(RSD) 3554 B2, B6 and B10 emergency ligh ~~~~~ (RSD) 3554 B2, B6 and B10 emergency ligh     Water damage observed on emergency light terminal block.Confirmed water from a/c pipe with damage insulation. Insulation patched and terminal block replaced.Emergency light ok. Done by Koh/Joshua. 01/10/20