#1529 - EVAP #2 INVERTER FAULT me(Requestor): SARAVANAN/RSWTNC/BSD te of Occurence: 03/06/2022 st Service Date: NIL U/Equipment/Location: 1529 #2 EVAPORATOR uipment Serial No.(if any): NIL scription of fault/cause: INVERTER FAULT asurement (if any): NIL ult found during CM or PM: PM quired rectification: REQUIRED EVAPORATOR C/OUT ~~~~~ #1529 - EVAP #2 INVERTER FAULT     #1529-Evaporator 2 c/o done.Charge freon and function test a/c able to cut in/out. Evaporator- New-032208 Old-535195 Not: 2389994 raise.