Project Number: AW-2271

Contract Number: TW-0663

November 4, 1994

SPECIAL SPECIFICATION

SECTION 10801

TOILET ACCESSORIES

[Page]{.underline}

PART 1 - GENERAL

1.01 Description Of Work 2

1.02 References 2

1.03 Submittals 3

1.04 Quality Assurance 3

1.05 Project Conditions 3

PART 2 - PRODUCTS

2.01 Manufacturers 3

2.02 Materials 3

2.03 Paper Towel Dispensers 4

2.04 Toilet Tissue Dispensers 4

2.05 Waste Receptacles 5

2.06 Combination Towel Dispenser/Waste Receptacle Units 5

2.07 Grab Bars 5

2.08 Sanitary Napkin Vendors 5

2.09 Sanitary Napkin Disposal Units 5

2.10 Soap Dispensers 6

2.11 Seat Cover Dispensers 6

2.12 Fabrication 6

PART 3 - EXECUTION

3.01 Installation 6

3.02 Adjusting And Cleaning 6

3.03 Toilet Accessories Schedule 7

SPECIAL SPECIFICATION

SECTION 10801

TOILET ACCESSORIES

# PART 1 - GENERAL

## 1.01 [DESCRIPTION OF WORK]{.underline}

A. [Toilet accessory items]{.underline} included in this section:

Paper towel dispenser

Toilet tissue dispenser

Waste receptacle

Combination towel dispenser/waste receptacle unit

Grab bars

Sanitary napkin vendor

Sanitary napkin disposal unit

Soap dispenser

Seat cover dispenser

B. [Mounting heights]{.underline} are specified in the Toilet Accessory
Schedule or shown on interior elevations.

C. [Related Section]{.underline}: Mirrored glass is specified in
Division 8, Section \"Glass and Glazing\".

## 1.02 [references]{.underline}

A. [American Iron and Steel Institute (AISI)]{.underline}

B. [American Society of Testing and Materials (ASTM)]{.underline}

A153 Specification for Zinc Coating (Hot-Dip) on Iron and Steel Hardware

> A366 Specification for Steel Sheet, Carbon, Cold-Rolled, Commercial
> Quality
>
> A527 Specification for Steel Sheet, Zinc-Coated (Galvanized) by the
> Hot-Dip Process, Commercial Quality
>
> B16 Specification for Free-Cutting Brass Rod, Bar, and Shapes for Use
> in Screw Machines
>
> B19 Specification for Cartridge Brass Sheet, Strip, Plate, Bar, and
> Disks (Blanks)
>
> B30 Specification for Copper-Base Alloys in Ingot Form
>
> B456 Specification for Electrodeposited Coatings of Copper Plus Nickel
> Plus Chromium and Nickel Plus Chromium

## 1.03 [SUBMITTALS]{.underline}

[Product Data]{.underline}: Submit product data for each toilet
accessory item shown on drawings or schedule, including details of
construction relative to materials, dimensions, gages, profiles, method
of mounting, specified options, and finishes.

## 

## 1.04 [QUALITY ASSURANCE]{.underline}

A. [Inserts and Anchorage]{.underline}: Furnish inserts and anchoring
devices as recommended by the manufacturer.

B. [Single-Source Responsibility]{.underline}: Provide products of same
manufacturer for each type of accessory unit and for units exposed to
view in same areas.

## 

## 1.05 [PROJECT CONDITIONS]{.underline}

[Coordination]{.underline}: Coordinate accessory locations,
installation, and sequencing with other work to avoid interference and
to assure proper installation, operation, adjustment, cleaning, and
servicing of toilet accessory items.

# PART 2 - PRODUCTS

## 2.01 [MANUFACTURERS]{.underline}

[Available Manufacturers]{.underline}: Subject to compliance with
requirements, manufacturers offering toilet accessories that may be
incorporated in the work include, but are not limited to, the following:

A & J Washroom Accessories

American Specialties, Inc.

Bobrick Washroom Equipment, Inc.

Bradley Corporation

## 

## 2.02 [MATERIALS]{.underline}

A. [Stainless Steel]{.underline}: AISI Type 302/304, with polished No. 4
finish, 0.034 inch (22 gage) minimum thickness, unless otherwise
indicated.

B. [Brass]{.underline}: Leaded and unleaded, flat products, ASTM B19;
rods, shapes, forgings, and flat products with finished edges, ASTM B16,
castings, ASTM B30.

