CE reported 3640 AC2 slight condensation ~~~~~ 3640 AC#2 slight condensation Evap Drain Pan flushed: Y Temp set to 25C: Y Diffuser Temp: 25?C Able to Cut in/out: Y Check for any aircon inverter failure FC: N Rectification action: Checked and found no chokage at drain pipes. Further checked found 3640 A/C #2 water ponding outside drain pan area. Drain and purge water. Raised Op20 to check evaporator drain pan for any damages.  SA KR //08.10.22 ------------------ 3640 AC 2 To remove evaporator unit and check drain pan and pipe for any leaking or crack.(Due to water ponding at drain pan).