3645 rep reported, CE confirm 3645-found ~~~~~ 3645 rep reported, CE confirm 3645-found few droplets of water at nos. 1 end top ceiling panel.flooring dry. Temp.23.7'c.  3645 A/c 1 & 2 adjusted temp. from 24'C to 25'C. checked cut in/out operation - OK. Monitor for 2 hrs & no condensation found.  Sarma 44059