**DRAFT**

TWIN PEAKS (GOAT MTN)

COMMUNICATIONS SITE MANAGEMENT PLAN

LAS CRUCES DISTRICT OFFICE

Prepared by the United States Bureau of Land Management

Las Cruces District Office

**State of New Mexico**

**Approved by:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_**

**District Manager Date**

**TWIN PEAKS (GOAT MTN) COMMUNICATIONS SITE PLAN**

[[I.]{.smallcaps} [INTRODUCTION 3]{.smallcaps}](#introduction)

[A. Terms and Definitions 3](#terms-and-definitions)

[B. Purpose 4](#purpose)

[C. Site Description 5](#site-description)

[D. Area Served 5](#area-served)

[E. Access 5](#access)

[F. Site History and Development 5](#site-history-and-development)

[G. Goals and Objectives of Site Management Plan
6](#goals-and-objectives-of-site-management-plan)

[II. AUTHORITY AND DIRECTION 6](#authority-and-direction)

[A. Authority 7](#authority)

[B. Relationship to Communications Site Leases/ROW Grants
7](#relationship-to-communications-site-leasesrow-grants)

[III. GENERAL RESPONSIBILITIES 7](#general-responsibilities)

[A. The BLM 7](#the-blm-retains-the-responsibility-for)

[B. Facility Owners and Facility Managers
8](#facility-owners-and-facility-managers-or-their-designated-representatives-are-responsible-for)

[C. FCC and NTIA/IRAC 9](#fcc-and-ntiairac-are-responsible-for)

[IV. AUTHORIZED USES AND USERS WITHIN A FACILITY
9](#authorized-uses-and-users-within-a-facility)

[A. Use by Multiple Users 9](#a.-use-by-multiple-users)

[V. FEES 10](#fees)

[VI. General Operation and Maintenance Direction
10](#general-operation-and-maintenance-direction)

[A. Unique Resource Considerations at this Communication Site
10](#unique-resource-considerations-at-this-communication-site)

[B. Wiring and Grounding 10](#wiring-and-grounding)

[C. Communications Equipment 11](#communications-equipment)

[D. Cables and Transmission Line (Wave Guides)
14](#cables-and-transmission-line-wave-guides)

[E. Radiation 14](#radiation)

[F. Utilities-Availability of and Requirements for:
15](#utilities-availability-of-and-requirements-for)

[G. Sanitary Facilities 16](#sanitary-facilities)

[H. Security and Law Enforcement 16](#security-and-law-enforcement)

[I. Site Maintenance 16](#site-maintenance)

[J. Inspections 17](#inspections)

[K. Fire Prevention and Hazard Reduction Requirements
17](#fire-prevention-and-hazard-reduction-requirements)

[L. Access Maintenance and Restrictions
18](#access-maintenance-and-restrictions)

[VII. CONDITIONS FOR CONSTRUCTION, MODIFICATIONS OR EXPANSION
18](#conditions-for-construction-modifications-or-expansion)

[A. New Facility Owner Responsibilities
19](#new-facility-owner-responsibilities)

[B. Construction Methods and Resource Protection
20](#construction-methods-and-resource-protection)

[C. Construction Inspection 21](#construction-inspection)

[D. New or Remodeled/Expanded Buildings
21](#new-or-remodeledexpanded-buildings)

[E. New or Remodeled/Expanded Towers
22](#new-or-remodeledexpanded-towers)

[VIII. SITE ASSOCIATION/ADVISORY GROUP
22](#site-associationadvisory-group)

[IX. APPENDICIES 23](#appendicies)

[A. Site Map 23](#site-map)

[B. Authorized Facilities 23](#authorized-facilities)

[C. Site Photographs 23](#site-photographs)

[D. Inspection Checklist 23](#inspection-checklist)

[[\_Toc121556528]{.smallcaps}](#appendix-a)

+-----------------------------------------------------------------------+
| # INTRODUCTION                                                        |
+-----------------------------------------------------------------------+

## Terms and Definitions

The terms used in this communications site management plan conform to
the definitions listed in the April 22, 2005, Federal Register notice
"Rights-of-Way, Principles and Procedures: Rights-of-Way Under the
Federal Land Policy and Management Act and the Mineral Leasing Act"

and clarifications provided in Bureau of Land Management(BLM) Handbook
2860-1 and the United States Code of Federal Regulations (CFR) 43 CFR
2800. In the event of a conflict, between the plan and these sources,
the Federal Register notice and the BLM Handbook will govern.

The words "lease" and "lessee" as used in this plan refer to the
relationship between the BLM and the communications use lease lessee, or
right-of-way (ROW) holder. The words "customer" and "tenant" refer to
the relationship between the lessee or holder and the occupants in the
lessee's facilities.

LEASE OR ROW -- A use authorization issued to a communication Facility
Owner or Facility Manager allowing for the use of public land to
construct and or operate a communications facility and, unless
specifically prohibited, to sublease to occupants in that facility.

LESSEE, OR LEASE OR ROW HOLDER -- Facility Owner or Facility Manager

CUSTOMER -- Entities that pay a facility owner, facility manager or
tenant for communications services and are not re-selling or
broadcasting communications services to others

TENANT -- A communications user who rents space in a communications
facility and operates communication equipment for the purpose of
re-selling or broadcasting communications services to others for profit.

COMMUNICATIONS SITE -- An area of BLM-managed public land designated
through the land and resource management planning process as being used
or is suitable for communications uses. A communications site may be
limited to a single communications facility, but most often encompasses
more than one. Each site is identified by name; usually a local
prominent landmark, such as Twin Peaks (Goat Mtn) Communications Site.

FACILITY MANAGER -- The holder of a BLM communications use authorization
who leases space for other communication users. A facility manager does
not directly provide communications services to third parties.

FACILITY OWNER -- Individuals, commercial entities, organizations, or
agencies, that own a communications facility on Federal land own and
operate their own communications equipment; and hold a communications
use authorization.

NON-BROADCAST -- This category includes Commercial Mobile Radio Service
(CMRS), Facility Managers, Cellular Telephone, Private Mobile Radio
Service (PMRS), Microwave, Local Exchange Network, and Passive
Reflector.

BROADCAST -- This category includes Television Broadcast, AM and FM
Radio Broadcast, Cable Television, Broadcast Translator, Low Power
Television, and Low Power FM Radio.

RIGHT-OF-WAY (ROW) -- The public land authorized to be used or occupied
pursuant to a ROW grant.

RIGHT-OF-WAY GRANT -- A use authorization issued pursuant to Title V of
the Federal Land Policy and Management Act of October 21, 1976 (43
U.S.C. 1701 *et seq.*) or issued on or before October 21, 1976, pursuant
to then existing statutory authority, authorizing the use of a ROW over,
upon, under or through public land for construction, operation,
maintenance and termination of a project.

HOLDER -- Any applicant who has received a ROW grant, lease or temporary
use permit.

USERS -- All ROW and lease holders, lessees, customers, and tenants that
own or operate a facility or communication equipment at the
communication site.

