CE:T202(2656) nos2 end ceiling having ac ~~~~~ CE:T202(2656) nos2 end ceiling having ac condensation. Temp 23.3c.  Check the above mention reported due to B side drainage pipe choke and cause the drain pan full of water. Vacuum and Flush the drainage pipe done. Tested with water and monitor water flow smoothly to drainage pipe. Monitor again for few hours ok. Check temperature setting was at 24. Adjusted to 25. To monitor at mainline Done by Saini/Asruddin 17.01.2024