Snaprep: Aircon Condensation @ 1668 Near door 5 ~~~~~ Snaprep: Aircon Condensation @ 1668 Near door 5  Check the above mention and found AHU tray pan full or water due to drainage chock. Purge the drainage pipe done and test water flow okay. Monitor for few hours - okay.    Done by: Shah, Alauddin, Farhan and Firdaus. 09/05/2024.