Snap:1623 aircon condensation ~~~~~ checked and found rubber lining lost adhesion to evap fins. lining removed ok. evap drain pan vacuumed ok. temp set to 25 ok. freon HP/LP ok. diffuser temp ok. tims A/C FC ok. no FC. A/C able to cut in/out. monitor for few hrs A/V running with no condensation.  Shaik / Zohri / Yusri / Suren 30.07.2023