Snap Feedback :3561 at A1 door, water co ~~~~~ Snap Feedback :3561 at A1 door, water co Check & found signsof condensation on ceiling.Check a/c able to cut in/out-ok.Adjust temperature setting from 22.5deg to 25deg for a/c 1.Monitored no condensation and a/c able to cut in/out ok.To be release for further monitoring on M/L. Checked by Johari. 12/08/22