![](media/image1.pct){width="2.5277777777777777in"
height="0.7361111111111112in"}

June 18, 2001

To: Distribution

From: Bob Ducar

Re: Update of Communication Duct Cabling Requirements for MiniBooNE and
NuMI

# MI-10 Service Building to MI-12 MiniBooNE Target Hall \~525 ft

+-----------------------+-----------------------+-----------------------+
| **Utility**           | **Type of Cable**     | **Comments**          |
+-----------------------+-----------------------+-----------------------+
| Accelerator Computer  | Fiber Optic Trunk     | Sourced from MI-10.   |
| Network               |                       |                       |
|                       | 24 Singlemode Fibers  |                       |
+-----------------------+-----------------------+-----------------------+
| Main Injector CAMAC   | Fiber Optic Trunk     | Sourced from MI-10    |
| Link                  |                       |                       |
|                       | 36 Multimode Fibers   |                       |
| Tevatron Clock (TCLK) |                       |                       |
|                       |                       |                       |
| Main Inj Beam Sync    |                       |                       |
| (MIBS)                |                       |                       |
|                       |                       |                       |
| Machine Data (MDAT)   |                       |                       |
|                       |                       |                       |
| MiniBooNE Beam Permit |                       |                       |
|                       |                       |                       |
| NuMI Beam Permit      |                       |                       |
|                       |                       |                       |
| DDC Utility Monitor   |                       |                       |
| Sys (?)               |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Innerduct for Above   | 1.25" ID Plastic      | One is Enough Here    |
| Two Fiber Trunk       | Innerduct with Pull   |                       |
| Cables                | Rope                  |                       |
+-----------------------+-----------------------+-----------------------+
| Bstr Extraction Sync  | Qty 2 -- 1/2"         | Sourced from MI-10    |
| (BES)                 | Cablewave/Heliax 50   |                       |
|                       | Ohm Coaxial Cable     |                       |
| Booster RF (BRF)      |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Beam Pos Monitor      | Qty 2 -- 7/8"         | Sourced from MI-10    |
| Signal                | Cablewave/Heliax Foam |                       |
|                       | Dielectric 50 Ohm     |                       |
| Spare 50 Ohm Mon      | Coaxial Cable         |                       |
| Cable                 |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Safety Interlock      | Qty 4 -- 20 Conductor | Two of these stop at  |
|                       | 18 AWG Cable          | MI-12. The other two  |
|                       |                       | continue on to MINOS  |
+-----------------------+-----------------------+-----------------------+
| Safety Data Links and | Qty 2 - Four Twisted  | Sourced from MI-10.   |
| Audio Warning         | Pairs, 18 AWG         | Stops at MI-12 and    |
|                       |                       | Continues on to MINOS |
+-----------------------+-----------------------+-----------------------+
| FIRUS                 | Qty 3 -- 1/2" 75 Ohm  | Sourced from MI-10    |
|                       | Hardline Coax Cable.  |                       |
+-----------------------+-----------------------+-----------------------+
| CATV                  | Qty 3 -- 1/2" 75 Ohm  | SWYD A System, a B    |
|                       | Hardline Coax Cable.  | System for Cameras,   |
|                       |                       | and a Spare. These    |
|                       |                       | are Minimum           |
|                       |                       | Requirements.         |
|                       |                       |                       |
|                       |                       | Sourced from MI-10    |
+-----------------------+-----------------------+-----------------------+
| Telecommunications    | Telephone Trunk Cable | Sourced from MI-10    |
|                       |                       |                       |
|                       | 25 or 50 Pair, 24 AWG |                       |
+-----------------------+-----------------------+-----------------------+
| NuMI Fire Protection  | Qty 1 -- Several      | Passes through MI-12  |
| Connectivity between  | Twisted Pairs, 16 or  | to MINOS              |
| NuMI Target and MINOS | 18 AWG                |                       |
| Bldgs                 |                       |                       |
+-----------------------+-----------------------+-----------------------+

