SnapRep: 3655 water leaking from ceiilin ~~~~~ SnapRep: 3655 water leaking from ceiling. CE checked & found 3655 No.1 end Ceiling slight Condensation.  3655 checked/found water from drain pipe discharge slowly due to drain pipe line clogged partially. Cleared the pipeline clog by purging & water discharge flow was fast &    smooth. A/c system able to cut-in/out & temp.set at 25*C. LP = 35psi, HP = 120 psi. Running current = 9.8amp. All OK. Replaced the evaporator filter.  Alan/Lee PT/Kamarul/Shafie/Sugu 45044