Snap: 1720 waterleaking from ceiling ~~~~~ Snap: 1720 waterleaking from ceiling CE: T413-1720 #2 End Water Dripping from Ceiling Panel.Temp 24.5*C.Floor Wet  1720#2 end found evaporator filter not install was left at top of return air damper cause evaporator condense water and over flow out from the drain pan. Drain pan also having some slug. Clean slug and cleared excess water from evaporator motor blower base and other affected area. Purging done for water drain pan. Install the evaporator filter, Monitor for an hour no ssign of condesation. Done by Saini/Asruddin/haskan 45243