snaprep: 1719 AC condensation on ceiling ~~~~~ snaprep: 1719 AC condensation on ceiling     Check the above mention reported found evap cooling coil icing and drain pan full of water.Purge drainage and clear drain pan done.Check and monitor freon level ok.Also check temperature setting ok. OPS 0020 raise to follow up evap c/o. Done by Saini/Haslan/Asruddin. 04/5/23 Ops20: 1719 A/C 1 AHU C/O Evaporator c/o done,function test ok. Evaporator unit:- Old s/n: 634115 New s/n: 331097 Not: 2487579 raise. Done by Sanip/Koh/Sufian. 11/05/23