## Purpose

This plan will be used by BLM officials administering communications
uses at Twin Peaks (Goat Mtn) existing lessees, holders, and applicants
desiring a lease, grant, or an amendment to an existing lease or ROW
grant. The plan will be kept updated by amending pages or sections of
the plan rather than issuing a revised edition of the plan. When a
revision is necessary, a letter from the Las Cruces District Office
enclosing a copy of revised pages or sections will amend the plan. The
amendments will be consecutively numbered.

Overall management direction for the administration of communications
sites is outlined in the CFR and the BLM Handbook and applicable BLM
Instructional Memoranda. Specific direction for site management planning
on designated communications sites is contained in BLM Handbook 2860-1.
Primary regulations and policy pertaining to issuance of ROW
authorizations by the BLM are found in Title 43 CFR Sections 2801- 2803
and BLM Handbook 2860-1.

[The previous communications site plan was approved December 1988. The
1988 plan designated this site for the protection of public health and
safety services. Since 1988, other non-public service]{.mark} and
[broadcast uses have entered the site in newer facilities and/or as
tenants and customers in existing facilities. The senior use at this
site is the two-way radio for public health and safety in the Dona Ana
facility. Physical construction space is fully occupied at this
site.]{.mark}

This Site Plan updates the management direction, adds current policy,
updates technical standards for better management of the Twin Peaks
(Goat Mtn) Communications Site. This plan governs development and
management of Twin Peaks (Goat Mtn) and will be modified in the future
as needs and conditions warrant. Any future such uses must be designed,
installed, operated, and maintained to be compatible and not interfere
with the senior uses as defined in Appendix B, Lessee Facility Table.
This site-specific plan is administrative in nature and is Categorically
Excluded from further review under the National Environmental Policy Act
(NEPA) (516.DM2, Appendix 1, 1.7). Any additional development of the
site will be addressed in a site-specific NEPA document.

## Site Description

The Twin Peaks (Goat Mtn) site is located east of Las Cruces, New Mexico
on lands administered by the Las Cruces District Office and the site is
specifically located in portions of Section 8, T. 22 S., R. 2 E., NMPM,
at approximately 32º 24' 17" North Latitude and 106º 45' 39" West
Longitude. The elevation at the Twin Peaks (Goat Mtn) Communications
Site is approximately 4,815 feet above mean sea level. A site map is
provided as Appendix A.

## Area Served

This site is within the Las Cruces Ranally Metro Area (RMA). The
population of this RMA is currently 113,000 which is Zone 6 on the fee
schedule). These zones may be adjusted in the future as populations
change. This information will be used for future rental determination.

## Access

Access to Twin Peaks (Goat Mtn) is from US 70 northeast of Las Cruces
and then to the frontage road and north on Emerald Street then north and
west on a gravel road to the locked gate on the Edginton Property thence
1,440' through this private land to public lands and then up a concrete
surfaced road to the top of the mountain. Four wheeled drive vehicles
are recommended to the main site and required to the west site.
Individual leaseholder and user agreements with the Edginton's are
required for access across their property.

## Site History and Development

In 1966, a right-of-way grant NM427 was issued to Dona Ana County. The
original grant was for exclusive use. Dona Ana County agreed to
relinquish this exclusive use when a Communication Site plan was
prepared in 1988 that designated the site for public health and safety
and limited ERP to 100 watts. High power broadcast uses were prohibited
at this site in the 1988 plan. According to the 1988 plan,. Additional
low power uses and facilities were authorized. The second facility now
owned by American Tower was authorized in 1988. In 1996, Crown
Communications was authorized to construct a facility which is now
utilized by Verizon Wireless for cellular use. Since 1997, the policy
has been to issue communications use leases to the owners of facilities.
Crown Communications owns the tower, but Verizon owns the building so
will be issued a separate lease.

The Subcarrier facility was authorized in 1997 and housed community
repeater and paging companies. In 2000, Sierra Industries, now
Richardson Communications Corp entered this facility as a tenant and was
reported as a CMRS use. This is a full power 1KM ERP FM station. Noise
floor and reduced receiver sensitivity has resulted in portions of the
Dona Ana County moving two-way radios to Tortugas Mtn. This facility
also houses cellular equipment.

In 1999, a new facility was authorized on the west point of twin peaks.
This new facility lease was issued to Las Cruces Radio Center. The final
facility was authorized in 2000 and sits between Dona Ana County and
American Tower facilities. This facility houses various CMRS users.

## Goals and Objectives of Site Management Plan

1\. Manage the [Twin Peaks (Goat Mtn)]{.mark} Site [as a joint
low-power]{.mark} two-way radio and microwave for [public health]{.mark}
and [safety uses and limited to the existing broadcast uses as long as
they can demonstrate that they and all other uses can be designed,
operated and maintained so as not to materially or electronically
interfere with the senior uses.]{.mark}

2\. [Grandfather the commercial CMRS, Cellular, and WISP uses which are
not specifically operating as public health and safety uses as long as
they are designed, operated and maintained to protect the senior uses
which are public health and safety.]{.mark}

3\. Manage communication equipment on the Twin Peaks (Goat Mtn) Site to
maintain the radio frequency (RF) hazard to be within the Public
Standard as defined by the Federal Communications Commission (FCC).

4\. Systematically develop the site to maximize the number of compatible
uses while ensuring safety and protection of resources. Development of
new towers or buildings within each of the authorized owner's facilities
will be authorized only after their respective tower or building space
area is filled to near capacity.

5\. Present a program for future growth, development and operation
within the site

6\. Help fulfill the public need for adequate communications sites.

7\. Protect the interests of holders, lessees, tenants and customers, by
preserving a safe and electronically "clean" environment.

8\. Encourage the efficient development and use of space and facilities
within the designated site, subject to the BLM's goal to provide the
best possible public service at reasonable cost.

9\. Achieve visual quality objectives by requiring design standards that
are unobtrusive and utilizing earth tone colors and non-reflective
surface material and stringent site maintenance requirements.

10\. Describe the BLM's policy for road maintenance.

11\. Create a Twin Peaks User's Association, which would provide
recommendations to the BLM authorized officer, coordinate and resolve
interference and/or noise floor concerns, and mutually participate in a
road use agreement.

12\. Develop new facilities only after the appropriate site-specific
NEPA analysis and coordination with current lease or ROW holders and
users. This future development must be consistent with the Las Cruces
District Office RMP orCalifornia Desert Conservation Management Plan.

13\. Amend this Communications Site Plan as necessary to be consistent
with future amendments to the Tri-County RMP.

+-----------------------------------------------------------------------+
| # AUTHORITY AND DIRECTION                                             |
+-----------------------------------------------------------------------+

## Authority

BLM's authority to authorize communications uses on public land
(administered by the BLM) is granted by the Federal Land Policy and
Management Act of 1976, 90 Stat. 2776 (43 U.S. C. 1761-1771) and is
reflected in Title 43, Code of Federal Regulations (CFR), Sections 2801-
2803 and BLM Washington Office Information Bulletin 98-23.

