1526 A/C 2-2 DT check having coolant fau ~~~~~ Check and found #1526 a/c 2-2 short cycling.Check pressure observed LP/HP freon was zero.Use vaccum p/p to vaccum to zero.Pump freon to system using weighting scale found CCU condenser capillary tube leak badly.Notification raise to RSW for CCU c/o. Not: 2303562 raqise to RSW. Checked by Koh/Faddzal.   11/08/21 ,,