# MI-12 MiniBooNE Target Hall to MiniBooNE Detector Building \~1,800 ft

+-----------------------+-----------------------+-----------------------+
| # Utility             | # Type of Cable       | # Comments            |
+-----------------------+-----------------------+-----------------------+
| Accelerator Computer  | Fiber Optic Trunk     | > Sourced from MI-12  |
| Network and           |                       |                       |
| Connectivity to       | 24 Singlemode Fibers  |                       |
| Feynman via Detector  |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Main Injector CAMAC   | Fiber Optic Trunk     | Sourced from MI-12    |
| Link                  |                       |                       |
|                       | 36 Multimode Fibers   |                       |
| Tevatron Clock (TCLK) |                       |                       |
|                       |                       |                       |
| Main Inj Beam Sync    |                       |                       |
| (MIBS)                |                       |                       |
|                       |                       |                       |
| Machine Data (MDAT)   |                       |                       |
|                       |                       |                       |
| MiniBooNE Beam Permit |                       |                       |
|                       |                       |                       |
| NuMI Beam Permit      |                       |                       |
|                       |                       |                       |
| DDC Utility Monitor   |                       |                       |
| Sys (?)               |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Innerduct for Above   | Qty 1 (or 2?) 1.25"   | Consider Pulling a    |
| Fiber Trunk Cables    | ID Innerduct with     | Spare Innerduct Here  |
|                       | Pull Rope             | to Facilitate Future  |
|                       |                       | Pulls                 |
+-----------------------+-----------------------+-----------------------+
| Bstr Extraction Sync  | Qty 2 -- 1/2"         | Sourced from MI-12    |
| (BES)                 | Cablewave/Heliax 50   |                       |
|                       | Ohm Coaxial Cable     |                       |
| Booster RF (BRF)      |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Beam Pos Monitor      | Qty 2 -- 7/8"         | Sourced from MI-12    |
| Signal                | Cablewave/Heliax Foam |                       |
|                       | Dielectric 50 Ohm     |                       |
| Spare 50 Ohm Mon      | Coaxial Cable         |                       |
| Cable                 |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Safety Interlock      | Qty 2 -- 20 Conductor | From MI-10 on the way |
|                       | 18 AWG Cable          | to MINOS.             |
+-----------------------+-----------------------+-----------------------+
| Safety Data Links and | Qty 2 - Four Twisted  | From MI-12 on the way |
| Audio Warning         | Pairs, 18 AWG         | to MINOS.             |
+-----------------------+-----------------------+-----------------------+
| Telecommunications    | Telephone Trunk Cable | From MB Detector      |
|                       |                       | Bldg. Cable exits     |
|                       | 25Pair, 26 AWG        | this ductbank at      |
|                       |                       | Giese Road manhole on |
|                       |                       | the way to Kirk Road  |
|                       |                       | Cell Tower.           |
+-----------------------+-----------------------+-----------------------+
| NuMI Fire Protection  | Qty 1 -- Four Twisted | From MI-10 on the way |
| Connectivity between  | Pairs, 16 or 18 AWG   | to MINOS. Part of the |
| NuMI Target and MINOS |                       | connection path.      |
| Bldgs                 |                       |                       |
+-----------------------+-----------------------+-----------------------+
| CATV                  | Qty Unknown of 1/2"   | At least 1 cable will |
|                       | 75 Ohm Hardline Coax  | be needed if          |
|                       | Cable.                | connection to 8GeV A  |
|                       |                       | System is desired.    |
+-----------------------+-----------------------+-----------------------+

