Snap: 1557 Aircon condensation ~~~~~ Found 1557 No.2 End ceiling having some micro droplets. Both AC units on 1557 could cut out. Temperature setting was at 25deg. Cleaned AC thermistor and changed AC filter. Furniter monitored - AC operating normally and no condensation observed. N.A/kwok/lee k.w/husin/24.07.22