Snaprep: 2708 water drip from ceiling ne ~~~~~ To change out #2708 evaporator.   2708 AC1 evaporator changed out due to drain pan crack and heavy condensation. Function tested ok, aircon able to cut in and cut out and was cooling. Monitored for a few hours no condensation at 2708 no. 1 end. Old SN: 634044 New SN: 032170 Notification: 2505511 Doneby: Jack/Rizman/Sanip/Koh 13.7.23 Snaprep: 2708 water drip from ceiling near door A1 CE: 2708 no. 1 end condensation During PM check and found condensation. Purging through a/c drain pipe done. Done by: Haikel/Zul 7/7/23 Ops 20 for further checks on evap leak/icing/drain pan crack. To check evaporator for leak, icing and drain pipe crack