2544 - No. 2 End Evap. Unit Leak Check ~~~~~ 2544 - No. 2 End Evap. Unit Leak Check.  check and found AHU 2 condenser unit heavy freon leak. Ops20 to follow up AHU 2 c/o. Done By: Jack/Koh Date:10/03/2024 2544 AHU2 condenser leak to c/o.   AHU 2 C/O done. Functtion test ok. Old: 032251 New: 032216 Notif: 2578907 Done by: Jack, Koh, Rizman, Sanip. 11/03/2024.