2711 A/C 1-1 DT check found coolant faul ~~~~~ #2711 A/C 1-1 LP=0 and HP=200 Sympthom of evaporator check.0020 raise to check evaporator condenser side check no sign of leakage. Checked by Zulq/Asruddin/Haslan. 22/12/20 2711 A/C 1 to check evaporator Check and found evaporator a/c 1-1 capillary tube choke,replace evaporator ok.Further check found a/c 1-1 CCU condenser fan ratting noise-replaced ok.Function test a/c able to cut in/out ok. Evaporator s/n-Old: 634054  New: 032354 Not: 2232235 raise. Condenser Fan s/n-Old:    New: 4533193039/00290097 Not: 2232236 raise. Done by Deeshan/Sanip/Faddzal. 24/12/20