SnapRep reported 1690 water leaking. ~~~~~ SnapRep reported 1690 water leaking.  1690 NO. 2 AHU found drain pan crack, water leak out from drain pan into no.2 end ceiling. Purging done. Ops20 To follow up change out AHU 1690 no.2 Done by Saini/Haslan 45265 1690 no.2 AHU to changeout due to drain pan crack  unit replaced by HM. Notification raised to HM for AHU C/O 2554071. Closed by Daniel. 22/12/2023