CE reported 3671 #1 end ceiling panel Co ~~~~~ CE reported 3671 #1 end ceiling panel Co   Checked and found #3671 A/C #1 drainage choked. Vacuummed and flushed the drainage pipe done, water from drain pan manage to flow out smoothly. Checked temperature setting was at 24 degrees celcius, adjusted to 25 degrees. Monitored for awhile ok, no recurrance of condensation. Done by: Kalees (8.3.24)