CE: 3614,both a,b side,no 1 end water dr ~~~~~ FAULT U BLE TO DUPLICATED.FOUND #3614 AC1 AHU EVAP COIL RUBBER TININGNTORN CAUSING CONDENSATION FROM EVAP EXCHANGE TO OVER FLOW INTO MOTOR AREA.REMOVE RUBBER LINING AND CHECKED AHU COVER INSULATION OK.MONITOR FOR 1 HOUR NO CONDENSATION FOUND AT 3614 AC1 CEILING.TO MONITOR MAINLINE.DRAIN PAN OK.DRAIN PIPE OK.JIMMY/RAGHU 03.10.2022