> ![](media/image1.png){width="2.7506944444444446in"
> height="0.42986111111111114in"}
>
> Operated for the U.S. Department of Energy by
>
> **Sandia Corporation**
>
> Albuquerque, New Mexico 87185-0942

*date:* Oct 24, 2000

*to:* Center 7800

*from:* Paul Duran, MS-0946 (7821)

Electrical Standards Committee Chair

*subject:* Revised Standard Drawings

A.  The following fire alarm standard drawings have been updated per
    recommendations from Paul Smith (Fire Alarm System Specialist).

**[FA001STD - F.A. Battery Calculations & Specifications]{.underline}**

At note directing designers to the Fire Alarm Calculator that has been
developed in MS Excel that simplifies voltage drop and DGP power
calculations.

**[FA502STD - Detectors, Sensors and Strobe Details]{.underline}**

1.  Revised the duct detector details on drawing to delete the outdated
    model and include wiring details for the latest duct detector model
    being used.

```{=html}
<!-- -->
```
1.  Included the wiring details for the Honeywell smoke detector base
    that has relay applications built in. This base is only used if the
    smoke detector is being used in shunt-trip, fan shutdown, or other
    relay applications.

2.  Revised the part numbers for the duct detector tubes, Remote Test
    Station, and Remote Annunciator.

**[FA503STD - Wheelock and Terminal Cabinet Detail]{.underline}**

Revised fire alarm terminal cabinet detail to require painting enclosure
red to identify the cabinet as part of the fire alarm system.

**[FA504STD - FS90 DGP Details - 1 Motherboard]{.underline}**

1.  Changed initiation device wire type from TFN to TFFN.

2.  Changed wire type in Key Note 7 from THHN to THWN for fire alarm
    wiring installed in underground raceways.

3.  Revised DGP detail to indicate installation of two (2) static
    modules on terminal strip \"TB8\".

**[FA505STD - FS90 DGP Details - 2 Motherboards]{.underline}**

1.  Changed initiation device wire type from TFN to TFFN.

2.  Changed wire type in Key Note 7 from THHN to THWN for fire alarm
    wiring installed in underground raceways.

3.  Revised DGP detail to indicate installation of two (2) static
    modules on terminal strip \"TB8\".

4.  Revised DGP detail to show installation of Battery Supervision
    Module on the bottom motherboard. For proper battery supervision, a
    Battery Supervision Module is required for each motherboard power
    supply.

**[FA601STD - Equipment Schedule]{.underline}**

1.  Added Equipment Symbols 55 - 60 to include the following FS90 DGP
    components: \"AA\" boards, card retainers, legend cards, and reset
    relays.

2.  Clarified that 2 Static Modules are required for each \"LD\" board.

3.  Revised Equipment Symbol 40 to delete the combination smoke/heat
    photoelectric detector and replace with the smoke detector base with
    built in relays for relay applications.

4.  Revised Equipment Symbol 43 to indicate the latest model Honeywell
    duct detector in use.

5.  Updated the part numbers for Equipment Symbols 44, 51, and 52.

6.  Added Equipment Symbols 53 and 54 for the FS90 1-Up enclosures to be
    used for 120 VAC control wiring at the DGP and for housing the 24
    VDC power supply used to power duct detectors.

7.  Revised DGP detail to indicate installation of two (2) static
    modules on terminal strip \"TB8\".

```{=html}
<!-- -->
```
B.  Electrical Standards Symbols List, drawing 73740E2 has been revised
    to show:

    1.  New exit lights

    2.  Modifications that interface with the Standard Specification
        16501, Fluorescent Luminaries.

C.  Personnel Access Control Standard Drawings

    1.  Per Sandia National Laboratories Electronic Security Systems,
        Organization 7133 the Hirsch Access Control System has been
        replaced with an Infographics Access Control System.
        Organization 7133 is in the process of developing standard
        drawings. In the interim designers should contact Organization
        7133 for design details.

    2.  The following Hirsch Personnel Access Control standard drawings
        should be used for maintenance only: 101417E1, E2, and E4
        through E9.

D.  Exterior Lighting Standard Drawings

    Added standard drawing ES515STD - Exterior Lighting Details and
    drawing ES601STD - Exterior Lighting Equipment Schedule.

***Note: The revised index sheets are not issued at this time. It is
planned to issue them in November when all the standard drawings will be
converted to the Uniform Drawing System numbering system that was
developed by the Construction Specification Institute.***

Please incorporate these revised standard drawings into the system ASAP
for use in future project.

Credits:

[Fire Alarm Modifications]{.underline}

Paul Smith, 7821

Michelle Appleman, 7821

[Lighting Modifications]{.underline}

Gary Hoe, 7861

Lee Hall, 7821

Michelle Appleman, 7821

[Exterior Lighting]{.underline}

Rick Ramirez, 7821

Michelle Appleman, 7821

Copy to:

MS-0942 Nenita U. Estes, 7926