Snap: 2655 Aircon leaking ~~~~~ Snap: 2655 Aircon leaking. CE: 2655 A/C 2 Water leaking @ B/S ceiling & flooring wet.     2655 No FC. Checked no.2 AC filter side, no signs ok choke. Purged drainage pipe done, water from drain pan manage to flow out smoothly. A/C able to cut in/out. Checked temp setting was at 24*C, adjusted to 25*C. Preventively replaced A/C filter. Monitored for 1hr, no abnormalities found.  Daniel/Aliff/Chan SW/Aiman/Farid 45362