SnapRep reported 1724 aircon condensatio ~~~~~ SnapRep reported 1724 aircon condensation 1724 AC1 opened up hatch cover found water trapped inside pan and evap fin icing. Cleared trapped water and purge drain pan. OPS20 to replace AHU. Done by Kamal, Haslan. 17/8/2023. 1724 A/C 1 evaporator fin coil icing to evaporator change out Checked and found evap #2 liquid pipe twisted causing inefficient freon flowing through the system. This caused evap heavy icing. Replaced new AHU and function tested satis. Notification to CSC: 2516530 S/N: 634144 (O) 331062 (N) Done by: Koh Boon Seng, Rizman, Sanip, Jack. 18/8/2023.