CE : 1606 found no.1E Ceiling sign of condensation. ~~~~~ CE : 1606 found no.1E Ceiling sign of condensation.
 1606 no.1 end ceiling no condensation.
Evap unit drain pan checked ok, perform pipe purging as preventive
measures. Replaced aircon filters.
Saloon aircon temp setting checked ok.
Checked freon pressure within criteria, AC able to cut in/out. Monitored
for 2 hrs, no signs of condensation.
 Hairi/Haziq
01/06/2024