Snap: 2690 condensation on ceiling ~~~~~ Do purging at A/C 1 pipeline to clean any water ponding. Remove    evap hatch cover found icing on the A/C grille. (due to choke). Remove rubber lining of the evap fin. Isolated and tag ops 20 to C/O AHU  M.Hairul / Zahir / Akhbar 03.08.2023  FOLLOW UP 0PS10 C/O 2690 AC 1AHU.VACUUM DONE.LEAK CHECK IN 5 MIN OK.CHARGE FREON TO CRITERIA DONE .SECURE/FUNCTION CHECK CUT IN/OUT DI USER TEMP OK.MONITOR FOR AN HOUR OK.HAFIZ R/LEONG/HARIHARAN 15.08.2023 #2690 AC1 AHU NOTIFICATION 2515299