SnapRep reported 1546 - Water leakage from roof.

CE 1546 No.2E ceiling heavy condensation. ~~~~~ CHECKED #1546 NO 2 END INTERIOR CEILING DRY.CONDUCTED PURGING.VACUUM DRAIN PAN AND CLEANING DONE.REMOVE RUBBER LINING.CHECKED LP/HP AND CCU CURRENT OK.SE CURITY CHECKED OK.CUT IN/OUT OK.M HAIRUL/ZAHIR/AZHAR 04.05.2024