Snap: 1563 Saloon leaking ~~~~~ Snap: 1563 Saloon leaking CE : 1563 #2 End Ceiling Panel Slight Condensation. Floor Dry. Temp 24.6* C.  1563 Found temp setting at 22?C. Change setting to 25?C. Replaced aircon filter. Pipe purging at no. 1 and no. 2 end. Monitored cut in/out ok.  Alan/Kamarul/Lee PT 45304