and all               |
|     |    |          | appurtenances, leak detection sight glass,    |
|     |    |          | catwalks, stairways, tank labels and          |
|     |    |          | identification labels, vents, stripper skid,  |
|     |    |          | sumps, pneumatic tank, electrical switches    |
|     |    |          | and panels, lighting; wet well, low           |
|     |    |          | level/pressure alarm, pressure switches,      |
|     |    |          | motors, covers; backflow preventers, warning  |
|     |    |          | lights, transformer and guide wires, system   |
|     |    |          | identification labels, safety showers and     |
|     |    |          | eyewash stations.                             |
+-----+----+----------+-----------------------------------------------+
| 1.5 | En | *        |                                               |
| .07 | vi | *Plating |                                               |
|     | ro | Waste    |                                               |
|     | n. | Pretre   |                                               |
|     |    | atment** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The system that provides for the collection,  |
| 5.0 |    | Des      | treatment and disposition of Preclean and     |
| 7.A |    | cription | plating type wastewaters.                     |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The treatment system shall be maintained to   |
| 5.0 |    | Output   | collect all wastewaters that are pumped to    |
| 7.B |    |          | and transferred to and from all tanks,        |
|     |    |          | modules and filter presses without overflows, |
|     |    |          | spill or leaks and must be available for use  |
|     |    |          | at all times. The system shall be maintained  |
|     |    |          | in accordance with all RCRA and other state   |
|     |    |          | and federal environmental regulatory          |
|     |    |          | requirements, permit conditions, JSC          |
|     |    |          | requirements and OHSA requirements. The       |
|     |    |          | system shall be maintained so that samples    |
|     |    |          | can be collected from all tanks as required   |
|     |    |          | by regulatory or \***JSC** requirements, and  |
|     |    |          | all collected wastes can be treated to meet   |
|     |    |          | the conditions of JSC's sewer ordinance and   |
|     |    |          | all State and Federal Clean Water Act         |
|     |    |          | regulations, RCRA and other state and federal |
|     |    |          | environmental regulatory requirements, permit |
|     |    |          | conditions, and OHSA requirements. All pH     |
|     |    |          | meters shall be maintained to continually and |
|     |    |          | accurately measure and record all pH levels.  |
|     |    |          | The membrane modules shall be maintained to   |
|     |    |          | provide optimum pressure and flow rates as    |
|     |    |          | identified in \*\***Memtek O&M Manual and     |
|     |    |          | \*\*Memtek Filter press O&M Manual**. All     |
|     |    |          | mixers shall be maintained to mix chemicals   |
|     |    |          | for treatment of wastewater at all times.     |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The treatment systems consists of tanks,      |
| 5.0 |    | Co       | pumps, mixers, dust collector, valves, level  |
| 7.C |    | mponents | controls, switches, filters, membranes        |
|     |    |          | modules, filterpress, filter cloths, filter   |
|     |    |          | bags, piping, pH probes and meters, ORP       |
|     |    |          | probes and meters, flow meters, instruments,  |
|     |    |          | metering pumps, regulators, alarms, lamps,    |
|     |    |          | relays, timers, probes, recorder, paper,      |
|     |    |          | sensors, gaskets, o-rings, batteries,         |
|     |    |          | strainers.                                    |
+-----+----+----------+-----------------------------------------------+
| 1.5 | E  | **Co     |                                               |
| .08 | nv | ntinuous |                                               |
|     | ir | E        |                                               |
|     | on | missions |                                               |
|     |    | M        |                                               |
|     |    | onitor** |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | The system that provides for the sampling,    |
| 5.0 |    | Des      | conditioning, analysis, and recording of      |
| 8.A |    | cription | emissions data from the B222-1 Nebraska       |
|     |    |          | boiler                                        |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | The system shall be maintained to allow for   |
| 5.0 |    | Output   | continuous operations to comply with TNRCC    |
| 8.B |    |          | Permit #C-19670 and other state and federal   |
|     |    |          | environmental regulatory requirements, permit |
