CE reported 3611 AC1 condensation ~~~~~ CHECKED FOLLOWING LOCATIONS FOR CONDENSATION #3611 AC1,#1611 AC1/2,#2611 AC2,#2612 AC 1,#1612 AC2. ACTION FOR ALL LOCATIONS AHU FOUND EVAP COIL RUBBER LINING TORN CAUSING CONDENSATION FROM EVAP EXCHANGE WATER TO MOTOR AREA.REMOVE RUBBER LINING.AHU INSULATION OK.MONITOR AN HOUR OK TO BE MONITOR MAINLINE.RASIMAN/HAZIQ/JIMMY 07.10.2022