3539 & 1539 A/C 1 Condensation.Check and ~~~~~ 3539 A/C 1 & 1539 A/C 1 CE reported Condensation near ceiling area.  3539/1539 replaced with KNS type of filters- Done. Monitor A/c cut in/out operation - OK. No sign of condensation.  Suhairi 43932