Snap: 1643 Aircon condensation ~~~~~ Snap: 1643 Aircon condensation CE: 1643 No 2 end ceiling panel condensation. Temp 24.8 * C  1643 Aircon condensation. Checked on filter side -No water choke. Replaced new A/C Filter done. Conduct water purge on A/C pipe outlet-Done. Checked A/C Setting -temp found at 24deg.C.    Reset A/C temperature to 25deg.C. Monitor - No condensation - OK. Aliff/Daniel/ChanSW. 45429