|     |    |          | conditions, and JSC requirements.             |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The continuous emissions monitor includes,    |
| 5.0 |    | Co       | but is not limited to: dual redundant Nox     |
| 8.C |    | mponents | analyzers, oxygen (O2) analyzer, in-stack     |
|     |    |          | sample probes, sampling lines, ssample        |
|     |    |          | conditioning, pumps, filters, data            |
|     |    |          | acquisition system KVB Enertec NT-DAHS.       |
+-----+----+----------+-----------------------------------------------+

**1.6.0 Other Equipment**

+-----+----+----------+-----------------------------------------------+
| \#  | Sy | #        |                                               |
|     | st | # System |                                               |
|     | em |          |                                               |
|     | Ty |          |                                               |
|     | pe |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.6 | O  | ## E     |                                               |
| .01 | th | levators |                                               |
|     | er |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Electric/traction/hydraulic elevators are     |
| 6.0 |    | Des      | vertical transportation systems designed for  |
| 1.A |    | cription | the movement of personnel and freight between |
|     |    |          | the various floors, or working levels of      |
|     |    |          | multi-story buildings. The passenger/freight  |
|     |    |          | cars of electric/traction elevators are       |
|     |    |          | suspended by wire ropes, which pass over a    |
|     |    |          | powered sheave, and terminate at a set of     |
|     |    |          | counterweights. The prime mover, or drive     |
|     |    |          | machinery, is generally located near the top  |
|     |    |          | of the elevator car shaft, or hoist way. In   |
|     |    |          | short, electric/traction elevators lift and   |
|     |    |          | lower a car which is suspended in the hoist   |
|     |    |          | way. The passenger/freight cars of hydraulic  |
|     |    |          | elevators are affixed atop, and are raised    |
|     |    |          | and lowered by, a telescoping hydraulic       |
|     |    |          | cylinder. This cylinder moves up or down in   |
|     |    |          | proportion to the increase or decrease in the |
|     |    |          | oil pressure inside the cylinder. Increases   |
|     |    |          | in oil pressure result from an electric motor |
|     |    |          | driven pump forcing oil into the hydraulic    |
|     |    |          | jack, or cylinder, which is typically buried  |
|     |    |          | in the earth beneath the building's elevator  |
|     |    |          | pit. Decreases in oil pressure result from    |
|     |    |          | the controlled opening of a valve, which      |
|     |    |          | allows the oil to return from the jack to the |
|     |    |          | supply reservoir. The hydraulic pumping       |
|     |    |          | assembly is generally located in a machine    |
|     |    |          | room near the elevator pit or hoist way. In   |
|     |    |          | short, hydraulic elevators move a car by      |
|     |    |          | pushing it up through the hoist way. A        |
|     |    |          | dumbwaiter is defined as a hoisting and       |
|     |    |          | lowering mechanism with a car of limited      |
|     |    |          | capacity and size which moves in guides in a  |
|     |    |          | vertical direction and is used exclusively    |
|     |    |          | for the transport of materials between        |
|     |    |          | floors, or levels of a building. Dumbwaiters  |
|     |    |          | shall never be utilized for the movement of   |
|     |    |          | personnel.                                    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | All elevators/dumbwaiters must safely operate |
| 6.0 |    | Output   | and perform per the manufacturer's design     |
| 1.B |    |          | criteria, and shall be maintained in strict   |
|     |    |          | compliance with all pertinent rules and       |
|     |    |          | regulations, as detailed in the most current  |
|     |    |          | edition of the Safety Code for Elevators and  |
|     |    |          | Escalators (ANSI/ASME A17.1). NASA shall      |
|     |    |          | verify such compliance through periodic       |
|     |    |          | safety inspections, which shall be conducted  |
|     |    |          | by certified inspectors, independently        |
|     |    |          | contracted by NASA, utilizing The American    |
|     |    |          | National Standard Practice for the Inspection |
|     |    |          | of Elevators, Escalators, and Moving Walks    |
|     |    |          | Inspector's Manual (ANSI A17.2) as the basic  |
|     |    |          | reference for said inspections. Any anomalies |
|     |    |          | or code violations, noted as a result of      |
