Snap: 2542 Condensation on ceiling. ~~~~~ Snap: 2542 Condensation on ceiling. CE : 2542 No 1 end ceiling heavy condensation.  2542 purged no.1 end A & B side on water outlet. Replaced evap filter. Monitored for 1 hr, no ceiling condensation, no abnormalities.  Chan SW/Daniel/Redzwan 45236