CE: T206-3631 #1 end Ceiling Panel condensation. Temp 24.1*C. Floor
slightlyWet. ~~~~~ to change out #3631 no.2 end thermistor  3631 no.2 end Aircon thermistor c/o and function test cut in/cut out ok. Temperature able to go down to 24 degrees celsius and cut out Done by Koh/jack 45461 CE: T206-3631 #1 end Ceiling  Panel condensation. Temp 24.1*C. Floor slightly  Wet.  Checked #3631 FC 618 AC2 HLPS1 operation. Checked #3631 no.1 end ceiling wet, with some water on the floor. Checked on TIMS #3631 AC1 stuck at 25 deg while AC2 was 22-23 degrees, resulting in AC1 unable to cut out. Checked FC Measured air temperature with hygrometer at #3631 no. 1 end 22.4 degrees correspond to TIMS AC2 temperature of 22-23 degrees. However, no. 2 end measured 23.7 degrees, but on TIMS, temperature indicated was 25 degrees. Wiped away and cleaned the condensation on the ceiling and on the floor. Ops20 to check and service #3631 no. 2 end thermistor, and to rectify #3631 AC2 HLPS1. Done by Luke 45454 check and service #3631 no. 2 end thermistor, and to rectify #3631 AC2 HLPS1.     Checked #3631 AC1 AHU internal no water, only on the external surface. Serviced #3631 No.2 end thermistor with compressed air to no avail. Confirmed that #3631 no.2 end was 22.4 degrees with hygrometer when TIMS and PTU indicate 25.2 degrees. Checked and confirmed temperature setting at 25 degrees. AC1 unable to cut out due to temperature sensor unable to go below 25.2 degrees. No.1 end temperature sensor ok. AC2 able to cut out. Ops30 to change out no.2 end temperature sensor at RAD. Done by Fazil/Rizman 45454