|     |    |          | these inspections, shall be immediately       |
|     |    |          | corrected under this COSS contract, unless    |
|     |    |          | specifically waived, in writing, by the       |
|     |    |          | Contracting Officer.                          |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Components for which this contract assumes    |
| 6.0 |    | Co       | responsibility shall include, but shall not   |
| 1.C |    | mponents | be limited to, buffers, car enclosures,       |
|     |    |          | gates, doors, car frames and platforms,       |
|     |    |          | hydraulic pumping units, tanks, hydraulic     |
|     |    |          | cylinders and casings, sheaves,               |
|     |    |          | counterweights, drive machines, governors,    |
|     |    |          | operating devices, controls, safeties,        |
|     |    |          | suspension ropes, guide rails, hoist way      |
|     |    |          | guards and covers, indicator lights and       |
|     |    |          | signaling devices, machine rooms, pits,       |
|     |    |          | wiring, piping, and ducts, hoist way guards   |
|     |    |          | and covers, indicator lights and signaling    |
|     |    |          | devices, pits, wiring, piping, and ducts.     |
+-----+----+----------+-----------------------------------------------+
| 1.6 | O  | ##       |                                               |
| .02 | th |  Lifting |                                               |
|     | er |  Devices |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Generally, a system shall be defined as a     |
| 6.0 |    | Des      | crane if it has been so designed as to        |
| 2.A |    | cription | possess the capability not only to lift a     |
|     |    |          | load in the vertical axis, but to move that   |
|     |    |          | load along any horizontal axis, as well.      |
|     |    |          | Generally, a system shall be defined as a     |
|     |    |          | hoist if it has been so designed as to        |
|     |    |          | possess the capability to lift a load in the  |
|     |    |          | vertical axis only, but cannot move that load |
|     |    |          | along any horizontal axis. Generally, a       |
|     |    |          | system shall be defined as a switchgear hoist |
|     |    |          | if it has been designed and installed so as   |
|     |    |          | to perform the sole function of lifting       |
|     |    |          | components from panels, cabinets and other    |
|     |    |          | installations housing electrical switchgear.  |
|     |    |          | Generally, a system is defined as a lift if   |
|     |    |          | it has a manually, electrically,              |
|     |    |          | hydraulically, or pneumatically driven        |
|     |    |          | platform or cage which travels along a        |
|     |    |          | substantially vertical axis which is          |
|     |    |          | controlled by some mechanical means, such as  |
|     |    |          | rails, guides, telescoping frame, or similar. |
|     |    |          | It typically consists of a simple manual      |
|     |    |          | winch mounted to a frame. Such lifts may be   |
|     |    |          | designed, operated, and maintained as         |
|     |    |          | personnel lifts, as freight lifts, or as test |
|     |    |          | article positioners. They may also be         |
|     |    |          | designed to be portable, or may be more       |
|     |    |          | permanently affixed to a building or other    |
|     |    |          | structure.                                    |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | A crane, hoist, switchgear hoist or lift must |
| 6.0 |    | Output   | safely perform all functions for which it was |
| 2.B |    |          | designed, and operate within the performance  |
|     |    |          | and safety parameters and specifications      |
|     |    |          | established by the equipment manufacturer,    |
|     |    |          | OSHA and ANSI/ASME, as well as all criteria   |
|     |    |          | and regulations set forth in the NASA Safety  |
|     |    |          | Standard for Lifting Devices and Equipment    |
|     |    |          | (NSS/GO-1740.9B). Lifts designed and utilized |
|     |    |          | for the movement of personnel require a more  |
|     |    |          | stringent level of maintenance than do other  |
|     |    |          | types of lifts. Cranes, hoists, switchgear    |
|     |    |          | hoists and lifts must be maintained, tested,  |
|     |    |          | and certified in a manner consistent with     |
|     |    |          | general guidelines established by the         |
|     |    |          | manufacturer, as well as those outlined in    |
|     |    |          | NSS/GO-1740.9B, which shall maintain          |
|     |    |          | precedence over all other governing criteria, |
|     |    |          | both expressed and implied.                   |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | Crane. Hoist, switchgear hoist and lift       |
