Snap: 3625 water leak form ceiling ~~~~~ 1)FOUND WATER PONDING AT FILTER SIDE 2)FOUND RUBBER LINING ALONG EVAP FIN DISINTEGRATE 3)REMOVE ALL THE RUBBER LINING 4)REMOVE ACCESS WATER PONDING 5)PURGING DONE 6)CLOSE UP ALL COVER AND MONITOR 2 HRS 7)AC ABLE TO CUT IN/OUT WITH CRITERIA. HAZIQ/JAYA/FAHMI S 25.02.2024