Snap:cabin 3547 Water is dripping down f ~~~~~ Found slight condensation at 3547 AC1. Temperature setting at 24deg. Adjusted to 25deg. Both AC units checked able to cut-in/out. Used venturi pump to purge drain pan - no chokage. Cleaned thermistor and replaced AC filters Monitored 1 hr - no condensation observed. N.A/fairuz/sankar/18.12.22