BLM's authority for communications site management planning is contained
in BLM Handbook 2801-1, Plan of Development. Direction on, and policy
for, communication use authorizations is contained in BLM Manual Section
2860.

Authority for the issuance of authorizations and/or licenses for the
transmission and reception of electronic radiation for communication
purposes is granted by Congress and administered by the FCC and/or the
National Telecommunication and Information Administration -- Interagency
Radio Advisory Committee (NTIA/IRAC).

## Relationship to Communications Site Leases/ROW Grants 

This site plan will be incorporated into all leases and ROW grants
issued (now and/or in the future) for this communications site and must
be used in conjunction with the granting authorization. **PROVISIONS OF
THE SITE PLAN ARE ENFORCED THROUGH THE GRANTING AUTHORIZATION.** Each
lessee or holder is expected to include the requirements of the
authorization and the site plan into any documents, which describe the
business relationship between the lessee or holder's and their tenants
and customers. The lessee or holder is responsible for enforcing those
provisions.

+-----------------------------------------------------------------------+
| # GENERAL RESPONSIBILITIES                                            |
+-----------------------------------------------------------------------+

## The BLM retains the responsibility for:

Issuing and amending authorizing instruments to Facility Owners and
Facility Managers, only for the areas actually occupied by the
authorized improvements. Granting occupancy and use of public land rests
exclusively with the BLM. The issuance of a FCC license (authorization),
or frequency assignment, does not authorize occupancy of public land.

1.  Approving any new facility(ies) at the site.

2.  Approving amendments to leases and ROW grants to qualified buyers of
    facilities on the site.

3.  Approving any modifications to existing facilities including the
    tower, antenna, equipment or building. Also, approving any changes
    to the existing FCC licensed uses, prior to the submission of an
    application to the FCC.

4.  Frequency Management. The BLM is not normally responsible for the
    resolution of conflicts when the licensees or agencies are operating
    within the limits of the FCC and NTIA/IRAC authorizations.

## Facility Owners and Facility Managers (or their designated representatives) are responsible for:

1.  Complying with their use authorization and all provisions of this
    site plan.

2.  Ensuring that all new facilities, expansions, or improvements are
    consistent with the Las Cruces District Office Planning Documents;
    any environmental document(s)/decisions for the site; and, this site
    plan.

3.  Ensuring facilities/equipment not complying with Federal/State/local
    laws/regulations/ ordinances will be removed or modified within one
    year of the approval of this plan. Any modification needs
    pre-approval by the BLM.

4.  Keeping all facilities within the established limits of their
    authorized area.

5.  Providing the BLM with the name, address and phone number for a
    local contact person. The Facility Owner and Facility Manager and
    the contact person may be the same individual. The contact person
    will be available for emergencies and will have the authority to
    make decisions about construction issues, facility maintenance and
    all equipment within the facility.

6.  Adhering to the Facility Owner/Facility Manager Lease/ROW as
    follows:

    a.  Facility Owners and Facility Managers with Communications Use
        Leases and ROW grants are authorized to rent building/tower
        space to tenants and/or customers without prior written approval
        from the BLM.

    b.  Tenants and/or customers may not construct their own equipment
        shelter (building, shelter or cabinet) or antenna support
        structure (tower or mast). The facility owner must own all
        communication shelters and towers under their lease or grant. If
        that is not possible, a separate SF-299 application,
        cost-recovery deposit, analysis, and authorization are required.
        This will also result in the use being a tenant/customer of the
        original lease/ROW in addition to being a separate facility for
        billing purposes.

    c.  Tenants and/or customers using a facility covered by a Facility
        lease/ROW will not have separate BLM leases/ROWs to authorize
        the use except in situations where regulations or policy require
        them.

    d.  Facility Owners and Facility Managers are responsible for
        complying with the terms and conditions of the facility
        lease/ROW. Facility Owners/Facility Managers are also
        responsible for ensuring that their tenants and customers are in
        compliance with the terms and conditions of the lease/ROW and
        applicable FCC or NTIA/IRAC license terms and conditions.

    e.  The Facility Owner and Facility Manager may not place any
        unreasonable restrictions nor any restriction restraining
        competition or trade practices on tenants and/or customers, or
        potential tenants and/or customers.

7.  Ensuring that all communications equipment is properly installed,
    operated, and maintained.

8.  Ensuring that all communication equipment meets American National
    Standards Institute (ANSI), FCC and BLM regulations, guidelines and
    standards concerning radiation limitations by:

    a.  Monitoring radiation levels at their facility and;

    b.  Immediately correcting any radiation levels that are, or could
        be a hazard to human health (FCC 47 CFR sections 1.1307(b),
        1.1310 and 2.1093) as defined in FCC Office of Engineering and
        Technology (OET) Bulletin 54, August 1999 and any amendments
        thereto).

9.  Providing a certified copy of all uses and the correct category of
    uses within the facility, along with the current phone numbers and
    addresses of all tenants and customers as of September 30th each
    year. This report is due by October 15th each year.

10. Keeping the premises around their buildings free of trash and
    debris.

11. Placing the BLM lease/ROW serial number on the door of their
    communications site building. The serial number must be on the tower
    if the tower is owned separately from the building.

12. Correcting all interference problems. The users are normally
    responsible for the resolution of conflicts when the licensees or
    agencies are operating within the limits of the FCC and NTIA/IRAC
    authorizations.

## FCC and NTIA/IRAC are responsible for:

Frequency Management. The FCC and NTIA/IRAC are not normally responsible
for the resolution of conflicts when the licensees or agencies are
operating within the limits of the authorizations.

+-----------------------------------------------------------------------+
| # AUTHORIZED USES AND USERS WITHIN A FACILITY                         |
+-----------------------------------------------------------------------+

##  {#section .unnumbered}

## A. Use by Multiple Users {#a.-use-by-multiple-users .unnumbered}

Multiple use of all facilities and improvements [will]{.underline}
[be]{.underline} required except where the facility owner is a
government agency. Site applicants will take the lead in this area and
design their proposals to accommodate multiple uses of facilities and
improvements. This includes multiple uses of buildings, towers, back-up
generators, grounding systems, fuel containers, access ways and parking
areas.

Due to the availability of building and tower space at the site, new
facilities, or major modifications to existing facilities will generally
not be approved until the empty space is utilized even if other users
are, or could be, competitors.

Facility Owners and Facility Managers are not required to lease facility
space to others if they can prove to the authorized BLM officer that:

1.  Space is not available;

2.  The use is incompatible with the existing facilities;

3.  Additional space is needed by the facility owner/manager;

4.  Additional users would violate system security needs; or,

5.  Potential interference is not resolvable.

+-----------------------------------------------------------------------+
| # FEES                                                                |
+-----------------------------------------------------------------------+

The BLM will charge Facility Owners and Facility Managers annual rental
fees based on the Fee Schedule for Communications Uses on Public Lands,
as adjusted annually. These fees will be fair market value for the use
of public land. The site is within the Las Cruces RMA. The Zone 6
population will be used for these calculations unless something else is
specifically agreed to in writing by the authorizing officer or until
populations change.

