Patent ID: 11883700
Assignee: FIRE & PUMP SERVICE GROUP
Field: Environmental technology (Chemistry)
Classification: CPC A | IPC A

Claim 0:
1. An integrated fire suppression system, comprising:
a cabinet including a plurality of environmentally isolated compartments;
a first walled compartment of the plurality of environmentally isolated compartments received with and mounting a plurality of fire suppression control systems including at least one of electrical components and controls coupled to at least one of water and gas solenoids, high pressure tank nozzles, and an emitter;
a second walled compartment of the plurality having at least one of fluid storage and high pressure gas components, and isolating fluids and gas therein by a sealing mechanism disposed in an opening between the first and second walled compartments;
a third walled compartment of the plurality further including solenoid and actuator systems; and
at least one high pressure tank disposed in both the first and second walled compartments, wherein the tank includes a nozzle that extends through the opening and sealing mechanism and into the second walled compartment.