SnapRep reported 2643 A/C condensation. ~~~~~ SnapRep reported 2643 A/C condensation.   Checked and found #2643 AHU drain pan filled with water. Checked drain pipe found to be choked. Clear the slug and dirt and purge the water out. Done by: Rosli, Lingkes (3/7/24)