CE reported:
#1539 no1E ceiling condensation.
#3539 no1E ceiling condensation. ~~~~~ Checked both AC able to cut in cut out. Replaced the AC filters. Also did venturi purge of the AC drain pipes. Monitored operation for extended period, no abnormalities detected. To further monitor. N.AFAIZAL/08.11.21 -------------------