CE reported 3623 Water dripping at airco ~~~~~ * ,N * 'Adjusted A/C#2 parameter setting from 23deg to 25deg Replaced A/C 1 and 2 evaporator filters Vacuum purged A/C drain pipe Check A/C operation Found no condensation (water leaking) DONE BY:MUTALIB/ZAINI 16.05.2024