**Lederman Education Center to MiniBooNE Detector Building \~1,500 ft**

+-----------------------+-----------------------+-----------------------+
| # Utility             | # Type of Cable       | # Comments            |
+-----------------------+-----------------------+-----------------------+
| FIRUS                 | 3 -- 1/2" 75 Ohm      | FIRUS already at      |
|                       | Hardline, Coax Cable. | Lederman Education    |
|                       |                       | Center. The FIRUS     |
|                       |                       | Mini is located in    |
|                       |                       | the utility closet    |
|                       |                       | near the center of    |
|                       |                       | the building.         |
+-----------------------+-----------------------+-----------------------+
| CATV                  | 3 -- 1/2" 75 Ohm      | # SWY                 |
|                       | Hardline, Coax Cable. | D & 8GeV Systems alre |
|                       |                       | ady at Lederman Educa |
|                       |                       | tion Center. SWYD A S |
|                       |                       | ystem, SWYD or 8GeV B |
|                       |                       |  System, and 1 Spare. |
+-----------------------+-----------------------+-----------------------+
| Telecommunications    | Telephone Trunk Cable | A spare 100 pairs     |
|                       |                       | connected to          |
|                       | 100 Pair, 26 AWG      | Tel-Switch room       |
|                       |                       | inside WH are         |
|                       |                       | available in existing |
|                       |                       | manhole CM-LEC-1 by   |
|                       |                       | Lederman Education    |
|                       |                       | Center. Splice at     |
|                       |                       | CM-LEC-1 to support   |
|                       |                       | MiniBooNE Detector,   |
|                       |                       | MINOS, and Kirk Cell  |
|                       |                       | Tower.                |
+-----------------------+-----------------------+-----------------------+
| Computing             | \~7/8" OD ABF Air     | Will Connect at New   |
|                       | Duct with 7 Interior  | Handhole by CM-LEC-1  |
| Data-Communications   | Cells, each with 8mm  | with 7 Cell ABF to    |
|                       | ID to Accommodate     | WH. 2 Cell ABF from   |
|                       | Blow In Fiber         | CM-LEC-1 to Lederman  |
|                       |                       | Education Center.     |
|                       | Will contain 12       |                       |
|                       | Singlemode Fibers. 6  | Supports Required     |
|                       | Each for MiniBooNE    | Connectivity to       |
|                       | and MINOS.            | Feynman for MB        |
|                       |                       | Detector, MI-12, and  |
|                       |                       | MINOS                 |
+-----------------------+-----------------------+-----------------------+

# Duct Bank Between NuMI Target and MI-10 Service Buildings \~2,500 ft Max

  ----------------------- ----------------------- -----------------------
  **Utility**             **Type of Cable**       **Comments**

  NuMI Fire Protection    Qty 1 -- Four Twisted   Part of the connection
  Connectivity between    Pairs, 16 or 18 AWG     path.
  NuMITarget Bldg and                             
  MINOS Bldg                                      
  ----------------------- ----------------------- -----------------------

**MiniBooNE Detector Building to MINOS Service Building \~1,775 ft**

+-----------------------+-----------------------+-----------------------+
| **Utility**           | **Type of Cable**     | **Comments**          |
+-----------------------+-----------------------+-----------------------+
| Accelerator Computer  | Fiber Optic Trunk     | Sourced from MB       |
| Network               |                       | Detector Bldg.        |
|                       | 24 Singlemode Fibers  | Supports desired      |
|                       |                       | connectivity to       |
|                       |                       | Feynman.              |
+-----------------------+-----------------------+-----------------------+
| Main Injector CAMAC   | Fiber Optic Trunk     | Sourced from MB       |
| Link                  |                       | Detector Bldg.        |
|                       | 36 Multimode Fibers   |                       |
| Tevatron Clock (TCLK) |                       |                       |
|                       |                       |                       |
| Main Inj Beam Sync    |                       |                       |
| (MIBS)                |                       |                       |
|                       |                       |                       |
| Machine Data (MDAT)   |                       |                       |
|                       |                       |                       |
| NuMI Beam Permit      |                       |                       |
|                       |                       |                       |
| DDC Utility Monitor   |                       |                       |
| System                |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Innerduct for Above   | 1.25" ID Plastic      | One is Enough Here.   |
| Fiber Trunk Cables    | Innerduct with Pull   | But May Want to Pull  |
|                       | Rope                  | a Spare Between       |
|                       |                       | Building and Exterior |
|                       |                       | CMH-MN-3              |
+-----------------------+-----------------------+-----------------------+
| Safety Interlock      | Qty 2 -- 20 Conductor | Sourced from MI-10    |
|                       | 18 AWG Cable          | and via MI-12 and MD  |
|                       |                       | Detector Bldg.        |
+-----------------------+-----------------------+-----------------------+
| Safety Data Links and | Qty 2 - Four Twisted  | Sourced from MI-10    |
| Audio Warning         | Pairs, 18 AWG         | and via MI-12 and MD  |
|                       |                       | Detector Bldg.        |
+-----------------------+-----------------------+-----------------------+
| FIRUS                 | Qty 3 -- 1/2" 75 Ohm  | Sourced from MB       |
|                       | Hardline Coax Cable.  | Detector Bldg.        |
+-----------------------+-----------------------+-----------------------+
| CATV                  | Qty 3 -- 1/2" 75 Ohm  | SWYD A System, a B    |
|                       | Hardline Coax Cable.  | System for Cameras,   |
|                       |                       | and a Spare. These    |
|                       |                       | are Minimum           |
|                       |                       | Requirements.         |
|                       |                       |                       |
|                       |                       | Sourced from MB       |
|                       |                       | Detector Bldg.        |
+-----------------------+-----------------------+-----------------------+
| Telecommunications    | Telephone Trunk Cable | Sourced from MB       |
|                       |                       | Detector Bldg.        |
|                       | 100 Pair, 26 AWG      |                       |
+-----------------------+-----------------------+-----------------------+
| NuMI Fire Protection  | Qty 1 -- Four Twisted | Passes through MI-8,  |
| Connectivity between  | Pairs, 16 or 18 AWG   | MI-10, MI-12, and MB  |
| NuMITarget and MINOS  |                       | Detector Bldg on the  |
| Bldgs                 |                       | way to MINOS.         |
+-----------------------+-----------------------+-----------------------+

