SnapRep.Reported 2531 A/c Condensation.C ~~~~~ SnapRep.Reported 2531 A/c Condensation.CE Confirm. To Check & Rectify.  2531 - Check Cut/In & Cut/Out.[OK] Changed Filter,Check Evaporator Passage Insulation.[OK] Monitor For 1Hr.[OK] No Condensation Found. N.AKWOK KT/SUHAIDY/HASZHAN/18.03.20