Fees that Facility Owners and Facility Managers may charge their tenants
and "customers" are to be:

> Reasonable (consistent with, and not in excess of, other fees for
> similar facilities) and commensurate with the uses and occupancy of
> the facilities and services provided to tenants and "customers".

+-----------------------------------------------------------------------+
| # General Operation and Maintenance Direction                         |
+-----------------------------------------------------------------------+

## Unique Resource Considerations at this Communication Site

> No unique resource considerations are currently identified in the
> current RMP. If they occur in the future, this plan will be amended to
> provide the appropriate coordination to minimize impacts to unique
> resources.

If any additional coordination measures are identified in the future
through the NEPA and or RMP process, the appropriate standards will be
amended to this plan.

## Wiring and Grounding 

> 1\. All equipment is to be installed within existing buildings and on
> equipment racks that are grounded and shielded. Grounding is to be
> installed in accordance with accepted standards.
>
> 2\. All electrical wiring and grounding must meet the "National
> Electrical Code" and applicable zoning codes. All permanent wiring
> shall be installed in metallic conduit. Surge protection shall be
> installed on all power distribution panels.
>
> 3\. Lightning protection "down" conductors installed upon
> communications towers shall be treated as "Transmission lines".
> Therefore, they shall have an insulating jacket. Periodic bonding of
> the down conductor to the tower (Galvanized) steel shall be made with
> proper bonding connectors that are tin plated or made of brass.
>
> 4\. Each building is to have its own separate grounding system for all
> users in that structure. Wherever practical, interconnection of
> individual grids and/or the simultaneous placement of a large sized
> copper ground wire with any new grounding systems that are buried on
> the site will be required.
>
> 5\. Site or facility grounding must be constructed of copper, with #2
> AWG or larger wire or 2" or larger solid copper strap, connected to an
> adequate site/facility ground electrode system. The site/facility
> ground electrode system shall be bonded to the power service entrance
> grounding electrode conductor. Guy wires should also be grounded using
> manufacturers approved methods to preclude bi-metallic junction and
> corrosion. All equipment on the site (buildings, towers, power units,
> transmitters, receivers, antennas, combiners, telephone systems, power
> cabinets, HVAC units, etc) must be connected to the site/facility
> ground by direct connection. Electrical system ground wiring is
> required for electrical ground fault protection and circuit breaker
> coordination. High power operations should use copper strap bonding in
> accordance with manufacturers specifications. The grounding systems
> shall comply with applicable laws, codes and in accordance with
> standard engineering practice. Below ground connections must use
> either an exothermic welding process (i.e. Cadweld, Thermoweld, etc.),
> copper wedge pressure devices (i.e. Ampact, Wrench-lock, etc.), or
> brazed copper connections in conjunction with a mechanical UL listed
> connector (to be used as a physical strength enhancement component).
> Brazing by itself is not an acceptable method of bonding below earth
> grade (buried).

## Communications Equipment 

[Equipment Ownership]{.underline}

All equipment shall be labeled with:

1.  The owner's name;

2.  Transmitter frequency(ies);

3.  A valid FCC, or IRAC, authorization;

4.  Transmitting power output(s); and

5.  A current 24-hour phone contact number.

[Transmitting Equipment]{.underline}

All transmitters will have protective devices (shields, filters,
isolation components), designed into or externally installed, to prevent
interference to other users. All transmitters shall be FCC type accepted
or meet type acceptance criteria.

Re-radiation of intercepted signals from any unprotected transmitter and
its associated antenna system will be prevented by the use of
appropriate filters (wide band and narrow band broadcast transmitters).

The direct radiation of out-of-band emissions (i.e. transmitter wideband
noise, spurious emissions, harmonics) will be reduced to a level such
that they may not be identified as a source of interference as defined
in the FCC Rules and Regulations (e.g. Part 90.209(e)). If site noise
(electromagnetic noise) becomes an issue, noise threshold limits will be
established, and amended into the site plan.

Direct radiation of out-of-bound emissions, (i.e. transmitter wide band
noise, spurious emissions, harmonics, etc.) shall be reduced to a
noninterference level by using bandpass, lowpass, and/or harmonic
filtering. Where duplexing is used, use of a notch type device should be
avoided. In situations where a notch type or a hybrid device is used, a
bandpass filter must be used with the transmitter.

Band-reject filtering may be required in certain applications.

Re-radiation of signals from a transmitter and its associated antenna
system shall be prevented by installing appropriate devices (i.e.
ferrite isolators), with minimum return loss of 25 db.

All transmitters not in immediate use and not specifically designated as
standby equipment shall be removed. Loads connected to circulators are
to be capable of dissipating the total power output of the transmitter.

[Receiving Equipment]{.underline}

All receivers shall comply with all applicable parts of the FCC rules,
including Parts 2 and 15.

All receivers shall have sufficient "front end" pre-selection to prevent
receiver spurious response. The use of bandpass, band-reject cavity or
crystal filters may be required to prevent receiver-produced
intermodulation or adjacent-channel interference is recommended at the
input of all receiving devices.

Where duplexing is used, use of a notch type device should be avoided.
In situations where a notch type or hybrid device is used, a bandpass
filter must be used with the transmitter.

[Tower]{.underline}

Generally only one tower is authorized for each facility owner. Facility
Owners and Facility Managers may obtain permission to construct a second
tower only after submitting evidence that demonstrates that their
existing tower is completely filled and full use has been made of
combining systems.

1.  All towers will be left unpainted, if they are dull, galvanized
    steel. If paint is required, the BLM will approve only
    non-reflective colors from the Munsell Soil Color Chart, Standard
    Environmental Colors.

2.  [Maximum tower height for this site is 125]{.mark} [feet.]{.mark}

3.  [Tower lighting will not be authorized at this site.]{.mark}

4.  All new and replacement towers will be self-supporting and
    non-guyed.

5.  Anti-climb devices, removable steps, or other means to discourage
    unauthorized climbing, are highly recommended to reduce or avoid
    liability claims.

6.  To avoid possible impacts to birds or bats, follow the most current
    version of the U.S. Fish & Wildlife Service's Interim Guidelines on
    the Siting, Construction, Operation and Decommissioning of
    Communication Towers (available at
    http://migratorybirds.fws.gov/issues/towers/comtow.html).

[Antennas]{.underline}

1.  [The maximum antenna height (including tower) will be 125
    feet.]{.mark}

2.  Microwave (dish) antennas (other than ground mounted satellite
    dishes) will be limited to a maximum of six (6) feet in diameter.
    The smallest diameter dishes are preferred if technically feasible.

3.  All antennas must meet all Occupational Safety and Health
    Administration (OSHA) safety standards. If an antenna exceeds FCC
    public or occupations standards (see FCC OET Bulletin 57), it will
    be remedied within 24 hours after measures are taken or isolated
    (e.g., fencing, signing, relocation, lowering power levels are all
    possible remedies). Ground measurements of radio frequency radiation
    (RFR) levels will be taken before mitigation measures are
    implemented.

