Source document: https://docs-lawep.s3.us-east-2.amazonaws.com/1698059399719.pdf (Liberia)
TECHNICAL DATA: 10/2018 Self-contained LED Downlight Access The Access unit offers a simple method of providing discreet emergency lighting in areas that require a surface mounted or recessed self-contained solution.

Supplied with a ‘clip-in’ symmetrical wide angle lens or asymmetrical ‘corridor’ lens for escape routes (both supplied) the Access downlight simply requires a permanent 230Volt supply to provide effective non- maintained emergency lighting with 3hour duration.
proSeries Standard DALI/Self-Test Incorporating tried and tested emergency driver technology from the ELP , the Access downlight offers self- contained, non-maintained operation emergency lighting with integral automatic Self-Test or DALI communication from a single product.

The enclosure may be surface mounted or recessed into the supporting surface.

With either mounting option the Access is both discreet and attractive.
Finished in white or black fire retardant plastic the Access blends in with the other architectural furniture.

The excellent performance allows the units to be mounted at very wide spacings making installation simple and cost effective.

D A L I Surface Operation indicator LED shines through a skin in housing plastic SPECIFICATION proSeries DALI/Self-Test LED driver and a The surface or recessed mounting enclosure houses an ‘intelligent’ Lithium Iron Phosphate (LiFe) battery.
A Nichia ‘3Watt’ high power white LED is mounted in the fascia plate in conjunction with a choice of wide angle or ‘corridor’ distribution lens.

The Lithium Iron battery technology ensures long life without the thermal concerns associated with the more common Nickel Metal Hydride battery technology.

120 Dia 43mm 41mm Recess 43mm Surface 142 Dia All details and specifications shown in this document are deemed correct at time of publication.
The right to modify equipment, change specifications and instructions without notice, is reserved as part of the Emergency Lighting Products Limited policy of continuous development and improvement.

We endeavour to keep all our customers informed of any alterations as and when they occur.

ACCESSDS-10-18 TECHNICAL DATA: 10/2018 Self-contained LED Downlight Fully integrated components and the latest software ensure that the Access luminaire can be connected to any approved DALI control system.
When the mains supply is initially connected, the Access circuit initiates the Self-Test commissioning mode and then activates the weekly and annual test routine starting at random times to ensure tests do not get carried out simultaneously in the same areas.

Faults such as charge failure, battery failure, etc.

will be indicated locally by a bi-colour LED.

The Access luminaire will continually be prepared for a DALI signal even when operating in Self-Test mode.
If a DALI signal is received the Self-Test mode will be disabled and the circuit will adopt full DALI mode.
OPERATION Subject Plastic housing Protection against electric shock Environmental Ingress protection Rated operating ambient temperature Class II IP44 0 to 25°C Surface and recess mounting Flammable surfaces and covered Mains operation Mains frequency Rated voltage supply Mains supply current Emergency duration Battery recharge period Battery charging 220/240V AC 50/60Hz 20mA 3 hours <24 hours Intelligent constant voltage Emergency operation Mechanical Battery discharge current — nominal 370mA Lumen output Integral test routine Dimensions (Surface) 260lumens (max) EN62034/DALI 142mm dia x 43mm (h) Dimensions (Recessed) 130mm dia cut-out x 43mm (h) Mains input unswitched L&N Emergency Lighting Spacings ACCESS/C ACCESS/WIDE Mounting height Hm (m) Spacing (m) min 0.5Lux open area Spacing (m) min 1Lux escape Spacing (m) min 0.5Lux open area Spacing (m) min 1Lux escape 2.0 2.5 3.0 n/a n/a n/a 14.0 15.3 16.5 13.9 15.1 14.8 12.8 14.0 13.6 ORDER CODES Description AC2/NM3/DALI/ST/WHT White surface/recessed mounted luminaire, self-contained DALI/Self-Test NM3 supplied with ‘Corridor’ and wide angle lens AC2/NM3/DALI/ST/BLK Black surface/recessed mounted luminaire, self-contained DALI/Self-Test NM3 supplied with ‘Corridor’ and wide angle lens Emergency Lighting Products Limited Parbrook House, Gillmans Industrial Estate, Natts Lane Billingshurst, West Sussex RH14 9EZ Telephone: +44 (0) 1403 786601 Fax: +44 (0) 1403 786602 e-mail:sales@elp.uk.com www.elp.uk.com ACCESSDS-10-18 Recessed Mounting options