Snaap reported: :1530 Air con leaking ~~~~~ Snaap reported: :1530 Air con leaking CE checked:1530 no 2 end ceiling condensation  1530 no.2 end purging done. Check drainage pipe hose secure. Further check and found water seepage out from drain pan cause water condensation, suspect drain pan crack. OPS20 to change ou AHU Done by Haikel/Zulf/Haslan 45457  #1530 AC 2 AHU C/O DONE.FUNCTION TEST OK.AC CUT IN/OUT OK.GANESAN/HARI/RAGHU 23.06.2024 AHU S/N OLD 031191 NEW 331062 NOTIFICATION 2610674