C. [Sheet Steel]{.underline}: Cold-rolled, commercial quality ASTM A366,
0.040 inch (20 gage) minimum, unless otherwise indicated. Surface
preparation and metal pretreatment as required for applied finish.

D. [Galvanized Steel Sheet]{.underline}: ASTM A527, G60.

E. [Chromium Plating]{.underline}: Nickel and chromium electro-deposited
on base metal, ASTM B456, Type SC 2.

F. [Baked Enamel Finish]{.underline}: Factory-applied, gloss white,
baked acrylic enamel coating.

G. [Galvanized Steel Mounting Devices]{.underline}: ASTM A153, hot-dip
galvanized after fabrication.

H. [Fasteners]{.underline}: Screws, bolts, and other devices of same
material as accessory unit or of galvanized steel where concealed.

## 2.03 [PAPER TOWEL DISPENSERS]{.underline}

[Surface-Mounted Towel Dispensers]{.underline}: Fabricate of stainless
steel with hinged front equipped with tumbler lockset. Provide pierced
slots at sides as refill indicator.

[Capacity]{.underline}: Not less than either 300 C-fold or 500
multi-fold paper towels without need for special adapters.

## 2.04 [TOILET TISSUE DISPENSERS]{.underline}

A. [Roll-In-Reserve Dispenser]{.underline}: Fabricate of stainless steel
for mountings indicated below, sized to store and dispense either
4-1/2-inch (110 mm) or 5-inch (130 mm) diameter core tissue rolls, with
reserve roll placed in service by automatic release or by action of
manual release bar. Hinge front of unit with pivot hinge.

1\. [Mounting]{.underline}: Surface-mounted, concealed anchorage.

2\. [Mounting]{.underline}: Partition-mounted, designed to service two
adjacent toilet compartments, two rolls for each.

B. [Double-Roll Dispenser]{.underline}: Size to accommodate two separate
rolls of core-type tissue to 5-inch (130 mm) diameter.

[Mounting]{.underline}: Surface-mounted, concealed anchorage.

## 2.05 [WASTE RECEPTACLES]{.underline}

[Open-Top, Semi-Recessed Waste Receptacle]{.underline}: Fabricate of
stainless steel with seamless exposed flange, removable receptacle with
seamless exposed walls, 4-inch (100 mm) projection from wall surface and
hemmed edges. Furnish heavy-duty vinyl removable liner, secured to
receptacle at not less than 4 points by means of grommets, stainless
steel hooks; 12-gallon (45 L) capacity.

## 

## 2.06 [COMBINATION TOWEL DISPENSER/WASTE RECEPTACLE UNITS]{.underline}

[Recessed Unit with Projecting Receptacle]{.underline}: Stainless steel
combination unit fabricated for nominal 4-inch (100 mm) wall depth and
with continuous seamless 1-inch (25 mm) wide wall flange. Provide towel
compartment in upper portion of unit, designed to dispense not less than
400 C-fold or 700 multi-fold paper towels; double-panel door with
continuous piano hinge. Waste receptacle in lower portion of unit
provided with reusable heavy-duty vinyl liner, minimum 12-gallon (45 L)
capacity.

## 

## 2.07 [GRAB BARS]{.underline}

[Stainless Steel Type]{.underline}: Provide grab bars with wall
thickness not less than 0.050 inch (18 gage) and as follows:

A. [Mounting]{.underline}: Concealed, manufacturer\'s standard flanges
and anchorages, adequate to support a 250 lb (113 kg) load applied in
any direction for a period of five minutes.

B. [Clearance]{.underline}: 1-1/2 inches (38 mm) clearance between wall
surface and inside face of bar.

C. [Gripping Surfaces]{.underline}: Smooth, satin finish.

D. [Heavy-Duty Size]{.underline}: Outside diameter of 1-1/2 inches (38
mm).

## 2.08 [SANITARY NAPKIN VENDORS]{.underline}

[General]{.underline}: Fabricate cabinet of stainless steel, not less
than 0.034 inch (22 gage), all welded construction. Provide door of
seamless stainless steel, minimum 0.050 inch (18 gage), with returned
edges. Provide identification reading \"Napkins\" and \"Tampons\"; brand
name advertising is not allowed. Capacity not less than 15 napkins and
72 tampons.

