Snaprep: 3528 A/C water dripping from ceiling

CE:3528(W)No 1 end ceiling condensation.Floor dry ~~~~~ #3528 AC1 ROOF TOP CHECK AHU DRAIN PAN WATER FOUND.USE PUMP PURGED OUT.BOTTOM AC1 END DRAIN PIPE PURGED WATER CAME OUT .AHU LINER REMOVED.COVER CLOSED.HATCH COVER QC CHECK OK.FUNCTION CHECK OK.RAM/AZNUR/FIRDAUS 20.07.2024