CE:1620-B/S A/C Condensation floor wet ~~~~~ No condensation found on 1620 no.2 end. 1620 AC2 able to cut-in and cut-out. operation normal. Opened evaporator cover and found water accumulation under drain pan. Purged drain pipe - no chokage observed. Used purging system to drain accumulated water manually. Suspect drain pipe or drain pan damaged. Unable to access area. OP20 raised for followup check at TWD. 1620 AC2 isolated and tagged. N.A/lai mk/sankar/07.09.22  FOUND DRAIN PAN DAMAGED OPS30 TO C/O #1620 AC2 AHU.JIMMY/KAMSANI/JIMMY/PUTRA/HASYRE  12.09.2022  1620 AC2 AHU C/O DONE FUNCTION TEST OK.SECURITY CHECKED OK.KAMSANI/HAZIQ/HASYIR/IBRAHIM 15.09.2022 S/N OLD 331117     NEW 032420 NOTIFICATION 2417906