517/518 - 2517 SMOKE EXTERNAL ALARM. ~~~~~ 2517 SMOKE EXTER L ALARM.  2517 SDRL11 isolated & removed. Shortloop to BSD to check on smoke detector. Fault cleared after removing SDRL11.  Huzzaidi 44988   FOLLOW UP OPS10.CHECK CONFIRM #2517 SDRL11 ISOLATED AND REMOVED REPLACE #2517 SMOKE DETECTOR DUE TO WATER INGRESS.SECURE CHECK DONE.PLASEAL ADDED TO SECURE SMOKE DETECTOR CONNECTOR.REPLACE SDR11 SECURE AND FUNCTION CHECK DONE OK .LEONG JW/SHAHRIE 05.03.2023 #2517 SMOKE DETECTOR NOTIFICATION 2467621 S/N OLD  NIL S/N NEW KSFD-16