3653 Snap rep. reported of water drippin ~~~~~ 3653 Snap rep. reported of water dripping from ceiling to the floor. CE confirm 3653 No.1 end condensation.  3653 A/c 1 evaporator filter replaced with KNS type. Purged No.1 end drain pipe - Done. Monitor  & no condensation found at 3653 No.1 end ceiling panel.  Chan SW 43886