Snap.3647 Air conditioning condensation ~~~~~ 3647-A/c 1 AHU unit Evap motor side wet condition. Found Evap coil linear torn & carry forward the water droplets to Evap motor side. Cleared the torn linear. Checked drain pan & Drain pipe-Ok. Security checked-Ok.   Jimmy / Teh / Raghu.  19.12.2022.