snaprep: 3519 aircon not cold ~~~~~ snaprep: 3519 aircon not cold   Checked and found 3519 AC2-2 & 1519 AC1-2 motor drawing high current. Both units isolated and tagged N2492604 and N2492915 raised for CCU c/o respectively Further check found 2520 AC1 faulty FC508 inverter fault. Ops20 raised for evaporator c/o Other AC units in 3519, 1519 and 2520 operating normally." N.A/rawi/yanto/suhaidy /30.05.23   #2520 AC 1 INVERTER FAULTY.REPLACED AHU.DISCHARGE FREON VACCUM AND CHARGED FREON.PERFORMED FUNCTION CHECK AC ABLE TO CUT IN/OUT.BOTH AC 1-1 ,1-2 PRESSURE AT LP 40PSI,HP 120 PSI. GANESAN/TEH/JIMMY 07.06.2023 2520AC 1 AHU    NEW 032083 OLD 032115 NOTIFICATION 2495463