snaprep: 3647 ceiling condensation ~~~~~ snaprep: 3647 ceiling condensation Check #2648 no 2 end no sign of condensation during monitoring for 1 & 1/2 hours.#3647 no 1 a/c set 25degC.#No 2 a/c set to 24degC monitor for 1 & 1/2 hours found ok. Checked by Saini/Haslan. 7/6/23 3647 no.1 end to check evaporator/ A/C 2-2 to check freon and evaporator check #3647 a/c 1 evaporator cover found alot condensation water seepage into insulation.Suspect evaporator cover insulation NG.Evaporator motor,drain pan check no water or icing.Replace evaporator cover to further monitoring.#2648 a/c 2 evap check ok.No sign icing or condensation. Done by Rizman/Sanip/Koh.  09/06/23