4.  Color(s) for dish antennas, or covers, must be pre-approved by the
    BLM. White dish antennas and/or covers will not be approved.
    Existing white dishes and covers must be repainted or replaced with
    gray dishes and covers, as repairs or replacement become necessary.

5.  Antennas will be treated for low to non-reflectance.

[Interference]{.underline}

The responsibility for correcting interference problems is a matter for
resolution between the lease/ROW holder of the facility(ies), the user
causing the interference, and the affected party(ies). First users on a
site have seniority with respect to the resolution of interference
complaints. Senior holders have an obligation to maintain their
equipment to industry standards, to operate their systems in accordance
with the terms of the FCC license and NTIA/IRAC frequency authorization,
and to comply with the BLM authorization.

New users on a site must correct, at their expense, interference
problems that they create. They may be required to furnish an
intermodulation study or other interference-related data and agree to
accept financial responsibility for elimination or prevention of any
interference caused by the facility before their application can be
evaluated. They must cease operation of the suspect equipment until the
problem is corrected. If interference problems cannot be resolved or
corrected within a reasonable time, the new use that is causing the
interference may be terminated and the equipment removed.

All users shall cooperate with the Site Users Association, to be formed,
and the BLM in identification and correction of any interference. The
BLM does not have authority for correcting interference problems, but
can act as a mediator to help all affected parties. Interference
problems must be coordinated with the FCC or NTIA/IRAC, whichever is
appropriate.

Interference with law enforcement and/or emergency communications must
be corrected immediately. The operation of equipment covered by this
site plan shall not interfere with United States Government radio or
electronic operations already in existence within two (2) miles of this
site. The user causing this interference, shall, at its own expense,
take all action necessary to prevent or eliminate such interferences. If
it does not eliminate such interference within ten (10) days after
receipt of notice from the BLM to do so, the use will be terminated.

If electromagnetic noise becomes an issue, noise thresholds will be
established and this site plan will be amended accordingly.

## Cables and Transmission Line (Wave Guides)

All new cabling will be jacketed and shielded and shall either be
flexible or semi-rigid type. Existing substandard cables will be
upgraded as repairs or replacement become necessary.

Cables will be properly installed and will be strapped and fastened
down. Use of ports at building entrance points will be kept to a minimum
by use of combiners.

When attaching power cables onto a tower, conduits should be used. Coax
and wave guides should be installed in a wave guide ladder or equally
divided among all tower legs.

All transmission lines (wave guides) are to be supported in accordance
with manufacturer's specifications.

Double shielded braided, or solid shielded cable will be used. No RG-8
type cable is permitted. No connector-type adapters will be used on
transmission lines. Only correct connectors that will mate to connected
devices are to be used.

Conduits will be shared when they service common areas and will be
buried where possible.

## Radiation

All communications uses must meet ANSI, FCC and BLM regulations
guidelines and standards concerning radiation limitations.

Monitoring radiation levels at the site is the responsibility of all
site users and will occur at intervals to comply with FCC regulations
and guidelines. A copy of these monitoring reports will be provided to
the BLM within 30 days of its completion. The FCC is responsible for
enforcement of the monitoring and standardization for compliance. The
FCC could revoke the license and/or issue a fine for failure to comply.
Additionally the BLM could terminate or suspend the use authorization
for failure to comply.

Onsite RFR measurements will be taken using appropriate equipment that
can adequately measure both on-tower and on the ground levels before
mitigation measures related to RFR are implemented pursuant to FCC
standards and requirements.

Security fences with RFR notice signs are required around areas that
exceed public use levels including anchor points outside the primary
facility compound fence, if necessary. Raising higher power transmitting
antenna on the tower or modifying the antenna type to half wavelength
may be necessary to eliminate RFR hazards. Reducing power may also be
required if other alternatives are not feasible. All fencing location
and design or new tower construction must be pre-approved by the BLM.

Warning signs will comply with ANSI C95.2 color, symbol, and content
conventions. Contact information, including name and telephone number,
will also be included on warning signs.

Lowering power levels for on-tower access during maintenance will be
coordinated between affected users.

Any identified RFR problems that are, or could be, a human health hazard
must be corrected within 24 hours after measurement tests have been
completed or be removed from the site by the site user(s). If the
proposed corrective action involves any new ground disturbance, it must
be pre-approved by the BLM.

## Utilities-Availability of and Requirements for:

[Commercial Electrical Power]{.underline}

Commercial power is provided to the site under separate ROW grants to El
Paso electric. The distribution lines and portions of the service drops
are aerial. Future service drops or modifications will be buried unless
a waiver is approved by the authorizing officer.

[Telephone Service]{.underline}

Commercial telephone lines service this site are under separate ROW
Grant to Qwest..

If additional service is ever deemed necessary, site users will pay for
the cost of:

1.  The necessary resource surveys and reports for service connections;
    and

2.  The cost of constructing service connections.

For visual reasons, overhead utility poles are generally not authorized.

[Fuel Tanks]{.underline}

All facility owners and facility managers are responsible for providing
fuel storage (propane and diesel) and emergency power for their tenants
and customers. No tenants or customers will be authorized to have
separate fuel tanks and/or generators. Each facility owner will
preferably consolidate fuel storage into a tank large enough in size to
accommodate all tenants and customers. At a minimum, tanks will be
grouped together in a consolidated area adjacent to their facilities.
All fuel, storage tanks (e.g. LPG, propane and diesel) must meet current
fire department, Federal, State and County safety and hazardous
materials requirements. Propane is the preferred fuel for future
generators

1.  All tanks will be:

> a\. Signed in red letters, "SMOKING OR OPEN FLAME PROHIBITED WITHIN 20
> FEET";
>
> b\. In conformance with National Fire Protection Association (NFPA)
> requirements; and,
>
> c\. Painted an approved color, or screened by an enclosure to blend in
> with the natural environment. If an enclosure is used, it must be
> pre-approved and painted an approved color from the Munsell Soil Color
> Chart, Standard Environmental Colors.
>
> 2\. Diesel tanks will also be:
>
> a\. Enclosed in BLM and fire department approved secondary containment
> vaults that are painted a BLM approved color from the Munsell Soil
> Color Chart, Standard Environmental Colors.
>
> b\. Constructed with underground fuel lines. Fuel line must be
> constructed of black, treated pipe and fittings, and must be posted.

## Sanitary Facilities

> 1\. Plans for any sanitary facilities must be pre-approved by the BLM.
> If it is determined by the BLM that the users need such facilities,
> they will be provided by the lease/ROW holder in a manner and location
> satisfactory to the BLM and within the requirements of the County
> Health Department.

## Security and Law Enforcement 

The County Sheriff's Department is the key law enforcement agency for
the area. They are responsible for most civil and criminal matters. The
BLM will be responsible for enforcing matters related to uses of BLM
lands (e.g. resource protection issues).

Patrolling and policing for security purposes is the user's
responsibility.

