SnapRep reported 1502 water dripping. ~~~~~ Checked and confirmed 1502 no.1 and no.2 end ceiling having condensation Checked 1502 both AC and found AC2-1 & 2-2 low freon - recharged to criteria Preventively replace 1502 both AC filters Monitored, both AC operating normally, cut-in/out ok. No condensation observed. N.A /LAI MK/YANTO/21.10.23