1684 A/C 1-1 PM check suspect evaporator ~~~~~ Evaporator c/o done and function test found AC 1-1 and 1-2 short cycling and no heat exchang. A/C 1-1 LP:35psi, HP:100psi and A/C 1-2 LP:45psi, HP: 100psi. Confirmed CCU choke. HM to follow up CCU C/O Notification to CSC:2507556 Old s/n: 032056 New s/n: 032147 Done by: Sanip, Koh and Rizman