Fence gates and key access must be approved in advance by the BLM and
must be adequate for BLM and County Fire Department access needs.

## Site Maintenance 

The objective of maintenance activities is to present a clean, neat, and
orderly appearance at the site and have all of the authorized
improvements safe for workers and the public. All users will keep up the
overall appearance of the site.

Miscellaneous debris remaining after any construction and/or equipment
installation, removal or modification, is not only a hazard, but can
cause interference or intermodulation problems. In particular, all loose
wire or metal objects are to be removed from the site.

The users of the site will remove all graffiti within 10 working days of
finding it. If graffiti is on natural features (e.g. rocks), the
graffiti will be removed in a method approved by the BLM Authorized
Officer.

Users will not be permitted to leave or dispose of trash, garbage or cut
brush on public lands. No outside trash or litter containers will be
provided. Site users will remove litter from the site as it is produced.

Policing of litter in common areas (i.e. areas between buildings and
developed sites) is the shared responsibility of those holders bordering
these areas.

During construction and/or maintenance, excess materials (e.g. cement,
wire, metal, building materials) will be removed from public land.

Peeling paint on buildings and/or towers will be re-painted within
thirty (30) days of discovery by the facility owner or facility manager
and within 10 days of notification of the holder by the BLM.

## Inspections

Enforcement authority is vested in the BLM as the Communications Site
Administrator for Twin Peaks (Goat Mtn) via 43 CFR 2800. In this
connection, a Users Association, through the Technical Standards
Committee functions as technical advisor to the BLM may conduct an
annual inspection of each user's facility. This inspection will verify:

a.  Compliance with technical standards.

b.  Structural integrity.

c.  As-built plan accuracy.

d.  Electromagnetic compatibility.

e.  General site health, safety, and cleanliness.

The Users Association shall provide written notice of the scheduled
inspection date at least 30 days in advance. Each user shall arrange to
have personnel available at the site at the time of the inspection.

Any non-compliance found by a user shall be reported to the BLM. The BLM
will conduct an inspection and a written copy of the inspection report
shall be forwarded to the violating user within 30 working days
following the inspection. The report shall include:

a.  A description of the violation.

b.  Corrective action required.

c.  Name, address, and organization of the responsible party.

d.  Time allowed for completion of corrective measures.

e.  Anticipated action in the event of noncompliance with remedial
    instructions.

## Fire Prevention and Hazard Reduction Requirements 

Facility owners and facility managers will be required to maintain brush
and grass vegetation around their facilities. Gravel or mineral soil
(i.e. bare ground) must be maintained to a minimum of (10) feet
clearance around buildings and a minimum of (10) feet clearance around
any propane tanks. Identified threatened, endangered, or sensitive plant
species must remain within the minimum clearance areas.

Smoking is prohibited in flammable vegetation areas.

Roof structure shall be kept reasonably clear of debris at all times.

No explosives will be stored at this site. Flammable materials shall be
stored in conformance with the requirements of local fire regulations.
Flammables will be placed in closed containers and stored away from
sources of ignition and combustible materials. If flammables are stored
within a building, the building will be locked, properly signed and well
ventilated.

Approved spark arresters will be required and maintained on all internal
combustion engines.

At least one (1) U.L. rated 40 B:C dry chemical fire extinguisher is
required inside each building. Prior to each June, fire extinguisher(s)
shall be inspected by holders and refilled, if necessary.

Any fire will be immediately reported to "911", the nearest BLM office
and/or County Sheriff.

BLM Officers will make periodic fire prevention inspections. They will
call to the holder's attention any lack of compliance with the above
regulations, plus any other existing hazards. Compliance with these
inspections is required within the time limits specified in the
inspection report.

## Access Maintenance and Restrictions

[Roads]{.underline}

[Portions of t]{.mark}he access road is [across private]{.mark} lands
[owed by the Edginton's with a locked gate and then up a steep concrete
surfaced road. Four wheeled drive vehicles are recommended on the road
to the east peak and required on the road to the west peak. Separate
agreements between the users and the Edginton's are required. Road
maintenance with surface replacement and repair, drainage and water bar
maintenance standards will be developed between the BLM, Edginton's, and
the Site Users Association. The users are responsible for implementing
road maintenance under a road maintenance agreement.]{.mark}.

Users who damage or disturb the access road, or any associated
structures, such as ditches, culverts, roadside vegetation, signs and/or
underground utilities or facilities, will be required to repair the road
or associated structures, to conditions equal to or superior to those
prior to any damage or disturbance. This work must be done according to
applicable road maintenance standards and may require appropriate NEPA
analysis.

[Interior Site Driveways/ Parking Areas]{.underline}

Interior site driveways within the communications site will be
maintained by the site users. Interior roads will be planned and
approved during establishment of new facilities. Interior roads will be
maintained in a manner to allow only one entrance to the site. Off-road
vehicle use by a user in and around the communication site will be
avoided.

+-----------------------------------------------------------------------+
| # CONDITIONS FOR CONSTRUCTION, MODIFICATIONS OR EXPANSION             |
+-----------------------------------------------------------------------+

## New Facility Owner Responsibilities

## Additional facility construction space is extremely limited at this site. If any new facility are proposed, the following conditions shall apply: {#additional-facility-construction-space-is-extremely-limited-at-this-site.-if-any-new-facility-are-proposed-the-following-conditions-shall-apply .unnumbered}

## In addition to the responsibilities listed in Section III, New Facility Owners and Facility Managers are responsible for: {#in-addition-to-the-responsibilities-listed-in-section-iii-new-facility-owners-and-facility-managers-are-responsible-for .unnumbered}

1\. Submitting a complete application to the Las Cruces District Office
(ATTN: "Realty Specialist") prior to any new construction, or
modifications to existing improvements. The application must include:

a\. The appropriate cost recovery and application fees as determined by
BLM.

b\. A copy of the approved Site Plan Base Map showing all of the
proposed (new) facilities including structures, towers, and auxiliary
equipment;

c\. Completed drawings/plans prepared by a registered engineer and Plan
of Development approved by the BLM;

d\. Identification of any microwave beam paths, a plot of their
azimuth(s), and their proposed elevation(s) on the tower;

e\. Documentation that shows that proposed facilities will not be
obstructing, or interfering with, any existing fixed point to point
antennas, omni directional broadcast antennas, or microwave beam paths
in the directions of primary population targets. Proposed beam path
needs must be shown on Site Plan Base Map; and,

f\. Any needed recommendations, changes or modifications to their
original proposal, based on any required resource surveys and/or
reports.

2\. Demonstrating that their proposals will not cause undue interference
with any existing uses before the BLM can approve new facilities. In
addition, it is the applicant's responsibility to show that any new
facilities will make the most efficient use of the limited amount of
space at the site.

3\. Showing their proposals will provide for future users without
additional construction.

4\. Providing engineering and geotechnical investigations for
development of specific foundation designs and grading plans.