| 6.0 |    | Co       | designs vary significantly according to       |
| 2.C |    | mponents | location and application. Component           |
|     |    |          | definition shall be generally described as,   |
|     |    |          | but shall not be limited to, any or all of    |
|     |    |          | the following system elements: (1) Cranes -   |
|     |    |          | hooks, blocks, wire ropes or chains, sheaves, |
|     |    |          | lifting drive systems, braking systems,       |
|     |    |          | trolleys, trolley drive systems, bridge       |
|     |    |          | structures, tracks and rails, motors,         |
|     |    |          | reduction gears, electrical bus tracks and    |
|     |    |          | pickup shoes, pneumatic motors, air supplies, |
|     |    |          | control systems, limit switches and safeties, |
|     |    |          | and any other ancillary elements associated   |
|     |    |          | with a crane, its supporting structure, or    |
|     |    |          | its power supply; (2) hoists - hooks, blocks, |
|     |    |          | wire ropes or chains, sheaves, lifting drive  |
|     |    |          | systems, braking systems, motors, reduction   |
|     |    |          | gears, pneumatic motors, air supplies,        |
|     |    |          | control systems, limit switches and safeties, |
|     |    |          | and any other ancillary elements associated   |
|     |    |          | with a hoist, its supporting structure, or    |
|     |    |          | its power supply; (3) switchgear hoists -     |
|     |    |          | hooks, blocks, wire ropes or chains, sheaves, |
|     |    |          | lifting drive systems, reduction gears,       |
|     |    |          | safeties, frames, and any other ancillary     |
|     |    |          | elements associated with a lifting device or  |
|     |    |          | its supporting structure; and (4) lifts -     |
|     |    |          | wire ropes, sheaves, lifting drive systems,   |
|     |    |          | braking systems, hydraulic pumps and motors,  |
|     |    |          | pneumatic and hydraulic cylinders, electric   |
|     |    |          | motors, reduction gears, pneumatic motors,    |
|     |    |          | air supplies, control systems, limit switches |
|     |    |          | and safeties, and any other ancillary         |
|     |    |          | elements associated with a particular lift,   |
|     |    |          | its supporting structure, or its power        |
|     |    |          | supply.                                       |
+-----+----+----------+-----------------------------------------------+

**1.7.0 User Equipment**

+-----+----+----------+-----------------------------------------------+
| 1.7 | Us | # User E |                                               |
| .01 | er | quipment |                                               |
|     | Eq |          |                                               |
|     | ui |          |                                               |
|     | p. |          |                                               |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | A.       | Those pieces of specific equipment which      |
| 7.0 |    | Des      | fulfill a user requirement in the facility.   |
| 1.A |    | cription | This equipment supports test or other         |
|     |    |          | specialized task.                             |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | B.       | Each piece of equipment shall provide the     |
| 7.0 |    | Output   | designed function with the manufacturer's     |
| 1.B |    |          | specified output as defined by the user and   |
|     |    |          | applicable documentation. Availability of     |
|     |    |          | output shall be 100% during user defined      |
|     |    |          | period of operation or requirement.           |
+-----+----+----------+-----------------------------------------------+
| 1.  |    | C.       | The equipment identified by this line item    |
| 7.0 |    | Co       | shall include, but not be limited to vacuum   |
| 1.C |    | mponents | pumps, refrigeration equipment, chillers,     |
|     |    |          | boilers, film processors, printers, water     |
|     |    |          | pumps, cooling towers. The line item shall    |
|     |    |          | include the listed, numbered piece of         |
|     |    |          | equipment only and not be inclusive of        |
|     |    |          | peripheral or support piping, wiring,         |
|     |    |          | equipment or other ancillary hardware. Other  |
|     |    |          | components which might be included as parts   |
|     |    |          | of a particular system in which the User      |
|     |    |          | Equipment is installed, yet are not integral  |
|     |    |          | parts of the specific piece of equipment, are |
|     |    |          | not included in this definition. Such parts   |
|     |    |          | and components are "ancillary hardware."      |
+-----+----+----------+-----------------------------------------------+