2656 Snap:A/con leaking    ~~~~~ SnapRep reported 2656 A/con leaking CE checked 2656 #1 end ceiling panel Slight Condensation and 2656 #2 end ceiling slight Condensation. Floor slightly wet.Temp 24.7*C  Check the above mention reported found both evaporator unit drainage tray pan full of water and drainage choke. Vacuum both unit drainage pipe done and clean the tray pan due to dirty and sluggish/jelly. Tested and monitor okay. To be further monitor on mainline. Done by Saini/Asruddin 45136