1568 TIMS showed Smoke External Alarm. ~~~~~ 1568 TIMS showed Smoke External Alarm.     Smoke detector obsered rusty at PCB no sign of water ingress.C/O done and tested ok. Dne by Sanip/Rizman. 05/04/23 Not: 2477158.