snaprep:  1718 aircon condensation on ce ~~~~~ snaprep:  1718 aircon condensation on ceiling CE: 1718 nos 1 end ac condensation.  found evaprator heavy condensation and cause water carry into evap motor area, also observed ceiling panel gather alot water into    saloon area, suspect evaprator drain pan crack cause water leaking. Ops20 to follow up evaprator c/o. Done by:Jack/Koh/Sanip Date:10/11/2023 To follow up #1718 Ac1 evaprator c/o.  #1718 AHU 1 Changeout and function test ok. Old s/n:624109 New s/n:032320 Noti:2541608 Done By:Jack/Sanip/Koh Date:11/11/2023