CE: 3602 No1 E ceiling having condensation ~~~~~ 3602-No1 E Ceiling & Saloon floor checked-Ok. A/c purging done. Rubber lining removed. Vacumm clean Evap Unit drain pan done-Ok. Function checked A/c Cut In/Out-Ok.   Akhbar / M.Hairul / Zahir. 14.05.2024.