Snap: 2529 Very stuffy ~~~~~ Snap: 2529 Very stuffy     #2529-A/C 1-2 having low freon and short cycling.Top up freon and check CCU no observed any freon leak.Monitor HP & LP 105psi & 45psi steady and cooling ok. A/C 2 found blowing cool air from CCU condenser fan.Further check found CCU motor U/V/W was isolated without tag.Measure CCU motor found shorted to ground. Notification raise to HM follow up. #2529 a/c 2-1 CCU c/o Not: 2451699 raise. Done by Sufian  09/01/23