Snap: 1619 Water dripping from ceiling ~~~~~ EVAP DRAIN PAN VACUUM YES,KSF FC NO,TEMP SET TO 25*C YES.ABLE TO CUT IN/OUT.OPEN HATCH COVER OBSERVED AHU GOT WATER PONDING,PURGE WATER.OPEN AHU COVER REPAIR RUBBER LINING.CLOSE BACK HATCH COVER.MONITOR FOR 1HRS NO CONDENSATION AT 1619 NO 1 END.FUNCTION/SECURITY CHECK OK.TEH/GENSAN/JIMMY 09.11.2023