Snap: 2567 aircon condensation ~~~~~ * ,N *

Checked and found 2567 all AC working normally, cut-in/out ok
Freon level checked ok. Preventively replaced 2567 both AC filters
Further check found 2568 AC2-1 motor shorted. Unit isolated and tagged
N2589158 raised for 2568 AC2-1 ccu c/o
No condensation observed during monitoring

DONE BY:LAI/KUMAR 14.04.2024