T410 1561 Fire external,now YCK NB ~~~~~ T410 1561 Fire external,now YCK NB CE: 1561 fire external alarm able to reset No abnormality  Replaced 1561 external smoke detector. Function test ok. Notif: 2581107 Done by: Martin/Rudy 18.3.24