2530 Both A/C faulty (TP) ~~~~~ 2530- A/c 1-1 HP/LP within criteria. A/c 1-2 found choke at CCU. Raise notification for CCU C/o.
2530-A/c 2-1 & 2-2 found low freon (HP/LP). Top up both unit. HP/LP within criteria. Cut In/Out-Ok. Cooling - Ok.   Akhbar / Victor / Mani. 01.04.2024.

2530-A/c 1 Noti to RSW-2584985.