Snap: 3718 aircon leaking ~~~~~ Suspect drain pan crack. To confirm before evaporator change out.  ffcheck and confirm AHU drain pan crack, C/O AHU 2 and function test ok. old:634105 new:032394 notif:2591312 Done by Sateesh/Sanip/Koh/jack 21.04.24 Snap: 3718 aircon leaking CE: 3718 no 1 end ceiling condensation  3718 no 1 end significant condensation. Wiped and observe water on ceiling. Check aircon 1and 2 temp set 25. Airon able to ccut in/Cut out. Suspect evaportor drain pan crack Ops20. Done by Luke 45397