5\. Provide for erosion control as part of the Plan of Development prior
to construction activities. At a minimum, erosion control must include:
sediment control, stipulations that cut/fill slopes will be graded and
contoured to prevent erosion and/or excessive runoff, and
recommendations for temporary erosion control measures, (e.g. netting,
silt fences, swales, and/or sediment collection areas).

6\. Coordinating with other Federal (e.g., FCC and FAA), State and
County agencies and obtain all required approvals and/or permits.

7\. Providing 30-day notice to all facility owners/facility managers at
the site, as well as the BLM, of all new frequencies proposed for the
site. A completed BLM technical data sheet or equivalent must be sent
with the 30-day notice to allow for comment of potential interference.
This would be for new frequencies for themselves and their tenants and
customers.

8\. Insuring that all written approvals have been obtained from the BLM
prior to construction. In addition:

a\. Directional broadcast antennas (e.g. translators) will only be
protected within the arch between their licensed 3 dB points.

b\. New and/or modified facilities will not obstruct existing fixed
point-to-point antennas or omni-directional broadcast antennas in
directions of primary population targets.

## Construction Methods and Resource Protection

Plans submitted by an applicant for any new construction or
modifications shall specify provisions for soil rehabilitation measures
including, but not limited to, soil replacement and stabilization and
for proper handling of runoff from buildings, parking area, access
roads, and undeveloped common areas.

The following methods and resource protection measures will be required
to minimize impacts during construction:

1\. Avoid and protect sensitive resource areas, as identified by the
BLM.

2\. Compliance with the Plan of Development and the Erosion Control
Plan.

3\. During construction and/or maintenance, no paint or paint thinners
will be disposed of on site.

4\. Minimize ground disturbance and vegetation removal as much as
possible during construction activities. All ground-disturbing
activities require BLM pre-approval.

5\. Disturbed areas will be re-vegetated with native vegetation species
pre-approved by BLM as soon as possible after construction. If
necessary, reseeding will be required until vegetation is successfully
established as determined by the BLM.

6\. No grading material will be cast off during
construction/reconstruction activities. Excess soil can be used for fill
material on road and/or building/tower pads.

7\. Temporary, on-site storage of construction materials will require
pre-approval by the BLM.

8\. Construction materials and supplies, except for hazardous materials
(see number 9. below) may be left unattended at the construction site at
the end of each workday, but at the owner's risk.

9\. Hazardous materials, including, but not limited to all fuels, oils,
and lubricants are not to be left unattended at the site at any time.
During construction, these materials are to be removed from the site at
the end of each workday, or temporarily stored inside a locked and
signed building until the following workday.

10\. All surplus construction materials and/or waste debris must be
removed from the site no later than thirty (30) days after construction
has been completed.

11\. Any earth moving or heavy equipment (e.g. dozers, graders, cranes,
backhoes, etc.) leaving the designated roadway and/or approved parking
area(s) to perform authorized activities at the site, will be washed off
prior to being brought onto public lands to prevent the introduction and
spread of noxious weeds into the area.

## Construction Inspection

1\. All new construction, reconstruction, or major modification shall
conform to the established technical standards and accepted engineering
practices (i.e., the Uniform Building Code).

2\. Any construction inspections required by other applicable agencies
are the responsibility of the lessee/holder. Copies of completed
inspections are to be provided to the District Office, Authorized
Officer, either as they occur or as part of the final as-built plan.
Inspection information shall become a permanent part of the holder's
lease/ROW case file.

3\. The Lessee/Holder agrees that corrective work detailed in BLM, or
other agency required compliance inspections, would be completed by the
scheduled completion date. If the Lessee/Holder disagrees or has
questions about specific items, the Lessee/Holder must contact the BLM
in order that the disagreement or item may be resolved.

4\. A final set of as-built plans will be submitted to the District
Office, Authorized Officer, within 90 days of acceptance of structure
(if contracted) or of completion date.

## New or Remodeled/Expanded Buildings

1.  Any new buildings must be designed to accommodate multiple users
    along with fitting into the physical environment as defined in a
    site-specific environmental analysis developed at the time of the
    proposal.

2.  Buildings are required to be one-story. The roof must be metal or
    covered with metal to be fire resistant. Roofs can be equipped with
    antenna support structures, such as poles and railings that can
    extend up to 25-feet above ground level.

3.  Facility Owners and Facility Managers are encouraged to construct
    the interior of their buildings in a modular fashion, so that they
    can:

> a\. Sublease sections to others;
>
> b\. Provide tenants and customers with internal separation and
> security;
>
> c\. Reduce physical interference; and
>
> d\. Increase management effectiveness.

4.  The following materials are approved for construction of new
    facilities (i.e. buildings)

#### a. Floors -- Concrete slab with drainage. {#a.-floors-concrete-slab-with-drainage. .unnumbered}

> b\. Walls -- Concrete block, metal or pre-fabricated concrete.
>
> c\. Roof -- Metal, or concrete, if painted to eliminate shiny
> surfaces, or other fireproof material as approved by the BLM.
> Proposals for wooden roofs will not be approved.
>
> d\. Partitions -- If it is felt partitions are necessary in buildings,
> ensure they are constructed with fire resistant material (e.g.,
> concrete block, reinforced concrete, or properly grounded fencing.
>
> e\. Color -- Proposed color for use on all exterior building surfaces
> must be pre-approved by the BLM. The goal of the color selection for
> the facilities is to make the building as inconspicuous as possible
> and make buildings located on the skyline look inconspicuous when
> viewed from a distance. The intent is to reduce or eliminate glare
> from reflective and/or illuminated surfaces such as windowpanes,
> sheeting and reflective paints. Non-reflective, BLM approved colors
> will be used on equipment buildings.

5.  Building entry lights must:

> a\. Only light the immediate area in the vicinity of the door;
>
> b\. Be motion activated and have a limited time duration (e.g., 3-5
> minutes); and
>
> c\. Have a shielded beam that is pointed at the building door.
>
> Requests for all-night (i.e. "dusk-to-dawn") lighting, or entry
> lighting that would be visible from outside of the site will not be
> approved. FAA required lighting would be the only exception.

## New or Remodeled/Expanded Towers

1.  All new construction, reconstruction, and modifications to towers
    will be pre-approved by the BLM prior to implementation.

2.  It is the applicant/holder's responsibility to assure that a new, or
    modified, structure will not unduly interfere electronically or
    physically with any existing equipment at the site. Towers must be
    spaced, so as to prevent ground level radiation and/or interference
    problems. This must be clearly demonstrated in writing to the BLM
    prior to issuance of a new lease/ROW or amendment.

3.  All new towers will comply with current structural and safety
    specifications and design standards, including safety-climbing
    devices. Towers should be as narrow and "open" as safety and
    structural integrity allow. New towers will be designed using
    maximum wind, snow, and/or tower loading anticipated for the site.