**Required at NuMI Target Building Exact Routing Partially Undefined**

+-----------------------+-----------------------+-----------------------+
| **Utility**           | **Type of Cable**     | **Comments**          |
+-----------------------+-----------------------+-----------------------+
| Accelerator Computer  | Fiber Optic Trunk     | Sourced from MI-62    |
| Network               |                       |                       |
|                       | 24 Singlemode Fibers  |                       |
+-----------------------+-----------------------+-----------------------+
| Main Injector CAMAC   | Fiber Optic Trunk     | Sourced from MI-62    |
| Link                  |                       |                       |
|                       | 36 Multimode Fibers   |                       |
| Tevatron Clock (TCLK) |                       |                       |
|                       |                       |                       |
| Main Inj Beam Sync    |                       |                       |
| (MIBS)                |                       |                       |
|                       |                       |                       |
| Machine Data (MDAT)   |                       |                       |
|                       |                       |                       |
| NuMI Beam Permit      |                       |                       |
|                       |                       |                       |
| DDC Utility Monitor   |                       |                       |
| System                |                       |                       |
+-----------------------+-----------------------+-----------------------+
| Innerduct for Above   | 1.25" ID Plastic      | One is Enough Here.   |
| Fiber Trunk Cables    | Innerduct with Pull   |                       |
|                       | Rope                  |                       |
+-----------------------+-----------------------+-----------------------+
| Safety Interlock      | Qty 2 -- 20 Conductor | Sourced from MI-62    |
|                       | 18 AWG Cable          |                       |
+-----------------------+-----------------------+-----------------------+
| Safety Data Links and | Qty 2 - Four Twisted  | Sourced from MI-62    |
| Audio Warning         | Pairs, 18 AWG         |                       |
+-----------------------+-----------------------+-----------------------+
| FIRUS                 | Qty 3 -- 1/2" 75 Ohm  | Sourced from MI-62 or |
|                       | Hardline Coax Cable.  | MI-8                  |
+-----------------------+-----------------------+-----------------------+
| CATV                  | Qty 3 -- 1/2" 75 Ohm  | Sourced from MI-62 or |
|                       | Hardline Coax Cable.  | MI-8                  |
+-----------------------+-----------------------+-----------------------+
| Telecommunications    | Telephone Trunk Cable | Sourced from MI-62 or |
|                       |                       | MI-8                  |
|                       | 50 or 100 Pair, 24    |                       |
|                       | AWG                   |                       |
+-----------------------+-----------------------+-----------------------+
| NuMI Fire Protection  | Qty 1 -- Four Twisted | Passes by or thru     |
| Connectivity between  | Pairs, 16 or 18 AWG   | MI-8, MI-10, MI-12,   |
| NuMITarget and MINOS  |                       | and MB Detector Bldg  |
| Bldgs                 |                       | on the way to MINOS.  |
+-----------------------+-----------------------+-----------------------+

Stated distances are subject to refinement and do not necessarily
include excess for interior building routing.

Distribution:

> Aesook Byon-Wagner 220
>
> Bruce Baller 220
>
> John Anderson 371
>
> Ron Cudzewicz 369
>
> Fernanda Garcia 122
>
> Tim Gierhart 360
>
> Terry Hendricks 307
>
> Carolyn Hines 228
>
> Larry Jackson 108
>
> Cat James 220
>
> Dave Pushka 220
>
> Tom Lackowski 214
>
> Jeff Sims 214
>
> Al Legan 307
>
> Bill Marsh 360
>
> Jim Niehoff 214
>
> Dan Stenman 360
>
> Al Thomas 368
>
> Greg Vogel 307