Snap: 1628 reported of water leak at the ~~~~~ Snap: 1628 reported of water leak at the ceiling, near door A1. CE: Water leaking at 1628 no 1 end ceiling OE request "to replace 1628 no.1 the evaporator unit " because it is reported leakage quite frequently by pax .  1628 removed ceiling panel & found insulation soaked with water. Cleared the water & dry the insulation. Used Armaflex silver wrap to wrap around the insulation. Security check - OK. Air flow temperature check at both return air grill - OK. To be monitored during M/L service.  Alan/Lee PT/Shafie 44732