+-----------------------------------------------------------------------+
| # SITE ASSOCIATION/ADVISORY GROUP                                     |
+-----------------------------------------------------------------------+

A Site Users' Association is recommended to for this site. All lease and
ROW holders would be encouraged to join the association. The goal of the
association will be to maximize the effective use of the site. The
objective of a sanctioned association will be to represent all site
users as a group when dealing with the Las Cruces BLM District Office on
matters relating to the site administration. The association will be
able to work in cooperation with the BLM to identify problems or
opportunities and make recommendations to the BLM for any changes in
management strategies at the site. The association could also provide
input to the BLM regarding the future addition of equipment and
facilities at the site. While the advice and recommendations of the
association would not be binding on the BLM, the BLM could use the input
for administration of the site. The BLM would be a member of such a
group and would help jointly develop the charter (i.e., the ground
rules).

+-----------------------------------------------------------------------+
| # APPENDICIES                                                         |
+-----------------------------------------------------------------------+

## Site Map

## Authorized Facilities

## Site Photographs

## Inspection Checklist

##  {#section-1 .unnumbered}

##  {#section-2 .unnumbered}

## APPENDIX A {#appendix-a .unnumbered}

**SITE MAP**

**(See associated AutoCAD Map on the website)**

**APPENDIX B**

**LESEE/HOLDER FACILITY TABLE**

**(See associated User's Table on the Website)**

<table>
<colgroup>
<col style="width: 18%" />
<col style="width: 0%" />
<col style="width: 12%" />
<col style="width: 0%" />
<col style="width: 12%" />
<col style="width: 0%" />
<col style="width: 11%" />
<col style="width: 0%" />
<col style="width: 11%" />
<col style="width: 0%" />
<col style="width: 16%" />
<col style="width: 0%" />
<col style="width: 15%" />
</colgroup>
<thead>
<tr class="header">
<th colspan="2"></th>
<th colspan="2"><p><strong>Auth</strong></p>
<p><strong>#</strong></p></th>
<th><strong>Use</strong></th>
<th colspan="2"><strong>Building</strong></th>
<th colspan="2"><strong>Tower</strong></th>
<th colspan="2"><strong>Access/Parking</strong></th>
<th colspan="2"><strong>Other</strong></th>
</tr>
</thead>
<tbody>
<tr class="odd">
<td colspan="2"><p><strong>Facility # 1</strong></p>
<p><strong>Dona Ana County</strong></p></td>
<td colspan="2"><strong>NMNM 427</strong></td>
<td><strong>PMRS</strong></td>
<td colspan="2"><p><strong>10’x 12’</strong></p>
<p><strong>block</strong></p></td>
<td colspan="2"><p><strong>120’</strong></p>
<p><strong>40’</strong></p></td>
<td colspan="2"><strong>Access and parking</strong></td>
<td colspan="2"><strong>3,000 diesel tank</strong></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td colspan="2"><p><strong>Facility #2</strong></p>
<p><strong>American Tower</strong></p></td>
<td colspan="2"><strong>NMNM 69973</strong></td>
<td><strong>FAM</strong></td>
<td colspan="2"><p><strong>2- 12’x 20’</strong></p>
<p><strong>metal</strong></p>
<p><strong>15’x 2-‘ fiberglass</strong></p></td>
<td colspan="2"><strong>2 -100’ lattice</strong></td>
<td colspan="2"><strong>Access and parking</strong></td>
<td colspan="2"><strong>Propane,</strong></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td colspan="2"><p><strong>Facility #3</strong></p>
<p><strong>Crown Communications</strong></p></td>
<td colspan="2"><p><strong>NMNM</strong></p>
<p><strong>94748</strong></p></td>
<td><strong>FAM</strong></td>
<td colspan="2"><strong>12’x 28’ block (Verizon owned)</strong></td>
<td colspan="2"><strong>125’ lattice</strong></td>
<td colspan="2"><strong>Access and parking</strong></td>
<td colspan="2"></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td colspan="2"><p><strong>Facility #4</strong></p>
<p><strong>Subcarrier Communications</strong></p></td>
<td colspan="2"><p><strong>NMNM</strong></p>
<p><strong>98518</strong></p></td>
<td><strong>FAM</strong></td>
<td colspan="2"><p><strong>16’x 20’</strong></p>
<p><strong>metal</strong></p></td>
<td colspan="2"><strong>65’ lattice</strong></td>
<td colspan="2"><strong>Access and parking</strong></td>
<td colspan="2"></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td colspan="2"><p><strong>Facility #5</strong></p>
<p><strong>Las Cruces Radio Center</strong></p></td>
<td colspan="2"><p><strong>NMNM</strong></p>
<p><strong>1007778</strong></p></td>
<td><strong>CMRS</strong></td>
<td colspan="2"><strong>20’x 24’ metal</strong></td>
<td colspan="2"><strong>60’ lattice</strong></td>
<td colspan="2"><p><strong>Access</strong></p>
<p><strong>and parking</strong></p></td>
<td colspan="2"></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td colspan="2"><p><strong>Facility #6</strong></p>
<p><strong>RGM Communications</strong></p></td>
<td colspan="2"><p><strong>NMNM</strong></p>
<p><strong>103660</strong></p></td>
<td><strong>FAM</strong></td>
<td colspan="2"><p><strong>8’x 8’</strong></p>
<p><strong>metal</strong></p></td>
<td colspan="2"><p><strong>40’ lattice</strong></p>
<p><strong>30’ guyed</strong></p>
<p><strong>20’ mast</strong></p></td>
<td colspan="2"><strong>Access and parking</strong></td>
<td colspan="2"></td>
</tr>
<tr class="even">
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
</tr>
<tr class="odd">
<td></td>
<td colspan="2"></td>
<td colspan="3"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td colspan="2"></td>
<td></td>
</tr>
</tbody>
</table>

**APPENDIX C**

**SITE PHOTOGRAPHS**

**(See associated Facility Photos on the Website**

**Appendix D**

"Twin Peaks (Goat Mtn) Annual Technical Inspection"

Date Inspected:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ Time
Inspection:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Permit Holder:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
Authorization \#
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Site Technician :
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_ Phone \#
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Number of Transmitters \_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_
License Posted
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

*Please mark the following Items as Acceptable (A) or Unacceptable (U).*

Electrical Wiring \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (A) (U)
Grounding \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (A) (U)

Equipment Installation \-\-\-\-\-\-\-\-\-\-\-- (A) (U) Housekeeping
\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (A) (U)

Building Repair \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (A) (U) Tower
Repair \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (A) (U)

*Please mark the following Items as Yes (Y) or NO (N) or (NA)*

Isolators \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (Y)
(N) (NA) Circulators \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (Y) (N)
(NA)

Cavities \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (Y)
(N) (NA) Terminators \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-- (Y) (N)
(NA)

Filters \-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\-\--
(Y) (N) (NA) Lightning Protection \-\-\-\-\-\-\-\-\-- (Y) (N) (NA)

Comments:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Recommended Corrective Action:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Required Corrective Action To Be Taken:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

Committee Representatives:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

BLM Representatives:
\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_\_

*Please make the required corrective action within the next 120 days.*

*Please make a written report of corrective action taken and submit to
the BLM in Las Cruces. If you should have any questions, please call the
BLM office at (525) 505-4454.*