Boundary Dam Power Station in Estevan, Saskatchewan, Canada. The successful bidder will then perform isokinetic fuel sampling to determine the following: the pipe to pipe fuel balance, ensure adequate air / fuel ratios are met, ensure minimum fuel line velocities are being met, determine pipe to pipe dirty air flow balance, and to obtain fuel samples for coal fineness analysis. Sieving will be performed by plant personnel according to standard operating procedures and / or direction from the successful proponent. Note that the sampling method and equipment must be suitable to high moisture lignite fuel. SaskPower will be completing a baseline clean air test on all four (4) fuel pipes in each of BD4's six (6) pulverizers. This information will be provided to the successful proponent upon request. The successful proponent may be required to perform a Primary Air Flow verification to all six (6) of BD4's mills. There are four test ports available on each of the ducts. A 6' or 8' 3D or Fecheimer probe will be required. The successful proponent will then recommend a course of action for addressing the slagging issues with the unit. This will involve at least one additional HVT test as modifications are proposed. Synopsis: Scope of Work Saskpower is seeking the services for a proponent that will design and facilitate training for two (2) separate courses.The subjects of each course, respectively, are 1. RP Mills and coal firing (T-Fired) performance and 2. MPS mills and coal firing (Wall-Fired) performances. The courses are