Snap: 3675 A/C condensation ~~~~~ Snap: 3675 A/C condensation CE : 3675 nos 1 end ac condensation.  3675 No aircon FC. Replaced aircon filters. Purge drain pan, blow ac thermistor. AC able to cut in/out. Monitor 2 hrs no signs of condensation. Set temp to 25*C.  Sarma/Alan/Lee PT/Shafie 45326