CE reported 2532 No.1E & 1531 No.2E ceil ~~~~~ Operated AC and monitored for condensation - none observed. 2532 and 1531 AC units found operating normally. Cut-in/cut-out ok. For preventive measure, adjusted temperature setting from 24deg to 25deg. Purged AC drain pipes and replaced AC filters. Monitored after preventive works. No AC faults or condensation.  N.AKUMAR //07.09.21