Snap: 2684 opposite of door A1 water leak ~~~~~ Snap: 2684 opposite of door A1 water leaking from there. CE checked : Found 2684 no.1 end top ceiling panel ac duct A and B water dripping. Floor slightly wet.  2684 No FC & no sign of condensation. A/c cut in cut out - OK. Drain pan no choke. Purging air con drain pan done. Air con filter replaced. Monitor for 2 hrs & no condensation occurred. Temperature setting - OK.  Daniel/Aliff/Chan SW 45469