Snaprep: 1671 water leaking from ceiling ~~~~~ Snaprep: 1671 water leaking from ceiling   #1671 checked and found drain pan pipe choked, causing water to pond. Cleared the choke with compressed air and cleared the water around the AHU unit. Conducted A/C function test ok. Unit able to cut in/out as per normal, no condensation recurred. Done by: Saini, Din (6.3.24)