SnapRep 2688 Water leakage. ~~~~~ FOUND NO WATER PONDING.PURGED DRAINLINES OK.CHECKED CUT IN/OUT TEMP FOUND CUT IN TEMP AT 23*C AND READJUSTED TO 25*C.MONITORED FOR A FEW HOURS NO FURTHER CONDENSATION.BASSANT 14.06.2022