Snaprep: 3630 A/C warm ~~~~~ #3630 NO 1 END CONDENSATION.CHECKED EVAP UNIT AND DONE CLEANING AT DRAIN PAN.REMOVE RUBBER LINING OF EVAPORATOR FINS.DONE AC PURGING.FUNCTIO L CHECKED AC LP/HP,CCU CURRENT WITHIN CRITERIA.MONITOR CUT IN/OUT OK.DI USER TEMP OK.MONITOR FOR 1 HOUR NO SIGN OF CONDENSATION. M HAIRUL/AKHBAR 28.02.2024