#1664 NO 2 END WATER SEEPAGE ~~~~~ #1664 NO 2 END WATER SEEPAGE.CHECK EVAPORATOR UNIT FOUND LINING WORN,DRAIN PAN DRY,EVAPORATOR FULL OF WATER.REMOVE LINING CLEAN THE EVAPORATOR.FUNCTION CHECK FILL WATER TO DRAIN PAN DRAIN LINE OK.DRAIN PAN NOT LEAK TO EVAPORATOR.MONITOR AC CUT IN/OUT CHECK EVAPORATOR OK NO POOL OF WATER. LEONG/GANESAN/SHAHRIE 19.10.2023