A. [Mounting]{.underline}: Fully recessed type for nominal 6-inch (150
mm) thick wall.

B. [Mounting]{.underline}: Semi-recessed type, with stainless steel
collar to extend unit from nominal 4-inch (100 mm) thick wall cavity.

C. [Mounting]{.underline}: Surface-mounted type for CMU wall.

D. [Operation]{.underline}: No coin (free) operation.

## 2.09 [SANITARY NAPKIN DISPOSAL UNITS]{.underline}

A. [Partition-Mounted Dual-Access Type]{.underline}: Fabricate of
stainless steel equipped with adjustable flanges to permit partition
mounting to service two toilet compartments. Provide self-closing door
and all-welded stainless steel receptacle removable from one side.

B. [Surface-Mounted Type]{.underline}: Fabricate of stainless steel with
seamless exposed walls, tightly self-closing top cover and locking
bottom panel with continuous stainless steel piano hinge.

## 2.10 [SOAP DISPENSERS]{.underline}

[Liquid Soap Dispenser, Wall-Mounted]{.underline}: Furnished by Sandia
National Laboratories (SNL).

## 2.11 [SEAT COVER DISPENSERS]{.underline} 

A. [Surface-Mounted Type]{.underline}: Fabricate of stainless steel with
concealed opening at bottom for filling; capacity not less than 250 seat
covers.

B. [Partition-Mounted, Dual-Access Type]{.underline}: Fabricate of
stainless steel and provide adjustable 1-inch (25 mm) wide seamless wall
flanges for installation in cutout in toilet partition to service two
compartments. Provide hinged access door for servicing from one side.

## 2.12 [FABRICATION]{.underline}

A. [Surface-Mounted Toilet Accessories]{.underline}: Except where
otherwise indicated, fabricate units with tight seams and joints,
exposed edges rolled. Hang doors or access panels with continuous
stainless steel piano hinge. Provide concealed anchorage wherever
possible.

B. [Recessed Toilet Accessories]{.underline}: Except where otherwise
indicated, fabricate units of all welded construction, without mitered
corners. Hang doors or access panels with full-length stainless steel
piano hinge. Provide anchorage that is fully concealed when unit is
closed.

# PART 3 - EXECUTION

## 3.01 [INSTALLATION]{.underline}

A. [Install toilet accessory units]{.underline} in accordance with
manufacturers\' instructions, using fasteners appropriate to substrate
and recommended by manufacturer of unit. Install units plumb and level,
firmly anchored in locations and at heights indicated.

B. [Secure mirrors to walls]{.underline} in concealed, tamperproof
manner with special hangers, toggle bolts, or screws. Set units plumb,
level, and square at locations indicated, in accordance with
manufacturer\'s instructions for type of substrate involved.

C. [Install]{.underline} SNL-furnished soap dispensers in locations
indicated on drawings.

## 3.02 [ADJUSTING AND CLEANING]{.underline}

A. [Adjust toilet accessories]{.underline} for proper operation and
verify that mechanisms function smoothly. Replace damaged or defective
items.

B. [Clean and polish]{.underline} all exposed surfaces in strict
accordance with manufacturer\'s recommendations after removing temporary
labels and protective coatings.

## 3.03 [toilet accessories schedule]{.underline}

A. [Women\'s Toilet]{.underline}

1\. Toilet tissue dispenser Dual access (2 units) 1 each

Surface mounted 1 each

2\. Combination towel diespnser/waste receptacle unit 1 each

3\. Grab bars (4\'-0\") 2 each

4\. Sanitary napkin vendor 1 each

5\. Sanitary napkin disposal unit Dual access (2 units) 1 each

Surface mounted 1 each

6\. Soap dispenser 2 each

7\. Seat cover dispenser Dual access (2 units) 1 each

Surface mounted 1 each

8\. Stainless steel framed mirror units 1 each

B. [Men\'s Toilet]{.underline}

1\. Toilet tissue dispenser Dual access (2 units) 1 each

Surface mounted 1 each

2\. Combination towel diespnser/waste receptacle unit 1 each

3\. Grab bars (4\'-0\") 2 each

4\. Soap dispenser 2 each

5\. Seat cover dispenser Dual access (2 units) 1 each

Surface mounted 1 each

6\. Stainless steel framed mirror units 1 each

7\. 12\" x 18\" Stainless steel framed mirror unit 1 each

END OF SECTION