Snap: 1621 -Water dripping from ceiling. ~~~~~ CONFIRM 1621  #1B END SLIGHT CONDENSATION BETWEEN A1/B1 DOORS.SLIGHT PONDING FOUND AT THE EVAPORATOR DRAIN PAN.PURGED PUT THE WATER PONDING TILL NO SIGNS OF WATER.REPLACED WITH NEW FILTER AS THE OLD FILTER IS FULLY CLOGGED AND BLACK. ZOHRI/HAFIZ/YUSRI/SURENDAR 30.03.2023